5853 - Honeywell Wireless Glassbreak Detector

The Honeywell 5853 wireless glassbreak detector offers uncompromised performance and unmatched false alarm immunity. The FlexCore™ signal processor utilizes an Application Specific Integrated Circuit (ASIC) processing sound data in parallel rather than sequentially. This permits sound frequency, duration and amplitude to be analyzed 50&per; faster to minimize false alarms while maintaining the highest possible level of detection. The 5853 can be mounted on any wall or ceiling within a 25' range, with no minimum range limitation. The LEDs indicate test mode, alarms and trouble conditions. It is compatible with all 5800-Series wireless devices.

The 5853 wireless glassbreak detector with transmitter senses the sound of breaking plate, tempered, laminated, wired, coated, and sealed insulating glass. The self-contained detector includes a transmitter that can send alarms, tamper signals, and low battery messages to the control panel. The sensor is compatible with 5800-series wireless hardware, and is designed for continuous operation using one 3V lithium battery (CR-123A or equivalent; included).

Choose a mounting location that is at least 2.1 (7 feet) from floor and no more than 7.6m (25 feet) from the farthest protected glass. Be sure the detector has an unobstructed line-of-sight to the protected glass. Before mounting the detector permanently, test it to ensure that it functions satisfactorily in the chosen mounting location. Verify that the detector can detect glasssbreak sounds, following the directions in the "Testing the Detector" section of the installation guide. Ensure that the 5853 is within range of the receiver, following the instructions for the signal-strength test found in the control panel's installation instructions. If the detector fails, relocate it and repeat both tests.

Product Features:

Test mode can be activated remotely with FG-701 Tester

Four selectable sensitivity settings (Max, Medium, Low and Lowest)

FlexCore™ signal processor

Senses the sound of a variety of glass (tempered, wired, laminate,ordinary plate, etc.)

Hinged-case styling nearly 180° opening

Test mode can be activated remotely with FG-701 Tester

25' range/no minimum range

Four selectable sensitivity settings (Max, Medium, Low and Lowest)

Senses the sound of a variety of glass (tempered, wired, laminate,ordinary plate, etc.)

Sleek design with front and back case tamper

Ten year battery life with easily replaceable batteries

Transmits supervisory, low battery and tamper messages to control panel