DI - Drop-In Chillers

SPACE SAVING DESIGN TO COOL FLUIDS IN A TANK

Mounted on Top of a Tank

Drop-In coolers save floor space and are ideal for installation on tanks where the coolant is too dirty to pump through a heat exchanger. The cooler can readily be lifted out for tank cleaning or inspection.

Model Selection Chart

NOTE: This information is being presented as a guideline only. Your specific application, options and requested features may alter the specifications. Please confirm all specifications with Turmoil.

MODEL

RATED COOLING CAPACITY*

COMP.

STANDARD VOLTAGE**

STANDARD COIL FRAME DIMENSIONS***

INCHES

CENTIMETERS

OIL

BTU/hr

Kcal/hr

hp

W

L

H

W

L

H

OCO-50DI

5000

1500

1/2

V1, V3

22

22

16

56

56

41

OCO-75DI

8060

2000

3/4

V1, V3

22

22

16

56

56

41

OCO-100DI

12000

3000

1

V2, V3

26

26

16

66

56

41

OCO-150DI

18000

4500

1 1/2

V6, V8, V10

26

26

16

66

66

41

OCO-200DI

24000

6000

2

V6, V8, V10

30

30

16

76

66

41

OCO-300DI

36000

9000

3

V6, V8, V10

30

30

16

76

76

41

OCO-500DI

60000

15000

5

V6, V8, V10

32

62

20

81

158

51

OCO-750DI

90000

22500

7 1/2

V6, V8

32

62

20

81

158

51

OCO-1000DI

120000

30000

10

V6, V8

42

70

20

107

178

51

*Capacities based on coolng oil to 80°F (28°C) in a 90°F (32°C) ambient.

**Refer to chart below.

***Options may affect dimensions

Please download our catalog or contact us for complete specifications.

STANDARD VOLTAGE

V0

100/50/1

V1

115/60/1

V2

200/50/1

V3

208-230/60/1

V4

208-230/60/1, 200/50/1

V5

200-240/50/3

V6

208-230/60/3

V7

380-420/50/3, 460/60/3

V8

460/60/3

V9

575/60/3

V10

200-240/50/3, 208-230/60/3

VC

Custom Voltage Contact our engineers for more information.

Click image for larger view.

Drop-In coolers are designed to be mounted on top of a tank to cool the fluid that is passing through it. The stainless steel immersion coil type evaporator is submerged into the fluid in the tank. A small agitation pump continuously moves the fluid around the evaporator coils ensuring proper heat transfer. The temperature controller senses the fluid temperature and controls the refrigeration effect to maintain the fluid in the tank at the desired temperature.

These are a few of our basic options. Click the button below to see all chiller options.

Request a Quote

Download Catalog

TURMOIL COOLER FEATURES

Heavy-Duty Construction. Coolers are designed for continuous industrial duty and dependable long life. Welded steel cabinet features lifting eyebolts and mounting skid. Panels are easily removable for complete access.

High-Ambient Condensers. Oversized to run cool in hot, dirty environments. All condensers are protected with a cleanable aluminum air intake filter.

Ozone-Friendly Refrigerants. Turmoil coolers use only approved, non-ozone-depleting refrigerants. HFC-134a refrigerant is standard on all models with up to 3 HP compressors and optional on all larger models. HCFC-22 refrigerant is standard on all models with 4 HP compressors or larger.