Provides heat recovery ventilation and air conditioning from the same ventilation system

Air flow range from 500m3/hr. to 2500m3/hr

Single system reduces installation time, costs and space

Can be operated in supply air or return air control

Built in drain pump to facilitate easy installation

Single remote controller provides basic functions. PZ-61DR-E can be added for full functionality

Available in 3 sizes, 01, 02 & 03

Product Images

(GUG-01SL-E)

Technical Data

Indoor Unit Technical Data

Model Reference

GUG-02SL-E

GUG-02SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

Connected Lossnay

LGH-80RVX-E

LGH-100RVX-E

LGH-150RVXT-E

LGH-200RVXT-E

LGH-250RVXT-E

LGH-150RVX-E

LGH-200RVX-E

Connected Condenser

PUZ-ZM50

PUZ-ZM71

PUZ-ZM71

PUZ-ZM71

PUZ-ZM71

PUZ-ZM71

PUZ-ZM71

Control Type

Supply Air**

Cooling (kW) - Nominal

8.3

9.5

13.3

15.9

17.6

13.4

15.9

Heating (kW) - Nominal

10

11.4

16.3

15.9

17.6

16.6

19.5

Cooling Mix (kW)

3.30 + 5.00

4.20 + 5.30

6.20 + 7.10

8.50 + 7.40

9.80 + 7.80

6.30 + 7.10

8.50 + 7.40

Heating Mix (kW)

4.00 + 6.00

5.10 + 6.30

7.40 + 8.90

10.30 + 9.20

12.10 + 9.50

7.70 + 8.90

10.30 + 9.20

Performance Index - Cooling

4.76

5.43

5.03

5.54

5.31

5.32

5.85

Performance Index - Heating

4.62

5.09

5.16

6.01

5.97

5.46

6.3

SHF

0.69

0.73

0.86

0.9

0.95

0.85

0.9

Air Flow Range at SP3 (m³/hr)

560

700

1050

1050

1000

1050

1050

Air Flow Range at SP4 (m³/hr)

1200

1200

2250

2600

2600

2250

2600

Required additional item 1

PAC-SH30RJ-E*

PAC-SH30RJ-E*

N/A

N/A

N/A

N/A

N/A

Required additional item 2

PAC-SH50RJ-E*

PAC-SH50RJ-E*

N/A

N/A

N/A

N/A

N/A

* Pipe size adapters

** Initial Setting only, not via Remote Controller

Indoor Unit Technical Data

Model Reference

GUG-01SL-E

GUG-01SL-E

GUG-02SL-E

GUG-02SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

GUG-03SL-E

Connected Lossnay

LGH-50RVXT-E

LGH-65RVX-E

LGH-80RVX-E

LGH-100RVX-E

LGH-150RVX-E

LGH-200RVX-E

LGH-150RVXT-E

LGH-200RVXT-E

LGH-250RVXT-E

Connected Condenser

PUZ-ZM35

PUZ-ZM35

PUZ-ZM50

PUZ-ZM71

PUZ-ZM100

PUZ-ZM100

PUZ-ZM100

PUZ-ZM100

PUZ-ZM125

Control Type

Return Air

Cooling (kW) - Nominal

5.60

6.60

8.30

11.30

15.80

18.40

15.70

18.40

22.30

Heating (kW) - Nominal

6.50

7.70

10.00

13.20

20.70

23.80

20.40

23.80

26.10

Cooling Mix (kW)

2.00 + 3.60

2.60 + 4.00

3.30 + 5.00

4.20 + 7.10

6.30 + 9.50

8.40 + 10.00

6.20 + 9.50

8.40 + 10.00

9.80 + 12.50

Heating Mix (kW)

2.40 + 4.10

3.20 + 4.50

4.00 + 6.00

5.10 + 8.10

7.70 + 13.00

10.30+13.50

7.40 +13.00

10.30 + 13.50

12.10 + 14.00

Perf. Index - Cool

4.69

5.03

4.76

4.98

5.27

5.86

5.03

5.59

4.59

Perf. Index - Heat

4.09

4.72

4.62

4.42

4.24

5.02

4.07

4.86

4.75

SHF

0.66

0.69

0.69

0.66

0.68

0.76

0.68

0.76

0.87

Air Flow Range at SP3 (m³/hr)

350

350

560

700

1050

1050

1050

1050

1750

Air Flow Range at SP4 (m³/hr)

695

900

1200

1200

2250

2600

2250

2600

2880

Required additional item 1

N/A

N/A

PAC-SH30RJ-E*

N/A

N/A

N/A

N/A

N/A

N/A

Required additional item 2

N/A

N/A

PAC-SH50RJ-E*

N/A

N/A

N/A

N/A

N/A

N/A

* Pipe size adapters

Notes

1. The running current and input power are based on 230V/50Hz. 2. The cooling and heating capacities are based on the air conditions listed below and the rated airflow of fan speed 4. Cooling Indoor: 27°CDB/19°CWB Outdoor: 35°CDB/24°CWB Heating Indoor: 20°CDB/15°CWB Outdoor: 7°CDB/6°CWB 3. The first figure in ( ) of the capacity specification is the heat recovery energy of the Lossnay unit. The second figure is the capacity specification for the Dx-coil connected to the outdoor unit. 4. ”Performance index” is the calculated value at the temperature conditions above and is reference purpose only. Performance index = Total capacity ÷ total power consumption of outdoor unit and Lossnay unit 5. The external static pressure listed above includes the static pressure loss of the Dx-coil unit when using a 50cm straight duct between the Lossnay and Dx-coil units. When the duct work between the Lossnay and Dx-coil units is longer and/or bent, the pressure loss of the duct work should be included in the pressure loss calculation. 6. The designed airflow of the system (Lossnay, Dx-coil and duct work) at fan speed 3 and4 should be kept within “Airflow range at SP3 and SP4” listed above. This range is shown as the green line in graphs of the characteristics curve. If the Lossnay airflow is out of this range, the compressor of the outdoor unit may stop for self-protection purposes. 7. By installing the Dx-coil unit with a Lossnay unit, the air blow noise level is quieter at fan speed 4 as shown below. LGH-150,200RVX-E: about 3dB quieter. 8. Refrigerant leakage contributes to climate change. Refrigerant with lower global warming potential (GWP) would contribute less to global warming than a refrigerant with higher GWP, if leaked to the atmosphere. This appliance contains a refrigerant fluid with a GWP equal to 1975. This means that if 1kg of this refrigerant fluid would be leaked to the atmosphere, the impact on global warming would be 1975 times higher than 1kg of CO2, over a period of 100 years. Never try to interfere with the refrigerant circuit yourself or disassemble the product yourself and always ask a professional.