Local Reviews for Potomac, MD

Great Service

Mehta - Potomac, MD23 days ago

The service is excellent. on time and done right. Satisfied GeoThermal customer for over 7 years

Overall Experience
5 / 5

Quality

Price

Convenience

Great service

Funari - Potomac, MD43 days ago

Review of Supreme Air

Youssef was very thorough and pleasant!

Response from Supreme Air:

Thank you for taking the time to write this review. We're thrilled Youssef provided you such great service. He always does such a thorough job, ensuring he provides our customers with the best care before leaving their home. We're looking forward to providing you many more years of this same great service. Have a supreme day!

Overall Experience
5 / 5

Quality

Price

Convenience

Terrific service by Chris.

Hobbins - Potomac, MD81 days ago

Review of Supreme Air

Chris arrived on time and proceeded to get acquainted with the heating unit in our Carriage House. He did an excellent job! He found the problem and reset it!

Response from Supreme Air:

Thank you for taking the time to leave a review. We're very pleased Chris was able to provide you with terrific service. Have a supreme day!

Overall Experience
5 / 5

Quality

Price

Convenience

Exceptional Service

Hobbins - Potomac, MD119 days ago

Review of Supreme Air

Very devoted to do great work!

Overall Experience
5 / 5

Quality

Price

Convenience

Excellent Service

Jim - Potomac, MD122 days ago

Review of Supreme Air

Chris was great. He was realistic and talked about how best to approach the problems we have.

Overall Experience
5 / 5

Quality

Price

Convenience

23 days ago

Christopher A.

I put amp meter on wires and h.w.h. pulling 9 amps across both elements. I noticed the wiring was not correct and the elements were always heating at 1/4 capacity. I fixed the wiring and tested lower element, it was pulling 18 amps. I had to replace the upper element and tested it after replacing. Both elements and thermostats are pulling 18-19 amps and are working properly.
I called the service manager to let them know. I took before and after pictures of the wiring.

Daniel M.

Pump down refrigerant . Repair leak on lineset and pressurize system with nitrogen and make sure it holds . Put system into a vacuum and make sure it holds . Then charge system with R410A and check operations . Suction pressure 125 , head pressure 290 . Return temp 67.8 , supply temp 46 . Suction line temp 54 degrees . System is operating properly now .

Near Garden Ct, Potomac,
MD20854

49 days ago

michaelr@supremeairllc.com

Customer asked to reschedule for earlier time Saturday or Sunday will call in with his available time and day in 30mins

Near Barn Wood Ln, Potomac,
MD20854

49 days ago

michaelr@supremeairllc.com

On arrival checked thermostats were calling for cooling. Measured temperature coming in, temperature going out, amps, voltage, water pressure, water temperature coming in and going out, system needed to be pressurized, replaced both filters provided by customer. Inspected electrical connections, voltage absorption systems, and contactors. Customer stated that he had his duct cleaned and thermostat was not communicating after the company that performed the job left. When I set carrier unit to call for cooling found outdoor unit not coming on, reset system and unit is operating normal at this time

Near Garden Ct, Potomac,
MD20854

52 days ago

Yonas M.

Spring Pm on 04/03/19 On arrival set units to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filters and replaced checked EWP and LWP recommended UV lights installation units tested units operating normal at this time. Also customer has problems with his water heater keep tripping he was reset Avery day or every other day and he have another problem with 2nd water heater the expansion tank leaking water the pipe rust I gave quote for customer he needs talk to Alex first about the price and he will decide.

Yonas M.

Spring pm on 03/14/19 On arrival set unit to call for cooling measured supply and return air temp measured voltage and amps inspected electrical connections checked drain and cleaned checked filter recommended air filter need to be replaced also the duct has a l lot of dust duct needs to be cleaned and UV lights installation gave quote for customer needs some time to decide unit tested unit operating normal at this time.

Near Stallion Ct, Potomac,
MD20854

71 days ago

Yonas M.

GEO water furnace spring Pm Potomac Md

Near Stallion Ct, Potomac,
MD20854

81 days ago

Christopher A.

Install Intellistart Module.
The aquastat controller had the heating set point at 68 degrees. The unit was cycling but turning off once the water reached 68 degrees. Iâ€™m not sure how the controller was reset but I set the heating set point to 110. The unit began heating up. I checked the refrigerant pressures, pressure drop and heat of extraction and run capacitor, all were within specification. I recommended adding Intellistart Module given the units age and tonnage. I installed a large retrofit Intellistart Module made by Water Furnace into the unit and restored power. After having the power cycled for controls and the unit the aquastat retained the set point of 110. I used a billing code for small electrical repairs for finding this problem. I used Intellistart installation code for the other invoice item. Unit is operating normal.

Near Tulip Ln, Potomac,
MD20854

100 days ago

Christopher A.

Wire pump relay.
The pump for unit #3 was not coming on. If one of the other units was running then enough water was moving through the unit for it to operate, which is what happened when I charged it. I wired 24 volts to the pump relay and tested the unit. Unit operating normal.
Customer to call the office to discuss service membership. I know we talked about it before but for whatever reason getting the units up and running was priority.

Near Tulip Ln, Potomac,
MD20854

102 days ago

Christopher A.

I replaced the heating txv. Leak checked the system, flushed it out and pulled into a deep vacuum. I charged the system until I had normal operating pressures and normal temperature rise at the air handler. Unit is operating normal.
Repair has been paid in full.

Near Tulip Ln, Potomac,
MD20854

109 days ago

Christopher A.

I replaced the reversing valve which had been disassembled by a previous serviceman. I pressure tested the system and went to test it and found the txv for heating is not opening and the system pulls into low pressure despite having adequate charge. The txv was most likely the original problem but there was no way for me to know.
Customer paid 477 toward replacing the txv.

Near Tulip Ln, Potomac,
MD20854

119 days ago

Christopher A.

Find refrigerant leak in unit #2, fix the leak, flush the system and charge using r22 substitute refrigerant.
I found the leak in the bend of the suction line just before the compressor. I believe the pipe was bent during manufacturing and had a crack which they brazed but it was leaking at the edges of the braze. I cleaned it with wire brush and sand paper and used silver brazing compound to help etch out the copper. I laid a thick braze over entire area. I pressurized and let it hold pressure for 15 minutes. I pulled it into a vacuum of 400 microns and when I turned the pump off it never increased. I charged the unit with 7 lbs 8 oz of Nu22. There was no system total charge information so I charged until I had 10 degrees superheat and 11-12 degrees subcooling and normal temperature rise. Unit #2 is operating normal.
Unit #3 needs a reversing valve and the customer paid $1000 as a deposit for this repair. I completed a part order form. The office will contact customer for scheduling

Near Tulip Ln, Potomac,
MD20854

122 days ago

Christopher A.

Unit #2 has a refrigerant leak somewhere in the system. I feel that itâ€™s in the cube portion but nitrogen will need to be added to be sure of its exact location and that there is only one leak. I did not want to spoil the charge tonight because it is heating somewhat. Itâ€™s r22 refrigerant so once the leak is identified and fixed of its in a place that can be fixed, replacement r22 will be added to specification. Customer paid $600 tonight.

Near Tulip Ln, Potomac,
MD20854

149 days ago

Youssef D.

On arrival found system locked on fp1 ,reset system ,checked system pressures refrigerant and water .i then increased water flow to 70 % minimum and 100 max on both system .also spoke to tech support and we found that system is operating normal at this time .

Near Tulip Ln, Potomac,
MD20854

164 days ago

Youssef D.

On arrival found systems are operating normal,checked history and found unit 2 did lock on fp1 4 times.called water furnace and advised me to increase min vs to 60 instead of 45% and leave the other unit at 45% since it didn't lock again .units are operating normal at this time

Near Tulip Ln, Potomac,
MD20854

169 days ago

Colin T.

Performed preventative maintenance on both hybrid systems. For gas furnaces, I cleaned flame sensors, measured ohms of igniters, measured rating of run capacitors, inspected heat exchangers. Ran furnaces and checked amperage of blower and inducer motor, measured heat rise. Furnaces operating normal. For Geothermal units, measured ratings of compressor capacitors, checked contactors, flushed out drains, and checked cleanliness of blowers and coils. Ran geothermal units. Measured amp draw of compressors, blowers, and loop pumps. Measured delta loop pressures and temps as well as delta air temps. Ran humidifier and checked operation. Turned Humidistat on and set to 45%. Units are operating normal at this time.

Near Swains Creek Ct, Potomac,
MD20854

178 days ago

Youssef D.

On arrival found system operating normal ,checked fault history,found system did locked on fp1 .raised vs to 45 minimum and 100 max instead of 25 and 75 . Units are operating normal at this time