Power Control Centre is considered to be the heart of an electrical system in any industry. Its offer to users long term reliability, safety, low maintenance & testing time.

More About Us

Power Control Centre (PCC Panel)

VCIPL is the leading manufacture of PCC panels (Power Control Centre) in India, which are used for diverse industrial applications and provide reliable and effective service. These panels are manufactured as per client's specifications and requirements which very well meet with the industry demands.

Power Control Centre is considered to be the heart of an electrical system in any industry. Therefore it shall offer users long term reliability, safety, low maintenance & testing time.

Vidhyut offers state of art VC-5100 series PCC panels, manufactured by employing modern engineering practices with consideration of safety & reliability main aspects of this series.

It has got numerous added features which were incorporated with the help of inhouse product analysis and continuous field feedback. VC-5100 PCCs are manufactured as per latest international standards link IEC439, EN60934, and IS8623 etc.

Construction

Incomer ACB is assembled in single tier. However, up to 1600A OUTGOING ACBs can be assembled in TWO Tier arrangements.

In TWO TEAR ACB FEEDER, the outgoing ACB links are made of different in length for easy cable termination, depending on cable incoming. Also for bottom ACB, vertical dropper is taken for ACB bus bar I/C Connection.

Rear Side of the panel is divided into two sections, first to accommodate vertical Bus bar dropper with a hinged door fabricated with perforated CRCA SHEET in between for a perfect combination of shrouding with the facility of heat dissipation & visibility. Alternatively, for single tier ACB feeder Hinged ACRYLIC DOOR is provided.

Technical Specification

Rated Insulator Voltage :

660 Volts

Rated Operator Voltage :

415V_+ 10%

RATED IMPULSE

Withstand voltage :

8-KV

Rated Current :

1000, 1250A, 1600A,2000A, 2500A, 3000A,4000A, 5000A, 6300A

Fault level :

50KA for 1 Sec, 42KA for 1 sec, 35KA for 1 sec

Ambient Temp :

50°C

Temp. Rise :

35°C over ambient

Busbar Support :

SMC/FRP

Degree of protection :

IP-54

Dimension (mm) :

H=2400, D=1000/1200/1400/1600, W=600, 800, 1100 (multiple)

Wire & Termination

Power wiring is done with colored flexible, copper multi stranded wires from leading manufacturers.

Feeder Sizes

VC 5100 series is totally front & rear access. Sizes are standardized for interchangeability of feeder if required as width & depth is fixed. The height use to vary in multiple of 225/300/450/600/900/1200 etc.

Salient Features

» A perfect compartmentalized construction where the partition sheet goes till EXTREME END OF REAR PANEL.