TSH Large Seawater Pump

Tobee® Large Seawater Pump is a single stage double suction horizontal centrifugal pump used for conveying sea water or the physical and chemical properties liquids similar to clean water, It is widely used in sea water, water plant, irrigation,drainage pumping station,power station,water circulation of air-conditioning, industrial water supply system, fire system and shipping industry as well as for the general purpose in the oil refaining industry.

Design Features:

• Horizontal, split case, double suction, single-stage, large capacity centrifugal pump design.• The inlet and outlet of TSH pumps are below the axial lead of the pump, vertical to the axial lead to form up a horizontal direction. For check and prepair, It don't need to dismantle the inlet and outlet pipes and motors.Viewed from the drving direction,The pump makes clockwise rotation.( If requested, It can be changed to counterclockwise).• Main parts of pump: pump casing, pump cover, impeller, shaft, double suction sealing ring and shaft sleeve etc.• Pump casing and Pump cover from up the workroom of impeller, On inlet and outlet flanges, there are bolt holes to mount vacuum gauge and pressure gauge.• Below the inlet and outlet flanges there is a bolt hole to drain.• Impeller with static balance is fixed onto the shaft by the sleeve and sleeve nuts on the two sides. Its axial position can be adjusted through sleeve nut.• Pump shaft is supported by two single-row radial ball bearings. The bearings are placed inside the bearing body, Mounted at teh two ends of the pump. and lubricated by grease.• Double suction sealing ring is used to reduce the water leakage from pump pressure chamber to the suction chamber• The pump is directly driven by the motor through resilient coupling, and if requested, It can be driven by an internal combustion engine• Shaft seal is soft packing seal (or mechanical seal if requested by users).

Tobee® Large Seawater Pump Performance Curve:

Tobee® Large Seawater Pump Performance Parameters:

Model

Capacity Q

(m3/h)

Head H

(m)

Speed n

(rpm)

Power P

(kw)

Eff. η

(%)

TSH150

112-220

35-84

2900

30-55

80

TSH200

160-351

31-100

2900

37-110

85

TSH250

324-612

8.6-65.1

1450

22-132

86

TSH300

504-1663

8.7-140

1450-1470

22-680

87

TSH350

745-1570

10-125

1450-1470

55-630

88

TSH400

900-1620

32-85.5

980-1480

440-500

84

TSH500

1150-3800

10.6-108

740-970

110-800

88

TSH600

2300-4000

13-80

730-970

145-730

91

TSH700

2111-4896

39.5-99.5

742-980

397-1252

92

TSHS800

3960-6878

23-84

600-750

450-1600

92

TSH1000

6600-9900

32-52

600

1250

88

TSH1200

5832-14400

6-95.7

500-745

710-3450

87

Tobee® Large Seawater Pump Structural Drawing:

Tobee® Large Seawater Pump Structural Design:

Tobee® Large Seawater Pump On-site Applications:

• Sea water

• Salt water

• Brine water

• Marine ballasting

• Water circulation

• Marine fire fighting

• Sea water booster

• Cooling water

• Mariculture

• Sanitation

• Seawater lift system

• Raw water

• Mining water supply

• Garden water supply

• Agricultural irrigation

• Aquaculture

• Reverse osmosis water

• Power Plant

• Chemicals

• Other industries

Tobee® Large Seawater Pump Dimensional Drawing:

* For detailed dimensional drawings, Pls get in touch with TOBEE PUMP by email directly!