• Microprocessor accuracy and dependability with ambient operation from -10 to 120°F• Large easy-to-read 40 character (20x2) backlit LCD display showing every parameter measured and controlled by the microprocessor.• PC DATA PORT with built-in transmitter allows optional adapter and up to 500 ft. cable to interface with computers for ease in startup and remote diagnostics. Or, for adding an optional large 80 character (4x20) backlit LCD display remote-mounted up to 150 ft. distances with a CAT-5 cable.• Long-term diagnostics and data logging is possible using communications software that's included in Windows’ OS.• Fault LED indicators for quick servicing and diagnostics• Fast and easy installation with "screwless" sensor terminals and easy access for all other wiring• Electrostatic discharge protected• One HP or 20 AMP high reliability relay• Polyester coated 16 gage rugged steel enclosure• Model available with 1/2” conduit holes for higher current permanent wiring• 2 industrial 400°F (204°C) rated 10K thermistors with +/- 1°F accuracy are included• Two auxiliary thermistor inputs for optional sensors that can be located up to 1000' away• Selectable overrides for low temperature shut down or freeze protection modes for safe operation

Eagle 2 Models come standard with 2 sensors

LCD DISPLAYThe LCD display has 2 lines of 20 characters each. The first line permanently displays the COLLECTOR and the STORAGE temperatures. The second line can be paged by pressing the button located just below the LCD display.

Eagle 2 Differential Controller - DC Models Features

DC operated controllers available for "12VDC" Battery operation or from direct PV panels. Relay options are from 5 AMPS to 30 AMPS. Power consumption is 2 watts for model D1 and 1/4 watt for model D2. D2 PV POWERED from 0 VDC to 22 VDC with SMART power management at very low PV power levels. A must for soft PUMP starts and smooth controller operation. Electrostatic discharge protected.