Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Had a full day

The service calls were coming in like crazy yesterday. We had a few good ones too.

Nice storm collar.

Complaint on this one was the suction line was sweating more than normal. I guess so. lol Needless to say, the unit was over charged. The black spot on the drain pipe was where it was running behind the single wall vent pipe.

This was the next to last call of the day. Contactor was stuck ("electrician" put in) and condenser wouldnt shut off. Customer was not happy at all with his other work too. lol Somebody knew just enough to make a big mess on this one. There were burnt connections everywhere. I just ripped it all out and started over.

Nice low pressure switch. They also left the factory drier in place when the compressor was changed out.

I'm not sure if there was a purpose to their piping method or if they were just trying to make it match the suction line.