Breadcrumb

Contributing Factors

Damage and Injuries

Equipment

Probable Cause

A hydrogen explosion occurred in an Uninterruptible Power Source (UPS) battery room. The explosion blew a 400 ft2 hole in the roof, collapsed numerous walls and ceilings throughout the building, and significantly damaged a large portion of the 50,000 ft2 building. Fortunately, the computer/data center was vacant at the time and there were no injuries.

The facility was formerly a large computer/data center with a battery room and emergency generators. The company vacated the building and moved out the computer equipment; however the battery back-up system was left behind. The ventilation for the battery room appeared to be tied into a hydrogen monitoring system. The hydrogen sensor was in alarm upon emergency responders arriving at the scene (post-explosion). 911 callers view more

Lessons Learned Corner

H2 Tools is intended for public use. It was built, and is maintained, by the Pacific Northwest National Laboratory with funding from the DOE Office of Energy Efficiency and Renewable Energy's Fuel Cell Technologies Office.