PUSH BUTTONS

On the front control display are three push buttons that control the operation of the generator and the ATS.

TRANSFER TEST:

use this button to test the system. this operation starts the generator and transfers the load.

BYPASS TIME DELAY:

Use this button to cancel the active time delay or exercise period (stops the generator after cooldown).

SET ENGINE EXERCISER:

Use this button to set the automatic generator exerciser

INDICATOR LIGHTS

On the front control display are five lights that indicate the status of the sources and the ATS.

UTILITY ACCEPTABLE:

This light indicates that the utility voltage is acceptable for connection to the load.

LOAD ON UTILITY, LOAD ON GENERATOR:

These two lights indicate which source (utility or generator) is connected to the load.

GENERATOR ACCEPTABLE:

This light indicates that the generator voltage is acceptable for connection to the load.

AUTOMATIC GENERATOR EXERCISER:

When the utility is acceptable and the load is on the utility, this light flashes the number of days until the next exercise period. when it is off, no exerciser period is set. the light is also off when the generator is running.