Lighting Panel Main Lug Only

Lighting Panel Main Lug Only

This design offers sufficient gutter space on sides to allow through wiring and easy lug connection. All enclosures are furnished with hinges, stainless steel quad lead cover bolts and are provided with NEMA 4 gasketing. All covers are removable for clear access to breakers and gutter space. The compact design of rectangular housings permits close grouping on switch racks and other structures. No additional space is required for cover removal except from the front.

Product Info

Standard Features

• Factory Sealed, no external seals required.• Fully Wired from Panelboard Enclosure to Terminal Enclosure.• External Operating Handles can be padlocked either in the “ON” or “OFF” positions.• Spring-loaded Operator Handles allow cover to close with handles in any position.• Copper Bus is standard.• Isolated Neutral and Ground Bar provided.• Available with GFI or EPD Breakers• Type 4 Gasketing provided for water and dust-tight seal.• Breather and Drain provided for each enclosure.• Removable Gland Plates for field installation of conduit entries.• Terminal Enclosure has folded lip around the door opening to provide complete and maximum gasket contact, and to prevent

liquids from dripping into the enclosure when the door is open.• Terminal Enclosure has continuously welded seams ground to a smooth finish.• Ample wire bending space allows for easy terminal connection.

Enclosure

The housings are copper-free cast aluminum alloy. The housings are Adalet XCE series and have precision ground cover and body joints.

The design offers sufficient gutter space on sides to allow through wiring and easy lug connection. All enclosures are furnished with hinges, stainless steel cover bolts and are provided with Nema 4 gasketing. All covers are removeable for clear access to breakers and gutter space. The compact design of rectangular housings permits close grouping on switchracks and other structures. No additional space is required for cover removal from the front.

Mechanical

The front mounted power panel and lighting panel branch handles can be padlocked either in "off" or "on" position. All breaker handles are spring loaded allowing closing over the cover with breaker toggle in any position. Operating handle shafts have "V" ring gaskets for watertight application.

Electrical

Breaker panel chassis, featuring bolt-on circuit breakers, are made by Cutler Hammer. Chassis for the (XPB2) series power distribution provide 480/277 volt connections. The circuit breakers are rated for 480 volt max.