422 works well, but very slight exhaust odor, only at start of each cycle

If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You may have to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.

422 works well, but very slight exhaust odor, only at start of each cycle

Question: on these 422's, do the heat exchangers or combustion chamber ever "wear out", from repeated decades of expansion / contraction? Such that they eventually develop micro cracks or warpages?

My 422 is working well here. But at the beginning of maybe 20% of the on-cycles, a very small amount of exhaust gas is smelled.

It's only noticeable in the first few seconds after the circulation fan starts running. After that the exhaust smell is gone and everything is fine.

The unit has 'always' had some exhaust whiffs, even before I did a burner pot and ring replacement (new parts and gaskets) in October 2017.

I have used soapy water to check for any air leaks at the beginning of cycles (combustion fan running), by applying the soapy water to the obvious joints and gaskets, including both ends of flue. Flue ends were also cleaned in Oct 2017 and new Monitor O-rings installed. One of the local 'experts' from the kerosene company said these old Monitors eventually just start to warp or leak gasses because it is a positive pressure system (as opposed to the Toyotomi, which is negative.) Not sure if that was completely unbiased, because the same company is pushing customers to purchase new Toyotomi replacements for their old Monitors.

Anyone here recommend or have experience replacing the heat exchanger or combustion chamber?

The Following User Says Thank You to hawkins111 For This Useful Post:

I too was just getting ready to suggest checking the heat exchanger for the possibility of cracks. I'd also double check the o-rings at the flue to be sure they haven't been damaged and leaking exhaust fumes into the living space. In 23 years of Monitor use I've never had any exhaust smells in my house.

I have installed many Toyostove heaters. Very, very, very seldom is there a problem with a Toyo right out of the box. If there is, it is usually an installation problem.

Whoever told you a Laser 530 was too big for the job a Monitor 422 was doing is completely incorrect. Both heaters are 20K BTU units, that produce the same amount of heat. If you got that information via EMAIL, I would like to see it.

The Laser 530 is one of the most reliable heaters on the market. It's time between failure or overhaul is the longest of all the Toyostove heating products.

All that being said, if there is a smell coming from a brand new Toyo heater I would first look at the air, exhaust and fuel connections. If that doesn't fix things I would look at the siphon break tube on the fuel sump. There is a small "O" ring between the tube and the sump. If that "O" ring is cut or out of place you can have a smell. A look at the Igniter guide gasket to make sure it comes together would be in order. Lastly, I would look at the Joint gasket between the heat exchanger and the burner. Keep us posted.

Pulled heat exchanger out of the 530. Applied about 1psi to it and soaped it all down. No leaks at the relief gasket or any of the welds or joints but there was some bubbles coming from around the peep window gasket. I dialed up the Px and the relief plate started to "buzz" and still no leaks elsewhere.

So I replaced all 3 gaskets, peep, relief and lower exchanger gaskets. Ran it on the bench in the Toyo guys big shop (1000sq-ft?) So I am confident all is well.

Toyo warrantied the gaskets and the Toyo guys time so that was good.

I will check those things suggested if it continues to smell. Its not the installation due to the fact I installed it ..... and yes, I am that good.