Commercial Series

Models produce from 4,500 to 14,400 gallons of water per day. Reduce heavy metals, nitrates, radionuclides, herbicides, pesticides, THM’s, VOC’s and other contaminants.

SSC Model

Features

RO Elements: 4″ x 40″ Extra Low Energy Thin Film

Pressure Vessels: 304 Stainless Steel (SS)

Pump: Centrifugal 304 SS Shell, 316 SS Shaft

Frame: 409 SS

Control: Programmable with LCD Readout

Flow Meters: Product and Waste

RO Pressure Gauges

Low Pressure Cutoff Switch

Pre Filter: 5 Micron Sediment

Inlet Filter Gauges (pre and post filter)

Inlet Feed Electric Solenoid Valve

Inlet Manual Shutoff Valve

Product Reverse Flow Check Valve

Waste Recycle Valve

Options

Total Dissolved Solids (TDS) Meter

Product Dump Valves (option requires TDS meter)

Remote System Status Indicator Lights

Carbon Tank for Chlorine Removal

Water Softener

UV Light

Dimensions

Height

Depth

Width

72 inches

18 inches

48 inches

Specifications

Membranes

Production*

Recovery

Motor**

Weight (Approx.)

Inlet***

Outlets

Qty. 3

4,500 GPD

50%

2 HP

350 Lbs.

1″ FNPT

3/4″ FNPT

Qty. 4

6,000 GPD

50%

2 HP

380 Lbs.

1″ FNPT

3/4″ FNPT

Qty. 5

7,200 GPD

50%

2 HP

410 Lbs.

1″ FNPT

3/4″ FNPT

Qty. 6

9,000 GPD

50%

2 HP

440 Lbs.

1″ FNPT

3/4″ FNPT

Qty. 8

12,000 GPD

50%

2 HP

500 Lbs.

1″ FNPT

3/4″ FNPT

Qty. 10****

14,400 GPD

50%

2 HP

560 Lbs.

1″ FNPT

3/4″ FNPT

* Approximate product flow based on properly pretreated feed water of 1000 ppm TDS (as NACL), 15°C (59°F) and silt density index less than 3. Production capacity may vary due to feed water temperature, pressure, quality and product back pressure.

* Approximate product flow based on properly pretreated feed water of 1000 ppm TDS (as NACL), 15°C (59°F) and silt density index less than 3. Production capacity may vary due to feed water temperature, pressure, quality and product back pressure.

Options

Dimensions

Specifications

Elements

Production*

Recovery

Motor**

Weight (Approx.)

Inlet***

Outlets

Qty. 1 (4″)

1,500 GPD

50%

1/2 HP

120 Lbs.

1/2″ FNPT

3/8″ JG

Qty. 1 (2 1/2″)

750 GPD

50%

1/2 HP

110 Lbs.

1/2″ FNPT

3/8″ JG

* Approximate product flow based on properly pretreated feed water of 1000 ppm TDS (as NACL), 15° C (59° F) and silt density index less than 3. Production capacity may vary due to feed water temperature, pressure, quality and product back pressure.