Capacity designs for maximizing the heat transfer relative to the energy consumption of the fan.
Tube and tube coupling design for low pressure drop in the coil on the media sides(maximum 100KPa at water designing condition).
Our thermodynamic and aerodynamic designing software is long year tested and proved in Germany

Fan

Only choose low specific energy consumption fans.
Fan nozzle designs for maximum air flow and air throw.
Our fans from the world`s leading manufacturer are practically proved to be reliable in operation and long lasting.
Motor: protection class IP 54 and insulation class F.
Voltage：400V/3N/50Hz
Air separator for each fan.

Testing

Heat exchangers are supplied clean and tested at a pressure of 30 bars

Note: Standard SHSL-D1 remote radiator is vertical air discharge, for horizontal air discharge please add “H” in nomenclature, for excmple:SHSL-D1-005H-1X350

Industrial field: process engineering, heat / power plant, power generation, chemical industry, air conditioning chiller, heat transformer, smelting, etc.. It is suitable for all equipment which needs heat dissipation and is installed in the open air.