Excellent resolution to the continuous blackout problems, as all generators of GMD - GTD and GID silent version and soundproofed 5kVA and up are available in automatic start version. Electrical panels with automatic intervention of the GATS 12-100 standard with ABB technology, allow the automatic start of the generator and then the electrical wire to the user, in a few moments from the power outage network main power; the provision of energy by the generator set is stopped immediately to the return of the mains voltage. All operating the control circuits, control and regulation are included in a single logic, equipped with a microprocessor programmed to the operation and control of the generator.

The generator is composed of a four-stroke diesel engine with direct injection tested to its maximum efficiency.

The alternator is constructed with the most modern techniques that satisfy the continuing needs of the customer, in fact, the electrical machine is equipped with ELECTRONIC CONTROLLER which automatically adjusts the voltage and frequency of the generator without that these can cause electrical surges (kW) in absorption peaks in demand.

The soundproofing is constructed respecting the strict laws on noise EUROPE according to art. 2005/88. The structure is painted with anti-rust eposidiche dust and sound-absorbing materials they do not burn, all in compliance with CE, CEI and VVFF.

THE CONTROL PANEL AND MONITORING FIXED THE GENERATOR IT'S COMPLETE DIGITAL ELECTRONICS BOARD MICROPROCESSOR THAT MANAGES The PARAMETRIC ELECTRICAL, MECHANICAL AND PROTECTION OF THE MACHINE.

MEASUREMENTS ON DIGITAL PANEL:

- VOLTAGE (V.c.a.);

- FREQUENCY (Hz);

- DELIVERED POWER (VA and / or kW);

- WORKING HOURS (h);

- ALARM BLOCK MACHINE.

TECNICAL DATA:

Power stand-by: 12,00kVA amounting to 9,60kW

Continuous power: 11,00kVA amounting to 8,80kW

Engine Type: 4-stroke diesel I.D .;

Displacement: 800;

RPM: 3,000 g / min .;

Power (HP / rpm): 16.50 / 3,000;

Cooling: Liquid;

Voltage: 400 / 230V.c.a.-PHASE;

Controller type: ELECTRONIC;

Current: 16 Amp .;

Frequency: 50 Hz;

Charger: N.P .;

Insulation grade: IP23S;

Starter: electric or AUTOMATIC + BATTERY P.B .;

Tank: 25litri;

Autonomy: 12 hours a 100% load;

Noise level: 65db (A) at 7 m;

Dimensions: 105X59X82 cm;

Weight: 325Kg.

STANDARD SUPPLY:

Electric control board and control with DIGITAL ELECTRONICS MICROPROCESSOR board for the 'intervention Automatic, CEI and IP45 protection, includes: control and measurement of the power and protection management; Network / generator switching with ABB contactors interlocked electrically and mechanically; Manual and automatic starter in the absence of the public network; Sensor and saves automatic network; Automatic battery charger; All this in a special Cabinet PREPARED with IP45 external protection.

SUPPORT

European leader for decades in the sale and rental of generating sets - power generators, do Mr. Generator Srl your supplier. We offer services of: sale and rental of generating sets and pre and post sales support throughout the italian national territory, 24/7, scheduled maintenance and extraordinary.

Sign up to our newsletter! You can access the promotions reserved for you!By clicking on "SUBSCRIBE" you agree to the Processing of Personal Data

This website uses third-party cookies to improve our services and analyze traffic.Update information about your browsing are shared with these third parties. Continuing the navigation, you accept their use.