For Drinking/Flushing/Industrial Pressurized Water Supply, Use under certain temperature up to and including 45ºC. Widely used in architectural water supply engineering, cities&towns water supply engineering, aquaculture, agriculture irrigation system, and so on.

Main Performance Indexes for UPVC Water Supply Pipes and Fittings:

Description

Item

Technical Indexes

Pipe

Density

1350-1460kg/m³

Vicat Softening Temperature

≥80ºC

Dichloromethane Soakage Test

No change in appearance

Falling impact test (0ºC)

TIR≤5%

Longitudinal Reversion

≤5%

Hydrostatic Test

No breakage, No leakage

Joint Sealing Test

No breakage, No leakage

Fitting

Density

1350-1460kg/m³

Vicat Softening Temperature

≥72ºC

Hydrostatic Test

No leakage

Water Absorption

≤40g/ cm²

Oven Test

No breakage, No leakage

Drop Test

No breakage

Sanitation

Properties

Plumbum Extractim

The 1st extract ≤1.0mg/L

The 3rd extract ≤0.3mg/L

Cadmium Extractim

Extract three times, each

time ≤0.01mg/L

Tin Extractim

The 3rd extract ≤0.02mg/L

Mercury Extractim

Extract three times, each

time ≤0.001mg/L

Contents of choride Vinyl Monomer

≤1.0mg/L

UPVC water supply pipe Outside diameter: 20-400mmLength: 4 or 6m, others on requestStandard: ISO4422, EN ISO 1452, SABS 966, BS 3505, DIN 8062Features and Benefits1. Light weightThe UPVC pipe weight with the same length is just one-fifth of cast iron. 2. Excellent intensionThe tensile strength can reach 45Mpa3. Low resistancesWith the smooth flow and low resistance, not defiled and blocked, the loss of water head is about 30% less than that of iron pipe. 4. Corrosion resistancesHaving the ability of acid-resisting, alkali-resisting, chemical resistance, corrosion resistance, the corrosive pitting can be avoided when being used. 5. Easy installingAdopting the cementation and flexible connection, it is easy to install and have good tightness. 6. Long life-spansUnder the normal working pressure, it can be used for more than 50 years7. Low cost. With low cost in transporting, installing and material, the whole project can save 30%-40% cost than that of iron pipe8. Innoxious, healthyIt meets the drinking water health standards and the water is not polluted in transporting