HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Trane chiller oil fault

I'm having the same problem for months with a trane chiller mod# RTAA100CYF01AODOF SER#U96033894 we have tried everything we have changed the thermistors we have checked them they all reading right but still we keep getting this oil system fault obviously the compressor on circuit B is being flooded it is sweating all the way till the crankcase heater we replace the crankcase heater also and we keeping the differential of 4 degrees or close between the saturated evap ref temp and the compressor suction ref temp so our superheat is fine if anybody has any comments or suggestions it will be aprecciate

I'm having the same problem for months with a trane chiller mod# RTAA100CYF01AODOF SER#U96033894 we have tried everything we have changed the thermistors we have checked them they all reading right but still we keep getting this oil system fault obviously the compressor on circuit B is being flooded it is sweating all the way till the crankcase heater we replace the crankcase heater also and we keeping the differential of 4 degrees or close between the saturated evap ref temp and the compressor suction ref temp so our superheat is fine if anybody has any comments or suggestions it will be aprecciate

Its possible the EXV is not either sealing correctly or just not controlling correctly. Ive seen them after pump down bleed refrigerant through the chiller barrel and back to compressor