We all struggle with those rooms that never get the right amount of air and end up feeling much too cold or way too hot.. But if you are not ready for a fully automated HVAC system...then the Advector inVent-M/C-R1 inVENT Manually Adjustable Register for New Construction might be just what you need. Using aerodynamic principles to promote 360 degree airflow distribution, the Manually Adjustable inVENT provides for more comfortable and balanced feeling temperatures. The inVENT closing plate has a full range of motion between the open and closed position allowing you to decide how much conditioned air is directed at each room. Adjust the closing plate to the shut position and stop wasting money heating and cooling empty rooms...adjust the closing plate to the open position to redirect the conditioned air to where you need it most. The manually adjustable inVENT gives you the ability to regulate temperatures by controlling the amount of air that enters each room.

This product is also available for , sold separately.

Additional Features

Quickly make adjustments to room temperatures to address changes in the weather or room occupancy.

The aerodynamic design causes the air to grip the ceiling, wall, or floor to maximize air distribution and comfort

Lower your energy usage without having to spend a fortune

Please Note: It is recommended that you install the Advector Duct Transition prior to installing sheet rock.

Performance Data

Closing Plate Position

CFM Flow Rate -->

50

100

150

200

250

300

350

Fully Open

Static Duct Pressure -->

0.05

0.09

0.14

0.22

0.34

0.57

0.73

Fully Open

Duct Diameter -->

8-inch

8-inch

8-inch

9-inch

9-inch

9-inch

9-inch

Fully Open

Noise Criteria -->

-

19

27

34

42

50

62

Fully Open

Horizontal Face Velocity -->

620

1180

1520

1900

2320

2733

3125

Fully Open

Horizontal Throw -->

7

16

22

32

41

51

58

Performance Notes

Airflow is in cubic feet per minute.

All pressure is measured in inches of water

Duct Static Pressure is based on 8inch and 9inch duct sizes as indicated

Face Velocity is in feet per minute

Horizontal Throw is calculated based on 50fpm air velocity and 360 degree distribution pattern

inVent cfm rate can be fully controlled by closing and opening of the Closing Plate

The Noise Criteria values are based on a room absorption rate of -10 db, referenced to 1pW and one inVENT