It only took a year for that prediction to come true. Hurricane Sandy storm surge, did in fact flood Lower Manhattan. And, as endlessly forewarned, the New York region is already drowning in stories of organizations that had inadequate IT contingency management plans.

For instance, several major websites, such as Gizmodo and the Huffington Post, went offline Monday night. According to the New York Times and the Wall Street Journal, those two sites, which are associated with Gawker Media, shared a common ISP located in Lower Manhattan by the name of Datagram. When the local utility's transformers blew up (check out the spectacular video of it, beginning at 0:20) and took out the power to Lower Manhattan Monday evening, Datagram’s backup generators were supposed to switch on and continue to provide power to its servers. However, as the NY Times noted, “Although Datagram uses backup electricity generators in the event of a storm, its offices were flooded, knocking those machines out as well.” The WSJ also pointed out that Datagram’s basement flooded and damaged the building’s electrical system.

As noted in anLA Times story on the Cerner outage, “Federal law requires medical providers and their vendors to have contingency plans for when systems go down.” However, Federal law doesn’t require the contingency plans to be thoroughly vetted, apparently.

There's perhaps no clearer example of this than the loss of power at 705-bed New York University Langone Medical Center also in Lower Manhattan, which took out its EPIC electronic health record system, and subsequently (in conjunction with rising water) caused the hospital to evacuate its patients during the height of hurricane. There are conflicting reports as to what happened, but according to news reports, after the hospital lost power due to the aforementioned transformer disruption, the hospital’s primary backup electrical generator failed as did the backup to the backup generator. A CBS News story says that flooding in the hospital's basement overwhelmed the primary backup generator. The other generator, which is on the roof, then also failed, CBS News said because “the pump that supplies fuel to that generator is on a lower floor and was [also] flooded.”

A story at the Huffington Post, which did eventually come back online, reports that a NYU hospital spokesperson vigorously defended the adequacy (and architecture) of the hospital’s backup power system, stating that, “Our generators are fully compliant with all state and federal regulations and, using good prudence, we test them all the time as we have to do anyway.”

What is a bit puzzling is that the hospital, which is in the Lower Manhattan hurricane evacuation zone, was closed last year on the orders of Mayor Bloomberg before Hurricane Irene, but was kept open as Sandy approached, even though the prediction was for a higher storm surge to come ashore this time around. The hospital claimed, according to the Guardian, that it did not anticipate Hurricane Sandy causing heavy flooding. Mayor Bloomberg, when questioned about why he didn’t order the hospital closed as before, claimed the hospital told him it could handle the risks posed by Sandy.

Ensuring the controversy will live for a while longer, the mayor's own Bloomberg News reported that the hospital knew full-well that the generators were vulnerable. It quoted a hospital trustee as saying that the hospital’s board “knew the facilities’ generators were outdated and at risk” and that the back-up generators “are not state of the art and not in the most state-of-the-art location.”

Other reliable sources indicate that the NYU hospital basement is prone to flooding during heavy rains, and that it wasn't unusual for the backup generator to go off-line as a result.

Here's one storm prediction you can take to the bank: More stories of poor IT contingency management will soon appear. The lessons to be learned from them will be written and soon then forgotten, at least until after the next disaster strikes.