What version firmware – 2.6 for third party, 2.10 for HLC.NOTE: Support for HLC was added in version 2.9 – the reason for the reference to 2.10 is an accounting for a modification added to the firmware.

Device type – HLC or other.

Configuration – controller or Upstart.

Setup>>Names>>Units - all desired units must be named NOTE: When using HAI lighting Control, the first unit of each room "must" be named, whether a Scene Switch is installed or not.

Setup>>Miscellaneous – House Code set to UPB or HAI Lighting

Setup>>Installer>>Control – Network ID and Password set properly

Setup>>Installer>>Expansion – verify proper Module/Serial function set to UPBNOTE: Double-check that there are no duplicate UPB entries.

Hardware Check:

PIM type – HLC or other

Connection type – on-board RS-232 or 10A17-1.NOTE: When using non-HAI PIM, it can only be connected to 10A17-1.

Adapter type (if using 10A17-1) – HAI (36A05-2) or other

Physical/Audible Inspection:

Status LED (10A17-1) – should blink once per second

RX and TX LED’s – should blink when commands are sent/received.NOTE: If the RX LED is solid red, it would indicate that either the PIM is in “Pulse” mode or the wiring connection between controller and PIM is bad.

PIM LED – should be amber when not active and red/amber flicker when active.