Archives

Categories

It was a hot day, it was a cold day. The tube transmitter was running, the solid state (HD-1) transmitter was off the air. The books show that the company has deep pockets, but the accountant has short arms. And so it goes. In a sordid, yet familiar tale of leaping three quarters of the way across a river, the builders of this transmitter site seemed to think of everything except the cooling requirements for a 35 KW FM transmitter.

Instead of installing real commercial AC units, someone decided that 34,000 BTU window units were the way to go. At one time, there were eight of those units, all single phase 240 volts sucking down gobs of power and freezing up when the outside temperature dropped below 40°F. This was always a problem, but became more so when we took over the maintenance of this site. When there was a full time engineer, his time, apparently, could be wasted running back and forth turning the window units on or off in the winter as required. Now that a contract company is doing the work, it becomes cost prohibitive to require such things.

Therefore, the time had come to make a change. To that end, six of the 34,000 BTU window units were removed from the building. Two of the existing holes in the wall where used to create an emergency cooling system, consisting of a 4,292 CFM fan and a couple of shutters. Two other holes were used for the new air conditioners and two holes were blocked up. The remaining two window units were left in place in the combiner room, which is a separate cooling zone.

Bard 5 ton wall mount AC unit and cooling fan shutter

The new AC’s are five ton wall mount Bard units. These are three phase and should be more than enough to keep the transmitters cool. Here is how I arrived at that conclusion:

The entire building load when the main transmitter is running at full power, without the transmitter room air conditioning, is 60 KW.

All of the building loads except the transmitters go through a single phase panel.

The load on the single phase panel is 10 KW, thus the transmitter load is 50 KW (this 10 KW is mostly the single phase AC units in the combiner room)

The TPO is 32 KW, therefore the transmitter is generating 18 KW of waste heat.

One watt hour = 3.412 BTU of energy, thus

18,000 watt hours equals 61,416 BTUs

One ton = 12,000 BTU, thus

61,416 BTU ÷ 12,000 BTU = 5.118 tons

That will take care of the main transmitter waste heat. The HD transmitter generates another 4,000 watts of waste heat or 1.37 tons. The combiner is an another room and doesn’t factor into the calculation. The rest of the equipment is inconsequential, adding up to less than 100 watts.

The solar gain is more difficult to calculate, as it is based on the building structure, the type of construction and the heat gain (loss) through the walls and doors. This building is concrete block, insulated, and has no windows. It is unshaded, however it is painted a light color. All in all, the solar gain should be less than two tons on a hot day. Therefore the total AC load should be 8.25 tons or less.

Bard 5 ton wall mount AC unit

All that is left now was to install the things. Just pull up the truck and use a crane to lift them in place, except, no; that plan won’t work. This is the transmitter site at the power plant and the 138 KV lines overhead precluded any lifting with a crane. We instead had to build ramps and move the things around on large hand trucks. One unit is installed on the rear of the building, the other on the front. It required several days to make the ramps and four people to muscle the things into place.

The bottom air intake holes needed to be cut out for the new units. Cutting into the concrete block while the BE FM 35A was running proved to be another challenge. We used several sheets of plastic, shop vacs and extra air filters on the transmitters to keep the concrete dust out of the PA cavities and motor bearings.

Plan B cooling consists of a 4,292 CFM Venturi fan mounted on the rear wall of the building. The fan is controlled by a ceiling mounted thermostat set to 95 degrees. If the AC’s fail, the ceiling temperature will rise and the fan will turn on.

Transmitter site emergency cooling fan

The room volume is about 3600 cubic feet, therefore this fan will change the room air about once every 60 seconds or so. It is not the best plan to move humid, potentially dirty outside air through a building, but it it keeps the station on the air while the main AC units are being repaired, then so be it.

Axiom

A pessimist sees the glass as half empty. An optimist sees the glass as half full. The engineer sees the glass as twice the size it needs to be.

Congress shall make no law respecting an establishment of religion, or prohibiting the free exercise thereof; or abridging the freedom of speech, or of the press; or the right of the people peaceably to assemble, and to petition the Government for a redress of grievances.
~1st amendment to the United States Constitution

Any society that would give up a little liberty to gain a little security will deserve neither and lose both.
~Benjamin Franklin

The individual has always had to struggle to keep from being overwhelmed by the tribe. To be your own man is hard business. If you try it, you will be lonely often, and sometimes frightened. But no price is too high to pay for the privilege of owning yourself.
~Rudyard Kipling

Everyone has the right to freedom of opinion and expression; this right includes the freedom to hold opinions without interference and to seek, receive and impart information and ideas through any media and regardless of frontiers
~Universal Declaration Of Human Rights, Article 19

...radio was discovered, and not invented, and that these frequencies and principles were always in existence long before man was aware of them. Therefore, no one owns them. They are there as free as sunlight, which is a higher frequency form of the same energy.
~Alan Weiner