Features

Works with 1" through 2" brace pipes and 1/4" angle iron braces to reduce inventory

Slotted design grabs service pipe for added gripping strength

Meets NFPA®-13 requirements for seismic sway bracing

Specifications

Part Number

CSBSTU1000EG

Material

Steel

Finish

Electrogalvanized

Pipe Size

10"

A

18"

B

2"

Brace Pipe Size

1" – 2"

Certifications

cULusFMOSHPD

Standard Packaging Quantity

5 pc

UPC

78285663459

EAN-13

8711893063691

UL Loads (Listed for
Restraints)

Part Number

Dyna-Flow® Service Pipe

Sch 10 Service Pipe

Sch 40 Service Pipe

CSBSTU0100xx

N/A

655 lb

655 lb

CSBSTU0125xx

655 lb

655 lb

655 lb

CSBSTU0150xx

655 lb

655 lb

655 lb

UL Loads (Listed for
Sway Braces)

Part Number

Lateral

Longitudinal

Dyna-Flow® Service Pipe

EZ FLOW™ Service Pipe

Sch 10 Service Pipe

Sch 40 Service Pipe

Dyna-Flow® Service Pipe

EZ FLOW™ Service Pipe

Sch 10 Service Pipe

Sch 40 Service Pipe

CSBSTU0200xx

3,000 lb

N/A

3,000 lb

3,000 lb

N/A

N/A

N/A

N/A

CSBSTU0250xx

3,000 lb

N/A

3,000 lb

3,000 lb

2,015 lb

N/A

2,015 lb

2,015 lb

CSBSTU0300xx

3,000 lb

N/A

3,000 lb

3,000 lb

2,015 lb

N/A

2,015 lb

2,015 lb

CSBSTU0400xx

3,000 lb

3,000 lb

3,000 lb

3,000 lb

2,015 lb

N/A

2,015 lb

2,015 lb

CSBSTU0500xx

N/A

3,000 lb

3,000 lb

3,000 lb

N/A

N/A

2,015 lb

2,015 lb

CSBSTU0600xx

N/A

3,000 lb

3,000 lb

3,000 lb

N/A

2,015 lb

2,015 lb

2,015 lb

CSBSTU0800xx

N/A

N/A

3,000 lb

3,000 lb

N/A

N/A

2,015 lb

2,015 lb

CSBSTU1000xx

N/A

N/A

3,000 lb

3,000 lb

N/A

N/A

3,000 lb

3,000 lb

FM Loads (Lightwall,
Sch 10 and Sch 40 Service Pipes)

Part Number

Horizontal Capacity
per Installation Angle from
Vertical

Lateral

Longitudinal

30°-
44°

45°- 59°

60°- 74°

75°- 90°

30°- 44°

45°- 59°

60°- 74°

75°- 90°

CSBSTU0100xx

860 lb

1,220 lb

1,500 lb

1,670 lb

970 lb

720 lb

860 lb

960 lb

CSBSTU0125xx

860 lb

1,220 lb

1,500 lb

1,670 lb

970 lb

720 lb

860 lb

960 lb

CSBSTU0150xx

860 lb

1,220 lb

1,500 lb

1,670 lb

970 lb

720 lb

860 lb

960 lb

CSBSTU0200xx

1,530 lb

2,160 lb

2,650 lb

2,960 lb

870 lb

690 lb

830 lb

930 lb

CSBSTU0250xx

1,530 lb

2,160 lb

2,650 lb

2,960 lb

870 lb

690 lb

830 lb

930 lb

CSBSTU0300xx

1,530 lb

2,160 lb

2,650 lb

2,960 lb

870 lb

690 lb

830 lb

930 lb

CSBSTU0400xx

1,570 lb

2,220 lb

2,720 lb

3,030 lb

1,550 lb

1,390 lb

1,680 lb

1,870 lb

CSBSTU0500xx

1,570 lb

2,220 lb

2,720 lb

3,030 lb

1,550 lb

1,390 lb

1,680 lb

1,870 lb

CSBSTU0600xx

1,980 lb

2,810 lb

3,440 lb

3,840 lb

1,470 lb

1,170 lb

1,410 lb

1,570 lb

FM Loads (0.188" wall
and Sch 40 Service Pipes)

Part Number

Horizontal Capacity
per Installation Angle from
Vertical

Lateral

Longitudinal

30°-
44°

45°- 59°

60°- 74°

75°- 90°

30°- 44°

45°- 59°

60°- 74°

75°- 90°

CSBSTU0800xx

2,040 lb

2,890 lb

3,540 lb

3,950 lb

1,200 lb

1,700 lb

2,090 lb

2,330 lb

CSBSTU1000xx

2,040 lb

2,890 lb

3,540 lb

3,950 lb

1,200 lb

1,700 lb

2,090 lb

2,330 lb

Pentair, CADDY, CADWELD, CRITEC, ERICO, ERIFLEX, ERITECH and LENTON are owned by Pentair or its global affiliates. All other trademarks are the property of their respective owners. Pentair reserves the right to change specifications without prior notice.

WARNING
Pentair products shall be installed and used only as indicated in Pentair's product instruction sheets and training materials. Instruction sheets are available at www.erico.pentair.com and from your Pentair customer service representative. Improper installation, misuse, misapplication or other failure to completely follow Pentair's instructions and warnings may cause product malfunction, property damage, serious bodily injury and death and/or void your warranty.