meter/main combo

If this metermain has the meter on the left, and the main on the right, you cannot feed IN the right and OUT the left. The left portion has a separate cover which is locked down by the utility.

the meter is on top and the main disconnect is on bottom. there are 3 ko's in bottom of can. the underground feed is coming from the right hand side and the home feed is to the left. so......i installed to pipe for the UG to the R and feeder to panel L, promblem is divider for primary is to left. any suggestions.....orjust tear everything down and start again

meter/main combo

Well, hopefully it isn't too big of a deal to change things around. You have to have the service feeders seperated from the panel/main disco section. An inspector should not pass it if the feeder is allowed to comingle with any other power.

anything now would be an alteration to the UL lsiting and would not be acceptable. You need to return the meter/panel to original configuration and use it as designed.