Construction:

Applications and Features:

Southwire’s 600 Volt power cables are suited for use in wet and dry areas, conduits, ducts, troughs, trays, aerial supported by a messenger, and where superior electrical properties are desired. These cables are capable of operating continuously at the conductor temperature not in excess of 90°C for normal operation in wet and dry locations, 130°C for emergency overload, and 250°C for short circuit conditions. For uses in Class I, II, and III, Division 2 hazardous locations per NEC Article 501 and 502.

Specifications:

ASTM B3 Standard Specification for Soft or Annealed Copper Wire

ASTM B8 Concentric-Lay-Stranded Copper Conductors

UL 44 Thermoset-Insulated Wires and Cables

UL 1581 Electrical Wires, Cables and Flexible Cords

UL 1685 FT4 Vertical-Tray Fire Propagation and Smoke Release Test

ICEA S-58-679 Control Cable Conductor Identification Method 4

ICEA S-95-658 (NEMA WC70) Power cables rated 2000 volts or less for the distribution of electrical energy