Controlling under-cabinet fluorescent fixtures with a wall switch

I just installed a set of 4 under-cabinet fluorescent fixtures. These are GE's with T5 tubes. The fixtures come with a 3-prong plug so they have to be plugged in to their own receptacles or daisy chained together. I plugged in the first one and daisy-chained the other three with the connecting cables supplied with the fixtures. I want to be able to be able to turn them all on from a wall switch instead of individually with the little rocker switches on each fixture. But I noticed a warning label on both the power cord and the connecting cables that said something like "not for interrupted power" or something like that. Does that mean I cannot turn these lights on with a wall switch? I was going to leave the first one plugged in to one side of a duplex receptacle and replace the other side of the receptacle with a switch. Why wouldn't that work?

Assuming that the receptacle that you are plugging into is over the countertop it would be a violation of the NEC as this countertop receptacle cannot support lighting.

Should you install a circuit just for the lighting then what you purpose would be compliant.

Click to expand...

Thanks for the reply! Is the code concern that the "over the counter top" outlet is on a 20 amp breaker and lights only need 15 amp? Other than that I couldn't imagine that the NEC would care whether I plugged in a 60 watt table lamp (aka under-cabinet light) or a 1200 watt crock pot.

The counter-top receptacles are required to be on their own circuit, which is not allowed any other use. You can purchase direct-wire lights in the same configuration, but you will need an alternate circuit to supply them.

Thanks for the reply! Is the code concern that the "over the counter top" outlet is on a 20 amp breaker and lights only need 15 amp? Other than that I couldn't imagine that the NEC would care whether I plugged in a 60 watt table lamp (aka under-cabinet light) or a 1200 watt crock pot.

Click to expand...

there is a big difference between a table lamp and a lamp that is fixed. The 20 amp circuit is for small appliances only. If we were allowed to install lights on this same circuit then we would load the circuit before we reached the wattage needed for portable applinces such as but not limited to 12 to 14 hundred watt coffee makers, 12 to 19 hundred watt crock pots. 12 to 19 hundred watt deep fryers, and the list goes on