Nominal cross-section area of main conductors, mm2Copper 1,5-16Aluminum 2,5-16

StrandingInsulated cores are laid parallel in one flat.

InsulationPVC- compound (color coded conductor).

Over sheath or protective coveringPVC-compound

The cables are designed for transmission and distribution of electricity in fixed electrical installations on a nominal alternating voltage 0,66, 1 and 3 kV, frequency - 50 Hz. Cables of types VVG-P, AVVG-P are designed for laying single cable lines in cable installations and premises.

Cables of types VVG-P, AVVG-P in a single-conductor modification is designed for use in DC voltage.

The class of fire hazard of the cables is according to GOST 31565 01.8.2.5.4.

Nominal voltage, kV

0,66 или 1

Ambient temperature during cable operation, 0C

from -50 to +50

Minimum bending radius, diameters of cable

10

The cables are laid at temperature (without preheat), 0C not below

- 15

To make an order

You can pre-order the products. After the receipt of your order a specialist of our company will contact you and offer the best delivery conditions.