Warning! It seems your Javascript settings on your browser have been disabled. i-sells.co.uk (and a lot of other websites) won't work as intended without re-enabling javascript. Simply Click Here to quickly fix this issue.

STANDARD RANGE WALL MODEL - VENTAXIA This model is 12".The proven Standard range wall models are designed to fit flush into most double brick walls using the rigid wall liner supplied with the unit. Provision is made within the liner for conduit entry. When installed, only the ivory fascia is visible on the internal wall face. The external...

STANDARD RANGE WALL MODEL - VENTAXIA

This model is 12".

The proven Standard range wall models are designed to fit flush into most double brick walls using the rigid wall liner supplied with the unit. Provision is made within the liner for conduit entry. When installed, only the ivory fascia is visible on the internal wall face. The external weather louvre fits flush to the outside. A shutter is available as an accessory which can be easily fitted within the unit, see below.

On new building work the installation and wiring of the wall liner can be completed prior to the final installation of the unit and controller. Fully shrouded connectors on the fascia automatically connect the wiring to the motor when fitted to the wall liner.

Easy Cleaning

Integrated component design allows all parts to be dismantled for cleaning without the use of specialist tools. The fascia, motor impeller assembly unplugs from the wall sleeve. The external weather louvre is removed into the room for cleaning. All plastic components can be washed.

Range Product Specification

Motor

The motor is purpose-designed. Suitable for running at any angle. Quiet running, enclosed, sealed for life ball bearings.

Supply voltage: 220-240V/1/50Hz.

Suitable for operation in ambient temperatures from -40°C to +40°C.

Fitted with Standard Thermal Overload Protection (S.T.O.P.).

Shutter

Type SD/R. This extract/intake shutter fits inside the Vent-Axia unit and closes against unwanted backdraughts. It can be fitted at the same time as the unit or at a later date if required. Airflow operated for extract use, cord operated lock for intake use.

Unit size

6

7

9

12

Type

S6/WL

S7/WL

S9/WL

S12/WL

Stock Ref. No.

13 15 10A

13 25 10A

13 35 10A

13 45 10A

Amps @ 240V

0.16

0.16

0.24

0.36

Extract Perf MAX m³/h

340

544

856

1767

Watts MAX.

32

34

53

84

dB(A) (med) @ 3m

39

35

43

46

Shutter Type SD/R

23 17 10

23 27 10

23 37 10

23 47 10

Range-master

RVS Surface

W30 01 10

W30 01 10

W30 01 10

W30 01 10

Flush Fitting

W30 01 10

W30 01 10

W30 01 10

W30 01 10

+ 40 01 44

+ 40 01 44

+ 40 01 44

+ 40 01 44

Time Switch Type TTC

W36 13 10

W36 13 10

W36 13 10

W36 13 10

Multi-unit Type MUC

W36 23 10

W36 23 10

W36 23 10

W36 23 10

Range Dimensions

Impeller dia.

150mm

190mm

230mm

300mm

A

279

279

279

279

B

203

279

279

356

C

279

362

362

448

Fixing hole Square

235

311

311

400

Weight

4.1kg

5.7kg

6.7kg

10.1kg

Details

Product Type

Misc

Quick Search:

QS3250

Delivery

Shipping Method

Under £100*

Over £100*

Economy: 4 to 7 Days (Orders under £20 inc VAT)4 to 7 Days (Orders over £20 inc VAT)

£2.99£4.99

FREEFREE

Courier:2 to 4 Days (Interlink or TNT)

£7.99

FREE

Next Day:Next Working Day Delivery+

£24.00

£24.00

* Usually £200+vat+ Order before noon for Next Working Day Delivery for items in stock

Questions and Answers, do you need more information about this product?

Your question will be sent to a member of our team. We'll email you the answer and post it on this page. If your question is about an order you already placed, please use our Contact Form to reach the customer service team.