Quizzes on the Code

Choose the best answer: 1. Which of the following methods does the Code allow you to use in selecting No. 8 grounded conductors? a. White color b. Three white continuous stripes c. Gray d. Answers “a” and “b” e. Answers “a” and “c” f. All of the above 2. Which of the following methods does the Code allow you to use in identifying No. 3 grounded conductors? a. White paint on the visible side b. White

Advertisement

Advertisement

Choose the best answer:

1. Which of the following methods does the Code allow you to use in selecting No. 8 grounded conductors?

1. d, Sec. 200-6. For the first time, three continuous white stripes join white as a permitted method for grounded conductor identification. The color “gray” is a controlled color, and can’t be used as a grounded conductor identifier. The term “natural gray” refers to the natural color of latex or unbleached muslin. Over 75 years ago when this first went into the Code, conductor insulation consisted of covered natural rubber. Although the term still survives in the Code, these conductors haven’t been in production for generations.

2. b, Sec. 200-6(b). The identifying method has to encircle the conductor. Taking a brush or marker to the outward side only of installed conductors doesn’t do it.

3. a, Sec. 200-7(c)(1). You can reidentify in this direction (making what was white, black) by right, without showing qualified supervision. However, the former allowance to do this on conductors in a raceway is no more. You can withdraw and replace raceway conductors with others having the appropriate insulation color.

4. c, Sec. 200—6(e) Ex. 1. This is the reverse of the previous question (making what was black, white). Here, you may do so only with qualified maintenance/supervision, only in cable assemblies.

5. d, Sec. 200-7(c)(2). Now the principle of reidentification applies to switch loops, just the same as in other cases where you want to take a white wire and use it as an ungrounded conductor. If you do reidentify these wires (as before, only in cable assemblies), then both answers are acceptable. Note this change makes Sec. 200-7(c)(2) functionally redundant to Sec. 200-7(c)(1). The first says you can reidentify white wires generally and use them as ungrounded conductors; the second says the same for switch loops, when you’re using them as ungrounded conductors. No difference.

7. d, Sec. 200-6(d). As previously discussed, gray isn’t allowed, even if this does happen to be a near universal convention. The options are white and white with a stripe. The Code doesn’t say which should be used with the lower system voltage, so it’s up to you to decide which system gets the plain white. Due to the universality of the 277V4gray convention, many local jurisdictions amend this requirement. However, so far, the panel has refused to modify this rule.

EC&M White Papers

In the United States, medium-voltage (MV) power distribution typically uses withdrawable circuit breaker switchgear (WCBS). Withdrawable breakers allow for regular maintenance and provide an easily visible confirmation of circuit isolation but at a cost — having removable parts and the act of inserting and withdrawing breakers could result in the possibility of arc flash incidents. Modern fixed circuit breaker switchgear (FCBS), which uses highly reliable and virtually maintenance-free vacuum and gas breakers, eliminates this concern and introduces other potential advantages....More

Data breaches and other cyber crime cost companies billions each year worldwide, and the damage to brand reputation can be incalculable. Since hackers look for weakly defended systems to attack, this paper presents 5 cybersecurity “best practices” to mitigate system vulnerabilities. Some are commonsense measures like effective password management; others involve securing open ports and other access points, software upgrades, user management, and vulnerability plans....More

A top priority for higher education institutions is to provide a competitive learning environment for their students. In order to succeed, they must address outdated, aging campus facilities. In these older buildings maintenance and operations costs are high, space utilization is inefficient and poorly managed, and current technology is lacking. This white paper explores four strategies for converting campus facilities into a network of smart buildings that address the needs of current and future students....More

Are you protected in the event of short circuit fault? Stainless steel cable ties provide a durable method of bundling, identifying and fastening cable in severe and harsh conditions.
Productivity. Reliability. Safety. We’ve Got You Covered....More