Confused by furnace wiring

Hello,

I'm confused because my furnace is not wired directly to the 20 amp breaker. The line from the breaker runs through a series of two junction boxes to an old fuse box (see attached photos). From the fuse box, a line runs back up to the junction box directly above, where it is pigtailed to the lines going to the furnace. Itís been this way since I purchased the house 25 years ago. However, because of a remodel, I need to move the junction/fuse boxes. Here are my questions:

Is the fuse necessary? If so, what is the reason? Isnít the fuse redundant because of the 20amp breaker that feeds it?

If itís not necessary, can I simply run a line directly from the breaker and tie it into the furnace wires in a junction box and bypass the fuse altogether?

Thanks for your help!
Tom

Attached Thumbnails

Advertisement

The fuse isn't necessary if both the fuse and breaker are the same value and the wire is sized properly. However, you do need a disconnect at the furnace. What you have now is a fused disconnect. How far is the breaker panel from the furnace?

Perhaps it was just easier to keep it the way it was and/or the disconnect of the original was easier to keep than installing a typical switch?
Shouldn't need two overload protection devices. It will need a disconnect (switch) though. Hard to tell from the picture; but is that 12g THW wire (new stuff)? If 15g, need to upgrade to 12g due to 20 amp breaker.

How many amps is your type S fuse?
"S and T fuses are heavy duty time delay fuses and used for circuits having critical or high motor loads or circuits having motors that cycle on and off often (e.g. a sump pump). "

I've seen fuses in series for the reason that the interrupting current rating of one fuse was much higher than the other, like in the RCA Voltohmyst.

When you compare the clearing time of the fuse to the trip time of the breaker you may get some surprises. I'd leave the fuse in; it's not doing any harm.

Yoyizit,
If you are suggesting the fuse won't blow before the breaker, the breaker will still have to be reset so what is the benefit of the fuse remaining?
He can't eliminate the breaker so the fuse and associated wire connections are nothing but a source of potential connection issues. IMO, there is no benefit to the fuse staying but perhaps I'm missing something?

Yoyizit,
If you are suggesting the fuse won't blow before the breaker, the breaker will still have to be reset so what is the benefit of the fuse remaining?
He can't eliminate the breaker so the fuse and associated wire connections are nothing but a source of potential connection issues. IMO, there is no benefit to the fuse staying but perhaps I'm missing something?

The clearing time vs. current of the type S fuse may be better tailored to protect the furnace than the trip curve of the panel breaker.

Which device clears first depends on the I squared T curve of each and the current drawn. Comparing time vs. current graphs may show this idea more clearly.

I'm reluctant to remove something unless I'm very clear as to its function in the circuit, but it's possible this fuse is redundant or useless or may cause unnecessary problems.

If it does do a better job of protecting the furnace and it's removed it may be a long time before the effects are seen.