EAMP020

Ruskin model EAMP020 includes factory programming to ensure complete compatibility with any Ruskin thermal dispersion product. The simplicity of the "plug & play" design provides quick and trouble-free installation. Dust proof housing has two electrical access points to the internally fused power supply. The control transmitter offers precise setpoint monitoring and adjustment for easy field calibration, when required. Unit provides 4-20 mA or 2-10 VDC (with 500 ohm resistor) velocity and temperature outputs to communicate with any building automation system (BAS). The microprocessor based EAMP020 comes standard with a multi-line, 16 x 2 alphanumeric, liquid crystal digital (LCD) display, indicating both CFM and Temperature of the measuring location. Average up to four probes and 16 sensing points with each control transmitter.