Electronic volume flow controllers of Type Universal (dynamic) are designed for use with VAV terminal units.

Dynamic differential pressure transducer and electronic controller are fitted together in one casing

Actuator or spring return actuator is separate

The output signals of the room temperature controller, central BMS, air quality controller or similar units control the volume flow rate setpoint

Override control by means of switches or relays

Volume flow rate actual value is available as linear voltage signal

Controller parameters are factory set

On-site adjusting is not required

Standard filtration in comfort air conditioning systems allows for use of the controller in the supply air without additional dust protection. Since a partial volume flow is passed through the transducer in order to measure the volume flow rate, please note:

With heavy dust levels in the room, suitable extract air filters must be provided.

If the air is polluted with fluff or sticky particles or contains aggressive media, Universal (dynamic) controllers cannot be used

Attachment (max. 10MB)

Your message

Your message to

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +61 (02) 8923 2551

Attachment (max. 10MB)

Your message

Your message to

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +61 (02) 8923 2551