7
S.Evrard - EN-MEF Recovery action on 13/04/2012 During its removal, one cup housing the downstream right foot of the table felt down and must be repositioned. Once re-installed, the table turned out to be misaligned by 4 cm at the level of the positioning grid system Investigation on spare parts confirm our feeling of a wrong repositioning of the cup. Decide an inspection on site Dose rate estimate around 20 mSv/h shielding required Shielding installation ( L shape 4 cm thick lead dose rate reduced to 2.3 – 2.7 mSv/h) Removal of the felt down cup + 3 rollers & inspection of the 2 other cups Replacement by spare parts 7