20 A (at 50 °C) for power circuit10 A (at 50 °C) for signalling circuit

Irms rated making capacity

110 A AC for power circuit conforming to NF C 63-110110 A AC for power circuit conforming to IEC 60947110 A AC for signalling circuit conforming to IEC 60947

rated breaking capacity

110 A at 415 V conforming to IEC 60947110 A at 440 V conforming to IEC 6094780 A at 500 V conforming to IEC 60947110 A at 220...230 V conforming to IEC 60947110 A at 380...400 V conforming to IEC 6094770 A at 660...690 V conforming to IEC 60947

[Icw] rated short-time withstand current

90 A 50 °C - 1 s for power circuit85 A 50 °C - 5 s for power circuit80 A 50 °C - 10 s for power circuit60 A 50 °C - 30 s for power circuit45 A 50 °C - 1 min for power circuit40 A 50 °C - 3 min for power circuit20 A 50 °C - >= 15 min for power circuit80 A - 1 s for signalling circuit90 A - 500 ms for signalling circuit110 A - 100 ms for signalling circuit

associated fuse rating

25 A gG at <= 440 V for power circuit25 A aM for power circuit10 A gG for signalling circuit conforming to IEC 6094710 A gG for signalling circuit conforming to VDE 0660