Fri3Oil System saves a flooded chiller from a certain death in Madrid

Flushing service on a 36Kw CIATESA MI-450 water chiller where the heat exchanger got communicated. This R22 installation was placed at a Museum in Madrid.

Detail of the outlet water liquid vesell.

Water pressure emanating from the crankcase of the compressor.

The work consisted in flushing the chiller to dry up humidity, oils, acids and contaminant to finally make a retrofit to R438A with all warranties of the components of the chiller.

In the flushing process was used 40 kg of refrigerant which was recovered afterwards for its later use.

Using our patented system, the whole installation got clean and dry from water, moisture, acids, oils and other contaminants.

In this 2-day-operation, the client could avoid the whole installation disposal, since both compressors were recovered after removing all water from inside with the unique HVAC and refrigeration cleaning system, Fri3Oil System.

Detail of water and oil recovered, which also contains acids and impurities, from the installation.