Payment & Shipping Terms:

Our company is an approved Cummins OEM partner.So we can provide genuine Cummins genset with very competitive price and comprehensiv Super Silent Diesel Generator With Ats e technical support.

Technical data

Genset Model

GNRC1000

Prime Power

1000KW/1250KVA

Rated Voltage

400/230V

Frequency

50/60Hz

Power Factor

0.8(lagging)

The regulating rate of steady voltage

≤±0.5%

The regulating rate of instantaneous voltage

≤-15%/ +20%

The time of steady voltage

≤1.5sec

The waving rate of voltage

≤1.0%

The regulating rate of steady frequency

≤3%

The regulating rate of instantaneous frequency

≤±10%

The time of steady frequency

3sec

Dimension (L×W×H) (mm)

5300*2100*2500

Genset weight (kg)

10000

Diesel Engine

Brand

Cummins

Model

KTA50-G3

Number of Cylinders

16

Rotating Speed

1500/18000RPM

Cycle

Four stroke

Type

waste gas turbine boost,direct spurting type

Bore×Stroke(mm)

159*159

Displacement(L)

50

Lubricating Capacity(L)

204

Speed Governor

Electrical

Cooling System

Water-cooled

Speed Stability (%)

≤5%

Fuel Consumption at 100% Load

205g/kw.h

Starting Method

DC24V Electrical starting

Alternator

Brand

Stamford

Model

LVI634G

Number of Phase

3

Connecting Type

Three Phase and Four Lines

Number of Bearing

1

Grading Protection

IP23

Altitude

≤1000m

Exciter Type

Brushless (AVR automatic voltage regulating)

Insulation Class

H degree

The components of the genset

(1) Cummins Diesel Engine; (2)Stamford Alternator; (3) Control Panel

Control Panel

The control panel is Quadruplication protection control panel, with the display of frequency table/water temperature/schedule/battery voltmeter. The genset with low oil pressure, high water temperature, over speed emergency, stop and other pre-protection

1. Optional Accessories of

1)ATS (Automatic Transfer switch);

Which can start the diesel generator when the main power is off; when the main power comes back, it will shut down generator.

And ATS have the function of AMF (automatic Main power failure)

2)MCCB(Molded case circuit breaker);

It can protect the loading machine and the diesel generator.

3)Batterycharger(float charger);

When the generator hasn’t been used for a long time, the batteries will be no power, in that way, you can’t start the generator. But the battery charger can charge the batteries from main power.

4)Extra daily fuel tank;

It will be requested while the base fuel tank capacity is not enough for daily fuel consumption.

5)Paralleling system;

This system can make several generators work together and automatically distribute the load according to set.

6)Remote Control Panel;

Which can control the generator by computer, if use a RS484 or RS232 digital cable to connect the generator to the computer.

7)Water separate (additional cooling system);

If the ambient temperature is too high, it will be harmful to the diesel generator. Fan and water cooling is not enough for radiate. The water separate system is much better for cooling, and the life of generator will be much longer.

8)Spare Parts of Cummins engine;

All the spare parts of each Cummins engine are supplied at very competitive price.