Fuses getting very hot in Fusebox

Im a young student living in an apartment with a roommate. My building administrator is absolutely useless and i have a problem.

My apartment unit is run with a fuse box and is heated by baseboard heaters. The fusebox says (15A MAX) so i use 15A fuses. However, whenever i try using the baseboard heaters (especially in this frigid time of year)
my fuses get very hot! I don't know whats causing it, and what ends up happening is that my apartment gets unbearably cold when i had to take them out of the socket. I don't know why its doing that.

I haven't the time (or money) to go constantly buying fuses, so im desperate.

The maximum fuse size is determined by several things: the design of the fusebox and the wire size that is being used (larger gauge wire, lower number, the higher the amperage you can use). It would be a rare baseboard heater that only used 15A unless it is fairly small, so it seems, something might be amiss. If the socket is dirty or corroded, the leads coming in/out are loose or corroded, it can act like a heating element by itself.

You don't want an elect. fire. It would be worth the money to spring the price of a service call with an electrician. They will check for : loose connections at the fuse, loose wire connections to the fuse holder, and the actual amp rating of the heat. Iy you have slo-blow fuses ( which I believe this application should NOT use) that fuse can run significantly over 15 amps for longer than you might expect, before it blows. Have you ever had a fuse blow, or just notice the heat??

Im a young student living in an apartment with a roommate. My building administrator is absolutely useless and i have a problem.

Click to expand...

Then go OVER his head.
This is NOT something you should be messing with, and you should not be responsible for replacing fuses unless you are running too much and blowing them. Keeping the place comfortable is not running too much.

Im a young student living in an apartment with a roommate. My building administrator is absolutely useless and i have a problem.

My apartment unit is run with a fuse box and is heated by baseboard heaters. The fusebox says (15A MAX) so i use 15A fuses. However, whenever i try using the baseboard heaters (especially in this frigid time of year)
my fuses get very hot! I don't know whats causing it, and what ends up happening is that my apartment gets unbearably cold when i had to take them out of the socket. I don't know why its doing that.

I haven't the time (or money) to go constantly buying fuses, so im desperate.

Thanks guys

Click to expand...

Check with your state or other local AHJD. There are rights given to tenants with regards to safety of the dwelling. Your first step would be to WRITE a letter stating the disrepair, make a copy for your records and mail it registered to the landlord. Now you have proof that he knows of it. Then depending on the laws in your location, they have so many days to rectify it. If not, you can often then withhold rent. Another option that is often available is to hire someone to repair it and deduct it off of your rent. BUT laws vary amongst the jurisdictions so check first. But remember, even though it's your home, he owns the place. Don't do anything stupid like repair it yourself. You will be held liable if somethings goes wrong. Your responsibility is to pay rent. Theirs is to maintain the darn place and make sure everything is safe.