…allocates 480V AC 3P power to four 480V AC 3P receptacles. This 200-amp unit is supported by a 20` 2/0 3/4 SOOW line-in cord with a 200-amp APL20468 line-in cord cap for connection to a 480V AC power source. The unit provides operators the ability to safely tap into and distribute 480V AC power from…

…KVA transformer converts 240V to 480V three phase and passes the current to the secondary panel. The secondary side of the transformer feeds two NEMA 3R 60-amp, 480V three phase disconnects, which contains three 50-amp time delay fuses each, protecting one 480V meltric Dr50a 31-34247-K04 connector…

…cord brings 480V three phase power to the NEMA 3R 30-amp, 480V three phase primary disconnect, which contains three 30-amp time delay fuses protecting one 30-amp, 480V ADR3034 receptacle and passes 480V single phase through to the second primary disconnect. The NEMA 3R 60-amp, 480V single phase…

…480V equipment to six 460RS2W 480V receptacles. On the secondary side, operators connect to four 2-Pole twist-lock receptacles for their 208Y equipment and twenty quad GFCI receptacles for 120V equipment. Operation: A customer provided cord brings 480V three phase power to the NEMA 3R 200-amp, 480V…

…cord brings 480V three phase power to the NEMA 3R 400-amp, 480V three phase main panel, which contains one 300-amp breaker and two 100-amp breakers protecting two 4100R7W receptacles and passes 480V three phase through to the transformer. The NEMA 3R 225 KVA transformer converts 480V three phase…

…of 10/3 SOOW cord (blunt cut). This whip is designed to be attached to welders or other equipment that will work with the feed-through 480 volt welding receptacles on our power distribution systems. Alternatively, this whip can be used to power equipment from an Appleton 3034 480v 30 amp receptacle.

…6/4 SOOW cord (blunt cut). This whip is designed to be attached to welders or other equipment that will work with the feed-through 480 volt welding receptacles on our power distribution systems. Alternatively, this whip can be used to power equipment from an Appleton ADR6034 480v 60 amp receptacle.

…provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 400-amp main lug only panel. The main lug only panel contains two 150-amp 3-pole 480V and five 20-amp 3-pole 480V breakers. Enclosure Design: This power distribution…

…A customer provided cord brings 480V three phase power to the NEMA 3R 400-amp, 600V three phase primary disconnect, which contains three 400-amp time delay fuses, and passes 480V three phase through to the transformer. The NEMA 3R 300 KVA transformer converts 480V three phase power to 208Y/120V…

…MPD-480-25K-100MB-24X20.120-DC-W Temporary Power Distribution System converts 480V to 120/240 Delta/Delta electrical current. This power distribution system provides operators the ability to safely tap into common 480V and distribute 120/240 Delta/Delta to their equipment. This portable substation…

…cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 600-amp main lug only panel. The main lug only panel contains one 400-amp 3-pole, one 200-amp 3-pole and one 100-amp 3-pole 480V branch breakers. Enclosure Design: This power…

…of operator provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through an 800-amp main lug only panel. The main lug only panel contains five 200-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution panel…

…of operator provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 600-amp main lug only panel. The main lug only panel contains four 200-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution panel…

…of operator provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through an 800-amp main lug only panel. The main lug only panel contains two 400-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution panel…

…provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through an 800-amp main circuit breaker panel. The main circuit breaker panel contains five 200-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution…

…designed to operate with 480V three phase voltage and contains 30 circuits. Power distribution for this panel runs 480V through a 600-amp main circuit breaker panel. The main circuit breaker panel contains one 200-amp 3-pole 480V, one 70-amp 3-pole 480V and three 50-amp 3-pole 480V branch breakers.…

…provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 225-amp main circuit breaker panel. The main circuit breaker panel contains two 100-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution…

…operator provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 1,200-amp main lug only panel. The main lug only panel contains seven 200-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution panel…

…provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 125-amp main circuit breaker panel. The main circuit breaker panel contains two 60-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution…

…operator provided cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through a 1,200-amp main lug only panel. The NEMA 3R main lug only panel contains four 400-amp 3-pole 480V branch breakers. Enclosure Design: This power distribution…

…cables. The panel is designed to operate with 480V three phase voltage. Power distribution for this panel runs 480V through an 800-amp main circuit breaker panel. The main circuit breaker panel contains one 250-amp 3-pole 480V and four 200-amp 3-pole 480V branch breakers. Enclosure Design: This…

…provided cord brings 480V three phase power to the NEMA 3R 100-amp primary main lug panel, which contains one 20-amp, 480V breaker protecting one L16-20R 480V receptacle, and passes 480V three phase through to the transformer. The NEMA 3R 15 KVA transformer converts 480V three phase power to…

…provided cord brings 480V three phase power to the NEMA 3R 100-amp primary main lug panel, which contains one 20-amp 480V breaker protecting one L16-20R 480V receptacle, and passes 480V three phase through to the transformer. The NEMA 3R 25 KVA transformer converts 480V three phase power to 120/240V…

…A customer provided cord brings 480V three phase power to the NEMA 3R 40-amp primary disconnect, which contains one L16-20C 480V receptacle and passes 480V through to the second NEMA 3R 60-amp primary disconnect. The second disconnect on the primary side passes 480V through to the transformer. The…

…A customer provided cord brings 480V three phase power to the NEMA 3R 40-amp primary disconnect, which contains one L16-20C 480V connector and passes 480V through to the second NEMA 3R 60-amp primary disconnect. The second disconnect on the primary side passes 480V through to the transformer. The…

…480V female receptacles in a pass through configuration for powering 480V equipment. On the primary and secondary sides, breakers are available for operators to complete power connections. Operation: A 10-foot #2 Type W line-in cord with a 150-amp, 480V Class I, Division 2 male plug brings in 480V…

…cord brings 480V three phase power to the NEMA 3R 600-amp, 480V three phase main circuit breaker panel, which contains six 60-amp breakers protecing six 60-amp, 480V AR642 receptacles, and passes power through to the transformer. The NEMA 3R 112.5 KVA transformer converts 480V to 240D/208-120V…