We supply the ceiling floor type fan coil unit which passed ISO 9001 and CE certificate. The unit has 18 months warranty. Our companies focus on fan coil unit producing for 10 years. We are expecting become your long-term partner in China.

Product introduction of ceiling floor fan coil nit.

MECO ceiling floor fan coil unit is aim to meet different kind of decoration needs. It can be installed as a high wall mounted fan coil or a floor standing fan coil unit. It have elegant design and quiet running noise. It makes the installation more flexible.

Products specification of ceiling floor fan coil unit

PERFORMANCE OF CEILING FLOOR TYPE FAN COIL(2 TUBE SYSTEM)

model（2 tube system）

MFP-51ZDM

MFP-68ZDM

MFP-85ZDM

MFP-102ZDM

MFP-136ZDM

MFP-170ZDM

MFP-204ZDM

MFP-238ZDM

power supply

220V,50Hz,1Ph

air volume

H

m3/h

510

680

850

1020

1360

1700

2040

2380

M

380

515

660

765

1040

1280

1550

1800

L

260

340

430

530

710

860

1050

1280

static pressure

Pa

0

0

0

0

0

0

0

0

cooling capacity

TH

H

W

2700

3600

4500

5400

7200

9000

10800

12600

BTU/h

9212

12283

15354

18425

24566

30708

36850

42991

SH

W

1990

2730

3174

4261

5385

6746

8109

9062

BTU/h

6790

9315

10830

14539

18374

23017

27668

30920

TH

M

W

2485

3030

3752

4467

6499

7926

9389

10605

W

1571

2015

2450

3071

4278

5447

6669

7262

SH

L

W

2078

2504

2950

3831

5660

7295

8619

8989

W

1212

1545

1844

2397

3317

4460

5300

5555

heating capacity

H

W

4050

5400

6750

8100

10800

13500

16200

18900

M

W

2792

3970

4941

5740

7987

10557

13101

14011

L

W

1788

2801

3533

3907

5464

7048

8714

9778

noise

H

0Pa

dB(A)

39

41

43

45

46

48

50

51

power input

H

0Pa

W

52

62

76

96

134

152

189

228

waterflow volume

m3/h

0.46

0.62

0.77

0.93

1.23

1.54

1.85

2.16

water pressure dropping

kPa

11.8

13.6

21

23

25

32

33

38

dimension of water(in & out)connection pipe

in

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

out

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

coil

type

high efficient copper pipe to wear Hydrophilic aluminum coil

The maximum pressure

MPa

1.6

1.6

1.6

1.6

1.6

1.6

1.6

1.6

dimension of water drain pipe

mm

￠26

￠26

￠26

￠26

￠26

￠26

￠26

￠26

unit dimennsion

L×W×H

mm

905*673*243

1288*673*243

1672*673*243

unit weight

kg

26

28

30

38

40

42

45

45

PERFORMANCE OF CEILING FLOOR TYPE FAN COIL(4 TUBE SYSTEM)

model（4 tube system）

MFP-51ZDM4

MFP-68ZDM4

MFP-85ZDM4

MFP-102ZDM4

MFP-136ZDM4

MFP-170ZDM4

MFP-204ZDM4

MFP-238ZDM4

power supply

220V,50Hz,1Ph

air volume

H

m3/h

510

680

850

1020

1360

1700

2040

2380

M

380

515

660

765

1040

1280

1550

1800

L

260

340

430

530

710

860

1050

1280

static pressure

Pa

0

0

0

0

0

0

0

0

cooling capacity

TH

H

W

2025

2700

3375

4050

5400

6750

8100

9450

BTU/h

6909

9212

11516

13819

18425

23031

27637

32243

SH

W

1532

2102

2444

3281

4146

5194

6244

6978

BTU/h

5227

7172

8339

11195

14146

17722

21305

23809

TH

M

W

1864

2273

2814

3350

4874

5945

7042

7954

W

1210

1552

1887

2365

3294

4194

5135

5592

SH

L

W

1559

1878

2213

2873

4245

5471

6464

6742

W

933

1190

1420

1846

2554

3434

4081

4277

heating capacity

H

W

1620

2160

2700

3240

4320

5400

6480

7560

M

W

1117

1588

1976

2296

3195

4223

5240

5604

L

W

715

1120

1413

1563

2186

2819

3486

3911

noise

high speed

0Pa

dB(A)

39

41

43

45

46

48

50

51

power input

0Pa

W

52

62

76

96

134

152

189

228

waterflow volume

cool

m3/h

0.34

0.45

0.56

0.67

0.89

1.11

1.33

1.55

heat

0.14

0.19

0.24

0.29

0.39

0.49

0.59

0.69

water pressure dropping

cool

kPa

8.4

9.7

14.9

16.3

17.8

22.7

23.4

27

heat

3.5

4.1

6.3

6.9

7.5

9.6

9.9

11.4

dimension of water(in & out)connection pipe

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

ZG3/4"

coil

type

high efficient copper pipe to wear Hydrophilic aluminum coil

dimension of water drain pipe

mm

￠26

￠26

￠26

￠26

￠26

￠26

￠26

￠26

dimension

L×W×H

mm

905*673*243

1288*673*243

1672*673*243

weight

kg

27

29

31

39

41

43

46

46

Products Feature and details

1 The classical elegant design. It can be installed by ceiling mounted, floor standing or wall mounted.

2 Completely model

3 Different kinds of controller can be choose, remote controller is standard

4 Stainless steel hose can be installed as inlet/outlet water connection

5 Easily interfaced with most widely used Mod-bus and proprietary supervisory system based on mod-bus protocol.