VEW 6DT1031 RED

Reversing contactor step regulator 2,2kW

Product Information

The original Siemens reversing contactor regulators are no longer available.Regarding connection, dimensions and functions, our newly developed and redesigned devices are fully compatible with the original, and can be installed/placed “plug-and-play” in the existing location.

The modular units with 2.2 kW output rating are mounted in a ½-19-inch 3HE rack. For maintenance each of the contactors and relays are easily replacable. The construction is designed for natural convection cooling in a control cabinet with a 50% overload rating, and an ambient temperature of max. 60°C. The units work as a 3-phase reversing switch, for change of rotation and with an automatic brake (if installed) for stopping.The rotation direction of the connected AC actuator motor is determined by contactor reversed phase switching. Hereby, the respective rotation (CW and CCW) are indicated by signalling LEDs in the front panel. The logical input conditions for CW and CCW control are mutually locked. A signal change at only one of the logic inputs during operation does not cause a change in the actuators rotation direction. Interference pulses are suppressed. Depending on how the module has been configured by means of jumpers, the turn-off time between the positioning pulse is 200ms, to avoid a short circuit between the phases.When the actuators rotation direction is to be changed, the contactor turn-off times preceding and following the braking time are added to give a total time, after which the actuator is reversed. Furthermore, the control unit monitors phases U and W with lamp H1, the system voltage, and the actuator temperature.Each of the two monitors can trigger a corresponding alarm signal, which can be processed by an external superordinate system.