Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Chiller with Plate and Frame heat exhanger

I am working on a chiller with a plate and frame heat exchanger on the leaving water side of the chiller. I am starting to trip on freezestat and want to clean the heat exchanger. I have never taken one apart and would love some advice on what to do and not do from others who have. This is a fairly large heat exchanger and I already purchased some new gaskets just in case. Wondering how you handle the plates once you take it apart to prevent damage while cleaning. Thank you in advance for any help.

I'm a little confused. What is the plate and frame used for? Why do you think it is causing your problem?

yes that's a good question I'm curious too. i had this set up using free cooling.

Also, i would run cleaning solutions through it first if you thinks it dirty. I would not take it apart unless i saw leaks or if you had a restriction. Also, i would look at their chemical treatment process as well.

I'm a little confused. What is the plate and frame used for? Why do you think it is causing your problem?

Sorry for being vague on description. The chilled water leaves the evaporator and is circulated thru a closed pressurised loop into a plate and frame heat exchanger. Chilled water on one side and very nasty process water on the other. Because of the nasty process water they use a plate and frame so it can be pulled apart for cleaning. Problem is I have never done it. Seems pretty straight forward but would like to hear from others who have taken them apart. Just to clarify, the plate and frame is not on the chiller. It is connected to the process side of things and the chilled water is used to cool the nasty process water. Hope this makes it a little more clear.

Take the measurement of the end plates before you loosen it up and write it on the plate.. Take your time and have help to switch out when cleaning.. I dont remove the plates if I dont have to. I clean them in place once you open everything up. Double check those gaskets to make sure they are in place and nothing is on them while putting them back together..

Gotta have the right tool for the job!

Where is all the stuff MADE IN THE USA?

"Thats what we do Troy. Incredible, Invisible, Imbelivable things. We are an Unseen, Unknown, Unvincible fraternity of craftsman.."

We use very large ones for this same reason and we use cleaning solution twice a year. Call a chemical company and they can help you if this is the route you wish to take. If not, call alpha laval or whoever made it and they will give you a procedure to follow.

Take the measurement of the end plates before you loosen it up and write it on the plate.. Take your time and have help to switch out when cleaning.. I dont remove the plates if I dont have to. I clean them in place once you open everything up. Double check those gaskets to make sure they are in place and nothing is on them while putting them back together..

By measurement I assume you mean the distance between the end plates? How do you clean them in place, with a hose?