10kVA UPS Backup Uninterruptible Power Supply

Uninterruptible Power Supply, 10kVA/8kW, line interactive UPS, provides a reliable battery backup for critical devices like PC, servers, networks against power surges and outages. High reliability 10kVA UPS is available with input and output voltages of AC 220V, 230V, 240V, 110V, and 120V. Different input power cables & output sockets for choice.

1500VA/1050W UPS battery backup, line interactive UPS, is an ideal uninterruptible power source for personal computers, servers, networks and other home & office devices during power outage with overload protection. Available AC 220V/230V/240V/110V/120V input and output voltage. Different power cables & sockets for options. Compact size, low cost and high reliablity.

5 Minutes Backup time; for long backup mode, it depends on outside battery

Charge Time

<12 hours (90%)

Display Status

LCD (NORMAL, FAULT, BATTERY, CHARGE, OVERLOAD)

Protection

Overload Protection

Automatic shut down when overload is within 110~130%

Shut down after 300ms when above 130%

Others

Peak Ratio for Load

3:1 (Max.)

Distortion Rate (full load) Linear Load

<3%

Distortion Rate (full load) Non-linear Load

<6%

Communication Software

NETCCA POWER

Operating Environment

Working Temperature

0°C~40°C

Relative Humidity

20~90% Non-condensing

UPS Input Power Cables (Optional)

UPS Output Sockets (Optional)

Tips: Troubshooting UPS - the battery voltage is low but the battery cannot be charged for more than 10 hours.

Judging from the phenomenon, it is the fault of battery and charging circuit, which can be inspected according to the following procedures.

Check whether the input and output voltage of the UPS charging circuit is normal.

If the charging circuit is in normal input and abnormal output, disconnect the UPS battery to test again. If it is still abnormal, it is the fault of the charging circuit.

If the charging circuit has normal input and output after the battery is disconnected, it indicates that the UPS battery has been damaged because of the long term charging, long time placement, due life period.