Product Details

1. FCGW Type Epoxy Resin Through Wall Bushing 10KV 35KV

FCGW series of composite insulator dry wall drivepipe is implied to indoor or outdoor power substation with AC power system's rated voltage lower than 35KV, frequency being 50Hz, it performs electric insulator and mechanic support function for high-voltage conductor when high-voltage conductor crosses through wall or other object of connection to land,

Epoxy resin through wall bushing is used as insulator and support for 10KV vacuum circuit breaker's high-voltage entry-exit wire. Especially, it is implied to dirty district for preventing from dirty-flash accident, therefore, it has been the upgraded product for vastly used china wall drivepipe.

2.Product specification

Product Model

Rated voltage (kV)

Rated mechanical bending load (kN)

Min. arcing distance(mm)

Min. nominal creepage distance (mm)

Diameter of shed (mm)

Uimp wts (peak)(kV)

Uw. 1min wts (peak)(kV)

FCGW-10/630

10

125

215

380

100/90

75

30

Product Model

Rated voltage (kV)

Rated mechanical bending load (kN)

Min. arcing distance(mm)

Min. nominal creepage distance (mm)

Diameter of shed (mm)

Uimp wts (peak)(kV)

Uw. 1min wts (peak)(kV)

FCGW-35/630

35

125

215

1030

100/90

200

80

3. Condition of Use

(1). Ambient air temperatures within the range of -40 degree Celsius to +40 degree Celsius;

(2). Frequency of A. C. Power supply not exceeding 100Hz;(3). The mechanical load no more than the rated value.