PID Controller

X96P

X96P is a full-featured PID controller. Typical applications are temperature control, RH control, thyristorised heating applications, AHU control in HVAC and BMS applications. It receives input from 8 types of thermocouples (B, E, J, K, N, R, S, T), Pt100, Cu53 as well as other 3-wire RTD sensors, 0 - 50 mV voltage and 4-20 mA or 0 - 20 mA analog current signals. A triple 7-segment LED display and individual LEDs on the front of the process controller indicate setpoint and process values, relay status, auto/manual power status and communication status. Buttons on the front of X96P allow operators to easily set up to 5 setpoints - 4 for the relays and a 4 - 20 mA signal. With an error of only 0.1% of the full-scale, this is a process controller of superior accuracy. X96P's electromagnetic relays trigger heating, cooling or any of 6 types of alarms - full-scale high/low, deviation high/low, inband and outband. It also retransmits an isolated output