In den Warenkorb

Menge

Spezielle Anfrage

Warenkorb aktualisieren

Der Artikel wurde zum Warenkorb hinzugefügt.

Cookies Required for Online RFQ

Santa Clara Systems uses cookies during the RFQ process. Please enable cookies in your browser to submit your RFQ online. You may also use our online contact us form or call us at shared-modal-phone-number

Rated Short-time Withstand Current (Icw): at 40 °C Ambient Temp, in Free Air, from a Cold State 10 s 650 A
at 40 °C Ambient Temp, in Free Air, from a Cold State 15 min 135 A
at 40 °C Ambient Temp, in Free Air, from a Cold State 1 min 250 A
at 40 °C Ambient Temp, in Free Air, from a Cold State 1 s 1000 A
at 40 °C Ambient Temp, in Free Air, from a Cold State 30 s 370 A

They Are Marked 1L1 For The Positive Terminal And 2T1 For The Negative Terminal. - Control Circuit: Dc Operated With Standard Double-Winding Dc Coils (With Add-On Factory-Mounted Lagging Contact For Insertion Of The&Quot;Holding&Quot; Winding) - Accessories: A Wide Range Of Accessories Is Available

Gae75 Contactors Are Designed For Dc Circuit Switching. Arc Suppression Is More Difficult In Dc Than In Ac. To Choose A Contactor

It Is Necessary To Know The Current And Voltage To Be Broken As Well As The L/R Time Constant Of The Power Circuit To Be Controlled. Gae 75 Contactors Are Of The Block Type Design. - Main Poles: The Contactors Are Fitted With Arc Chutes With Permanent Magnets Specially Designed For Dc Breaking. The Three Contactor Paths Are Arranged In Series Via Two Supplied And Fitted Insulated Connections (25 Mm²). The Gae75 Are &Quot;Single-Pole&Quot; Devices For Which The Connection Polarities Indicated Next To The Connection Terminals Must Be Respected. Furthermore