The space efficient PPT Series Pump Tank Station utilizes a vertical
dimension for water storage, and an integral pump platform deck to
minimize floor space footprint. The polyethylene reservoir is rust and
corrosive resistant and will not degrade. The PPT Series is designed
and engineered for round-the-clock operation with minimal services,
providing maximum return on investment.

Features:

Capacities From 450 to 3200 Gallons

Tower or Chilled Water Systems

Flows From 40 to 1250 GPM

Rotationally molded linear low-density polyethylene construction

One piece, seamless, cylidrical shape reservoir

Water-level Control

Pre-wired Magnetic Pump Motor Starters

Structural Steel Deck for Pump Mounting

Flexible Connections

System can be customized to meet any needs

The PPT Series Pump Tank Station is space efficient, utilizing and vertical dimension for water storage and an integral pump platform to its minimize floor space footprint.

High flow, high turbulent pumps offer maximum heat transfer across the process. A paten pending polyethylene reservoir is a seamless, one-piece design that resists rust, corrosion, and will not degrade.

Safety features include overload protection and thermostat control of the tower fan where necessary.

The centrifugal, motor driven pump has flexible connections, a bronze impeller, and suction/discharge service vale kits. The structural steel pump deck mounting is sturdy yet minimizes the floor space necessary for the unit.

All components are shipped loose and field assembled. All drawings are supplied for easy assembly.

Available options include; a standby pump and discharge manifold with isolation valves, and a pre-wired control cabinet for starters and controls.

PPT SERIES SPECIFICATIONS

PPT-450

PPT-850

PPT-1600

PPT-3200

WATER
CAPACITY
(Gallons)

TO OVERFLOW

450

850

1600

3200

TOWER DRAIN

225

425

800

1600

CHILLED WATER

350

675

1200

2400

CONNECTIONS

WATER MAKE-UP

1"

1"

1"

1"

TANK DRAIN

1-1/2"

1-1/2"

1-1/2"

1-1/2"

TANK OVERFLOW

4"

4"

6"

6"

DIMENSIONS

HEIGHT

60"

72"

96"

96"

WIDTH

48"

60"

72"

160"

DEPTH

50"

62"

74"

74"

DEPTH w/PUMP BASE

36"

36"

48"

48"

WEIGHT

DRY

860 lbs

1590 lbs

2243 lbs

4636 lbs

OPERATING

2750 lbs

5160 lbs

8963 lbs

18076 lbs

MAXIMUM

4640 lbs

8730 lbs

15683 lbs

31516 lbs

SHIPPING

860 lbs

1590 lbs

2243 lbs

2636 lbs

P SERIES PUMP SPECIFICATIONS
Process/Standby Pump Model

PP-2

PP-3

PP-5

PP-7.5

PP-10

PP-15

PP-20

PP-25

PP-30

PP-40

PP-50

PP-60

PUMP

HP

2.0

3.0

5.0

7.5

10.0

15.0

20.0

25.0

30.0

40.0

50.0

60.0

GPM/PSI

40/40

60/60

90/60

150/60

210/60

360/60

405/60

525/60

600/60

900/60

1000/60

1250/60

FULL LOAD
AMPERAGE 1

230/3/60

6.8

9.6

15.2

22.0

28.0

42.0

54.0

68.0

84.0

104.0

130.0

154.0

460/3/60

3.4

4.8

7.6

11.0

14.0

21.0

27.0

34.0

42.0

52.0

65.0

77.0

575/3/60

2.7

3.9

6.1

9.0

11.0

17.0

22.0

27.0

32.0

41.0

52.0

62.0

TP SERIES PUMP SPECIFICATIONS
Tower/Evaporator Pump Model

TP-2

TP-3

TP-5

TP-7.5

TP-10

TP-15

TP-20

TP-25

TP-30

TP-40

PUMP

HP

2.0

3.0

5.0

7.5

10.0

15.0

20.0

25.0

30.0

40.0

GPM/PSI

60/30

90/30

210/30

255/30

405/30

525/30

810/30

900/30

1100/30

1750/30

FULL LOAD
AMPERAGE 1

230/3/60

6.8

9.6

15.2

22.0

28.0

42.0

54.0

68.0

84.0

104.0

460/3/60

3.4

4.8

7.6

11.0

14.0

21.0

27.0

34.0

42.0

52.0

575/3/60

2.7

3.9

6.1

9.0

11.0

17.0

22.0

27.0

32.0

41.0

1 Full Load Amps shown. No allowance for in-rush. Full Amps are higher than Run Load Amps and must be used for sizing disconnects and supply wiring

Manufacturers of High-Quality
Products for the Plastics Molding Industry