Meters with built-in wireless transceivers can be
mounted inside buildings within approximately 500 feet line-of-sight from
each other and up to 200 feet through walls, depending on wall material.

Patented 0-2 volt output split-core current sensors
promote enhanced safety and accurate remote mounting of current sensors up
to 2,000 feet from the meter without power interruption. (Optional
solid-core current sensors available in 100 & 200 Amp.)

Meters are equipped with a current sensor
installation diagnostic indicator to assist in installation.

Parallel up to three (3) sets of current sensors for
cumulative reading.

Meter can be used in the following configurations:
- 3-Phase, 4 Wire
- 3-Phase, 3 Wire
- 2-Phase, 3 Wire
For other configurations contact factory.

Compatible with E-Mon D-Mon accessories.

UL/CUL Listed. CSA Approved

Certified to ANSI C12.1 and C12.16 electronic meter
national accuracy standards. (+/-1% from 1% to 100% of rated load.)