The TP-MST816BXX family of ceiling mountsensor switch with built-in sensor provideslarge coverage to detect the human motion incontrolled area&period; The sensor can turn the lighton and off automatically within range &lpar;8 to 12meters&rpar;&period; They offer convenient&comma;cost-effective and energy savings for users&comma;energy saving up to 35 &percnt;&lpar; compared to manualswitch&rpar;&period;

Product Features&colon;

&ast;Automatic&comma; digital passive infraredsensor to adjust the work status&period;

&ast;Adjustable time delay from 15 sec to 30mins&lpar; can be customized&rpar;&period;

&ast;Photocell version for daylight&colon;function disabled in daylight or ambient lightis over 10 lux&lpar;can be adjusted&rpar;&period;

&ast;360° coverage pattern&period;

&ast;Lightning protection device&period;

&ast;Easy to install with only two screws&period;

Attention&colon;

1&period; Don't conduct the hot line job&comma; please electrify only after that it has beeninstalled&period;

2&period; The installation position of the switch should be more than 1 meter to theload &lpar;the installation distance to the lighting fitted with shade may be above50 cm&rpar;&comma; and the switch should not be installed at the place where there is directstrong light or at the inlet and outlet of the hot and cold air currents&semi; within thesame power loop should not use the mechanical switches and other electricalappliances as far as possible&comma; otherwise it is easy to cause interference andmalfunction&period;

3&period; It is prohibited to exceed the power limit&period;

4&period; Once the switches were connected&comma; the load will start to work&comma; regardless ofthe light environment&period; Only if there are people activities in the induction field&comma;it will keep connecting&comma; and will close when the people leave its induction field&period;

5&period; The time delay should be adjusted based on the reasonable situation of theusage premises&comma; for example&comma; the people may stay at some places withoutmovement within 20 seconds&comma; at this circumstance the time delay should beadjusted to be about 30 seconds&comma; if there is people activity within 30 seconds&comma;the switches will always be connected&comma; therefore&comma; there will not appear frequentswitching phenomenon&comma; but the time delay should not be too long&comma; otherwisethere will be unnecessary waste after people leaving&period;

6&period; The switches use the unit doublet probes&comma; when people walk from left to rightor from right to left&comma; the sensor will be sensitive&period; But when people walk fromthe front or from top to down or even from bottom to top&comma; the sensor will beinsensitive or does not work&period; To meet the shortfall&comma; the induction field hasbeen increased&comma; the switches have used the circular lens&comma; so that all the four sidesof the probe will be sensitive&comma; but the up-down direction is still more insensitivethan the right-left direction&comma; therefore&comma; when install the switch&comma; should make theright-left direction to be parallel with the direction of human movement as far aspossible &lpar;the wall switch position precisely meets this requirement&comma; can not beconsidered&comma; but the ceiling attached method should consider this requirements&rpar;&period;

7&period; The infrared switches are used to detect the variance of the difference betweenthe human body temperature and the ambient temperature&comma; and the detected datawill be affected by all kinds of factors such as the ambient temperature&comma; theclothes worn by people&comma; as well as the walk speed and direction&period;&lpar; When the ambient temperature is low in Spring&comma; Autumn and Winter&comma; theinduction distance is normal or further far&comma; but when the ambient temperature ishigh at the Summer&comma; the sensitivity will drop&comma; the induction distance will beshortened&comma; this is normal&rpar;&period;

Automatic human body infrared induction switch manual

TypeDescriptionTP-MST816BSuction point type&comma; bipolar&period;Resistive 1000W&comma; inductive 400W&comma; all kinds of loadTP-MST816B-XSuction point type&comma; bipolar&period;Resistive 1000W&comma; inductive 400W&comma; all kinds of loadLine of fire with a fire emergency switchTP-MST816B-RSuction point type&comma; unipolar&period;Resistive 200W&comma; sensuous 5-100W&comma; various types of lampsTP-MST816B-12VDCSuction point type&comma; the DC power supply&period;Resistive 100W&comma; sensual 40W&comma; types of load

The automation products based on infrared technology&comma; they are high sensitivehigh reliable&comma; safety&comma; and intelligent energy-saving&comma; and therefore it will be thefirst choice for the intelligent buildings and the modern property management&period;

Features&colon;

1&period; Full automatic induction&colon; it will open when people are here and will close if the timedelay is up after people leaving automatically&period;

2&period; It can measure the light automatically&colon; photosensitive control&comma; it will have no inductionwhen there isdaylight or when the light is strong &lpar;set before leave factory&rpar;&period; It can also besensitive to any light condition or be sensitive all-day long&period;

3&period; Automatic random time delay&colon; when the induction switches are connected&comma; they willkee theconnection state within the time delay even if there is no people activity&comma; and it willonly close after thetime delay is up after people leaving&period; &lpar;The time delay will be renew ifthe switch has detect anotherhuman body movement&comma; and take the time delay of the lastdetected people activity as the starting point for timing&rpar;&period;The automation products based on infrared technology&comma; they are high sensitivehigh reliable&comma; safety&comma; and intelligent energy-saving&comma; and therefore it will be thefirst choice for the intelligent buildings and the modern property management&period;

Application scope

The automatic lighting of the aisle&comma; corridor&comma; bathroom&comma; basement&comma; garage and otherplaces&comma; the automatic ventilation of the exhaust fan&comma; the automatically switching controlof the electrical equipments&comma; as well as the anti-theft function and so on&period;

Direction for use

1&period; Install the switches properly according to the figure&comma; there will be one minute ofinitialization time afterthe power-on of the switches&comma; in the initialization time&comma; the switchwill automatically be alternative on- off for 0-3 times &lpar;if it is at the night or the light is low&comma;or even has turn the sensitivity adjusting knob to theleft position which is the state of thedaylight or strong light induction&comma; the load will begin to work after the switch power-on&rpar;&comma;one minute later&comma; the switch will be at the normal control state&period;

2&period; Time delay &sol; sensitivity adjustment&colon; time delay adjusting knob will be at the right endwhen leaving factory &lpar;the time delay is about 16 seconds&rpar;&period; The time delay will extendwhen adjusting the knobcounter-clockwise &lpar;the longest time delay is about 350 seconds&rpar;&semi;Sensitivity adjusting knob will be at the right end when leaving factory &lpar;no inductionunder the strong light&rpar;&comma; the sensitivity will increase whenadjusting the knob counter-clockwise&comma; to the end of theadjusting strode&comma; it will be sensitive all-day long&period;&lpar;Note&colon; cut off the power prior to regulating&comma; the adjustingrangeof the knob is only about 180 degree &lpar;it is only onehalf-circle&comma; not one whole-circle&rpar;&comma; please adjust lightly&comma;so as to avoid damage the potentiometer&rpar;&period;

&lpar; Wall mount&comma; is on the most sensitive sensor lateral movement&comma; vertical movement a littleslow&comma; due to the installation Height limitations&comma; the first to enter a person's legs sensingrange infrared signal is weak&comma; because four weeks sense Should be shorter distances&comma; sothe actual sensing range is smaller&period; &rpar;Note&colon; The sensor sensitivity level has a directrelationship with the installation

Wiring indication &lpar;wiring in accordance with the wiring diagram&rpar;

1 Screw the base fixed on the ceiling&comma; or 86 on the bottom box&period;&lpar;2&rpar; in accordance with product instructions properly connected to the wiring diagramto connect switches and lamps&comma; installation&lpar;To ensure your security&rpar; must be bya professional electrician&comma; please follow the wiring safety norms3 Align the switch up the base card&comma; the right can be tightened&period;4 installed&period;