In cables of types VBaShv-KhL, AVBaShv-KhL cable armor is laid with two aluminum tapes.

In cables of types VKaShv-KhL and AVKaShvKhL cable armor is laid with aluminum wires.

Cable sheath or jacket

PVC-compound

The cables are designed for transmission and distribution of electric energy in stationary installations on a nominal alternating voltage 0,66 and 1kV, nominal frequency 50 Hz

The cables are used for single installation in cable constructions, open-air electrical installations (cable overpasses, arcades).

The cables armored with steel, galvanized wires or wires of aluminum or aluminum alloy are designed for laying on the route, where the tensile forces during exploration are possible, including for installation in seismically active areas, in conditions of permafrost and areas, subjected to offset soil, in bulk and dry soils.

While manufacturing the cables the materials, which allow the cables to be resistant to low temperatures up to – 600C (degrees below zero) are used.

The class of fire hazard of the cables is according to GOST 31565 01.8.2.5.4.

Nominal voltage, kV

0,66 or 1

Ambient temperature during cable operation, 0C

from – 60 to + 50

Minimum bending radius, diameters of cable

for multi-core

7,5

for single-core

10

The cables are laid at temperature (without preheat), 0C not below

- 15

TABLE 1

Nominal voltage of the cables, number and nominal cross-section of current-carrying conductor

* – for operation in DC voltage only

Type of cable

Number of conductors

Nominal cross-section of main conductors, mm2

Nominal voltage, kV

0,66

1

VBaShv-KhL, VKaShv-KhL

1

1,5 – 50

1,5 – 1000

AVBaShv-KhL, AVKaShv-KhL

2,5 – 50

2,5 – 1000

VKShv-KhL

–

(1,5 – 1000)*

AVKShv-KhL

–

(2,5 – 1000)*

VKaShv-KhL, VKShv-KhL

2, 3, 4, 5, 6

1,5 – 50

1,5 – 400

AVKShv-KhL, AVKaShv-KhL

2,5 – 50

2,5 - 400

To make an order

You can pre-order the products. After the receipt of your order a specialist of our company will contact you and offer the best delivery conditions.