Application

For indoor and outdoor installation, in open air, in the ground, for power stations, industry and distribution boards or subscriber networks, where additional protection against mechanical damage is required and in the case of increased tensile forces during installation, laying and operation.

The cables are insensitive to occasional impacts of oils and fuels.

Type Designation Codes

N

cables acc. to standard

(N)

cables based on standard

Y

core insulation made of polyvinyl chloride (PVC)

FG

flat steel wire armouring SWA, counter helix

Y

outer sheath made of polyvinyl chloride (PVC)

J

cable with green-yellow core

O

cable without green-yellow core

RE

circular conductor, solid

RM

circular conductor, stranded

SM

sector-shaped conductor, stranded

Additional Informations

Other designs, fitted lengths and larger delivery lengths on request.

Order Example

NYFGY-J 3 x 95 SM 0,6/1 kV (F 0,8v)

BayEnergy® Power cables, PVC insulation, armouring, PVC sheath

NYFGY-J

3-cores acc. to DIN VDE 0271

Product

CPR
DoP *)

Bayka
Order No.

Cu
No.

Outer ∅
approx.

Net weightapprox.

Rated short-time current

Max. tensile force

Bending
radius
one-off

Bending
radius
repeated

kg/km

mm

kg/km

kA

daN

min.
mm

min.
mm

NYFGY-J 3x50 SM 0,6/1kV (F 0,8v)

N/A

4237014

1440

31

2600

5.75

830

190

380

NYFGY-J 3x70 SM 0,6/1kV (F 0,8v)

N/A

4237124

2016

35

3400

8.05

1050

210

420

NYFGY-J 3x95 SM 0,6/1kV (F 0,8v)

N/A

4237024

2874

40

4400

10.93

1350

240

480

NYFGY-J 3x120 SM 0,6/1kV (F 0,8v)

N/A

4237134

3456

42

5200

13.80

1570

260

510

NYFGY-J 3x150 SM 0,6/1kV (F 0,8v)

N/A

4237044

4320

49

6550

17.25

2100

300

600

NYFGY-J 3x185 SM 0,6/1kV (F 0,8v)

N/A

4237144

5328

53

7900

21.28

2530

320

640

NYFGY-J 3x240 SM 0,6/1kV (F 0,8v)

N/A

4237054

6912

59

9950

27.60

3050

360

720

NYFGY-J 3x300 SM 0,6/1kV (F 0,8v)

N/A

4237154

8819

64

12050

34.50

3600

390

780

Errors and omissions excepted, weights and dimensions are approximate values.Other designs, fitted lengths and larger delivery lengths on request.Tensile force only valid when cable sheath and cable core involved.The bending radius one-off is for professionally installed cables, unique molding over a stencil and a cable temperature >30 ° C.*) N/A (not applicable) Cable is not subject to the Construction Products Regulation CPR.Due to the flame-retardant outer sheath, it could be classified as Eca.
If necessary, inform our sales team.