PRODUCT SPECIFICATION:

Construction & Impellers
The axial fan at the heart of the Super T range is based on an integrated impeller and internal rotor motor design which produces a very compact unit. A specially designed bellmouth inlet and mounting plate, ensures an excellent performance to sound level ratio. The mounting plate is formed from a single sheet material protected with a tough epoxy finish.
Motor supports are manufactured from steel rod. Manufacture is controlled to BS EN ISO 9001 standards.
Impellers are moulded in glass filled polyamide for resistance to harsh conditions and abrasive airflow.
Electrical
Single phase 220-240V 50Hz. Capacitor start and run. An IP65 terminal box is supplied with all models with conduit entry from the side of the wall liner. All motors are fitted with Standard Thermal Overload Protection (S.T.O.P.), which should be wired via the controller.

DIMENSIONS:

Impeller dia.

355

400

450

500

A

550

597

657

727

B

550

597

657

727

C

470

520

580

650

D

470

520

580

650

Weight (kg)

17

22

28

33

---

Impeller dia.

355

400

A

552

640

B

520

622

C

390

440

D

100

100

E

364

420

F

520

622

G

436

486

H

81

70

Super T ST355-16-WL

Super T - Gravity shutters Extract model incorporating gravity shutter and internal grille. When installed only the room side aluminium fascia grille is visible. The outside is finished with an external gravity shutter and frame.

Automatically switches on fans on either a rise or fall in air temperature. Can be used for Trickle/ Boost operation on
either intake or extract systems. Setting range: +6°C to +30°C. Two internal range limit/locking rings are included to allow setting within a limited temperature range or locking at a fixed set-point. IP20 rated. Sealed sensing mechanism. Mounting direct on surface only. Dimensions: 80 x 104 x 36mm (H x W x D).

PDF DOWNLOADS:

Calculate estimated running costs for this product using the tool below. For average costs, leave the default values in place or enter your own figures in the boxes to recalculate. Where a product has multi speeds, a typical installation has been used for the below calculations.

Cost per hour per kW:

pence

(Your current electricity cost in pence per hour. This will be listed on your electric bill)

PRODUCT SPECIFICATION:

Construction & Impellers
The axial fan at the heart of the Super T range is based on an integrated impeller and internal rotor motor design which produces a very compact unit. A specially designed bellmouth inlet and mounting plate, ensures an excellent performance to sound level ratio. The mounting plate is formed from a single sheet material protected with a tough epoxy finish.
Motor supports are manufactured from steel rod. Manufacture is controlled to BS EN ISO 9001 standards.
Impellers are moulded in glass filled polyamide for resistance to harsh conditions and abrasive airflow.
Electrical
Single phase 220-240V 50Hz. Capacitor start and run. An IP65 terminal box is supplied with all models with conduit entry from the side of the wall liner. All motors are fitted with Standard Thermal Overload Protection (S.T.O.P.), which should be wired via the controller.

Automatically switches on fans on either a rise or fall in air temperature. Can be used for Trickle/ Boost operation on
either intake or extract systems. Setting range: +6°C to +30°C. Two internal range limit/locking rings are included to allow setting within a limited temperature range or locking at a fixed set-point. IP20 rated. Sealed sensing mechanism. Mounting direct on surface only. Dimensions: 80 x 104 x 36mm (H x W x D).