Window/Wall Fan

The Window / Wall Fan SAX is a stylish, high performance range of axial flow fans which provide powerful extract of air through windows, walls, ceilings and panels for a variety of domestic and commercial applications.

FEATURES & BENEFITS

Learn more about individual features and benefits of our products.

SPECIFICATION

The SAX range of Window/Wall fans as manufactured by Elta Fans Ltd.

TECHNICAL INFORMATION

The technical information available to you from ELTA Fans is exhaustive - Choose from either sound, performance and electrical or dimensional data for each and every product

ACCESSORIES

Elta supply a full range of accessories for each of their products.

COMPARE

Choose up to three products to compare their features side-by-side.

DOWNLOADS

Get the full brochure, wiring diagrams and operation and maintenance instructions.

Features & Benefits

Reliability

Motors have sealed for life bearings.

Mounting

Each unit is suitable for window, wall, panel or ceiling mounting installations.

Versatility

The SAX is designed for installation into windows, panels, ceilings, as well as most solid or cavity walls.

Casing

Unit casings shall be manufactured from shockproof, heat resistant white plastic. The fans shall be suitable for installation into window, wall or ceiling mounted applications. All ‘built in’ units shall have a telescopic wall liner for installations between 240mm and 315mm and 5m 4 core cable to assist installation.

The unit shall comply with Documents F1 of the Building Regulations and is BEAB approved. All units have IPX4 protection and are splash proof as required under current electrical regulations.

Motors

Motors have sealed for life, self lubricating bearings which do not require ventilation. They are sealed in a housing, ensuring quiet operation of the fan. Motors shall be Class B insulated to EN 60034-5. Motors are connected in accordance with EN60335-1, double insulated with in-built thermal overload protection. The fan shall be suitable for operating temperatures up to +40°C.

Impellers

Quality Management

Units are to be designed and manufactured with procedures as defined in BS EN ISO 9001:2008. All SAX units are to be tested to ISO 5801:2007 (airside performance) and BS 848 Part 2:1985 (sound performance).

Typical Application

Pubs

Restaurants

Offices

Kitchens

Factories

School and Shops

Dimensional Data

† Units that are suffixed with an A include a silent operated shutter. These are either intake only, extract only or both (in conjunction with a double pole switch).

Units that are suffixed with an AR and ARB include silent operated shutters. These units are five speed extract and supply, operated through a control provided with the unit. Units suffixed with ARB include a telescopic steel wall liner.