YJLHV

Sino-cables YJLHV type is constructed with AA-8000 series aluminum alloy, compact stranded conductor. The conductor is extruded with XLPE(cross-linked polyethylene) insulation. The insulated conductors are cabling together with non-hygroscopic fillers inside for round shape and reinforcement tape for added strength and conformity. A PVC outer jacket covers the entire assembly.

1.YJLHV Type cable is specially designed for the common residence, commercials and industrial buildings, such as civilian constructions, hospitals, schools, etc. It’s also widely applied in the circumstances without armored mechanical protection, such as office building, hotel, plaza, factory lighting and other feeder circuits of electrical equipment.

2.Suitable for installation of both indoor and outdoor environment, uprightness, bracket, being along wall and direct burial.

0.6/1KV YJLHV Physical index

Nominal C.S.A. Of conductor
(mm2)

Approx. overall diameter of cable (mm)

Approx. Weight of cable (KG / KM)

1 core

2 core

3 core

4 core

5 core

3+1 core

3+2 core

4+1 core

1 core

2 core

3 core

4 core

5 core

3+1 core

3+2 core

4+1

core

10

10.9

16.7

17.5

18.9

20.4

18.5

19.6

20.1

98

233

261

305

369

297

341

354

16

12.0

18.9

19.9

21.6

23.4

20.9

22.2

22.8

126

289

342

415

507

393

457

484

25

13.6

21.9

23.2

25.2

27.5

24.3

25.8

26.6

171

386

483

580

711

557

626

665

35

14.6

24.1

25.6

27.8

30.7

26.3

27.6

29.1

211

490

603

728

907

682

781

854

50

16.3

27.4

29.1

32.1

35.2

30.2

32.1

32.5

273

580

762

977

1198

858

996

1101

70

18.0

30.8

32.9

36.3

40.0

34.1

36.2

38.1

351

784

1031

1341

1652

1134

1311

1473

95

19.5

34.0

36.2

39.8

44.0

37.9

40.4

42.3

436

981

1294

1782

2103

1492

1763

1899

120

21.3

37.6

40.3

44.3

49.3

42.4

45.4

47.5

531

1230

1588

2136

2578

1893

2162

2388

150

23.3

41.8

44.8

49.5

54.7

46.2

48.9

51.3

648

1475

2011

2590

3217

2261

2598

2949

185

25.2

46.1

49.2

54.7

60.3

51.0

53.7

57.8

779

1631

2476

3201

3906

2877

3417

3743

240

28.0

52.0

55.4

61.4

68.1

57.5

60.5

64.4

974

2389

3166

4057

4895

3572

3823

4578

300

30.3

56.3

60.2

67.1

74.2

62.8

66.4

72.3

1188

2786

3681

4878

6072

4334

4859

5659

400

34.1

63.8

68.4

75.3

84.5

70.6

74.6

79.4

1545

3691

4906

6351

7981

5657

6397

7314

500

37.6

70.8

75.8

84.5

92.6

78.5

83.6

88.5

1906

4510

6079

7903

9798

7028

8008

9153

630

41.9

79.0

84.8

94.6

104.8

85.5

90.4

97.7

2387

5769

7704

10110

12463

8663

9891

10898

0.6/1KV YJLHV Ampacity

Nominal C.S.A. Of conductor (mm2)

Dia.of conductor (mm)

Insulation thickness (mm)

D.C. Resistance at 20℃ (Ω / KM)

Resistance of insulation (M Ω / KM )

Current rating

In the air (A)

Direct in soil (A)

10

3.8

0.7

≤ 3.080

≥ 5.23 × 104

55

63

16

4.8

0.7

≤ 1.910

≥ 4.31 × 104

71

81

25

6.0

0.9

≤ 1.200

≥ 4.44 × 104

94

105

35

7.0

0.9

≤ 0.868

≥ 3.79 × 104

116

124

50

8.4

1.0

≤ 0.641

≥ 3.55 × 104

146

152

70

10.0

1.1

≤ 0.443

≥ 3.35 × 104

180

185

95

11.6

1.1

≤ 0.320

≥ 2.90 × 104

218

223

120

13.0

1.2

≤ 0.253

≥ 2.82 × 104

256

252

150

14.6

1.4

≤ 0.206

≥ 2.94 × 104

295

285

185

16.2

1.6

≤ 0.164

≥ 3.03 × 104

338

323

240

18.4

1.7

≤ 0.125

≥ 2.83 × 104

398

375

300

20.6

1.8

≤ 0.100

≥ 2.63 × 104

459

423

400

23.8

2.0

≤ 0.0778

≥ 2.59 × 104

547

485

500

26.5

2.2

≤ 0.0605

≥ 2.56 × 104

625

547

630

30.0

2.4

≤ 0.0469

≥ 2.49 × 104

714

608

In the air: 40℃ Direct in soil: 25℃, the coefficient of Soil thermal resistance 1.2Km/w