In this article: CE code Section 20 — Locations in which corrosive liquids, vapours, or excessive moisture are likely to be present. The code is a comprehensive document. Sometimes it can seem daunting to quickly find the information you need. This series of articles provides a guide to help users find their way through this critical document. This is not intended to replace the notes in Appendix B or the explanations of individual requirements contained in the CEC Handbook, but will provide some help in navigating the code.

General

Section 22 amends or supplements the general requirements of the code. It provides specific rules for locations classified as Category 1 (moisture) or Category 2 (corrosive) environments that are sufficient enough to interfere with the normal operation of electrical equipment.

A Category 1 location is defined as one where moisture in the form of vapour or liquid is present. The moisture can be caused by condensation, dripping or splashing of liquid, or other means. A Category 2 location is defined as one where corrosive liquids or vapours are likely to be present. Where neither Category is mentioned in a rule in this section, then the rule applies to both categories. Appendix B contains examples of Category 1 and 2 occupancies.

Equipment

As per rule 22-100, only equipment that is essential to the process being carried out in that area may be located in a Category 1 or 2 location. Service equipment, motors, panelboards, switchboards and similar equipment need to be installed outside the category area. This includes any enclosures containing moulded case circuit breakers in a Category 2 location unless they have been approved and marked as suitable for that application, because internal corrosion can occur.

Rules 22-102 (1) to (6) outline the types of construction required of equipment to be installed in the various moist or corrosive atmospheres. This information is marked on the equipment if not self-evident.

Rules 22-104 to 22-108 specify requirements for pendent lamp holders, luminaires, receptacles, plugs, and portable cords to be installed or used in Category 1 or Category 2 locations.

Wiring

Rule 22-200 provides the requirements for wiring in Category 1 locations. Generally conductors must be selected in accordance with rule 4-008(1) and table 19. Note that NM cable must be NMU or NMWU, MI cable must be spaced 6mm from any wall at supports, and aluminum conductors must have joints adequately sealed against moisture.

Rule 22-202 provides the requirements for wiring in Category 2 locations. All conductors must have protection from corrosion. NMW and NMWU cable is permitted. Raceways, conductors and cables may only be used as permitted by Table 19. MI, alu-sheathed and copper-sheathed cable must be suitably corrosion protected. Any termination or joint of aluminum conductors must be adequately sealed against ingress of corrosive liquids or vapours.

Rule 22-204 outlines the appropriate wiring methods in buildings housing livestock or poultry. Again generally, these are wet or damp locations and all wiring must be selected in accordance with rule 4-008(1), with consideration given to adequate ventilation for a damp location. NMW or NMWU cable may be used, but aluminum conductors may not, and NMS cable must be provided with mechanical protection against damage by rodents.

Rule 22-206 deals with wiring in curling and skating rinks. Generally, lighting areas are subject to condensation so wiring must be selected in accordance with Rule 4-008(1) and Table 19 for wet locations. Other areas may be wired in accordance with Section 12 observing any moisture conditions. Areas with adequate mechanical ventilation (at least three changes per hour) may be considered dry locations.

Drainage, sealing, and exclusion of moisture and corrosive vapour

Rules 22-300 and 22-302 specify methods for excluding moisture and corrosive vapours from entering conduit, cables, equipment or locations through the use of approved fittings, drip loops, adequate drainage, sealing, and orientation.

Circuit control

Rule 22-400 requires that each circuit in a Category 1 or 2 location must be capable of being de-energized from outside the location.

Materials

Rule 22-500 specifies that all metal materials including conduit, enclosures, and even every nut bolt and screw must be corrosion protected or resistant to the specific corrosive environment.

Bonding

Rule 22-600 requires all non-current carrying metal parts of equipment to be bonded to ground as per Section 10.

Rule 22-704 provides guidelines for the classification of these types of areas that may be both Category 1 or 2, and hazardous locations under Section 18. Reference material for hazardous area classification can be found in NFPA 820. Appendix B also has some notes regarding safety issues in these types of facilities.

Rule 22-706 specifies that wiring methods in these types of areas shall be in accordance with Rules 22-200, 22-202 or Section 18 depending on the location classification. Note that there are some restrictions, conditions and special handling for metal conduit, tubing, armoured cable, mineral-insulated cable, aluminum sheathed cable, and copper-sheathed cable.

Electrical equipment

Rule 22-708 specifies that electrical equipment in these types of areas shall be in accordance with the other applicable sections of the code or Section 18, depending on the location classification. Note that there are some restrictions, conditions and special handling for receptacles, lighting switches, unit emergency lighting equipment, emergency lighting control units, heating equipment, motors, and any electrical equipment in a wet well. Also note in sub-rule 22-708(4) that ventilation fans shall not be located in a wet well. One other significant sub-rule, 22-708(5), requires that areas provided with continuous positive ventilation must be interlocked to de-energize all electrical equipment if the ventilating equipment becomes inoperative, unless the electrical equipment in that area is approved for a Class 1 hazardous location.

Rule 22-710 requires all structural steel below ground, in contact with earth to be bonded to the system ground.

In the next instalment we will be discussing Section 24 — Patient care areas.

* The source for this series of articles is the Canadian Electrical Code, Part I, published by CSA

William (Bill) Burr is the former Chair of the Canadian Advisory Council on Electrical Safety (CACES), former Director of Electrical and Elevator Safety for the Province of BC, and former Director of Electrical and Gas Standards Development and former Director of Conformity Assessment at CSA Group. Bill can be reached at Burr and Associates Consulting billburr@gmail.com.

Electrician Forum Brought to you by Schneider Electric

As industry experts you know the products you use everyday better than anyone and should have input on what information you receive about products and what could improve them.

Therefore, we want your insight on the biggest challenges or issues you face when installing loadcentres, breakers (CAFI, GFI's…) and other surge protection devices. We ask that you do not provide product specific details but rather your general issues and concerns or any questions that have come to mind while working with these product types. Provide us with your valued expert insight into the issues you have faced so manufacturers can better inform you about the installation and use of these products. Lets generate some discussion that will help guide the Industry.

The invisible impact of powerlines should never be underestimated. In the past decade alone, 19 people in Ontario have lost their lives from overhead powerline contact. May 13 to 19 is Powerline Safety Week, which is meant to inform people across the province to stay vigilant of powerlines when doing work at home or on the job.

"Our work in raising awareness of powerline safety won't be finished until there are zero injuries or lives lost from contact," says Dr. Joel Moody, Chief Public Safety Officer, Electrical Safety Authority (ESA). "All it takes is a misstep or careless error to change the life of you, your colleagues or family."

ABB has an extensive portfolio of eco-efficient solutions and services that can help decouple economic growth from environmental impacts. In fact, over half of ABB's worldwide revenues are generated by technologies that combat the causes of climate change. The company’s goal is to increase this contribution from 57 percent in 2018 to 60 percent by 2020.

The company’s commitment to combatting climate change includes limiting the environmental impact of its own operations. ABB’s current target for climate action is to reduce its own GHG emissions by 40 percent by 2020 from a 2013 baseline.

Canada’s wind energy industry further expanded its installed capacity in 2018, while solidifying its status as the lowest-cost source of new electricity generation. Newly commissioned projects brought total national wind energy capacity to close to 13,000 megawatts (MW). Meanwhile, competitive auction results in Saskatchewan and Alberta confirmed the wind industry’s ability to continue to deliver record-low prices.

The six wind energy projects that were powered up in 2018 added 566 MW of installed capacity — a continuation of steady growth that contributed to an average annual growth rate of 20% per year since 2008.

A joint research team has developed a new type of highly flexible and stable solar cell that could be used in wearable electronics.

The power supply is vital to the safety of wearable electronics. Perovskite solar cell (PSC) has been widely used to manufacture flexible batteries because it is highly efficient, cheap, and easy to use. Perovskite is a material with the same type of crystal structure as calcium titanium oxide.

The flexible substrate is the key factor to determine the performance of PSCs.

FLIR Systems have released the FLIR VP40, a non-contact voltage detector for use in North America designed for field-troubleshooting and verification of residential, commercial, and industrial electrical installations. The VP40 makes it easy to quickly troubleshoot live and neutral wiring to ensure a safe job site.

With its built-in flashlight and CAT IV safety rating, the FLIR VP40 is a must-have for preliminary job site checks for live wiring. The durable, pen-sized tester quickly identifies the presence of AC voltage without contacting wires, even in the latest safety outlets.

Expanding on its extensive product line for motion control applications, Sensata Technologies recently released the Crydom DRMS Series hybrid motor starters.

These new hybrid starters integrate the benefits of both solid state and electromechanical relay technologies to produce a compact device that can control electrical power delivery to motors as large as 4kW. Suitable applications range from access control, packaging equipment, lifts and escalators to industrial process control and machine tooling systems.

Use of this Site constitutes acceptance of our Privacy Policy (effective 1.1.2016)
The material on this site may not be reproduced, distributed, transmitted, cached or otherwise used, except with the prior written permission of Kerrwil