Cased Axial Fans

Cased Axial Fans – External Rotor Motor

A comprehensive range of high efficiency and high performance cased axial fans. Versatile and suitable for a wide range of applications. Short case axial fans are general purpose fans designed to move large volumes of air in low pressure systems, this often means systems with a short duct run.

Features and Construction

High efficiency cased axial fans are used wherever large air volumes must be conveyed against low to medium pressure and benefit from low installation depths. Alongside plated axial fans, cased axial fans are versatile as they can be mounted in any position and suitable for many applications including ventilating restaurants, gymnasiums, conference rooms, workshops, ware-houses, swimming pools and greenhouses. High efficiency axial fans with double flange ring are used in duct systems for air conditioning, cooling and drying applications.

Casing

The casings of our high efficiency cased axial fans are made from galvanised sheet steel and are plastic coated.

Impellers

Our EQ and DQ range of axial fans have aerodynamically profiled blades (sizes 200 to 300 made from galvanised and lacquered sheet steel; from size 315 to 630-6 made of plastic and sizes 630-4 up to 1000 made of aluminium). The blades are made of galvanised sheet metal, and are mounted directly to the rotor of the external rotor motor and are balanced dynamically together with the rotor according to quality level G2.5 to DIN1940.

Electrical Connection

The motors are fitted with an outgoing cable. The electrical connection can be made via an IP44 terminal box, which is supplied loose.

Fan Types

To request a quotation for any of our cased axial fans, simply find the product reference below and submit a request a quote direct to our engineers who will endeavour to get back to you within 24 hours.

Model / Product Code

Type

Product Article Number

Phase (Ph)

Impeller Diameter (mm)

Rated Voltage (V)

Motor Power Consumption (kW)

Rated Current (A)

Fan Speed

Capacitor

Max Temp (C)

Request a Quote

ER 200-2

Cased Axial Fan

E10-20001 or E00-20001

1

200

230

0.07

0.30

2550min-1

2uF

70

ER 200-4

Cased Axial Fan

E00-20000 or E00-20000

1

200

230

0.033

0.150

1410min-1

1.5uF

70

ER 250-2

Cased Axial Fan

E10-25001 or E00-25001

1

250

230

0.14

0.60

2600min-1

4uF

60

ER 250-4

Cased Axial Fan

E10-25000 or E00-25000

1

250

230

0.06

0.27

1270min-1

1.5uF

70

ER 300-2

Cased Axial Fan

E10-30001 or E00-30001

1

300

230

0.22

0.95

2500min-1

6uF

60

ER 300-4

Cased Axial Fan

E10-30000 or E00-30000

1

300

230

0.10

0.44

1270

3uF

55

ER 315-2

Cased Axial Fan

E10-31510 or E00-31510

1

315

230

0.69

3.0

2610min-1

14uF

50

DR 315-2

Cased Axial Fan

E10-31560 or E00-31560

3

315

400

0.57

0.95

2460min-1

-

60

ER 315-4

Cased Axial Fan

E10-31505 or E00-31505

1

315

230

0.12

0.55

1380min-1

3uF

60

DR 315-4

Cased Axial Fan

E10-31555 or E00-31555

3

315

400

0.12

0.33

1385min-1

-

60

ER 350-2

Cased Axial Fan

E10-35010 or E00-35010

1

350

230

0.98

4.3

2670min-1

20uF

40

DR 350-2

Cased Axial Fan

E10-35060 or E00-35060

3

350

400

0.86

1.62

2680min-1

-

55

ER 350-4

Cased Axial Fan

E10-35005 or E00-35009

1

350

230

0.15

0.65

1300min-1

3uF

65

DR 350-4

Cased Axial Fan

E10-35055 or E00-35055

3

350

400

0.15

0.35

1330min-1

-

65

ER 400-4

Cased Axial Fan

E10-4005 or E00-40005

1

400

230

0.21

0.95

1340min-1

5uF

60

DR 400-4

Cased Axial Fan

E10-40055 or E00-40055

3

400

400

0.2

0.42

1340

-

65

ER 400-6

Cased Axial Fan

E10-40004 or E00-40004

1

400

230

0.10

0.46

885min-1

2uF

55

ER 450-4

Cased Axial Fan

E10-45005 or E00-45005

1

450

230

0.33

1.5

1360

8uF

55

DR 450-4

Cased Axial Fan

E10-45055 or E00-45055

3

450

400

0.33

0.75

1390min-1

-

60

ER 450-6

Cased Axial Fan

E10-45007 or E00-45057

1

450

230

0.14

0.78

930min-1

4uF

70

DR 450-6

Cased Axial Fan

E10-45057 or E00-45057

3

450

400

0.13

0.25

900min-1

-

60

ER 500-4

Cased Axial Fan

E10-50005 or E00-50005

1

500

230

0.49

2.3

1375min-1

12uF

50

DR 500-4

Cased Axial Fan

E10-50055 or E00-50055

3

500

400

0.41

1.0

1370

-

60

ER 500-6

Cased Axial Fan

E10-50007 or E00-50007

1

500

230

0.2

0.88

935min-1

5uF

60

DR 560-4

Cased Axial Fan

E10-56053 or E00-56053

3

560

400

0.81

1.7

1240min-1

-

50

ER 560-4

Cased Axial Fan

E10-56008 or E00-56008

1

560

230

0.83

3.80

1200min-1

16uF

40

ER 560-6

Cased Axial Fan

E10-56001 or E00-56001

1

560

230

0.38

1.8

920min-1

10uF

40

DR 560-6

Cased Axial Fan

E10-56052 or E00-56052

3

560

400

0.35

0.90

920min-1

-

55

DR 630-4

Cased Axial Fan

E10-63080 or E00-63080

3

630

400

2.15

3.9

1305min-1

-

50

ER 630-6

Cased Axial Fan

E10-63001 or E00-63001

1

630

230

0.53

2.6

9110min-1

12uF

40

DR 630-6

Cased Axial Fan

E10-63052 or E00-63052

3

630

400

0.5

1.15

920min-1

-

55

DR 710-6

Cased Axial Fan

E10-71080 or E00-71080

3

710

400

0.87

1.8

835min-1

-

70

DR 710-8

Cased Axial Fan

E10-71090 or E00-71090

3

710

400

0.49

1.1

620min-1

-

70

DR 800-6

Cased Axial Fan

E10-80080 or E00-80080

3

800

400

1.3

2.6

845min-1

-

70

DR 800-8

Cased Axial Fan

E10-80090 or E00-80090

3

800

400

0.75

1.85

665min-1

-

70

DR 1000-8

Cased Axial Fan

E10-10050 or E00-10050

3

1000

400

2.15

4.40

675min-1

-

45

DR 1000-12

Cased Axial Fan

E10-10000 or E00-10000

3

1000

400

0.71

2.1

445min-1

-

80

Request a Quote

Notice: JavaScript is required for this content.

Typical applications are general ventilation and extraction, fume extraction, ventilation for cooling; within factories, workshops, warehouses, and other commercial premises. For more information on our supplier partner Rosenberg, visit our supplier page. Here you can utilise fan selection software. Contact us for more information or advice on using RoVent.