Dual system installed in closet

This 30 kilowatt system (MS Super 6E) requires two (2) steam generators in tandem which makes two of every thing to be installed. This install does not meet access requirements as the left side is pressed up to the closet wall when 12” of clearance is required. Also, the pressure relief valve (PRV) is piped into the steam shower which is a danger of scalding hot water if the PRV were to activate during a steam bath session.