KRIPAL offers a comprehensive range of isolating switches designed with safety in mind stand-stone and enclosed formats, this switch range are padlockable and availiable in yellow/ red or grey/black making it idea for any electrical isolation requirement, such as repair, maintenance installation and inspection.

Features:

1) Standard: IEC-60947-3 DC-21B

2) Protection degree: IP66/IP67

3) UV resistance: ASTMD4459

4) Flammability: UL-94VO

5) Mechanical life: 20000

6) Electrical life: 2000

7) Enclosure color: Grey

8) Handle color: Black / Red

10) Warranty: 3 Years

11) Extremely short power shut off time of less than 3ms

12) Padlockable handle

13) The isolator has 4 seperate poles
14) Jumpers can be used to change the way that the poles are connected
15) Poles can be connected in series parallel or a variation of both series and parallel
16) Interconnection of the poles dictates the load that the switch can make and break
17) As the mumber of poles used increases so the load switching capacity of the device increases.

Specifications:

Protection grade

IP66/IP67

19A

1380VDC

23A

1200VDC

25A

1000VDC

Wiring size

6mm2

Applications:

UKPD25 series DC solar switch disconnetors in plastic enclosure, are apllicable in 1-15KW residential or commercial photovoltaic system, independent with inverter.This model are designed to keep solar more safe, the higest voltage can be reached 1000V.To ensure its stability and long service.

1. It is important to ensure that all electrical connections(including factory connections) are tight, ensure that

all terminal screws are tightened firmly.

2. It is recommended that for DC, multi-stranded cable, crimp ferules are used to ensure that the wires do not become loose,loose cables can cause excessive watt loss and generate excessive heat causing severe

damage to the switch.

3. After installing and wiring the switch carry out the following test: switch on and off several times making

sure that a positive snap action can be felt and heard.

4. If the switch cannot be felt and heard to operate correctly then it is important that che switch is not used