Air Conditioning Disconnects Molded Case Switches

Air conditioning disconnects from Schneider Electric are Underwriters Laboratories (UL) Listed NEMA Type 3R rainproof. They are designed to meet all current National Electrical Code (NEC) requirements for a disconnecting means on residential and commercial air conditioning installations, as well as other single-phase applications, such as swimming pools and pump houses. (3150CT0401)

Square D Load Center Short-Circuit Current Ratings

This document defines fully-rated systems, two-tier series short circuit current protection and three-tier series short circuit current protection. It also addresses NEC requirements and illustrates series rating labels currently provided with Square D multi-mete ring and load center equipment manufactured by Schneider Electric. The location of series rating labels applied to Square D load centers is depicted on pages 2 and 3 of this document (4100DB0301)

Switchboard/Panelboard Short-Circuit Current Ratings

This document addresses Underwriters Laboratories (UL) short-circuit current rating (SCCR) requirements for switchboards and panelboards, along with three methods of system protection. It also provides circuit breaker interrupting ratings, series ratings tables, a fuse cross reference table, and typical application examples. (2700DB9901)

Air Conditioning Disconnects Molded Case Switch

Air conditioning disconnects from Schneider Electric are Underwriters Laboratories (UL) Listed NEMA Type 3R rainproof. They are designed to meet all current National Electrical Code (NEC) requirements for a disconnecting means on residential and commercial air conditioning installations, as well as other single-phase applications, such as swimming pools and pump houses. (3150CT0401)

Solar Disconnect Switches

The Square D brand 1000 VDC disconnect switch functions as a local disconnect for a string of Photovoltaic (PV) panels and is UL98B certified (file E343341) and IEC 60947 compliant (file 136861) for use in PV Systems at a maximum of 1000 VDC. This disconnect is available in both 100 and 200 amp, three and four pole versions. (3100HO1101)

PowerLogic Factory Assembled Equipment

This catalog covers equipment for service entrances and on-site generation, power mitigation and main power distribution equipment, PDUs and data servers, feeders for process, lines, machines or equipment, and high density metering for tenants, departments, and subcontractors. (3000CT0801)

XR Series Surge Protective Devices

Square D brand Surgelogic XR series products are compact and affordable Surge Protective Devices (SPDs). XR series SPDs offer a simple means to bring down initial surges to manageable levels and can offer additional value in a cascaded SPD system. Their compact design allows surge suppression to be installed adjacent to power panels or directly on sensitive equipment. (9990-0121)

Masterpact NW DC Circuit Breakers

Masterpact NW Circuit Breakers are designed to protect electrical systems from damage caused by short circuits. All Masterpact circuit breakers are designed to open and close a circuit manually, and too pen the circuit automatically at a predetermined overcurrent setting. Selection of a dc circuit breaker is based on the type of dc system, the rated voltage, and the maximum short-circuit current at the point of installation. UL® Listed circuit breakers are for use on ungrounded systems rated 500 Vdc (600 Vdc unloaded) or less. IEC Rated circuit breakers are for use on ungrounded, grounded middle point, or grounded negative systems. (0613CT0501)

Multi 9 System Catalog

The Multi 9 modular system of miniature circuit breakers and supplementary protectors, accessories, and peripherals provides complete protection of equipment or especially sensitive circuits within the equipment. Installation labor and space are both minimized by the modular architecture of the Multi 9 system, whether a single protective device or multiple devices with their accessories are being used. Schneider Electric offers an extensive line of UL 489 Circuit Breakers and UL 1077 Supplementary Protectors. In addition, a variety of IEC certified Circuit Breakers and Accessories are available forOEM's whose products are destined for export beyond North America. To an OEM, this means that one family of electrical protection products can be used regardless of equipment destination. The Standards include: Potential applications include semi-conductor machines, communication equipment, process control panels, computers, medical equipment, electronic controls, transformers, power supplies, and other electrical equipment. (0860CT0201)

PowerPact D-Frame Circuit Breakers & Switches

PowerPact D-frame electronic trip molded case circuit breakers are designed to protect electricalsystems from damage caused by overloads and short circuits. All circuit breakers are designed to open and close a circuit by nonautomatic means and to open the circuit automatically on a predetermined overcurrent. The D-frame circuit breakers use an electronic trip system to signal the circuit breaker to open automatically. (0616CT0801)

PowerPact H-, J-, & L-Frame Circuit Breakers

H-frame and J-frame and L-frame molded case circuit breakers are designed to protect electrical systems from damage caused by overloads and short circuits. All circuit breakers are designed to open and close a circuit by nonautomatic means and to open the circuit automatically on a predetermined overcurrent. (0611CT1001)

PowerPact Q-Frame Circuit Breakers & Switches

The PowerPact Q-frame line of circuit breakers include QB, QD, QG and QJ molded case circuit breakers and QB automatic switches. They are rated 240 Vac, 250 A max. and are available in lug or bus-connected unit-mount constructions, or I-Line group-mounted construction. (0734CT00201)

QO and QOB Miniature Circuit Breakers

This catalog provides general information on QO and QOB circuit breakers and special application circuit breakers. This document also includes trip curves, and basic qo circuit breaker dimensions. (0730CT9801)

QOU Unit Mount Miniature Circuit Breakers

QOU miniature circuit breakers are unit-mount (lug/lug) thermal-magnetic circuit breakers which: provide a means to manually open a circuit, automatically open a circuit under overload or short circuit conditions, feature common tripping of all poles, have a Visi-Trip trip indicator, can be flush-, surface-, or DIN rail-mounted, have lugs at both ends (cable-in/cable-out construction), operate in any position, and are fully tested, UL Listed, and CSA certified for reverse connection without restrictive line/load markings. (0720CT9401)

Vigirex Ground-Fault Relays

Vigirex ground-fault relays, with associated sensors (current transformers), measure the leakage current in an electrical installation to detect levels that may be damaging. When used for protection, they cause an associated circuit breaker or switch to interrupt the supply of power to the protected system. They may also be used for monitoring only, with output to an alarm. (0972CT0401)

Manual Motor Control Switches and Disconnects

This catalog covers Mini-VARIO and VARIO manual motor control switches and GS1 and GS2 fusible and LK4 nonfusible disconnect switches. This document also includes related accessories and dimensions. (9420CT0301)

I-Line Combo Panelboards

The I-Line Combo Panelboard combines an NQ or NF lighting section with an I-Line power distribution section in a single panelboard. This is an industry-exclusive addition to the Schneider Electric Square D brand I-Line Power Distribution Panelboard offer, designed for use in both AC and DC systems. It is available in single or duplex configurations, which determine the number of included lighting sections. All main circuit breaker panelboards rated 800 A or less are suitable for use as service entrance. (2110CT1301)

Replacement Parts: NF Panelboards, Main Lugs and Main Circuit Breakers

Integrated Power Center

Integrated Power Centers (IPCs) manufactured by Square D combine power distribution and controls into one integrated package. The IPC may consist of I-Line power panels, NQOD, NF, and Powerlink lighting and appliance panels with starters, relays, timers, power meters, circuit monitors, TVSS units, lighting contactors, HVAC cont roller, energy management systems, lighting controls, time clocks, transformers, and power conditioners. Integrated Power Centers are suitable for use on ac systems through 480 V and can be applied as service entrance equipment. IPCs are Underwriters Laboratories (UL) Listed under file E83877. (2735CT0001)

IPC2 Transformer Combo

IPC2 Integrated Power Center 2

Square D Integrated Power and Control Solutions (IPaCS) integrates electrical distribution and controls in a factory assembled and pre wired solution. Designed with the flexibility to meet individual customer requirements, Integrated Power Center 2 (IPC2) enclosures are available with NQ, NF, and I-Line panelboard interiors and distribution dry transformers. (2230DB0601)

Integrated Power Center

Integrated Power Centers (IPCs) manufactured by Square D combine power distribution and controls into one integrated package. The IPC may consist of I-Line power panels, NQOD, NF, and Powerlink lighting and appliance panels with starters, relays, timers, power meters, circuit monitors, TVSS units, lighting contactors, HVAC cont roller, energy management systems, lighting controls, time clocks, transformers, and power conditioners. Integrated Power Centers are suitable for use on ac systems through 480 V and can be applied as service entrance equipment. IPCs are Underwriters Laboratories (UL) Listed under file E83877. (2735CT0001)

Masterclad Medium Voltage Arc-Resistant Switchgear

Square D Masterclad medium voltage passive arc-resistant (AR) switchgear is designed with utilities and industrial customers in mind who demand the highest quality power distribution equipment available today. This switchgear and all its components meet ANSI/IEEE C37.20.2 and all other applicable ANSI, UL and CSA standards for metal-clad switchgear. The use of Masterclad medium voltage AR switchgear provides an additional degree of protection to personnel working in close proximity, while the equipment is operating

Power-Style Low Voltage Switchboards

Power-Style Low Voltage Switchboards QED-2 and Speed-D Merchandised Service Section Switchboards. Power-Style Low Voltage Switchboards provide a convenient and economical means of distributing electric power. These enclosed, free-standing structures contain circuit breaker or fusible overcurrent protection for services rated up to 5000 A with a maximum voltage of 600 Vac. Power-Style QED-2 switchboards are custom-made for use as service entrance equipment or as distribution centers in commercial, institutional, and industrial applications.

I-Line Panelboards and Switchboards

Power-Style QED-2 Low Voltage Switchboards

Power-Style QED-2 switchboards provide a convenient and economical means of distributing electric power. These enclosed, free-standing structures contain circuit breaker or fusible overcurrent protection for services rated up to 5,000 A with a maximum voltage of 600 Vac. Power-Style QED-2 switchboards are custom-made for use as service entrance equipment or as distribution centers in commercial, institutional,and industrial applications. (2742CT9501)

Power-Style QED-2, Series 2 Low Voltage Switchboards

Power-Style QED-2, Series 2 switchboards provide a convenient and economical means of distributing electric power. These enclosed, free-standing structures contain circ uit breaker or fusible overcurrent protection for services rated up to 2,500 A with a maximum voltage of 600 Vac. Power-Style QED-2, Series 2 switchboards are custom-made for use as service entrance equipment or as distribution centers in commercial, institutional, and industrial applications. (2742CT1001)

Power-Style QED-6 Rear-Connected Switchboard

Power-Style QED-6 rear-connected switchboards with Masterpact and PowerPact Circuit Breakers are designed to provide superior electrical distribution, protection, and power quality management for the entire facility. The prime components are Masterpact NW, Masterpact NT, Powerpact D, Powerpact H, and Powerpact J circuit breakers. QED-6 switchboards are designed to maximize the functionality of these circuit breakers, which, in turn, delivers maximum uptime, system selectivity, and circuit protectionall of this in a fully withdrawable construction. (2746CT0101)

Power-Zone 4 Metal-Enclosed, Drawout Switchgear

Power-Zone 4 low voltage, metal-enclosed, drawout switchgear with Masterpact NW and NT Low Voltage Power Circuit Breakers is designed to provide superior electrical distribution, protection, and power quality management for the entire facility. The prime components of the switchgear are the Masterpact NW and Masterpact NT ANSI-rated circuit breakers. Power-Zone 4 switchgear is designed to maximize the functionality of the Masterpact NW and NT circuit breakers, which, in turn, deliver maximum uptime, system selectivity, ease of maintenance and circuit protection. All of this in the smallest footprint available for low voltage drawout switchgear. (6037CT9901)

Power-Zone Load Center Unit Substations

The unit substation is a vital piece of equipment to be considered when planning industrial, commercial, and institutional electrical system demands. Square D Company can provide a unit substation to receive up to 34,500 volts, transform this to a lower utilization voltage, and control its distribution to nearby load areas. Square D Company is a single source supplier of both primary and secondary unit substations. (6020CT9401)

Power-Zone Model III Package Unit Substations

Power-Zone Model III package unit substations combine a medium voltage primary switch, a dry-type transformer, and an I-Line distribution section into a single compact unit. When a Square D brand HVL/cc(TM) load interrupter switch is used as the primary switch, Model III package unit substations offer the smallest footprint in the industry. The substation is available with an Underwriters Laboratories (UL) Listing upon customer request. (6010DB1001)

Spending Too Much Time and Money on Ageing Equipment?

Harmonic Applications in Busway

There are two schools of thought on proper application of busway when loads with high harmonic content are anticipated. The first offers a simplistic approach which doubles the cross sectional area of the neutral conductor. This approach is based on the rationale that the theoretical maximum impact of harmonics is to increase the current flow in the neutral to 173% of the load in a phase conductor. Therefore, to address this concern, all you need to do is double the capacity of the neutral. A second, more conservative approach takes into account the additional heat generation as well. Increased cross section of the neutral is required to handle the increased neutral current, but must also compensate for the added heat generated within the busway by current flowing in the neutral

Busway System Catalog

Square D brand I-Line Busway, manufactured by Schneider Electric, offers a complete line of compatible, sandwich-type feeder and plug-in busway lengths and fittings. It allows maximum flexibility, ease of installation, and offers electrical efficiency in the distribution of low voltage power for both commercial and industrial applications. (5600CT9101)

Square D Multi-Link Structured Wiring

Square-Duct Wireways

Wireway is designed to protect electrical wiring from dust, dirt, oil, and water. It is also designed to carry electrical feeders, branch circuits, and other groups of conductors. Most sections and fittings are completely open on one side so wires and cables can be laid in along an entire wireway run. No pulling through of wires or cables is required with most designs. (5100CT0101)

Trench Duct Electrical Raceway System

Trench duct is a flush electrical raceway system. It is commonly used as a feeder for the cells of a cellular steel floor system, a feeder for the distribution ducts of an under floor duct system, and a flush self-contained raceway system for computer areas, laboratories, and medical imaging facilities. (5230CT9601)

Wall Duct Metal Raceway System

Wall duct is a UL Listed, metal raceway used to enclose the wiring to diagnostic-imaging machines. Wall duct is used in combination with trench duct to provide a complete raceway system from the power and control consoles to the patient table. The raceway system enables a complete lay-in system. Cables can be installed by removing all covers and laying in the conductors. This is an important advantage due to the large diameter connectors used on the high voltage power cables. Whether these connectors are installed on the cable after fishing and pulling or factory-assembled into one customized unit, a lay-in system is necessary. Branch connection from the system is accomplished by pipe-nippling out of the covers or sides of the duct, or by removing sections of covers. (5250CT9201)

Buck and Boost Transformers

Class 7414 Catalog - A Buck and Boost Transformer is an insulating transformer with either a 120 V x 240 V primary with a 12/24 V or 16/32 V secondary, or a 240 V x 480 V primary with a 24/48 V secondary. A Buck & Boost Transformer is also useful in applications where the primary and secondary are interconnected for use as an autotransformer. The equipment enclosure is designed and constructed for indoor or outdoor use and is NEMA 3R rated. (7414CT0201)

Energy Efficient Transformers

Schneider Electric introduced the first TP1-compliant low voltage dry-type distribution transformers in December 1998. With the 2005 Energy Act, Schneider Electric is expanding its offering of TP-1-compliant products by launching a new line of TP-1 qualified transformers. Additionally, The Office of Energy Efficiency (OEE) of Natural Resources Canada (NRCan) has amended Canada's Energy Efficiency Regulations to require Canadian dealers to comply with minimum energy performance standards for dry-type transformers imported or shipped inter-provincially for sale or lease in Canada. (7400CT0601)

Harmonic Mitigating Transformers

These energy efficient, dry type transformers are part of a complete line of lean power products from Schneider Electric. Our power conservation, management and monitoring products, systems, and services help to reduce energy consumption in business and industry environments. (7400CT0301)

Industrial Control Transformers

Control power transformers from Schneider Electric set the industry standard for design innovation and performance. They are designed with low impedance windings for excellent voltage regulation, and can accommodate the high inrush current associated with contactors, starters, solenoids, and relays. (9070CT9901)

Instrument Transformers, 600 V Indoor Type

Square D 600 Volt rated current and voltage transformers are field-proven in well over a million installations where accuracy and longer, more dependable operation are essential. In most cases, the information contained in this catalog should be sufficient for the proper selection of the instrument transformer best suited for your application. (4210CT9701)

Mini Power-Zone® Unit Substation

The Mini Power-Zone Unit Substation from Schneider Electric is a miniaturized version of our Power-Zone Unit Substation. Includes primary main circuit breaker, sealed step-down transformer, secondary main circuit breaker, and distribution panelboard.Because the Mini Power-Zone Unit Substation is furnished as a complete package, considerable savings in installation time and costs can be realized. (7440CT0901)

Transformer Disconnects

Schneider Electrics Square D Transformer Disconnects mount inside or outside a control system enclosure and provide power to auxiliary, single-phase loads when the main three-phase disconnect is either ON or OFF. The transformer disconnect is normally wired to the line side of the control panel's main disconnect. (9070CT0301)

Medical Isolated Power Panels

This catalog provides information about medical isolated power panels and accessories from Schneider Electric. Isolated power systems offer an invaluable advantage in medical settingsearly detection allows critical systems to remain online when hazardous current is present. The system gives a visual indication of the level of current in milliamperes (mA). If the system reaches a threshold of 3.7 mA, the visual and audible alarm indicates the presence of an excessive amperage level instead of disconnecting the circuit. These systems provide isolated power in operating rooms and other critical areas. (4800CT1201)

Definite Purpose Control Products

Definite purpose contactors are ideal for heating, air conditioning, refrigeration, data processing, and food service equipment. New, compact 1- and 2-pole contactors are available as well as full-size devices with 2, 3, or 4 poles. They feature the following: Quick connect terminals and binder head screws allow for easy wiring, box lugs are standard on 40 A contactors and larger, an exclusive DIN track mounting option may reduce installation costs, coils can be changed quickly, without a tool, on the Type DPA, 5090 A contactors, and auxiliary contact modules snap on either side of the Type DPA contactors. (8910CT9301)

Overload Relays & Thermal Unit Selection

Overload relays are intended to protect motors, controllers, and branch-circuit conductors against excessive heating due to prolonged motor overcurrents up to and including locked rotor currents. Protection of the motor and the other branch-circuit components from higher currents, due to short circuits or grounds, is a function of the branch-circuit fuses, circuit breakers, or motor short-circuit protectors. (9065CT9701)

Combination Starters

Class 8538 and 8539 Type S combination starters combine the requirements of motor overload and short circuit protection into one package. These starters are manufactured in accordance with NEMA standards and are UL Listed (although some FORM numbers may not be listed – contact your local Square D representative for information). Class 8538 and 8539 combination starters are designed to operate at 600 Vac maximum, 50 to 60 Hz – and are supplied with melting alloy overload relays as standard. (8538CT9701)

Concerned with the Reliability or Dated Technology of Your Low-voltage Motor Control Centers?

Motor control center structures and internal bus work typically have a long life. Their unit racking systems are simple and most likely, in good shape. So why replace the entire MCC when problems arise? You now have an option to upgrade your motor control centers with industry leading components, without replacing the structure and bus.

New Installation Services

GV2, GV3, and GV7 Manual Motor Starters, Controllers, and Protectors

Catalog 2520CT0001 - Schneider Electric offers a complete line of products for the manual control and protection of motors. This catalog covers those devices designed to meet IEC standards for protection and control. The GV2 and GV3 manual starters and protectors provide manual isolation, manual motor control, and overcurrent protection in one compact unit. The GV7 controls and protects motors with full-load currents up to 220 A. (2520CT0001)

TeSys U-Line Motor Starters

TeSys U-Line motor starters provide motor control for choices ranging from a basic motor starter with solid-state thermal overload protection to a sophisticated motor controller which communicates on net works and includes programmable motor protection. (8502CT0201)

Push Buttons, 16 mm, XB6/ZB6

Harmony XB6/ZB6 16 mm push buttons, pilot lights and selector switcheswith plastic bezelsare specifically designed for applications where the surface area is restricted. The IP 65 degree of protection enables these products to be used in all types of application. (9001CT1102)

SEMI S2, Guarding, & EMO Buttons

Electrical and safety standards are often subjected to individual interpretation, creating the potential for confusion. As a global manufacturer of electrical equipment for the semiconductor industry and the worlds largest supplier of 22 mm push buttons and operators, Schneider Electric has a long history of providing products that meet the intent of guidelines such as SEMI S2. (9001DB0601)

Harmony Wireless, Batteryless Push Buttons

The Harmony wireless, batteryless push button product range enables remote control of a relay (receiver) by means of a push button (transmitter). The control is by radio transmission, where the transmitter is fitted with a "dynamo" type generator that converts mechanical energy – produced when the push button is pressed – to electrical energy. A radio-encoded message with a unique ID code is sent as a single pulse to one or more receivers located several dozen metres away.

Electronic Timing Relays, Type JCK

Variable time delay relays, fixed time delay relays, and programmable timers. Class 9050 Type JCK programmable timers are microprocessor controlled to provide flexibility with accurate timing. The Type JCK 60 On Delay timer has seven programmable timing ranges. The Type JCK70 multifunction timer has 10 timing functions and seven programmable timing ranges. To program the timers, remove power and select the timing range and timing functions. Settings of less than 0.05 seconds are not recommended due to the response time of the electromechanical outputs. (9050CT9601)

Phaseo Power Supplies ABL1/ABL7ABL8

The Phaseo electronic switch mode power supply offer is designed to provide the DC voltage necessary for the PLC and automation system equipment control circuits. These power supplies include five ranges:Modular, Optimum and Universal ranges for common applications (ABL8 and ABL7), the AS-Interface range for the AS-Interface cabling system (AS-Interface), and the dedicated range for repetitive equipment (ABL1). (DIA3ED207041EN-US)

Zelio Timing Relays

Timing relays designed to time events in industrial automation systems by closing or opening contacts before, during, or after a set period. There are two main families of timing relays: DIN rail mounted relays (RE7, RE8, RE9 , RE11, REXL...) designed for mounting on DIN rails in an enclosure, and panel-mounted relays type RE48A designed for mounting on the front of a panel to give users easy access to the settings. These relays have one, two, or four outputs. Sometimes the second output can be timed or instantaneous. If the power is switched off during the timing period, the relay reverts to its initial position. (9050CT0001)

Terminal Blocks, Type AB1

All electrical equipment or installations require the connection of cables or wires to ensure the flow of very low to very high currents. Depending on the application, there are several types of connection: spring terminal, screw terminal (box lug), and insulation displacement. (9080CT9901)

Altistart 01 Soft Starts

Altistart 48 Panel-Mount Soft Starts

The ATS48 soft start is a controller with 6 thyristors. It is used for torque-controlled soft starting and stopping of three-phase asynchronous squirrel cage motors with power ranges between 3 and 1200 hp. ATS48 soft starts offer soft starting and deceleration functions, machine and motor protection functions, and functions for communicating with control systems. These functions are designed for use in state-of- the-art centrifugal machines, pumps, fans, compressors, and conveyors in the construction, food and beverage, and chemical industries. The high-performance algorithms of the ATS48 soft start contribute significantly to its robustness and ease of setup. (8636CT0201)

Altistart 48 Soft Start Motor Controllers

The ATS48 soft start is a controller with 6 thyristors. It is used for torque-controlled soft starting and stopping of three-phase asynchronous squirrel cage motors with power ranges between 3 and 1200 hp. ATS48 soft starts offer soft starting and deceleration functions, machine and motor protection functions, and functions for communicating with control systems. These functions are designed for use in state-of- the-art centrifugal machines, pumps, fans, compressors, and conveyors in the construction, food and beverage, and chemical industries. The high-performance algorithms of the ATS48 soft start contribute significantly to its robustness and ease of setup. (8636CT9701)

Altivar 12 Variable Speed Drives

For 3-phase motors from 0.18 to 4 kW. This catalog includes specifications, references, dimensions and mounting recommendations, connections and installation recommendations, combinations for customer assembly, and functions. (DIA2ED2081004EN-US)

Altivar 71 Drives Brochure

Altivar 312 Drives Brochure

This brochure covers the Altivar 312 Drive - Designed to make industrial and commercial machines more efficient, while at the same time simplifying its integration into a single control system architecture. (8800BR0904)

Lexium Integrated Drives Motion Control

Lexium Integrated Drives are used as decentralized drives in machine building. When combined with a Schneider Electric Lexium Controller or a PLC, they can be used to create complex control system architectures simply and at minimum cost. Ready-to-use function blocks are available for programming movements with Schneider Electric or third-party motion controllers. (DIA7ED2110701EN-US)

HVAC & R Machine Control Solutions

This catalog will introduce you to a complete family of Schneider Electric automation products that will help you optimize the design, functionality, and reliability of your HVAC & R machines. And, in addition to these products, Schneider Electric offers comprehensive machine control solutions based on Tested, Validated, Documented Architectures, as well as service and support throughout the complete machine life cycle (DIA6ED2110101EN-US)

TELEFAST 2 Prewired System ABE7

The Telefast 2 system is a set of products for rapid connection of I/O modules (24 Vdc discrete, analog and counter) to operative parts. It acts as a substitute for screw terminal blocks, remotely locating and partly eliminating the single-wire connection. The Telefast 2 system only connects to channels which have HE 10 and SUB-D connectors or to standard terminal blocks with a cabled connector. It consists of connecting cables and interface modules. The relay and connection functions, with or without polarity distribution, considerably reduce wiring time and eliminate the risk of error. 8501CT9801

Electric Vehicle Charging Solutions

Schneider Electric has developed a line of Electric Vehicle (EV) charging solutions for your unique needs. Schneider Electric will work with you to deliver the best charging infrastructure solution that includes product, installation, maintenance, and an infrastructure management system. Our EV charging products are compatible with safety standards and industry specific standards, such as the Society of Automotive Engineers standards (SAE J1772). (2800CT1001)

Customer Learning Center

Pocket Digest

The 2014 Pocket Digest contains Schneider Electrics bestselling catalog numbers from a broad range of product lines, as well as an index for quick reference, catalog number logic tables, a weekly planner, a 22-page notepad and How to Select information. The following resources are also helpful to keep on-hand.

Proposal Based Conditions of Sale

Conditions of Sale are subject to change. All transactions for all products sold by Schneider Electric USA ("Schneider Electric"), including all Schneider Electric brand products, are subject to the latest published Conditions of Sale of Schneider Electric and to any Special Conditions of Sale which may be contained in applicable Schneider Electric quotations and acknowledgments. (0100PL0043)

Standard Conditions of Sale

Conditions of Sale are subject to change. All transactions for all products sold by Schneider Electric USA ("Schneider Electric") including all Schneider Electric brand products, such as Square D and Telemecanique brand products are subject to the latest published Conditions of Sale of Schneider Electric and to any Special Conditions of Sale which may be contained in applicable Schneider Electric quotations and acknowledgments. (0100PL0041)

Digest Updates Since March 2012

Digest 176 product line sections revised or updated since printing in March, 2012. Included are changes related to new products, revised pricing, technical corrections, and more. These sections contain the most accurate, up-to-date information available. They may also reflect new features, expanded product lines, and globalization efforts.