we can supply many kinds of Distribution-Cabinet &comma;if you need please contact us Low Voltage MCB & RCCB

The low voltage MCCB&sol;MCBs shall comply with the following requirements&colon;

MCCB&sol;MCBs shall comply fully with IEC 898&comma; 1995 or IS 8828&comma; 1996 or BS EN 60947-2 and the case shall be of moulded insulating material of good mechanical strength and non-tracking properties&period;

RCCB&sol;MCBs shall be of manual&sol;automatic tripping operation&period; The automatic type shall each incorporate a trip unit to provide overload and short circuit protection&period;

Each RCCB&sol;MCB shall incorporate "Trip free" mechanism to ensure that the breaker can not be held closed in fault condition&period;

The operating mechanism of the RCCB&sol;MCBs shall be hermetically sealed&period;

MCCB&sol;MCBs shall be of Energy limitation Class 3The rated voltage shall be 415&sol;240V ACThe breaking capacity shall be 6kA&period;The degree of protection - IP 20The Impulse withstand voltage- 6kVElectrical life - 10&comma;000 operationsHouse Service RCCB&sol;MCB The house services RCCB&sol;MCBs shall be installed on the house distribution board to protect the meter and also the distribution system from any possible fault in the house&period; The supplier shall include the appropriate fixing attachments of each of the RCCB&sol;MCBs with the house distribution boards&period; The RCCB&sol;MCBs shall comply with the following requirements&colon;

i&rpar; RCCB&sol;MCBs shall comply fully with IEC 898&comma; 1995 or IS 8828&comma; 1996 or BS EN 60947-2 and the case shall be of moulded insulating material of good mechanical strength and non-tracking properties&period;

ii&rpar; RCCB&sol;MCBs shall be of manual&sol;automatic tripping operation&period; The automatic type shall each incorporate a trip unit to provide overload and short circuit protection&period;

iii&rpar; Each RCCB&sol;MCB shall incorporate "Trip free" mechanism to ensure that the breaker can not be held closed in fault condition&period;

iv&rpar; The operating mechanism of the RCCB&sol;MCBs shall be hermetically sealed&period;