Hi, I have installed 21 PLC-BUS modules. One of them is a shutter module 3160MH.What macro commands do I need to simulate the Shutter Up, Shutter Up one step, Stop, Shutter down one step and Shutter down?The macros will be started by a timer each.

For Shutter up I tried Scene-On PLCBUS: SCENE-ON A1 B9 3SYSTEM: DELAY 180000 <- This is meant as delayed stop to power off teh internal relay of the modulePLCBUS: STOP A1 B9 3The same way for Scene-Off

What I see is various behaviour. Sometimes the stop command is not fired after 3 minutes.Sometimes the Scene-On or Scene-Off command is not fired.This is clearly visible in the Rx/Tx monitor.

But I think you have activated “macro flow control”.So if scene command does not get an ACK back macro execution will stop.That means macro recognizes first command is not executed well, so following commands are not necessary.Disable “macro flow control”

Why you are using the SCENE-ON command.You said you are using only one shutter module.SCENE-commands are for groups. So you can control two ore more shutter at the same time with only one command. In your case you can use normal ON-command or BRIGHT-command to open a shutter. Alternative OFF ore DIM-command for shutter down.

Who is online

Users browsing this forum: No registered users and 1 guest

You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum