Thermoplastic White Emergency Light Unit

$18.50

Availability : In Stock

Product Type : Modern Emergency Lighting

Vendor : Modern Emergency Lighting

SKU : ESW-EML-W

PRODUCT OVERVIEWThe ESW-EML series emergency units have become an industry standard. The architecturally appealing design, ease of installation and economical price are all contributing factors. The injection molded thermoplastic housing is corrosion and flame resistant. The universal mounting plate allows for effortless installation. The standard 5.4W incandescent lamps can be...

PRODUCT OVERVIEWThe ESW-EML series emergency units have become an industry standard. The architecturally appealing design, ease of installation and economical price are all contributing factors. The injection molded thermoplastic housing is corrosion and flame resistant. The universal mounting plate allows for effortless installation. The standard 5.4W incandescent lamps can be positioned as needed. Damp location rating is standard.

EXTERNAL SPECIFICATIONSThe ESW-EML series is constructed from high quality corrosion and flame resistant thermoplastic. White finish is standard (black color optional). Emergency lighting heads are molded from high impact thermoplastic in a matching color and positioned on a ratcheted track for accurate positioning. Lens material is a high-impact polystyrene. Universal mounting bracket is easily snapped onto the EML housing. External test switch and monitor LED are standard.

BATTERY & CIRCUIT TECHNOLOGYThe ESW-EML series is supplied with a maintenance free, sealed valve regulated lead acid battery for emergency operation that provides a minimum emergency duration of 90 minutes (for the listed rating). The EML-1 model comes standard with a 6V 4.5Ah battery. The ESW-EML-2 model comes standard with a 6V 7Ah battery for remote capability. Recharge time of the battery is twenty-four (24) hours. The maximum working temperature is 50&deg; C.

HOUSINGThe ESW-EML series utilizes a corrosion and flame resistant injection molded thermoplastic housing and mounting bracket. Lightweight and durable, the ESW-EML is ideal for use in areas where materials such as steel and aluminum may deteriorate. The bracket connection allows installation to a standard wall mounted junction box. The ESW-ELM series emergency luminaires come standard rated for damp location installations. The ESW-EML is an ideal solution for exterior covered breezeways, warehouses, covered corridors and high humidity regions.

LAMP HEAD FEATURESThe ESW-EML series is normally supplied with two (2) front mounted square heads with 5.4W wedge base incandescent lamps. Lamp heads are mounted within a ratcheted track that allows correct and accurate beam positioning. Lamp heads are constructed of high impact thermoplastic in a color matching the finish of The housing (white is standard). Lens material is a high-impact polystyrene.

UNIVERSAL MOUNTINGThe ESW-EML emergency lighting unit uses a universal mounting bracket that snaps into the XLP housing. Easy field wiring and durability make the ESW-EML a favorite among contractors.