The Ecosys contoller provides intelligent monitoring and control of your Armarac, with an integrated web server for remote IP access, settings and email alarms. SNMP in tegration of settings and alarms is included.

Monitor

Armarac MX-800-FAN comes standard with the EcoSys controller and sensors for monitoring

Temperature

Humidity

Fan Speed

Door access

Alarms

Alarms can be set for communication by email or SNMP

Reporting

A history is maintained and reports can be run for remote IP access in order to diagnose performance history.

Active FAN ambient cooling

Armarac MX-800-FAN comes with 6 input and 4 extraction fans. These provide up to 240CFM of airflow.

The ambient room air is forced through your equipment. A typical result is that equipment is maintained at 5 degrees above ambient temperature.

Our EcoSys controller monitors both the inlet and outlet temperatures, and adjusts the fan speed to meet your preset temperature. This means that where your room has a lower ambient temperature the equipment will be kept cooler at lower fan speed, and therefore the fans can operate at a quieter, lower speed.

AirConditioning

Armarac MX-800-N4X comes with airconditioning options. See the link at the bottom of this page for more details.

The A/C has a variable capacity operation mode, which provides between 2000 and 6000 BTU of cooling, depending on the equipment load. Note that because of the targeted efficiency of our closed-cycle system, this is able to cool equipment with a nameplate heat output of much higher levels.

The closed cycle airconditioning unit is mounted into one (or both) of the doors. Ambient room air is taken into the door cavity, passing through the compressor and heat exchanger unit. The warmed air is vented externally. The cooled air is cycled internally through the equipment back to the heat exchanger unit where it is cooled again, providing targeted cooling in a sealed environment with corresponding benefits of efficency in operation.

A low ambient heating option is available on request which provides heating for winter environments in addition to the cooling.

If an A/C unit is placed in each door then a failsafe fallback mode of operation can be implemented. If one unit fails then the other unit will take over and continue operation. The faulty unit can then be swapped out by a non-A/C support person, and can be replaced with a swap-in replacement.

All items have a 12 months return to factory warranty. Higher levels including on-site support can be arranged.