Electrolysis of brine type sodium hypochlorite generator is an
electro chemical reaction process, the only raw material are salt
and water, no other additional ingredients. The design of generator
system has the character of energy saving, cost saving, high
reliability, long service life, simple operation etc...

Electrolytic cell: Tube type electrolytic, use the organic glass
pipe fabrication and high corrosion resistance to the internal
electrode plate between the anode and cathode materials which were
isolated by PVDF, with the feature of full transparency, corrosion
resistance, high stability, long service life;

Electrode plate: Tube-plate electrode, electrode cathode and anode
substrate are all made of pure titanium TA1 material in the
electrolysis process, the cathode is protected, and the anode is
affected by the loss, so the anode surface must do coating
protection, CNJS generator electrode anode surface by treatment of
nanotechnology, ruthenium, iridium oxide particle fineness reaches
20 nm the coating is 25 times more than the coating and the
thickness can up to 20 microns which can ensure the service life of
the electrode long-term and stable.

The temperature control switch: between the plate electrode and
power supply contact with a temperature control switch, when the
machine starts running, the control center began testing the
temperature control switch, if the temperature control switch
setting error data then the machine stops working, a temperature
alarm signal, at the same time a corresponding alarm signal send to
the PLC control the machine is in standby state, to ensure safe and
reliable operation of the machine;

Manual operation panel: touch panel and manual operation panel LCD
touch screen in synchronization, if there is something wrong with
the touch screen , through the operation panel can be operate the
machine, the panel can switch from remote to local , main dosing
pump switch with standby pump etc.;

Online salinity monitor: The dilution ratio of dilute brine for
online monitoring and display, the instrument can be set high
concentration limit and low limit, when more than the set range,
the system send alarm and stop the machine running