Controller interface: Operating mode default setting for a single fume cupboard controller, readout of individual operating values such as volume flow rates for single controllers, or individual alarms

Can be used with fume cupboard, supply air, extract air or differential pressure controller EASYLAB TCU3 and with adapter module TAM

For use in laboratories, clean rooms in the pharmaceutical and semiconductor industries, operation theatres, intensive care units, and offices with very demanding control requirements

Factory mounted or for retrofitting into the EASYLAB base component casing

Special characteristics

Ready for installation, can be easily connected to the main PCB

Interface for EIA-485 networks BACnet MS/TP and Modbus RTU

BACnet Protocol Revision 12.0

Only standard BACnet objects or Modbus registers are used for communication

Data interface for an EASYLAB controller or for an EASYLAB room with different functional profiles

Slide switch to switch between BACnet and Modbus communication protocols

Two address switches, X and Y, to set equipment addresses 1-99

8-way DIP switches to adjust the communication parameter

Double-stack terminal blocks for the EIA-485 network (simple wiring)

Two indicator lights indicate communication and errors, respectively

Connection to update the firmware

EIA-485 terminal resistor that can be activated

Construction features

PCB dimensions and fixing points correspond to the EASYLAB main PCB and the casing

Fixing with screws

Pin header to connect the module to the main PCB of the TCU3 or TAM

Información técnica

Function

Technical data

Specification text

Order code

Functional description

The expansion module EM-BAC-MOD-01 is used to integrate EASYLAB controllers Type TCU3 or EASYLAB adapter modules Type TAM into a BACnet (MS/TP) network and in this way connect them to the central BMS.

The BACnet or Modbus interface supports the EASYLAB room operating mode concept. It is possible to set operating mode defaults in order to control different volume flow rates for daytime and night-time operation; it is also possible to increase or reduce the air change rate (volume flow rate setpoint change), e.g. to influence the room temperature.

Using the BACnet or Modbus interface, an individual alarm management system can be set up by consolidating configurable EASYLAB alarms. The interface also enables the transfer of actual operating values such as volume flow rates and damper blade position for a controller or for all controllers in a room.

Expansion module to supplement an EASYLAB base component (controller TCU3 or adapter module TAM) with a BACnet or Modbus interface to link rooms or individual volume flow controllers to the central BMS.

The expansion module includes an interface for EIA-485 networks that can be used for BACnet MS/TP or Modbus RTU (switching), a switch to enter communication parameters, a connection to update the firmware, and indicator lights.

Special characteristics

Ready for installation, can be easily connected to the main PCB

Interface for EIA-485 networks BACnet MS/TP and Modbus RTU

BACnet Protocol Revision 12.0

Only standard BACnet objects or Modbus registers are used for communication

Data interface for an EASYLAB controller or for an EASYLAB room with different functional profiles

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +54 (11) 4233 5676

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +54 (11) 4233 5676