With isolated repeater：1000 m up to 187.5kbaud, 1200 m up to 38.4kbaud

Without isolated repeater: 50 m

Max. number of stations

32 per segment, 126 per network

Max. number of masters

32

Peer to peer（PPI Master Mode）

Yes

Power

Input voltage

20.4 to 28.8 VDC

Input current

110mA while CPU only at 24 VDC

700mA while Max. load at 24 VDC

Inrush current

12A at 28.8 VDC

Isolation(field to logic)

Not isolated

Hold up time（loss of power）

10ms at 24 VDC

Sensor voltage

L+ minus 5 V

Current limit

1.5A peak，thermal limit non-destructive

Ripple noise (sensor to logic)

Derived from input power

Isolation (sensor to logic)

Not isolated

CPU Digital Input Specifications

Built-in digital input

14

Input type

PNP/NPN

Rated voltage

24 VDC at 4mA

Max. continuous permissible voltage

30 VDC

Surge voltage

35 VDC for 0.5s

Logic “1” voltage range

15 to 30 VDC

Logic “0” voltage range

0 to 5 VDC

Input delay

Selectable (0.2 to12.8ms)

Connection of 2-wire proximity sensor (Bero)

Premissible leakage current (Max.)

1mA

Isolation (field to logic)

Yes

Optical galvanic

500 VAC for 1minute

Isolation groups

Refer to Wiring diagram

High Speed Counter (HSC) input rate

HSC logic level 1(15 TO 30 VDC)

20K Hz (Single phase), 10K Hz (Tow phase)

HSC logic level 1(15 TO 26 VDC)

30K Hz (Single phase), 20K Hz (Tow phase),

Inputs on simultaneously

all

Cable length Max.

Shielded

500m normal inputs, 50m HSC inputs

unshielded

300m normal inputs

CPU Digital Output Specifications

Built-in outputs

10 outputs

Output type

Solid State-MOSFET(Sourcing)

Rated voltage

24 VDC

Voltage range

20.4 to 28.8 VDC

Surge current (Max.)

8A for 100ms

Logic “1” (Min)

20 VDC,at maximum current

Logic “0” (Max)

0.1 VDC with 10KΩ load

Rated current per point（Max.）

0.75A

Rated current per common（Max）

6A

Leakage current (Max)

10µA

Lamp load (Max)

5W

Inductive clamp voltage

L+ minus 48 VDC, 1w dissipation

On State resistance (contact)

0.3Ω Typical（0.6Ω max.）

Isolation

Optical (galvanic, field to logic)

500 VAC for 1 minute

logic to contact

-

Resistance (logic to contact)

-

Isolation groups

Refer to wiring diagram

Delay(Max)

Off to on

2µs(Q0.0,Q0.1), 15µs(others)

On to off

10µs(Q0.0,Q0.1), 130µs(others)

Switching

-

Pulse frequency (Max.)

20KHz (Q0.0 and Q0.1)

Lifetime mechanical cycles

-

Lifetime contacts

-

Outputs on simultaneously

All at 60℃(horizontal)

All at 50℃ (Vertical)

Connecting two outputs in parallel

Yes, only outputs in same group

Cable Length (Shielded)

500m

Cable Length (unshielded)

150m

Order number

6ES7214-1AD23-0XB0

Shipping

DHL, UPS, Fedex, TNT, EMS, Post

Payment

T/T, Western Union, Moneygram, Paypal

Minimum Order Quantity

1 pcs

Technical Support

free

Programming Software

free

Kollewin Technology now brings quality 6es7214-1ad23-0xb0 products from its professional factory made by its qualified workers. Our 6es7214-1ad23-0xb0 products have already been sold to different regions like Europe, North America, UK, and so on. We can provide you a competitive price, and you can check the price list with us first if necessary. Come and get some!