Local Reviews for Westminster, MD

Daniel M.

Clean coils and completed AC inspection .

Near Baltimore Blvd, Westminster,
MD21157

140 days ago

Daniel M.

Found unit #3 with a black thermostat. Went on roof and found my transformer was receiving 210 volts and only putting out 8 volts . Replaced 208 volt 75 va transformer with one with a built in fuse and checked operations . System is operating properly

Near Baltimore Blvd, Westminster,
MD21157

141 days ago

Daniel M.

Changed out filters and it started raining . Waited 30 minutes for rain to slow down or pass and it did not . Need to come back to complete maintenance
01-03-19 . Completed heating maintenance on systems

Near Baltimore Blvd, Westminster,
MD21157

144 days ago

Daniel M.

Changed out filters and it started raining . Waited 30 minutes for rain to slow down or pass and it did not . Need to come back to complete maintenance