Available in 120VAC and 220VAC with 9VDC Battery Back-Up (Battery Included)

Horn Frequency 3100Hz (Nominal)

Nominal 2.5% Sensitivity

Patented Three Position Test Switch

On-Site Maintenance Washing Program

Relays operate on battery back-up

Quick-Disconnect Wiring Harness

90dBA Solid-State Piezo Horn

Temporal 3 Evacuation Sounding Device (9223 Series)

5-to-1 Signal-to-Noise Ratio

Pulsing LED Sensing Chamber

Fully Insect Screened

Red LED pulses every 30 seconds, green LED for AC power on

Mounting Hardware Adapts to Standard Junction Boxes

Dust Cover to Prevent Contamination During Installation

Low or Missing Battery Indicator

Description

The 9000/9003 Series of photoelectric smoke alarms is designed for residential applications and commercia/residential, including homes, apartments, hospitals, hotels and motels, in compliance with UL 217, applicable IBC/IFC Standards and NFPA 72.

Available in many different models, the 9120/9123 Series is engineered to virtually eliminate nuisance alarms and deliver outstanding performance wherever reliable fire protection is required. The 9000/9003 Series is provided with a 9 VDC alkaline battery for backup in the event building power is lost. The battery impedance is verified and the detector provides a low or missing battery warning.

The Gentex 9000/9003 Series provides an exclusive patented three position test feature that simulates a 0.85% and 3.5% actual smoke condition in full compliance with NFPA 72 and UL Standards.

Options include self-restoring 135°F integral or isolated heat thermals and Form A/Form C dry contacts for remote annunciation.Tandem interconnection of up to 12 units is available on several models; tandem interconnection of up to 6 units is available on "F"models, which activate the dry contacts from a remote alarm through the tandem wire or a local alarm.

The 9003 Series provides the temporal 3 evacuation tone as a standard feature. When testing the 9123 Series it may take up to 16 seconds longer to go in or out of alarm.