***This is a do-able replacement motor for Lennox in regards to part specification. Mounting bracket is not included. May need some additional hardware to help blower motor mount correctly.***

WHEN PLACING YOUR PARTS ORDER, YOU CAN ORDER ONLINE 24 HOURS A DAY OR BY CALLING OUR SALES CENTER MONDAY THROUGH FRIDAY 7AM TO 5PM PACIFIC TIME. WE WILL SHIP YOUR PART FROM THE CLOSEST WAREHOUSE PER YOUR ZIP CODE. WE CAN SHIP YOUR PARTS TO YOU NEXT DAY AIR, SECOND DAY AIR OR 3 DAY SELECT OR U.S. POST OFFICE, AND WHEN PLACING YOUR ORDER ONLINE SHIPPING ESTIMATES WILL BE PROVIDED TO YOU FOR EACH SHIPPING CLASS.

PLEASE NOTE: Replace the Run Capacitor EVERY TIME the Motor is replaced. All PSC Motors are design to be used with an external capacitor. The Capacitor operates in the Motor Circuit continuously. It is commonly referred to as a run capacitor. The Run Capacitor is designed to keep a constant and even flow of power going to the Motor. The Run Capacitor is sold separately. * Order New Run Capacitor Part Number: CAP15370

INSTALLATION INSTRUCTIONS:

Old Motor has 4 Speeds but system is only using two motor speeds at any given time.
Connect from new motor BLACK wire to Black Hi Speed for Air Conditioning.
RED wire to Red wire for Low Speed for Heating.
WHITE wire to White wire Common.
The two Brown wires go to the Run Capacitor either wire to either side of the Capacitor.
The other two wires left over are Med Low and Med High connect to the proper colors or just cap off using wire nuts and electrical tape.