Hydroflo VFD Pump Sets

Product Overview

Product Details

Variable Speed control is a widely used technology for pump control and works by varying the pump speed to provide system water output at a constant pressure. This provides the following benefits:

Constant pressure providing consistent, even supply to the consumer.

Large energy cost savings as systems are always operating at peak efficiency for the demand conditions.

Extended pump life due to reduced electrical and mechanical operating loads.

Silent operation with no pressure shocks.

Simplified installation due to compact dimensions and integral pump control - no separate panel is required.

Principle system components include the controller, which for larger systems is mounted on top of the pump motor to provide cooling while smaller units are mounted in line on the pump outlet, a quality Grundfos pump, a pressure sensor and a small surge tank to smooth the operating cycle. Controllers offer the following features:-

Varies pump speed to maintain pre-set system pressure.

Over voltage, under voltage, single phasing and electrical overload protection.

All Dayliff booster sets use the latest technology controllers coupled to quality Grundfos pumps and are supplied complete frame mounted with inlet and outlet manifolds and valves for simple installation. Nominal system sizes are 2.5, 4 and 6 Bar, though pressures can be set to suit site conditions and the option of two and three pump configurations are available. Three pump systems can be specified with three controllers or two controllers/1 DOL start unit. In all systems pump operation is sequenced with the number of pumps operating increasing with system demand.

Variable speed drive is now accepted as the most efficient way to provide on-demand water supply in all sorts of industrial, commercial and domestic applications. Dayliff booster sets are the ideal solution in the application of this efficient technology.

Controllers- WACS inline variable speed controllers incorporating in-built pressure sensor and flow switch. Pressures can be set between 1-6Bar incorporating various protection functions including over current, dry running and over temperature.

Controllers - VASCO motor mounted fully programmable variable speed controllers with settable system pressures up to 8Bar that are linked to provide automatic sequenced pump operation. Operating and protection parameters are displayed on an illuminated crystal panel and full control and protection functionality is provided so no external control accessories are required other than isolators and coarse current MCB's.

All pumps and controllers are 1P55 rated enabling installation in dusty and humid environments.