NOVARA SL

Cast aluminum and stainless steel create a synthesis of form and function in the NOVARA. The angular heavy cast aluminum housing is punctuated by distinctive cooling fins. Mounting knobs are constructed of polished high-grade stainless steel. Single or twin configurations are fitted with clear tempered glass lens. Electrical conductor is housed in attractive braided stainless steel line. Straight round pole with flush handhole is avialable in steel or aluminum. Steel pole and mounting bracket are hot-dip galvanized prior to being finished in finely textured paint. All hardware is stainless steel. Standard color; matte silver grey metallic. Special colors available.

Specification

NOVARA SL 450 LVC

HOUSING Wedge-shaped housing is cast from high-grade aluminum alloy with integrated cooling fins to enhance heat dissipation. Segregated ballast compartment with separate cast aluminum cover is thermally isolated from the optical system, ensuring optimal operating environment for electrical components. Door assembly is one piece brushed stainless steel and sealed with closed cell silicone gasketing when closed. Hinged door is retained by two captive stainless steel socket head cap screws for ease of maintenance. Braided stainless steel line houses weatherproof electrical cord, terminating in watertight couplings at both ends. Housing is adjustable to 0°, 10°, 20°, 30°, or 40° above horizontal by means of two precision machined polished stainless steel knobs and locked into place with two regressed locking bolts. Hot-dip galvanized steel mounting bracket with integral slip fitter for 3.25" O.D. tenon has two offset rows of three stainless steel setscrews to secure and level luminaire to the pole

OPTICSOptics include a choice of one, two, or three individual LED modules. Each module consists of a field replaceable aluminum core PCB with four high-power LEDs and a single piece lens molded from optical quality acrylic. Light distributions include a choice of Type II, III, or IV optics. Luminaire emits zero uplight at 90 degrees horizontal and above and is suitable for use in all LEED lighting zones. CRI is 80+.

NOTE: Due to rapid and continuous advances in LED technology, LED luminaire data is subject to change without notice and at the discretion of HessAmerica. Consult factory for current technical data.

ELECTRICALElectronic LED driver supplies 700mA drive current to LED modules with input voltage range from 120v through 277v at 50/60Hz. Power consumption is 36 watts for models with one module, 72 watts for models with two modules, or 108 watts for models with three modules. Optional 0-10v DC dimming is available on request.