Home Health Care (UL 1637) Listed Installations
Requirements described under UL985 plus:
• A minimum of two (2) keypads are required with one keypad powered from .+VKP. and one keypad powered from .+VAUX..

Commercial - Central Station (UL 1610), Police Station Connected (UL 365),Local Burglar Alarm (UL 609)
Listed Installations
Requirements described under UL1023 plus:
• The Alarm Cutoff timer must be set to 00900 sec. (15 min.) or greater.
• UL Commercial Burg requires 4 hours of standby power. Limit combined continuous current draw from terminals +SAUX,
+VAUX, +VKP, and connector J16 to 450 mA max. and use one (1) 8 Ah battery.
• An acceptable Commercial enclosure must be used (see Listed Enclosures below)
• Tamper Switch(s) must be installed on the enclosure and connected to a 24 hour Burg Tamper defined Zone.
• All Keypads need to be installed within the protected area (they have no tamper)
• DO NOT USE an A B Attack Cabinet for the external sounder
• A Whenever/And/Then rule should be written (using ElkRP software) to enable the Output 2 Siren to .chirp.
upon closing ringback.

UL Canada Listed Installations (ULC S304 and ULC S303)
Requirements described under UL1023, 1610 plus:
• Entry Delay must be set to 60 seconds or less.
• Exit Delay must be set to 120 seconds or less.
• The Alarm Cutoff timer must be set to 00900 sec. (15 min.) or greater.
• UL Canada Commercial Burg requires 24 hours of standby power. Limit combined continuous current draw from terminals
+SAUX, +VAUX, +VKP, and connector J16 is 450 mA max. and use two (2) 8 Ah batteries in parallel.
• Zone Expanders must be in an acceptable Commercial enclosure (see Listed Enclosures below)

ELK is a leading designer and manufacturer of customized security, automation, energy management and convenience solutions. We stand behind the products we sell with industry leading customer service, technical support and product warranties.