Tag Archives: RG-6

From the day after Christmas on through fours days past the New Years holiday, two teams of Delta Engineers were busily working long 12+ hour days testing, repairing and certifying Modicon remote I/O and Modbus Plus networks during a plant … Continue reading →

We recently had a client with many, many Modicon remote I/O and Modbus plus networks installed and in use in their plant, pose this question. The short answer is usually every one to two years or if they are having … Continue reading →

﻿This is the TDR trace that shows the original cable system on a recent project that Delta Automation, Inc. was tasked with repairing. This system shows many issues: excessive dB losses, poor splices, poor connections and terminations. This is the … Continue reading →

Delta Automation, Inc. is fully capable of the developing the layout for any sized remote I/O network. Our engineers have successfully installed thousands of these systems worldwide. We offer the most comprehensive testing and troubleshooting available, to bring your system … Continue reading →

A prison facility was having intermittent issues with the locking and unlocking of cells and passageways in one of its’ inmate housing facilities. This is not a good thing to have occurred in a facility such as this! After extensive … Continue reading →