From shott at snf.stanford.edu Sun Jun 7 11:03:40 2009
From: shott at snf.stanford.edu (shott at snf.stanford.edu)
Date: Sun, 7 Jun 2009 11:03:40 -0700
Subject: Shutdown wbmiscres SNF 2009-06-07 11:03:40: DI water leak ....
Message-ID:
Lots of DI in the plenum. It appears as if a fitting on the left side of the sink (under the plenum) has come loose or developed a severe leak.
I've shut off DI water to this bench in the fingerwall.
John
From shott at snf.stanford.edu Sun Jun 7 11:19:32 2009
From: shott at snf.stanford.edu (shott at snf.stanford.edu)
Date: Sun, 7 Jun 2009 11:19:32 -0700
Subject: Shutdown wbmiscres SNF 2009-06-07 11:03:40: DI water leak ....
Message-ID:
Re-threaded fitting but didn't turn water back on to the bench until Jim Haydon can check it out in the morning. However, I'm clearing this shutdown and reporting it as a problem so that folks can use the SRD next to this bench (which has it's own water supply).
John
From shott at snf.stanford.edu Sun Jun 7 11:21:03 2009
From: shott at snf.stanford.edu (shott at snf.stanford.edu)
Date: Sun, 7 Jun 2009 11:21:03 -0700
Subject: Problem wbmiscres SNF 2009-06-07 11:21:03: DI Water Leak .... status ...
Message-ID:
Mario and I found the fitting that had come loose (a threaded 3/8" DI line). He reattached and retightened it, but did not turn the water back on to this bench (shutdown in the fingerwall) to insure that the DI system has a chance to recover.
Thanks,
John
From vilanova at snf.stanford.edu Mon Jun 8 08:33:31 2009
From: vilanova at snf.stanford.edu (vilanova at snf.stanford.edu)
Date: Mon, 8 Jun 2009 08:33:31 -0700
Subject: Problem wbmiscres SNF 2009-06-07 11:21:03: DI Water Leak .... status ...
Message-ID:
Turn Water Back On and Checked for leaks , System Fine.
Haydon/Mario V.