Local Reviews for Bear, DE

Daniel M.

Found both units not calling for heat and neither running . I made both call for heat and both turned on and then I removed the call and both shut down . I did this twice and both times the systems did what they were supposed to . Front area was 72 degrees and back area was 73 degrees when I arrived. Front set to 72 and back set to 68 . Units are working properly .

Near E Songsmith Dr, Bear,
DE19701

40 days ago

Colin T.

Upon arrival I found thermostat reading 85, set for 72 and heat on indicator. Went to roof and found jumper. Removed and heat shut off. Thermostat heat on indicator now off. Unit operating normal.

Near E Songsmith Dr, Bear,
DE19701

42 days ago

Yonas M.

Fall pm on 02/07/19 On arrival set units to call for heat measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced checked belts and replaced units operating normal at this time.