Question:

Is acceptable a TEMPORARY 120lnft AC feeder (4-2/0 & 1-#4 gnd) running through plenum area without conduit? Also, a 150lnftDC 2/0 feeder running in the same way?

Rafael Colon

A

Answer:

Hey Rafael thanks for your question. You don't say what the temporary wiring is for or which type of wiring method is used for the feeders. Rules in Chapters 7 through 7 can modify the rules in Chapters 1 through 7 as stated in the second sentence of 90.3. Certain cable assemblies and flexible cords can be used for feeders installed as temporary wiring under the conditions provided as stated in 590.4(B). For example, NM cable can be used for temporary wiring in any building or structure because this section modifies 334.10 and 334.12. Typically, this is done during the time periods described in 590.3(A) when the area is not being used for its final intended purpose. The rules in 300.22(C) which apply to spaces used for air handling (plenums) are not specifically modified in Article 590 so they still apply as stated in 590.2(A). If the space is being used as an air handling space, during the time the temporary wiring is installed, it seems the wiring needs to meet the rules in 300.22(C). The AHJ will need to make the final determination.

ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.

IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.

ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.

NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.