YARMAX Pwer Automatic Synchronization System is adoping the PLC (programmable logic controller) or the DSE8610 Intelligent Parallel Generating Set made by UK Deep Sea Electrics plc. The DSE8610 series module has been specially designed to allow the operator to start and stop the generator, and if required, transfer the load to the generator either manually ( via fascia mounted pust-button) or automatically.Automatic Synchronization system is suitable for 2 or more than 2 units gensets using in the same time. The main function as following:1. Each genset running and providing power in the time,2. After genset is synchronized, the power is distributed resonably and the distance rate is not less than 10%3. To add power when heavy loading and reduce power when loading,4. Both operation type by manual or automatic,5. To synchronized by manual, then to distribute or transfer actual power,6. The safety protecting function including over current, over loading, high voltage or low voltage.

Standard control panel is the basic configure for normally operation and usage. The advantages of this panel are easy operation, aomprehensive function and reliable protection and so on. There are indicating gauges, lamps, transfer switches and emergency stop button, etc. The control panel wil stop the whole generator set and alarm as well when malfunction appears.

LED Automatic Control Panel is a kind of intelligent controller with LED displaying the operating mode of the controller and the running state of the generator sets. It can configure the control procedure and protection parameter of the generator set, and completely satisfied the automatic controlling requirement of the generator sets for the user or factory.

LCD Automatic Control Panel is the configuration for nobody on duty controlling generator sets. This kind of panel adopts module control system, with large LCD screen to show the menu. The module can receive output signal from ATS and realize automatic start and stop the generator sets. ATS(Fully Automatic) is the standard configure of emergent power system. It detects the voltage andFrequency of main power timely. While there is something wrong, such as high voltage, low voltage, phase missing, electricity cutting off, etc., it will signal to start the generator set automatically; While main power resumes balanced, it controls the generator set to shut down after cooled.

All canopy designed with modular principlesAll metal canopy parts painted by electrostatic polyester power paintSoundproof design ensure that the noise level be controlled in small scopeConvenient to lift and moveEasy to maintenance and operate

Base Frame

Base frame including position for forklift and craneIntegral fuel tankDaily fuel tank continuously supply for 8-24 hoursFuel tank easy to maintain and cleanAnti-vibration pads are flexed between engine and alternator.

Control SystemControl, monitor and protect the Generator Set including:

High water temperatureLow oil pressureOver and under speedOver currentUnder/Over generator voltageStart and stop failureLow and high battery voltageCharge failEmergency stop