Specifications

Specifications include,
but are not limited to: The rehab project
consists of, but is not limited to, the
following: o Removal and reinstallation of
complete motor, columns, shafts and bearings,
bowls and related appurtenances. o Cleaning,
inspection and possible replacement of the 12"
columns and couplings. o Cleaning, inspection
and possible replacement of 2 3/16" AISI 416
stainless steel shafts and couplings. o
Cleaning, inspection and possible replacement
bushings of existing spiders. o Cleaning,
inspection and possible replacement of 2 3/16"
AISI 416 stainless steel head shaft. o Cleaning
and inspection and possible replacement of
existing pump bowls with an assembly capable of
3000 gpm at 361' of total dynamic head. o
Removal, inspection and cleaning, and
installation of the rubber packer. o Cleaning,
inspection and replacement of applicable
bearings of the 400 Hp motor. o Replace of 1"
transducer tubes and install an additional 5/16"
poly air line for rubber packer inflation. o
Video inspect integrity of well casing(s) and
well screen(s) using color capable video
equipment. o Chlorinate well, pump equipment and
lines, flush to waste. The City will acquire a
bacteria sample for approval prior to final
connection. o Start up services upon final pump
assembly to distribution system after approval
of sample(s).