Description

Powrmatic OUH 60kW Oil Fired Unit Heaters

The Powrmatic OUH range of Oil fired unit heaters currently comprises of 4 different models, with heat outputs ranging from 20kW to 60kW. The unit heater is designed to be suspended directly in the work space that it will heat. Ducted versions are available with an up rated centrifugal fan option to overcome ducting resistance. The OUH can be supplied for use with 28 Sec Kerosine or 35 Sec Diesel. Various burner control options allow for basic on/off operation or high / low fire.

Powrmatic Guarantee
• Powrmatic – More Than Sixty Years Experience in Warm Air
• Made And Fully Assembled In The UK
• Two Year Parts And One Year Labour Guarantee
• Ten Year Heat Exchanger Warranty
• Proven Track Record, Exceptional Reliability

Powrmatic OUH

The Powrmatic OUH Oil fired unit heaters are built around minimal fuel usage, efficiency and reduced flue gas emissions. The entire range meets or exceeds current Building Regulations and additional control options are available. Hi/Low fire offers a two stage operation, ideal for use with enhanced time and temperature control stations or links to building management systems.
The heater chassis contains separate modules, one to contain the heat exchanger and a second insulated compartment holding the main electrical components. A Riello burner is used which is externally mounted. The cabinet is finished in a heavy duty stove baked epoxy powder paint.

The Powrmatic OUH heat exchanger is of exceptionally modern design . Heat exchangers are produced in 304 grade stainless steel for increased life in rough service conditions. A ten year sliding scale warranty as standard on the heat exchanger.

The OUH utilises a Riello Burner which is perfectly matched to the heat exchanger, for a proven long life in service.

Air movement is provided by a standard axial fan arrangement. Adjustable louver sections on the front of the heater allow the discharged heat to be directed to the required location in the work place. Additional horizontal louvers can be added for even greater air control.

The duct mounted version of the OUH heater is supplied with a heavy duty centrifugal fan fitted directly to the heater. The front discharge grill is replaced with a heavy duty duct spigot to allow direct mounting to the air distribution duct.

The entire range of Powrmatic OUH heater is supplied with automatic ignition and flame safety monitoring provided by the Riello Burner, high limit overheat protection and separate control of heat and fan to allow a summer operation mode. The OUH unit heater can be interfaced to almost any control station including the Powrmatic Powrtrol, MC200, MC300 (forthcoming) and the Heatmiser IQ+ controllers.
Powrtrol stations provide basic time and temperature options whilst the MC200, MC300 and Heatmiser IQ+ provide enhanced control when required. Control stations are not supplied as standard and require on site installation.

The range of Powrmatic OUH heaters are type tested to meet the stringent requirements the Oil Directive and are CE approved.

Delivery
UK normal delivery charges are INCLUDED within this price, excluding Scotland & Ireland (contact us for additional costs). Lifting equipment is required to unload product at destination and should be arranged before delivery. Tail Lift delivery can be arranged at an additional cost if required.

PDF Brochure Download
Please click on the image below to download a brochure for the Powrmatic NVx range and the handy flue selector in PDF format.