Quick Details

Packaging & Delivery

Packaging Details

standard exporting package

Delivery Time

ASAP

This type product is special used in high-low pressure protect control of air-conditioning cooling system.When the pressure inside the system is over or below rated safe pressure,the disc in sensor will start move instanly,and this works together with connecting rod and push the swith connector to open or close.When pressure duduce or rise to rated reset point,the disc wil reset accordingly,and the switch also auto reset.

The series technique is as follows:

Ordinal number

Name

The technique request

1

The pressure value sets the scope

3-667PSl / 0.02-4.6Mpa

2

The pressure value business trip scope

1.45-14.5PSl / 0.01-0.1Mpa

3

Touch some form

NC (H) NO (L)

4

Contact capacity

AC240V 3A AC120V 6A

5

Contact resistance

« 50mΩ

6

Insulate the electric resistance

» 100mΩ Connect the line carries with a » 100mΩ

7

The anti-electricity strength

The AC1500V last the 1 min clock and did not broke through and gleam

8

Biggest blow up the pressure

At the « 5000PSl of («34.5Mpa) blows up the pressure under the 1min clock did not burst the phenomenon

9

Air tightness

The 4.8Mpa/ 1 min no leakage

10

Adapt the temperature

The environment temperature -30 ~ +80°C

Lie the quality temperature -50 ~ +120°C

Transaction History of the Supplier

Below is the information about the supplier's transactions conducted via Alibaba.com. If you require further details regarding the transaction data, please contact the supplier directly.