Building of single-unit switchgears with fixed components or double-unit ones, where a main circuit-breaker is installed on withdrawable unit

Building of free-standing switchgears or wall switchgears. All activities connected with switchgear service and including power cable connection are carried out from front in wall switchgears

Building of switchgears with high protection degree against touch of live parts - standard protection degree is IP4X acc.to IEC 60529

Building of metal-enclosed switchgears resistant to electric arc acc. to PN-EN 62271-200, which ensure high protection degree of people against electric arc effects

Building of switchgears, where changing over of a withdrawable unit from “work” position” to “test” position is carried out at closed door of a switchgear. Withdrawable units are equipped with very easy to service withdrawable mechanism including a system of interlocks, which eliminates switching mistakes. Changing over of the withdrawable unit can be done also remotely by means of an electric motor.

WEGA double unit, metal-clad switchgears

WEGA type double-unit metal-clad switchgear in air insulation consists of a fixed and withdrawable unit.

There are following compartments in the switchgear:

Bus bars compartment,

Connection compartment,

Auxiliary circuits compartment,

Withdrawable unit compartment.

The compartments have been arranged thanks to metal – clad design. Frame assembled construction is made of screwed perforated profiles and steel sheets. Applied reinforced door, shields and ventilation flaps (top or bottom) ensure full protection against electric arc and its effects (up to 1 s) acc. to PN-EN 62271-200.

High safety degree of service has been achieved thanks to following solutions:

Changing over the withdrawable unit from “work” position to “test” position and inversely is carried out at closed door of the withdrawable unit compartment,

Metal partitions shield automatically live parts when the withdrawable unit is moved to “test” position,