These transducers are used in HVAC systems to
provide an accurate signal for positioning damper
and valve actuators based on branch line pressure.
They convert an analog voltage (E) or current (I)
signal into a linear pneumatic (P) output signal for
accurate positioning of damper and valve actuators
used in HVAC systems.

They are not position sensitive devices and can be
mounted vertically or horizontally. They provide
a direct output feedback signal for branch line
pressure.

They can be powered by either 24 VAC or 24 VDC,
and have three selectable input ranges. The analog
signal may be either 1 to 5 VDC, 2 to 10 VDC, or 4 to
20 mA, which provides a 3 to 15 psi linear pneumatic
output signal. A 1 to 5 VDC output feedback signal,
proportional and linear to the 3 to 15 psi output
signal, is provided. A gauge tap is also provided
for pressure output indication. Standard 3.25" Snap
Track is supplied for mounting.

The XEC-3004 (only) also has a manual override that
may be initiated by moving a jumper and adjusting a
potentiometer.

MAP Price

There is a Minimum Advertised Price (MAP) allowed by the manufacturer on this product. Add item to cart for lowest price.

Lead Content Warning

This product does not comply with the Safe Drinking Water Act,
which requires that products used in any system providing water for human consumption (drinking or cooking) to meet low-lead standards.
Please check the box below to confirm you are aware that this item is for non-potable water applications only.

This product will NOT be used in the installation or repair of a potable water (human consumption) application.

Warning

This product must be installed by a qualified/licensed contractor and set up with properly calibrated combustion test equipment. Failure to comply with this could result in substantial property damage, severe personal injury or death.

By checking this box I am verifying that this product will be installed by a qualified/licensed contractor and will be set up with properly calibrated combustion test equipment.

Lead Content Warning

Do not use this item for any installation or repair of potable water applications.
This product does not comply with the "Safe Drinking Water Act,"
which requires that products meet low-lead standards in order to be used in systems providing water for human consumption (drinking or cooking).
This item is for non-potable (non-human consumption) water applications only.

Modal title

Available TurboTrack Time Slots

Select at checkout

=

TurboTrack

*
items only

* Free slots for orders with water heaters, boilers and other bulky items only