HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

I actaully double checked the manual J and know it is spot on. I need someone to double check the duct /register distributions. Anyone who is interested in doing this please contact me at tony@tdavlin.com thanks!

Originally posted by tdavlin I actaully double checked the manual J and know it is spot on. I need someone to double check the duct /register distributions. Anyone who is interested in doing this please contact me at tony@tdavlin.com thanks!

it was done with the software from hvac software (hvcalc residential) I am not sure if that is man D? a very expensive local hvac contractor said the heat load was spot on, I have a suggested register layout from another guy who seems to know what he is talking about but his company doesn;t have the reputation.. anyways the house has a lot glass and it would be great if someone could double check the register layout we have ( the house is 1700 sq feet.