Have had three AB power flex 70 frame 8 drives fail losing bus caps and transistors. with no trip alarms over/under bus voltage, over current. Have monitored line voltage for six months finding no problems. Has anyone else had similar problems

if you are blowing caps the voltage rating of the drive circuit is being exceeded.

you have to check the voltage on the caps and the incoming ac voltage againts the respective ratings,

with a lot of equipment being manufactured who knows where, you run into nominal voltage ratings that may not be compatable with your area,

case in point we had a system rated at 3ph 440 vac blowing caps left and right,

that particular unit was made to EU 400 vac ratings, we and were assured by the factory that 440 vac was okay, but the power company had the transformer taps set at 500 vac!

Only the high dollar model could handle that, our units could not, the factory seemed to be living on another planet, they had no clue, but replaced all units as they had performed the installation and checkout!

It is clear that the DC-Link is being overloaded (overvoltage). Does the application work in regenerative mode? In other words, does the motor brake the load often? If yes, you can try extend the deceleration ramp or install a brake resistor to make the DC-Link voltage lower when stopping the application.

There is no "Frame 8" in a PowerFlex 70 drive, although there is a Frame B.

Generally, this sort of issue is the result of one of two issues:

1) Extreme line transients, sometimes too fast for the drive Over Voltage protection to respond, in which case it might be too fast for an inexpensive meter to detect as well. You would need a feast sampling recording meter, like a Fluke Scope meter or a Dranetz meter to see it.

2) You have a line contactor ahead of the drive and are opening the contactor every time you shut down. All drives have a pre-charge circuit, in this drive is is a resistor that is shorted out by a contact after the bus charges. By constantly cycling power to the drive, you burn out that resistor, after which the caps and transistors fail in short order.

Users of this site are benefiting from open source technologies,
including Linux,
PHP,
MySQL and
Apache. Be happy.
This page served by Yesod4 in the beautiful
Blackstone Valley of Massachusetts, the home of the American Industrial
Revolution.

FortuneHe who wonders discovers that this in itself is wonder.
-- M. C. Escher

You have clicked on the "?" button for search help. To search the
site, enter your search terms in the box labeled "search the site"
and hit Enter.

Some tips for better search results...

Precede each search term with a "+", as follows:

+Modbus +TCP

Otherwise, any post with either term will match.

Use double quotes around phrases, as follows:

+"Allen Bradley" +ethernet

Otherwise, posts containing these words in separate locations will match.

To exclude a word, precede it with a "-", as follows:

+Modbus -Plus

This will return only posts containing "Modbus" but NOT containing
"Plus".

Note that common words (and, that, etc.) and words shorter than 2 characters
are automatically excluded from searches.

Your subscription request is being
processed.

You must be a Control.com member
to subscribe to threads. Please log in and try again.

If you're not already a member, consider joining. It's free,
and you can customize the content you view, as well as being
able to subscribe to threads and topics, getting new posts
delivered to your email as they appear.

Username

Password

Remember me on this computer

Select the categories for which you would like to
see messages displayed...

Applications

Application Questions and Problems

Automation Business

The Business of Automation and Control

Communications

Communications systems and equipment.

Engineering

Engineering and workplace issues.

HMI

Human-Machine Interface and SCADA.

Information

Information resources, documentation.

Languages

Programming languages.

Motion Control

Motion control, servos, steppers, etc.

Networking

Local and wide area networking in factory automation.

Open Control

Open interfaces, software and hardware

PCs in Automation

Computers in manufacturing; also hardware discussion.

PLCs

PLCs and related questions.

Power Generation

Power generation equipment control.

Process Control

Continuous process industries, DCS questions.

Sensors

Sensor technologies.

Software in Automation

Software, including programming, OS issues, etc.

You must be a Control.com member
to vote on a post. Please log in and try again.

If you're not already a member, consider joining. It's free,
and you can customize the content you view, as well as being
able to subscribe to threads and topics, getting new posts
delivered to your email as they appear.