Transcription

1 SEC 4100 SYSTEM MONITOR Programmable Serial Interface Card Series 2 USER MANUAL Rev. P1.11 September 13, 2006 DeltaV is a trademark of Emerson Process Management, Inc Emerson Process Management, Inc. 1998, All rights reserved. Printed in the U.S.A. While this information is presented in good faith and believed to be accurate, MYNAH Technologies does not guarantee satisfactory results from reliance upon such information. Nothing contained herein is to be construed as a warranty or guarantee, express or implied, regarding the performance, merchantability, fitness or any other matter with respect to the products, nor as a recommendation to use any product or process in conflict with any patent. MYNAH Technologies reserves the right, without notice, to alter or improve the designs or specifications of the products described herein.

2 1 INTRODUCTION 1.1 Scope This document is User Manual for the SEC 4100 communications driver firmware for the Emerson Process Management (EPM) DeltaV Control System. The driver runs on the DeltaV Series 2 Programmable Serial Interface Card (PSIC). The reader should be familiar with EPM s DeltaV PSIC and connected SEC 4100 devices. 1.2 Document Format This document is organized as follows: Introduction Theory of Operation Downloading Firmware Configuration Information Operational Check DeltaV Field Device Electrical Interface Technical Support Describes the scope and purpose of this document. Provides a general functional overview of the SEC 4100 Driver. Describes downloading procedures for the driver firmware on to the DeltaV PSIC. Describes procedures and guidelines for configuring the DeltaV PSIC. Provides tips and assistance to ensure PSIC is properly setup and configured. Describes the electrical interface between DeltaV and the SEC 4100 devices. Also describes the cable pin assignments for RS-232. Describes who to call if you need assistance. 1

4 2 THEORY OF OPERATION POWERFUL SOLUTIONS FOR DIGITAL PLANTS The Programmable Serial Interface Card (PSIC) has 2 ports which can be configured for RS-232, RS-422/RS-485 Half Duplex or RS-422/RS-485 Full Duplex communications with external devices. For communications with SEC 4100 devices, the PSIC connects to the RS-232 port of the SEC A single SEC 4100 device can be connected to each PSIC port, as illustrated below. The driver runs in Slave mode only. Each device uses a maximum of nine datasets with the gas level reading from each sensor being placed in the appropriate register of one of the first four datasets, sensor status information being placed in the appropriate register of datasets five through eight, and system status information being placed into the first register of dataset nine. PSIC with SEC 4100 Driver DeltaV Power Supply and Controller DeltaV I/O RS-232 Mode 4100 # #2 SEC 4100 DeltaV Setup Information 3

5 3 Downloading the firmware POWERFUL SOLUTIONS FOR DIGITAL PLANTS The driver software distribution comprises 14 files, distributed on a CD. These files must be copied to the DeltaV directory on your ProPlus Workstation. The path is: \DeltaV\ctl\ProgSerial\S2-SEC4100 Note that you will have to create the \S2-SEC4100 subdirectory. The following files will be copied: 4

6 After copy completion, you are ready to program (or upgrade) the Programmable Serial Card with the supplied custom driver software. The steps are as follows: 1. Click on the Start button and select DeltaV-> Installation-> Controller Upgrade Utility as shown below, and the following dialog will appear: 5

7 2. Choose Upgrade I/O Modules from the drop down menu and click Next. 3. The above dialog will appear, listing all the available Controllers in your network. From this dialog, select the appropriate Controller and then Click Next. 4. The following dialog will appear, listing all the I/O modules in your selected Controller. The shown list of I/O modules is an example only. Your list will be different. 6

8 Note: The first time a standard Serial card is upgraded to the ControlNet Driver, the dialog will be as shown below. When upgrading an existing Programmable Serial Card, skip Steps 4, 5 and 6, and go to Step Click the Browse button and select the DeltaV path as shown below, and then click Ok. Note that the disk drive could be C or D. 7

9 6. Select the I/O module again as shown below and then click Next. Go to Step If you are upgrading an existing Programmable Serial Card, the dialog will be as shown below. From this dialog, select the Programmable Serial Card I/O Module in the list. 8

10 For example, we will select I/O Module 1. This will give you a dialog, from which you will select the file path to where the driver software is located. This path will be: \DeltaV\ctl\ProgSerial\S2-SEC4100\ Once you are in the specified directory, you will need to select the following file: S2-SEC4100.S2F This is shown in the following dialog. 9

11 8. After selecting the.s2f file, Click on Open. This dialog will close and you will be back to the following: 9. In this dialog, Click Next again. You will get the following dialog, confirming the Controller and I/O Module to program. 10

12 10. Click Next and the I/O Module upgrade process will begin. After completion, you will receive the following dialog, indicating success. 11. This completes the I/O Module upgrade process. 11

13 4 CONFIGURATION INFORMATION POWERFUL SOLUTIONS FOR DIGITAL PLANTS Under each port, there exist 16 datasets. Each attached SEC 4100 needs one to nine datasets for operation. There can only be one SEC 4100 per port. Under the port a Device is created for the attached SEC The device address is not needed and may be disregarded in this driver. Under each device, one to nine datasets are defined that will receive the data of each of the 400 possible gas sensors. The figure below shows an example SEC 4100 setup: Control Network Controller Name I/O C01 - Programmable Serial Card P01 DEV01 DS01 Gas level for Sensors DS02 Gas level for Sensors DS03 Gas level for Sensors DS04 Gas level for Sensors DS05 Sensor status for Sensors DS06 Sensor status for Sensors DS07 Sensor status for Sensors DS08 Sensor status for Sensors DS09 System Status 4.1 Port Configuration The port should be configured as Slave. Transmit delay may be left as the default. The Port Type should be defined as RS-232. The Baud Rate, Parity, Data Bits and Stop Bits should match the settings of the SEC 4100 devices. 4.2 Device Configuration One device should be configured for each SEC 4100 connected to a given port. The device address is not used in this driver. Only one device may be configured per port for a total of two per PSIC. 12

14 4.3 Dataset Configuration Data Direction: POWERFUL SOLUTIONS FOR DIGITAL PLANTS One to nine datasets are to be defined under each device. The number of datasets is determined by the device ID s of the sensors in the field. The gas level data from devices is placed in dataset 1, data from devices is placed in dataset 2, data from devices is placed in dataset 3 and data from devices is placed in dataset 4. Sensor Status data from devices is placed in dataset 5, status from devices is placed in dataset 6, status data from devices is placed in dataset 7, status data from devices is placed in dataset 8 and system status data is placed in the first register of dataset 9. If the needed dataset is not configured, the data will be lost. Since this is a slave driver, input or output does not need to be selected DeltaV Data Type, Device Data Type and Number of Values Table 1 Dataset Configuration DATASET DeltaV DATA TYPE DEVICE DATA TYPE DATA START ADDRESS NUMBER OF VALUES Bit UINT Bit UINT Special Data The Special Data values (1-5) will not be used in this driver and can be left as default Register Mappings Table 2 Dataset Register Mapping DATASET REGISTER DESCRIPTION Gas Level Data for Devices Gas Level Data for Devices Gas Level Data for Devices Gas Level Data for Devices Sensor Status Data for Devices Sensor Status Data for Devices Sensor Status Data for Devices Sensor Status Data for Devices System Status 13

16 5 Operational Check 5.1 Scope POWERFUL SOLUTIONS FOR DIGITAL PLANTS The following sections provide some assistance to ensure the interface is working properly. 5.2 Verify Hardware and Software Version Number The user can verify that the SEC 4100 driver has been installed using the DeltaV Diagnostics tool. The Diagnostics tool will show the Hardware Revision No. (HwRev) and the Software Revision No. (SwRev). To begin the DeltaV Diagnostic tool select Start-> DeltaV-> Operator-> Diagnostics. In the Diagnostics tool expand the Controller, I/O and then double click on the Programmable Serial Interface Card that has the driver installed. The following information will be displayed: : : : SwRev Software Revision 1.10 (or later) HwRev Hardware Revision 2.3 (or later) 5.3 Verify Configuration Verify port configuration: The serial port must be enabled. It must be set to Slave mode. User needs to make sure communication settings such as baud rate, parity, and number of data bits match the SEC 4100 settings. Verify Dataset configuration: up to nine datasets, which contain bit UINT registers. 15

17 5.4 Verify I/O Communication With Control Studio User can create I/O modules in the control studio to verify correct values are read and written between the foreign device into the PSIC. For input data, the values should be changed in the foreign device and verified that the new data are correctly reported. For output data, change the values in the controller and then verify that the values are transferred to the foreign device. To assign a Dataset and a register in the Dataset to an I/O module, follow these steps: 1. Double click the IO_IN/IO_OUT parameter for the module. This brings up the IO_IN/IO_OUT Property window. 2. Click on the Browse button. This brings up the Browse window. 3. Click on the Object_Type drop down list, select All. This displays all the Dataset tags. 4. Double click on the desired Dataset tag. This assigns the tag to the module and closes the Browse window. 5. Choose the desired register in the Parameter drop down list. 6. Click the OK button. For output modules, user also needs to change the MODE parameter to Manual for Normal Mode and Target. 5.5 Using Diagnostics Verify PSIC communication: Select the PSIC on Diagnostics and press the right mouse button. Select Display Real -Time Statistics from the drop down menu. If the Programmable Serial Interface Card is functioning then the user will see the Valid Responses counter and the Async and/or Sync Transactions counters incrementing. There will not be any error counting up. Verify port statistics: Select the Port on the Programmable Serial Interface Card and press the right mouse button. Then select Display Port Statistics form the drop down menu. Verify that the port communications statistics are being displayed properly and are counting as expected for the protocol s functionality. Verify dataset values: Select a dataset and press the right mouse button. Select View Dataset Registers from the Drop down window. Verify that the dataset values are displayed as expected. 5.6 LED Indication The Yellow LED for the port should be on solid when all communications on that port are valid. The Yellow LED should be blinking if there is some valid communications and some communications with errors on that port. The Yellow LED should be OFF if there are no valid communications on that port. 6 DeltaV Field Device Electrical Interface 16

20 7 Technical Support For technical support or to report a defect, please give Mynah Technologies a call at (636) If a defect is discovered, please document it in as much detail as possible and then fax your report to us at (636) You can also send us your questions via . Our address is: Thank you for using DeltaV. 19

POS function Marchen POS-DVR surveillance system is a professional surveillance integrated with POS system. By bringing video and POS transaction data together, the POS-DVR surveillance system provides

User Guide Modbus Communications for PanelView Terminals Introduction This document describes how to connect and configure communications for the Modbus versions of the PanelView terminals. This document

MODEL ATC-2000 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2000 is a RS232/RS485 to TCP/IP converter integrated with a robust system and network management features designed

GV- RK1352 Card Reader The GV-RK1352 is a card reader with keypad, designed to recognize PIN codes, identification cards or both. Featured with the Wiegand and RS-485 outputs, the unit can be connected

Programming and Using the Courier V.Everything Modem for Remote Operation of DDF6000 1.0 Introduction A Technical Application Note from Doppler System July 5, 1999 Version 3.x of the DDF6000, running version

MODEL ATC-2004 TCP/IP TO RS-232/422/485 CONVERTER User s Manual 1.1 Introduction The ATC-2004 is a 4 Port RS232/RS485 to TCP/IP converter integrated with a robust system and network management features

PC Configuration Requirements: Configuration Requirements for ipc Operation The hardware and operating system of the PC must comply with a list of minimum requirements for proper operation with the ipc

Using HyperTerminal with Agilent General Purpose Instruments Windows HyperTerminal can be used to program most General Purpose Instruments (not the 531xx series counters) using the RS-232 Serial Bus. Instrument

How to setup a serial Bluetooth adapter Master Guide Nordfield.com Our serial Bluetooth adapters part UCBT232B and UCBT232EXA can be setup and paired using a Bluetooth management software called BlueSoleil

This document covers tasks associated with connecting a console port to a PC, and includes the following topics: Console (rollover) Cable and Adapters Making the physical connection Connecting using HyperTerminal

Work Off-Line Set up a new database or modify a previously saved database (without being connected to the telephone system). This helps minimize on-site programming time. Work On-Line (connected directly

Installing ABACUS ELECTRICS USB Optical Probes under Windows 7 AN17a This note assumes that you are installing the drivers on to a clean system, i.e. one on which ABACUS ELECTRICS Optical Probe drivers

Overview This application note describes the steps necessary to configure the SST DeviceNet OPC Server for use under Windows NT (Service Pack 3 or higher). This example shows how to set up a configuration

Campus Component Pvt. Ltd. DISCLAIMER Information furnished is believed to be accurate and reliable at the time of publication. However, Campus Component Pvt. Ltd. assumes no responsibility arising from

Title Page PowerChute plus Version 5.0.1 for Windows 95 Notice Page : PowerChute plus for Windows 95 version 5.0.1 PowerChute plus License Statement This software is protected by both United States copyright

TM SECURITY SYSTEM MANAGEMENT SOFTWARE FOR WINDOWS Quick Start Instructions Introduction WinLoad for Windows was developed to simplify and speed up the task of programming Paradox control panels. Remote

Develop a Dallas 1-Wire Master Using the Z8F1680 Series of MCUs AN033101-0412 Abstract This describes how to interface the Dallas 1-Wire bus with Zilog s Z8F1680 Series of MCUs as master devices. The Z8F0880,

Guide to Installing BBL Crystal MIND on Windows 7 Introduction The BBL Crystal MIND software can not be directly installed on the Microsoft Windows 7 platform, however it can be installed and run via XP

Tech Tip 7 64-Bit Compatibility with Micromeritics Applications Micromeritics products are designed to operate in most Microsoft Windows environments. However, more current versions of Microsoft Windows,

WA Manager Alarming System Management Software Windows 98, NT, XP, 2000 User Guide Version 2.1, 4/2010 Disclaimer While every effort has been made to ensure that the information in this guide is accurate

SMS Database System Quick Start [Version 1.0.3] Warning ICP DAS Inc., LTD. assumes no liability for damages consequent to the use of this product. ICP DAS Inc., LTD. reserves the right to change this manual

Introduction: Implementation of the MVI56-MCM module for modbus communications: Initial configuration of the module should be done using the sample ladder file for the mvi56mcm module. This can be obtained

Application Note: Connecting to a 2500 Series Processor using PLC Workshop This application note will describe a step by step process for the three ways to connect to a 2500-CXXX with PLC Workshop. The

SECURITY SYSTEM MANAGEMENT SOFTWARE FOR WINDOWS WINLOAD MODEM SETUP The modem setup is a very important step in the connection process. If the modem setup is not properly completed communication between

SA-9600 Surface Area Software Manual Version 4.0 Introduction The operation and data Presentation of the SA-9600 Surface Area analyzer is performed using a Microsoft Windows based software package. The

R32 to RS422/485 Converter Installation Guide 1. Introduction Thank you for purchasing this R32 to RS422/485 Converter. It is designed for your PC, workstation, thin client, or server to provide instant

XPort Universal Demo Board User Guide Part Number 900-563 Revision A September 2009 Copyright and Trademark Contacts 2009 Lantronix. All rights reserved. No part of the contents of this book may be transmitted

LHC Gas Systems 28 th February, 2007 Schneider OS-Loader usage via Ethernet or USB. Jacques ROCHEZ - IT/CO/FE Abstract This document is a guideline on how to configure correctly a PC for the use of the

User Guide 00809-0300-4975, Rev A June 2016 WinHost Configuration and Diagnostic Software for Rosemount 975 Flame Detectors Legal Notice The Flame Detector described in this document is the property of

GETTING STARTED NI Condition Monitoring Systems and NI InsightCM Server Version 2.0 This document contains step-by-step instructions for the setup tasks you must complete to connect an NI Condition Monitoring

Installing the Gerber P2C Plotter USB Driver 1 You can install a Gerber P2C plotter using a USB connection and communicate with it using compatible design software. The following procedures describe installing

SECTION 3 - INTRODUCTION This section explains how to install the Strategic Enterprise Management Application Programming Interface (semapi) software and how to use the ICICONF.EXE program to configure