Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

I rebuild heat pumps for an assisted living complex and these are of the horizontal slide in type. They are connected to a water source that is suppose to maintain a constant 67 degree water temp.The problem is that each pump will put out various degrees of cooling/heat.The water temp is the same through out the building.I guess my real question would be.. could the water canister that is with each pump be the problem child? It seems to be a nonservisable devise.Could buildup of mineral deposits maybe keep the unit from extracting enough heat? I change the compressor,reversing valve,filter drier,clean the coil, and change all the electric components but rarely do I get a completed unit to perform like the way I believe it should.Any suggestions would be appreciated. Also I want to point out that the company that made these heatpumps went out of buisness so getting new water tanks is probably going to be impossable. Thank you.

Flushing heatpump water coil

I picked up some scale remover but haven't quite figured out how to flush it through.Has any one used it before? I think it has to be pumped through but I haven't figured out how I'm going to do that concidering it is made with hydrocloric acid.Thanks in advance!

I use a 5 gallon container with a hole in the lid, I drop a small acid, submersible pump down in the container which is filled above the pump with the scale remover. I then connect the tubing from the pump to one end and other tube back to the container as a return. The container, pump and tubing is all reusable.