Direct and direct/indirect general area lighting distributions and
independent Up | Dn dimming control available.

Fold Spoke

Innovation takes shape in a new form.

Endcaps + Dimensions

[A] ARCH

[B] OBLIQUE

[D] SHADE

[S]SLANT

Finishes

[B] Black Powdercoat

[S] Metallic Silver Powdercoat

[W] White Powdercoat

Energy + Light - Fold 3 Spoke

[A] 45Up | 55Dn

A - 28W|3225 lm

B - 34W|3900 lm

C - 44W|4889 lm

D - 57W|6251 lm

[B] 100Dn

A - 28W|3035 lm

B - 34W|3671 lm

C - 44W|4601 lm

D - 57W|5882 lm

[D] 20Up | 80Dn

A - 28W|3056 lm

B - 34W|3695 lm

C - 44W|4632 lm

D - 57W|5922 lm

[E] 55Up | 45Dn

A - 28W|3497 lm

B - 34W|4227 lm

C - 44W|5300 lm

D - 57W|6776 lm

[F] 65Up | 35Dn

A - 28W|3405 Im

B - 34W|4118 Im

C - 44W|5162 Im

D - 57W|6600 Im

[B] Indep Up | Dn

D - 57W|6408 Im

Energy + Light - Fold 4 Spoke

[A] 45 Up | 55 Dn

A - 38W|4300 lm

B - 46W|5200 lm

C - 58W|6518 lm

D - 76W|8334 lm

[B] 100Dn

A - 38W|4046 lm

B - 46W|4894 lm

C - 58W|6134 Im

D - 76W|7842 Im

[D] 20Up | 80Dn

A - 38W|4074 lm

B - 46W|4926 lm

C - 58W|6176 Im

D - 76W|7896 Im

[E] 55Up | 45Dn

A - 38W|4662 Im

B - 46W|5636 Im

C - 58W|7066 Im

D - 76W|9034 Im

[F] 65Up | 35Dn

A - 38W|4540 Im

B - 46W|5490 Im

C - 58W|6882 Im

D - 76W|8800 Im

[B] Indep Up | Dn

D - 76W|8544 Im

[A] Area 45 Up | 55 Dn

[B] Area 100 Dn

[D] 20 up | 80 dn

[E] 55 up | 45 dn

[F] 65 up | 35 dn

Other Options

CCT

[30] 3000 K

[35] 3500 K

[40] 4000 K

Driver

[F1] Non-Dim

[F2] 0-10V Dim 3% 120-277V

[F3] 0-10V Dim 3% 347V

[E1] eldoLED ECO 0-10V Dim 1%

[E2] eldoLED SOLO 0-10V Dim 0.1%

[E3] eldoLED ECO DALI 1%

[E4] eldoLED SOLO DALI 0.1%

[L1] Lutron Hi-Lume 1% EcoSystem (LDE1)

Voltage

[3] 347 V

[M] 120-277 V

Suspension

[03] ≤ 3ft

[06] ≤ 6ft

[12] ≤ 12ft

[25] ≤ 25ft

Wiring + Emergency

[B] Battery Pack

[C] Chicago Plenum

[H] Emergency Switching

Sensors + Controls

[SE1] Canopy Integrated Enlighted Smart Sensor

[RE1] Remote Enlighted Smart Sensor

[VN1] Acuity nLight Converter

Independent Up | Dn Lighting Control

Fold Spoke U|D provides fully dimmable or switchable independent control of the indirect and direct distributions. Ideal for multipurpose rooms and spaces with presentation, projection or video conferencing requirements, the separated circuitry allows simple adjustment of the proportions of up|down light to suit the lighting and energy needs of the space and people in the environment.

Fold Spoke UD is available with a native distribution of 60 Up | 40 Dn with a maximum total delivered output of 5850 lumens for Fold Spoke 3 and 7800 lumens for Fold Spoke 4.

[B]Independent Up| Dn Ctrl

Distribution

[B] Independent Up | Dn Control

Energy

[D] 3 Spoke: 57 W

[D] 4 Spoke: 76 W

CCT

[30] 3000K

[35] 3500K

[40] 4000K

Ceiling + Mounting

Powered by low voltage stainless steel conductive aircraft cables, Fold Spoke comes with pre-wired and tested drivers that are fully integrated with power junction box, mounting and suspension components. Integrated drivers with ceiling and mounting components are designed for multiple orientations and to accommodate grid, drywall or hard lid ceilings.

Elements can be installed in advance or with fixtures for existing or new construction.

3 SPOKE | Straight cables up to 3 ft

3 SPOKE | Tapered cables over 3 ft

4 SPOKE | Straight cables up to 3 ft

4 SPOKE | Tapered cables over 3 ft

Canopies

Minimalist consistent designs to suit all types of ceiling conditions.

Grid / Drywall

Structure / Remote

For a complete order guide, dimensions and other details see Fold Spoke spec data sheets in the resources section:

Optics

Transparent, vertical optics engineered specifically for LED sources are integrated with minimalist design and architectural materials to create a broad range of solutions with superior optical and energy performance.