Federal Pump Corporation was formed in 1927 by a group of experienced, dedicated pump specialists. The product line is geared towards the commercial heating industry in the U.S.A.

CCV Condensate Units

RECEIVER: Cast iron receivers are standard. Steel receivers are available as an option. Maximum internal receiver pressure is 5 psi. Receivers are designed for venting to atmosphere.

PUMP: Bronze fitted centrifugal design, flanged to the receiver with leakless mechanical shaft seal. The seal chamber has a relief line back into the receiver to prevent air pockets or collection of abrasives near the mechanical seal. Motor and rotating assembly are removable without disturbing retum or discharge piping. Maximum water temperature at pump suction is 210°F.

FLOAT SWITCH: One for each pump, provides automatic operation, mounted and wired on unit.

STARTERS: All polyphase units (208-230/460v), and integral H.P., single phase units (115/230v.) are furnished with magnetic starters mounted and wired on the unit. Single phase fractional H.P. motors have built-in overload protection and do not require magnetic starters.

FLOAT SWITCH: Built into motor and fully protected from damage. Operated by float ball, rod, and adjustable stops.

OPTIONAL HIGH WATER CUT-OUT AND ALARM SWITCH: (MMC-1 UNIT) Standard MC-1 unit can be modified by the addition of an extra integral float switch with one set of normally open and one set of normally closed contacts. This modification is called the MMC-1 unit. On the MMC-1 unit the float switch is actuated if water in the tank rises to a dangerous level. Switch will automatically shut down the air conditioning unit and simultaneously activate an audible or visual alarm, thus preventing overflow from the tank.

VCU Condensate

PUMPS: bronze fitted centrifugal, flange mounted to the receiver with 250 degree rated mechanical shaft seals, the seal chamber has a relief line back into the receiver to prevent air pockets or collection of abrasives near the mechanical seal. Motor and rotating assemblies are removable without disturbing discharge or return piping.

VRC Condensate Units

RECEIVER: Single piece cast iron. Rated for a maximum internal pressure of 5 psi. Designed for venting to atmosphere.

PUMP: Bronze-fitted centrifugal design, flanged to the receiver, with leakless mechanical seal. The seal chamber has a relief line back into the receiver to prevent air pockets or collection of abrasives near the mechanical seal. The motor and rotating assembly are removable without disturbing the return or discharge piping. Maximum water temperature at the pump suction is 210degrees F.

FLOAT SWITCH: Single units have a float switch (mounted and wired on the unit) to automatically operate the pump. Duplex units have an alternating float switch (mounted and wired on the unit) to automatically alternate the operating cycles of the pumps and provide simultaneous operation when required.

UNITS: Unit is factory assembled. Simplex unit has one receiving tank, one makeup valve and one pump and motor. Duplex unit has one receiving tank, one makeup valve, and two pumps and motors. Triplex unit has one receiving tank, one makeup valve and three pumps and motors. Quadruplex unit has one receiving tank, one makeup valve and four pumps and motors.