HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

What to do with flooded water heaters

It rained in Albany, New York over the past couple of weeks. Alot of homes were flooded causing heavy damage. I was called in to inspect the heating units. Most of the time, the heating units are raized off the ground enough not to get flooded but, others are sitting on the floor. My question is, what to do with flooded water heaters? The older models were an easy fix. The newer ones have a sealed chamber. Is there an easy fix besides replacement?

110&#37; sure?
Will you sign off on it?
What got wet the legs, or is it flat bottomed.
Structurally may rust and weaken.
How old, Maybe wise for Ho to replace even if not water damaged.Most important is it in safe operating condition. Only the qualified tech. checking the tank can make these calls.

I'm the first one to say replace. I'm just trying to be sure that there isn't something I missed, like some old guy showing up on the job site making me look bad. By the way, these are home depot flat bottom water heaters.

I'm the first one to say replace. I'm just trying to be sure that there isn't something I missed, like some old guy showing up on the job site making me look bad. By the way, these are home depot flat bottom water heaters.

When you make a call explain your position and allways put safety first.
Don't worry about someone else's opinion you will sleep good

If it was my water heater, I'd dry it out and replace the thermostats if electric. A lot of the electrics these days are foam lined and the water is not going to get between the foam and the heater anyway. The foam is encased in a plastic too so the tank shell probably isn't going to rust much faster then it normally would ,if you dry it out. If it was a fiberglass insulated tank it will take a long time to dry out and will probably rust the shell out over time. If it was gas and didn't get into the gas valve, I'd dry it out and run it and check its operation. Most gas water heater are required to be put on a pedestal these days. Sealed chambers are not sealed against water infiltration. If you're doing it for a customer, I'd let them make the call, and if they want to keep it get them to sign off on it so you aren't liable in any way. David