By Setpoint with Percent of time feature as part of spaced feed for setpoint “creep”.

Trace chemistry capable with user definable correction factors as part of programming.

By makeup totalized gallons

By blowdown totalized gallons

Percent on time

Scheduled feed by time and day

Alarm relay-User selected alarms powered output shall be selectable to either feed chemical or to alarm on the following conditions.

Inputs:

Up to 8 active Sensor inputs (2 TWR Conductivity, 2 pH and 2 ORP, 2 MU Conductivity) can be ordered in various combinations.

Water meters- Two Water meter inputs are standard and be factory or field upgradeable for two additional (Total four) water meter inputs

Each relay shall be capable of being configured to operate with either of the two flow (digital) input for activation or deactivation

Expansion capabilities: The unit will be factory or field upgraded. Additional expansion features include:

4 Additional Fully programmable relays ( NRLY Nodes)

8 Sensor inputs. Combo of Conductivity using NCON and pH or ORP Probes using NpH/ORP Nodes. Requires the purchase of additional probes/Plumbing kits.

8 Additional 4-20MA inputs (2 N420I Nodes)

4 Additional Digital Inputs (NDIG Node)

Interface/Communications:

The NexSys® comes standard with the following system interfaces : LON EIA 709 FTT10, BACnet IP (Read this link before ordering) and MODbus TCP (As well as Incorporate DMX outputs). The unit shall comes from the factory with all tables and outputs defined for Information being transmitted , including:

The state of any installed relay (On/Off)

Water meter readings

Conductivity reading

Any additional sensor reading (ph, ORP)

Any sensor alarms

Any Additional 4-20mA input readings

Any Additional 4-20 mA output reading

Flow condition (and any other digital inputs)

Remote Communications:

The NexSys® controller has standard Ethernet capability through and HTML interface that allows 100% access to all features and control parameters of the controller.

The NexSys® remote access allows the user to alter, confirm and manipulate 100% of configurations.

All features, parameters, settings and functional requirements to operate, program and monitor the NexSys™ controller are accessible from the touch screen and DO NOT require the use of an external input, PC or device to operate or access. (BMS config requires use of interface program)

The NexSys® will be upgradeable to send E-service reports to a subscribed service (user to set up account with a service at their discretion).

The NexSys® displays operating values, via a color touch screen, color coded graphs for all sensor and relay operation times and readings with time and date stamps. User shall be able to manipulate graph via zoom and scroll features.

Approvals

Is in qualification testing for UL and CSA Listed (ETL listing is acceptable)

NEMA 4X enclosure

Power:

Transformer power ratings of 120/240 VAC 50/60 Hz.

Release date: 30 March 2014

For More Information about the NexSys® Control systems, Contact Lakewood Instruments at 800.228.0839

Screen Shots

Operator Screens for setup and System notes (user fields changeable)

Screens shown above:

Upper left: The main screen where you can manually operate relays and verify system readings

Upper Right: The built in calculation screen for figuring Pre Bleed for Bio feeds. (User inputs)

Lower Left: Current alarm conditions. The user can choose to be notified by email and also have the alarms logged.

Lower Right: A system notes screen where the user can leave instructions for the next person.

Screens shown above:

Upper Left: Relay configuration screen allows operator to choose how and when relays operate and interact.

Upper Right: System choice screen for configuration and documentation.

Lower Left: Configuring a setpoint Blowdown relay. All on one screen. Tap and enter. No need to go between or use up down arrows to try and enter a number

Lower Right: Internal Manual Documentation to show how to wire and care for probes and boards.

Screens shown above:

Screens can be viewed from HTML5 capable browsers (Chrome, Firefox,etc) and Smartphones using remote access. The screen you see is the exact same screen you see at the controller. No more mucking about to find a function on a web page that is not laid out in the same menu system as the actual controller interface. (Including live graphing of features IN COLOR.