ATEX instruction for PAHT G 2-90 in dust applications

Transcription

1 MAKING MODERN LIVING POSSIBLE Instruction ATEX instruction for PAHT G 2-90 in dust applications danfoss.high-pressurepumps.com

2 Table of Contents 1. Common demands for Category 2 and 3 installations Design guide for Category 2 (zone 1) systems Temperature sensor Pressure sensor Preferred system design and P&ID for Category 2 pump Design guide for Category 3 (zone 2) systems Pressure sensor Preferred system design and P&ID for Category EU Declaration of Conformity....9 The Danfoss pumps are marked for application in Group II Category 2 or Category 3 systems. II 2 DG c b T6 II 3 DG c T6 Nessie MADE IN DENMARK PUMP PAHT G 12.5 SERIAL NO CODE NO. 180B6184 II 2 DG c b T6 II 3 DG c b T6 Example ATEX pump label This document describes how to integrate a pump in a system depending on the Category demand. Equipment groups (Annex I of the EC-Directive 94/9/EC) Group I (mines, mine gas and dust) Group II (other explosive atmospheres gas/dust) Category M Category 1 Category 2 Category G (gas) (Zone 0) D (dust) (Zone 20) For equipment providing a very high level of protection when endangered by an explosive atmosphere For equipment providing a high level of protection when likely to be endangered by an explosive atmosphere For equipment providing a very high level of protection when used in areas where an explosive atmosphere is very likely to occur G (gas) (Zone 1) D (dust) (Zone 21) For equipment providing a high level of protection when used in areas where an explosive atmosphere is likely to occur G (gas) (Zone 2) D (dust) (Zone 22) For equipment providing a normal level of protection when used in areas where an explosive atmosphere is less likely to occur 2 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

3 1. Common demands for Category 2 and 3 installations This instruction is a supplement to existing product instruction as ATEX components are subject to some limitations compared to standard components. The limitations are described in this ATEX instruction. Validity: Approvals are only related to water as fluid. If other fluids are used these must be non-flammable fluids. The pumps are designed to pump liquids and not gasses! It is the user s responsibility to ensure that the pump is fluid filled during start-up and operation. Fluids: If the pump is to operate on other fluids than water, please contact Danfoss. Other operation and maintenance conditions might apply. Minimum suction pressure: The user must always ensure that the pump is bleeded. The pumps must always be operated with a positive head on suction port. The allowable minimum and maximum inlet pressure for the suction port can be found in the pump data sheet. Maximum discharge pressure: It is the user s responsibility that the pump discharge pressure does not exceed the max continuous discharge pressure stated in the pump data sheet. Temperature: The pump is not to be operated in systems where the fluid temperature exceeds 50 C/122 F. Filtration: The fluids entering the pump must as a minimum always be filtered according to the specification found in the pump data sheet. External impacts due to: Gases: The pumps are made in materials resistant to most common gases. The user of the pump must ensure that materials used are resistant to the gases applied. In ATEX dust applications, the layer of dust may never exceed 5 mm [0.002 inch], we recommend to paint the components in contrasting colors, to make deposits more visible. Assembly of pump drive unit: Motor - Pump assembly and system integration: When assembling the pump with the bell housing, flexible couplings and motor, it is the builder s responsibility that the parts used conform to the ATEX directive and that the components are assembled and running according to the operational data/design found in product data sheets and instructions. In order to avoid dust accumulations, the system design must be with smooth surfaces and with as few dead spaces as possible. All parts must be potential equalized in a Category 2 and 3 system, according to local regulations. The wire gauge must be equal to the wire gauge applied in the supply of the electric motor and may as a minimum not be smaller than 16 mm 2 [0.63 inch 2 ] (EN , item 15.4). Grounding connectors Grounding connectors, mark with Grounding connectors It is important to potential equalize each component directly to a base point. 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

4 Choice of bell housing and coupling The material for the bell housing can be steel, stainless steel or aluminium with a magnesium content below 7,5%. The bell housing must have an inspection and a drain hole. The drain hole must be placed at the lowest point to ensure the fluid can get out if there is a small leak from the pump shaft seal. In dust applications, the bell housing, which covers the rotating parts, must minimum be an IP5x, dust proof. Make sure that inspection and drain holes are dust proof and we recommend often inspecting for dust or fluid accumulations. The dust may not come in contact with rotating parts, as this can cause an increased temperature. The distance between bell housing and the rotating parts must be at least 5 mm [0.2 inch]. Coupling for use in hazardous areas are marked with regard to the respective permissible conditions of use. Aluminium as coupling material is generally excluded for explosive areas. See special conditions for safe use in coupling operation- and ATEX instruction from coupling supplier. Mounting of bell housing and coupling: 1. Mount the coupling on pump shaft. Ensure an air gap between end of coupling and pump flange of min. 4 mm [0.16 inch] D. 2. Mount the bell housing on pump. Secure bolts with the right torque - see pump instruction. 3. Measure the longest distance A from top of bell housing to the bottom of coupling claw. 4. Mount the coupling on motor shaft. Ensure the coupling and motor flange are not in contact with each other. 5. Measure from motor flange to the top of the coupling. That measurement B shall be 3-5 mm [ inch] shorter than the measurement A. 6. Adjust respectively, verify the measurement, and secure both couplings with the right torques on the locking screws (see coupling operation & mounting instruction). 7. Mount the elastic spider and mount the bell housing/pump on the motor. After mounting it must be possible to move the elastic spider 3-5 mm [ inch] axial C. The check can be done through the inspection hole of bell housing. Secure motor flange bolts with the right torque - see pump instruction. Caution! Read the pump & coupling Installation, Operation, Maintenance instructions before mounting. Electric motor Motor for use in hazardous areas are marked with regard to the respective permissible conditions of use. Marking: Category 2, Zone 1: Ex d, Ex de, Ex e Category 3, Zone 2: Ex na All rating plate values relating to certification must be carefully checked to ensure that the motor protection, atmosphere and zone are compatible. See special conditions for safe use in electric motor operation manual and ATEX instruction. Caution! Ensure with regular inspection the motor flange is not affected by severe corrosion. Motors in variable speed operation: Certain criteria must be considered to ensure that the combination of VFD and motor can be used safely. The requirements depend on the protection type in use. The motor must be dimensioned so that its surface temperature remains at a safe level with respect to the temperature class. In most cases 4 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

5 this requires either combined type tests or the use of direct temperature control. Caution! Consult motor manufacturers for right dimensioning. Cabling and electrical connections Suitable cable lugs must be used for the connection of all main cables. The cable connection must fulfil the requirement stated in the national standards for installation or in the standard EN and EN In addition, earthing or bonding connection facilities on the outside of electrical apparatus must provide effective connection of a conductor. Caution! Read the Installation, Operation, Maintenance manual of the chosen motor to ensure all applicable warranties. Failure modes due to operational conditions Following operational conditions can cause a pump failure: Pump running dry Too high inlet pressure Too low inlet pressure Too high temperature of the fluid being pumped Too high ambient temperature Pump is pumping against blocked port Pump operate with a non-specified/ approved fluid Pump running the wrong direction Non-return valve in front of the pump inlet Insufficient filtration Pump is not being serviced accordance to Danfoss specifications. Danfoss recommends building systems with a high inherent safety degree. The PI&D on the next pages shows how a high degree of safety can be reached when using a Danfoss pump. 2. Design guide for Category 2 (zone 1) systems 2.1 Temperature sensor Pump housing temperature increase causing problems due to pump breakdown/failure in a Category 2 rated system. In a Category 2 system, the pump housing temperature must be monitored. Pump housing temperature must always be lower than 85 C / 185 F. Surface temperature must never exceed 2/3 of minimum ignition temperature of the dust cloud, not even in the case of malfunctions. A sensor integrated on the pump must be used to monitor pump housing temperature. This sensor must be mounted on the pump as shown in the drawings. The system must stop the pump, if a temperature of 60 C / 140 F is exceeded. Electronic equipment/control of temperature and pressure measuring must comply with EN 954 (Category 3) or EN to fulfil IPL2. Caution: The sensors may not be exposed by direct cooling as it will affect the thermal readings. Therefore they shall be protected against direct wind. S1 PAHT G PAHT G Use the M6x10 (A) or M8x10 (B) thread to locate the temperature sensor. Ensure good thermal contact between the sensor and pump end cover and avoid corrosion (material choice of sensor, crevice corrosion). Temperature sensor WIKA TR50-O Explosion protected version with stainless steel contact block can be used (see S1 at picture). Mount the sensor with a M6 screw on the pump end cover. Ensure good thermal contact between the sensor and pump end cover and avoid crevice corrosion. 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

6 Temperature sensor WIKA TR50-Q Explosion protected version with worm drive hose clip made of stainless steel can be used on these pump types (see S2 at picture). Select the right diameter size of the worm drive hose clip. Find the diameter of pump housing in the pump data sheet. S2 Ensure good thermal contact between the sensor an pump housing and avoid crevice corrosion. 2.2 Pressure sensor Checking whether suction port is fluid filled and fluid flows unrestricted: To monitor if suction line is fluid filled at right pressure, a pressure switch/sensor must be placed in the pump suction port. This switch/ sensor must as a minimum be set to the minimum suction pressure specified in the pump data sheet. Pump must be stopped by system, if pressure declines below sensor pressure setting. PAHT G Preferred system design and P&ID for Category 2 pump Pressure and temperature sensors are mounted due to a direct demand originating from ATEX risk evaluation. The pump is directly fed by a pressure line (feed pump). Fluid has to be filtrated down to 10µm absolute Pressure switch, Pump is stopped when pressure is below minimum suction pressure according to pump datasheet Category 2 certified electric motor, bell housing and flexible coupling. Pressure feed Temperature swicth set to max 50 C M Temperature sensor mounted on pump. P in P out Danfoss ATEX pumps R out Relief valve To fluid reservoir / drain 6 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

7 System where fluid is supplied from tank. Pump is placed outside the tank. Pump suction port is always below fluid level. P in Fluid has to be filtrated down to 10µm absolute Tank Minimum Water Level Switch Maximum Water Temperature Switch set to 50 C Pressure switch, Pump is stopped when pressure is below minimum suction pressure according to pump datasheet Category 2 certified electric motor, bell housing and flexible coupling. M Temperature sensor mounted on pump. P out Danfoss ATEX pumps Relief valve 3. Design guide for Category 3 (zone 2) systems 3.1 Pressure sensor Checking whether suction port is fluid filled and fluid flows unrestricted: To monitor if suction line is fluid filled at right pressure, a pressure switch/sensor must be placed in the pump suction port. This switch/ sensor must as a minimum be set to the minimum suction pressure specified in the pump data sheet. Pump must be stopped by system, if pressure declines below sensor pressure setting. 3.2 Preferred system design and P&ID for Category 3 Pressure sensor is mounted due to a direct demand originating from ATEX risk evaluation. The pump is directly fed by a pressure line (feed pump). Typical Category 3 systems Fluid has to be filtrated down to 10µm absolute Temperature swicth set to max 50 C Pressure switch, Pump is stopped when pressure is below minimum suction pressure according to pump datasheet Pressure feed M Category 3 certified electric motor, bell housing and flexible coupling. P in P out Danfoss ATEX pumps R out Relief valve To fluid reservoir / drain 180R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

10 Danfoss A/S High Pressure Pumps DK-6430 Nordborg Denmark Danfoss can accept no responsibility for possible errors in catalogues, brochures and other printed material. Danfoss reserves the right to alter its products without notice. This also applies to products already on order provided that such alterations can be made without subsequential changes being necessary in specifications already agreed. All trademarks in this material are property of the respective companies. Danfoss and the Danfoss logotype are trademarks of Danfoss A/S. All rights reserved R9313 / DKCFN.PI.012.B2.02 / 521B1305 /

Oil and Coolant Circulating Heating System Model - OCSM Installation & Operation Manual 216280-000 REV 2 Identifying Your System The HOTSTART heating system is designed to heat fluids for use in marine

Catalogue Directional Cetop Valves DCV 03 Power Flu uid Power d Power P wer Power Power Power Power Power d Power Power Power ower Power Power wer Power Power P Power Power Powe d Power Power Power Power

INSTRUCTION MANUAL (ATEX / IECEx) BExBGL2D LED BEACON For use in Flammable Gas and Dust Atmospheres BExBGL2D 1) Warnings DO NOT OPEN WHEN AN EXPLOSIVE ATMOSPHERE IS PRESENT DO NOT OPEN WHEN ENERGIZED POTENTIAL

1 2 INTRODUCTION / TABLE OF CONTENTS Step One Offered in small and large sizes, the compact junction box is ideal for sensor wiring and conduit termination. The junction box is universally compatible with

M3 Designed for industrial continuous duty, the M3 series features a compact shape, reduced overall dimensions, terminal box underneath which means also a high electric protection in dusty environments.

RIELLO BURNER SYSTEM mectron 3M TYPE 215 OWNER MANUAL INSTALLATION INSTRUCTIONS We are delighted that you have chosen the Riello burner. It is modern. clean, efficient and like any quality product. must

SAFETY VALVES SERIES 3030 EC Marking in conformity with 97/23/EC Directive (PED) GENERAL DESCRIPTION Valves series 3030 are safety devices according to the definition given in Article 1, Point 2.1.3, 2

Coolant Circulating Heating System TCR Controlled Installation & Operation Manual 216261-000 REV 5 Identifying Your System The HOTSTART heating system is designed for use in marine propulsion, diesel-powered

BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained

10 BPS Pneumatic stepping motor Product characteristics For set and adjustments Compact and powerful Stays in position when power line fails Optional with confirmation of position (internal sensors) Operation

BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained

SPOOL VALVES operated / to / tapped body and NAMUR for integrated pilot ATEX /-/ Series - FEATURES The valves offer environmental protection against the ingress of liquids, dusts or other foreign matter

Important information: These instructions contain safety information, read and follow them carefully. Dialight will not accept any responsibility for injury, damage or loss which may occur due to incorrect

Worldwide Contacts www.tyco-fire.com Model F thru F3 Mulsifyre Directional Spray Nozzles, Open, High Velocity General Description The Mulsifyre Nozzles are open (nonautomatic) nozzles and they are designed

CASE STUDY 1 COMMISSIONING A GAS FIRED STEAM BOILER A steam boiler has been built and installed at a factory for the provision of process steam. The following lists the requirements used in the commissioning

280C AIR COMPRESSOR KIT PART NO. 28021 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual before installing and using this product.

BQ FIXED DISPLACEMENT HYDRAULIC VANE PUMPS BQ SERIES Versatility, power, compactness and low running costs are the main characteristics of B&C vane pumps. All the components subject to wear are contained

200 PSI COMPRESSORS - MODEL NUMBERS 380C AIR COMPRESSOR KIT PART NO. 38033 480C AIR COMPRESSOR KIT PART NO. 48043 380C 480C IMPORTANT: It is essential that you and any other operator of this product read

A Health and Safety Guideline for Your Workplace What is static electricity? What causes it? How is it hazardous? And, most importantly, how can it be controlled? All of these questions will be answered

Operation Manual Magnetically coupled centrifugal pump OR 1200 OR 2500 OR 3500 OR 6500 Circulation pumps for fresh and salt water aquariums. In purchasing this pump you have selected a top quality product.

7 814 Actuators for air dampers and control valves of oil and gas burners SQM45... SQM48... Electromotoric actuators Torques: SQM45... up to 3 Nm SQM48... up to 20 Nm SQM48.6... up to 35 Nm Running times:

IMPORTANT SAFETY NOTICE To: Our Valued Customers User safety is a major focus in the design of our products. Following the precautions outlined in this manual will minimize your risk of injury. ITT Goulds

INSTR3010 0406 Installation and Operating Instructions Installation Instructions for SS EPE-316L Series Congratulations on your purchase of this Aqua-Pure high flow, single housing filtration system. This

Type FX4 FX4 Explosion-Proof Electric Air Heaters FX4 heaters are UL listed and/or CSA certified for use in hazardous locations. They are designed for dry indoor industrial applications such as oil refineries,

Installation and Operating Instructions Borehole Submersible Pumps These instructions apply to STAIRS submersible pumps, type SP fitted with Franklin 4"-8" motors. If the pump is fitted with a motor of

Industrial Process Pump Safety Manual IMPORTANT SAFETY NOTICE To: Our Valued Customers User safety is a major focus in the design of our products. Following the precautions outlined in this manual will

Hydraulic Control Solutions Vexve s Hydrox hydraulic control solutions are suitable for even the most challenging installation sites and conditions. Specifically designed for district heating and district

FILTER, REGULATOR AND FILTER/REGULATOR stainless steel L compact /, high flow / - / Air Preparation Series FEATURES Stainless Steel, and intended for corrosive environment and suitable for use in potentially

Catalogue & Installation Guide 10 GUARAN T E E year www.airpipe-eu.com Full Performance Compressed Air Pipe System AIRpipe founded in 1997, operates within the air compressor and air transmission industry.

To ensure the functioning of the site, we use cookies. We share information about your activities on the site with our partners and Google partners: social networks and companies engaged in advertising and web analytics. For more information, see the Privacy Policy and Google Privacy &amp Terms.
Your consent to our cookies if you continue to use this website.