Addressable Module 2 Powered Supervised Relay with Isolator

The range of MAD-400-I modules has been developed to offer a wide and complete range of input and output ports to be used with Detnov's CAD-150 family of analogue fire control panels. These modules let you manage a wide variety of situations, by monitoring and acting according to the installation's requirements.

The MAD-400-I modules have been designed to facilitate their installation process, and they may be installed using screws or fitted into a DIN rail. Each module is equipped with removable terminal blocks and a LED status indicator. The addressing of the modules is carried out through the PGD-200 programmer.

The MAD-431-I and MAD-432-I modules provide 1 or 2 supervised 24V outputs which may be configured through a micro-switch as supervised voltage outputs or a supervised sounder outputs. When they are configured as a sounder output, switching the sounder control panel's keys on and off will control the modules by switching the outputs of the modules on and off.

The MAD-431-I and MAD-432-I modules require a 24V auxiliary power supply to supply the loa

■ Simple installation on the wall or fitted into a DIN rail■ Non-polarity supported■ Addressing through a programmer■ Stable communication protocol with immunity to noise■ Requires an auxiliary 24V power supply■ Connections through removable terminal blocks, and simple fitting of the cable■ EN54-18 and EN54-17 approved

The MAD-431-I and MAD-432-I modules are ideal for connecting conventional sounders to the analogue system, and provide savings in the total installation cost. They are ideal for activating any device which requires 24V.