Application: Self-contained eyewash and eyewash/drench hose units are ideal for use in low traffic areas, and where a continuous supply of potable water is unavailable for plumbed units. 56.78L pressurized units are ideal for floor placement near any hazard, and deliver approximately 37.9 usable liters of water for 15 minutes, thus complying with the provisions of ANSI Z358.1-2014 for eyewashes.

Operation: To operate unit, fill with clean potable water and add bacteriostatic additive (supplied with unit). Additive protects against growth of bacteria, fungus, algae and acanthamoeba. After filling with water, pressurize unit to 80 PSI. If necessary, adjust pressure regulator to achieve maximum flow for 15 minutes. Unit should be inspected regularly and water should be changed at least once every six months. Filling instructions included.

Weight: 16.15kg empty and 53.93kg filled

Sign: ANSI compliant identification sign permanently affixed to tank.

Quality Assurance: Unit is fully assembled, pressurized and water tested at the factory. Unit is depressurized and emptied prior to shipping. Some assembly required in field.