Nicholas L.

Nicholas L.

Fire Suppression Inspection
Semiannual Kitchen Fire Suppression System Inspection - QTY 2Main Hood - PCL-460 - HYDRO 2011
Small Hood - KP-275 - HYDRO 2007
Deficiency: Main kitchen system: System is non compliant due to improper coverage of the lava chargrill and range with back shelf. Chargrill currently has 2x 1H nozzles, these need to be changed to 3x 1L nozzles and piped under the shelf for proper protection. Range currently has a 1H and a 2H, these need to be changed to 2x 2L due to back shelf.Lava Rock Char-Broiler (624 in. 2 (40257 mm 2) x 26 in.
(660 mm) longest side maximum)
Note: Synthetic rock charbroilers are distinguished by the use of lava, pumice, or synthetic rocks that are used for cooking.
One nozzle is available for lava rock char-broiler protection: High proximity and low proximity.
The 2L Nozzle (Part No. 551027) is used for high proximity lava rock char-broiler protection. This nozzle is a two flow nozzle. The nozzle must be located anywhere within the perimete

Near Duck Mill Rd, Fitchburg, MA01420

230 days ago

Nicholas L.

Kitchen Hood Suppression System - NON COMPLIANT
Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiencies were found on order 14196023Correct system deficienciesRepair of these deficiencies is essential to overall life safety. Please see attached compliance quote. If you have any questions, feel free to call me.
Thank you
Mike McDonald
603-988-5512Fire Suppression Repair
The nozzles for the appliance protection are all outside the perimeter of the appliances. The fryer nozzles are not in the proper position. The griddle requires a second 11982 nozzle for its protection.the nozzles for the 6 burner (with back shelf)protection are not the proper ones. The nozzle for the griddle protection is not the proper one ( there is an upright broiler on top of the griddle). The nozzle for the upright broiler is not the proper one. All the pipe and conduit outside the hood is painted

Near Lunenburg St, Fitchburg, MA01420

230 days ago

Nicholas L.

Kitchen Hood Suppression System - NON COMPLIANT
Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiencies were found on order 14196023Correct system deficienciesRepair of these deficiencies is essential to overall life safety. Please see attached compliance quote. If you have any questions, feel free to call me.
Thank you
Mike McDonald
603-988-5512Fire Suppression Repair
The nozzles for the appliance protection are all outside the perimeter of the appliances. The fryer nozzles are not in the proper position. The griddle requires a second 11982 nozzle for its protection.the nozzles for the 6 burner (with back shelf)protection are not the proper ones. The nozzle for the griddle protection is not the proper one ( there is an upright broiler on top of the griddle). The nozzle for the upright broiler is not the proper one. All the pipe and conduit outside the hood is painted

Near Lunenburg St, Fitchburg, MA01420

231 days ago

Michael S.

Near Clarendon St, Fitchburg, MA01420

231 days ago

Michael S.

Near Fairmount St, Fitchburg, MA01420

231 days ago

Michael S.

Near Fairmount St, Fitchburg, MA01420

231 days ago

Michael S.

Near Prichard St, Fitchburg, MA01420

239 days ago

mark g.

Near Fairmount St, Fitchburg, MA01420

241 days ago

mark g.

Near Plymouth St, Fitchburg, MA01420

241 days ago

mark g.

Near Clarendon St, Fitchburg, MA01420

242 days ago

mark g.

Near Prichard St, Fitchburg, MA01420

242 days ago

mark g.

Near Academy St, Fitchburg, MA01420

262 days ago

Michael S.

Near John Fitch Hwy, Fitchburg, MA01420

371 days ago

mark g.

Near Townsend St, Fitchburg, MA01420

438 days ago

Nicholas L.

Customer is COD. see comment below for pricingFire Suppression Inspection
KITCHEN SYSTEM - QTY 1
PCL-460KS ALL INCLUSIVE
Deficiency: System is non compliant due to system cylinder needing hydro testing. Cylinder (PCL460) is dated for 2005 and is due for hydro every 12 years per nfpa.