Third party tested, Lighting Facts certified and backed by a 5-year warranty.

Loop - Suspended

Design is the continuous pursuit of perfection.

Endcaps + Dimensions

Fixtures are available in 4′, 6′ and 8′ nominal sections that can be ganged together to create continuous runs.

[R] RADIUS

[S] SQUARE

Finishes

[A] Clear Anodized

[B] Black Powdercoat

[S] Metallic Silver Powdercoat

[W] White Powdercoat

Energy + Light

65 Up | 35 Dn

A - 19W | 2500 lm

B - 23W | 3050 lm

C - 29W | 3750 lm

D - 38W | 4900 lm

100 Down

A - 19W | 2550 lm

B - 23W | 3050 lm

C - 29W | 3750 lm

D - 38W | 4800 lm

20 Up | 80 Down

A - 19W | 2600 lm

B - 23W | 3100 lm

C - 29W | 3750 lm

D - 38W | 4850 lm

55 Up | 45 Down

A - 19W | 2500 lm

B - 23W | 3000 lm

C - 29W | 3700 lm

D - 38W | 4850 lm

[A] 65 Up | 35 Dn

[B] 100 Dn

[D] 20 Up | 80 Dn

[E] 55 Up | 45 Dn

Options

CCT

[30] 3000 K

[35] 3500 K

[40] 4000 K

Ceiling Type

[D] Drywall

[G] Grid

[S] Structure

[R] Remote

Voltage

[M] 120-277 V

[3] 347 V

Suspension

[03] ≤ 3ft

[06] ≤ 6ft

[12] ≤ 12ft

[25] ≤ 25ft

Driver

[F1] Non-Dim

[F2] 0-10V Dim 3% 120-277V

[F3] 0-10V Dim 3% 347V

[E1] eldoLED ECO 0-10V Dim 1%

[E2] eldoLED SOLO 0-10V Dim 0.1%

[E3] eldoLED ECO DALI 1%

[E4] eldoLED SOLO DALI Dim 0.1%

[L1] Lutron Hi-Lume 1% EcoSystem (LDE1)

Wiring + Emergency

[A] Alternate wiring for AV, EM or NL

[B] Battery Pack

[C] Chicago Plenum

[H] Emergency Switching

Sensors + Controls

[SE1] Canopy Integrated Enlighted Smart Sensor

[RE1] Remote Enlighted Smart Sensor

[VN1] Acuity nLight Converter

Options - Independent Up | Dn Lighting Control

Loop Suspended U|D provides fully dimmable or switchable independent control of the indirect and direct distributions. Ideal for multipurpose rooms and spaces with presentation, projection or video conferencing requirements, the separated circuitry allows simple adjustment of the proportions of up|down light to suit the lighting and energy needs of the space and people in the environment.

Loop UD is available with a native distribution of 55 Up | 45 Dn with a maximum total delivered output of 4200 lumens.

55 Up | 45 Dn

Distribution

[B] Independent Up | Dn Control

Energy

[D] 38 W

CCT

[30] 3000 K

[35] 3500 K

[40] 4000 K

Ceiling + Mounting

Loop comes with pre-wired and tested drivers that are fully integrated with power junction box, mounting and suspension components. Integrated drivers with ceiling and mounting components are designed for multiple orientations and to accommodate grid, drywall or hard lid ceilings.

Elements can be installed in advance or with fixtures for existing or new construction. See Drivers + Controls for details.

Loop - Suspended

With cutting-edge Radial Anidolic optics and the latest LED technology, Loop delivers an optimal balance of modern design, technical performance, and minimal energy consumption to combine quality illumination with contemporary architecture.

Precisely controlled axially symmetric batwing distribution optics for wide row spacing and exceptional ceiling and workplane uniformity with no view of the the LED light sources

The initial stage of the optical technology mixes light as it rotates around the fully transparent Radial Anidolic element. The result is a floating ring of light with accurate and consistent color that losslessly eliminates any visible images of the intense LED point source.

(C) PRECISE EXTRACTION

The second stage uses precise extraction elements to emit high performance distributions with exceptional optical control and efficacies.

(D) 360° SYMMETRIC BATWING

Radial Anidolic optics deliver a batwing distribution that is symmetrical on all planes around the horizontal axis for optimal visual comfort from all viewing angles and exceptional work plane uniformity.

Best Practices - Area Lighting

Open Office

Environment

60 x 60

Product

65 Up | 35 Dn / 23W

QTY

4 runs @ 52'

Drop + Spacing

18" | 15' o.c.

Uniformity

6.5

Light + Energy

40 fc | 0.33 W/ft2

Open Office

Environment

60 x 60

Product

65 Up | 35 Dn / 19W

QTY

5 runs @ 52'

Drop + Spacing

18" + 12' o.c.

Uniformity

4.1

Light + Energy

39 fc | 0.33 W/ft2

Open Office

Environment

60 x 60

Product

65 Up | 35 Dn / 23W

QTY

30 runs @ 8'

Drop + Spacing

18" | 10' x 12'

Uniformity

3.3

Light + Energy

42 fc | 0.38 W/ft2

Classroom

Environment

32 x 30

Product

55 Up | 45 Dn / 23 W

QTY

2 runs @ 28'

Drop + Spacing

18" | 15' o.c.

Uniformity

6.5

Light + Energy

38 fc | 0.33 W/ft2

Laboratory

Environment

36 x 30

Product

20 Up | 80 Dn / 38W

QTY

3 runs @ 24'

Drop + Spacing

18" | 12' o.c.

Uniformity

3.1

Light + Energy

68 fc | 0.64 W/ft2

Computer Lab

Environment

32 x 30

Product

65 Up | 35 Dn / 19W

QTY

9 runs @ 8'

Drop + Spacing

18" | 10'x10'

Uniformity

3.6

Light + Energy

35 fc | 0.34 W/ft2

Loop - Suspended

These Loop resources can help you with your Fluxwerx product specification needs. Visit our general resources page for complete performance data, images and other resources related to our entire product line.