Patented 0-2 volt output split-core current sensors
promote enhanced safety and accurate remote mounting of current sensors up
to 500 feet from the meter without power interruption. (Optional solid-core
current sensors available in 100 & 200 Amp.)

Current sensor installation diagnostics indicator on
display.

Revenue Grade Accuracy.

RS-485 Communications capability supports the
following connection configurations (or combinations not to exceed 52
devices per channel):
- Up to 52 Class 3000 meters and/or IDR-8 interval data recorders
- Up to 26 IDR-16 interval data recorders (IDR-16 counts as two devices)
Cabling can be either daisy-chain or star configuration, 4-conductor, 24-26
AWG, up to 4,000 cable feet total per channel.