The RemotaPro Twin is a fully automatic floor mounted pumping system suitable for pumping waste from a complete bathroom to a higher level when gravity drainage is not possible and/or economical to install.

The system is suitable for installing either at the initial building stage or retro fitting to existing buildings and can accept waste connections from a toilet, basin, shower or bidet. The system does not need to be connected directly onto the toilet and as so is ideal for remote installation (indoors only) therefore the system can be concealed out of sight. The system is highly reliable due to powerful macerating pumps and is available in single or twin pump configurations.

Dimensions:

Model

Length

Width

Height

RemotaPro Twin

1140mm

850mm

815mm

Specification

Model

Remota Pro Twin

Power Supply

230V AC

Rated Current

5.1a

Motor Rating

750W

Frequency

50Hz

Revolutions per Minute

2850rpm

Max. Vertical Output

14m

Max. Horizontal Output

150m

Max Flow Rate

400 l/m

Max. Liquid Temperature

<40°C

Discharge Size

2”

Cable Length

10m

Weight

115kg

Colour

Black

Control Panel Dimensions

Model

Length

Width

Height

AutoFlushSS Twin

400mm

400mm

210mm

Installation Guidelines

These instructions are for guidance only. Please refer to the full Installation and Operating Guidelines when specifying / installing the product.

Siting the product

The RemotaPro Twin does not need to be connected directly onto the WC pan and so can be sited away from the appliances served. The RemotaPro Twin should be located on a firm level surface lower than the outflow spigot of the WC so as to provide a gravity fall into the unit. It is extremely important to site the RemotaPro Twin with access in mind in the event of maintenance being required.

Inlet connections

The RemotaPro Twin comes complete with 1no. 110mm inlet to accept standard soil pipe. The plastic tank allows other inlets to be drilled to suit. To connect to the Remota Pro from the WC a 110mm soil pipe must be run with sufficient gradient to gravity drain into the unit and pushed into place using the 110mm rubber connector provided.

Discharge connection

The discharge line should be connected to the tank connector on the side of the unit. The pipework required to connect to the RemotaPro Twin should be 2" PVC class E pressure pipe. All joins in the discharge

pipework should be made using solvent cement, under no circumstances should push fit or compression fittings be used.

The RemotaPro Twin is designed for one lift only and the vertical lift should be within 500mm of the unit.

IMPORTANT It is recommended that there are no bends in the vertical lift, however if this is unavoidable a minimum of slow radius bends may be used.

Electrical connection

A qualified person in accordance with the Institute Of Electrical Engineers Regulations should connect the unit to the appropriate mains supply taking into account all the electrical information provided.

IMPORTANT All pump systems must be used with an appropriate motor rated protection device.

Maintenance

It is recommended that the RemotaPro Twin be flushed through every two weeks using standard domestic bleaches, WC cleansers, etc.

IMPORTANT The following items must not be disposed of into the RemotaPro Twin:

• Cotton Wool Buds,

• Baby Wipes,

• Any hard objects, i.e. wood, metals, plastics etc.

• Any fibrous materials such as cloths, rags etc.

• Or similar.

NOTE It is recommended that a service agreement be taken out with a technically qualified company.

Health & safety

As with all site work, the danger of working with water and electricity can pose a severe threat to health if obvious and fundamental precautions are not taken. Therefore if you are in any doubt regarding the installation, please contact us.

All site work must be undertaken by qualified personnel only.

These notes are for guidance only and it is for the installer to ensure the installation is in accordance with all structural and regulatory requirements.

IMPORTANT These instructions are for guidance only. Please refer to the full Installation and Operating Guidelines when specifying / installing the product.