A lot water on the drain panel

I used a similar today but I had to make about 4 trips. I was thinking to use a small water pump to pump the water to the primary drain line. I'm worried about any damaged for the client and speed the process.

__________________

**Always kill the power ** Hot air rises, but heat will always move from higher to lower temperatures. ** Real man shoot in manual. ** If it ain't grounded, it ain't dead.

A lot water on the drain panel

is this the pan under the air handler shouldn't have water in it what going on with the one inside the unit.then run a PVC line out from the emergency pan to a stoop or back yard so they see water running when it over flows....and the emergency PVC is totally seperate from the uit drain line

A lot water on the drain panel

Quote:

Originally Posted by JJboy

I used a similar today but I had to make about 4 trips. I was thinking to use a small water pump to pump the water to the primary drain line. I'm worried about any damaged for the client and speed the process.

2 gallons taken out of the pan will get any drain pan drained low enough for the float switch to let the A/C run again. 120 degree attics will evaporate the rest of the water in a day or 2.

My tool bag weighs more. So no real worry about spilling water. plus, you can get the crap out of the trap that clogged it up in the first place.

A lot water on the drain panel

Quote:

Originally Posted by biggles

is this the pan under the air handler shouldn't have water in it what going on with the one inside the unit.then run a PVC line out from the emergency pan to a stoop or back yard so they see water running when it over flows....and the emergency PVC is totally seperate from the uit drain line

I know that. The A-coil is cracked. The water is going straight to the drain pan instead of primary drain line. The secondary drain pan doesn't have drain line....but the flow safety switch saved for water damage.

The A-coil will be replaced.

Advertisement

__________________

**Always kill the power ** Hot air rises, but heat will always move from higher to lower temperatures. ** Real man shoot in manual. ** If it ain't grounded, it ain't dead.