Pleiad SLD G2 245

About Pleiad SLD G2 245

InstallationSuitable for recessed mounting in unventilated or ventilated ceilings. Light sources are fitted in the luminaire. Assembly springs for quick, tool-free installation included. An assembly plate should be used when installing in soft tile ceilings. The ballast box can be detached for flexible installation. The luminaire must not be covered with insulation. For further details please refer to the assembly instructions on our website.

ConnectionSnap-in terminal block 5x2.5 mm², 3-phase through-wiring possible. The luminaire for emergency lighting has a separate emergency lighting box, which is connected to the luminaire with snap-in connector. All connections are made in the emergency lighting box.

Fagerhult's emergency lighting for Pleiad contains both
electronic parts and batteries (NiMH). The batteries
have 1 or 3 hours operating time. The box is available
in three different styles: A standard version without
self-test, a potential free version with self-test and a
DALI version with self-test. The self-test is in accordance
with EN 62034. The boxes are intended to be recessed
in unventilated or ventilated ceilings. The diode that indicates
the charge/status is connected to the luminaire.
The battery has its own space on the side of the box;
protecting all heavy current components against unintentional
when changing the batteries. The boxes are
designed in class II, IP 20 and are F marked.

ConnectionThe box is supplied with a 15-way multi connector
installed on 0.25 m wiring, for simple connection to
the intended luminaire. All external connections are
made in a separate space in the emergency box. The
boxes are prepared for the connection of control cables
that allow for dimming. The terminal block is equipped
with integrated fuses for incoming phases (ignition and
charging phases). If there is a fault in the emergency
lighting luminaire, or faulty work in the installation, the
fuses create greater safety. Boxes with self-test are also
equipped with separate terminal blocks for connecting
DALI or supervision systems based on the use of potential
free contacts.

MiscellaneousThe emergency boxes require specially prepared luminaires
with HF-standard or HF-dim, which are supplied
with diodes for charging/status and equipped with the
corresponding multi connector as the box. The box can
be combined with luminaires with 13–57 W FSQ-E/
FSM-E light sources. We recommend mercury type light
sources, but amalgam light sources may also be used.