In addition to variable parameter measurement, the DDS238-2 ZN single phase DIN-rail meter is also ideal for measurement of single phase two-wire AC active energy with time of use (TOU) function. That is, it can be applied to measure the power flow during different periods of time, such as the peal time, mid-peak time, off-peak time, and super off-peak time.

The product offers technical requirements conforming to IEC61036 standard. Meanwhile, its data communication rules are designed as per requirements of DL/T645 or MODBUS-RTU. Owing to its good performance in stability, overload capability and power loss, the small-sized meter can be used for a long time.

Basic Function
1. The LCD display of the product comes with a backlight and backup battery against power failure.
2. Besides the measurement of bi-directional total active energy and TOU active energy, the single phase DIN-rail meter can also realize the measure of reverse active energy in the total active energy.
3. In addition to real time and date, the device also supports display of realtime voltage, current, power, power factor and frequency.
4. The meter supports measuring power flow during peak time, mid-peak time, off-peak time, and super off-peak time. According to application demands, it can be programmed as single tariff, double tariff, triple tariff and quadruple tariff modes.
5. The device can be programmed to offer 14 time intervals to facilitate TOU tariffs. The shortest time interval can be 1 minute.
6. The meter can automatically switch calendar.
7. With data save function, the product can save the daily energy consumption data for continuous 30 days and the monthly energy consumption data for continuous 12 months.
8. Infrared and RS485 communication port are available.
9. Pulse LED indicators are installed to indicate the device working status. The pulse output is available with optical coupling isolation.
10. Event log is available.
11. The single phase DIN-rail meter adopts 35mm DIN-rail installation method.

Optional Function
1. The measure and display of total forward/reverse active energy is allowable.
2. Accumulative working time display and reset energy function. Meanwhile, these two data can be reset to zero via keypad.

Technical Data

Rated voltage

110V, 120V, 220V, 230V, 240V

Working voltage range

0.8~1.2Un

Rated current

5(65)A, 5(30)A, 10(40)A, 5(60)A or other as required

Rated frequency

50Hz or 60Hz

Connection mode

Direct type

Display

LCD

Accuracy class

Class 1

Power consumption

<2W/10VA

Start current

0.004Ib

Constant

800~3200 IMP/KWh

Clock accuracy

<0.5s/day (23℃)

Pulse output

Passive pulse, pulse width is 80+5 ms

Communication port

RS485 port, baud rate 1200~9600 bps, default is 4800bps

Infrared port

Executive standard

IEC62053-21, DL/T645-2007 or MODBUS-RTU

Working temperature

-30℃~70℃

Outline dimension LXMXH

90×35×60mm

Weight

Approx 0.14kg

Wire connection

Outline dimension

Feedback Form

Related products

DDS238-2 ZN/S Single Phase DIN-rail Meter
It is used to measure variable parameter and single phase two-wire AC active energy.
With the data communication rules designed as per the requirement of DL/T645 or MODBUS-RTU, this small-size meter also has many good ...