Our products

451-TYPE CYLINDER PRESSURE REGULATOR

Cylinder pressure regulator with two pressure gauges used on cylinder outlets to reduce the pressure to that of the line or equipment; max inlet pressure 200 bar, outlet pressure can be regulated to 12 bar.The gas specific inlet is fitted with an Ø 8 mm hose connector on the outlet.Max. nitrogen capacity at 12 bar 90 Nm³/h, 1500 Nl/min.

451-TYPE CYLINDER PISTON PRESSURE REGULATOR

Cylinder pressure regulator with two pressure gauges used on cylinder outlets to reduce the pressure to that of the line or equipment; max inlet pressure 200 bar, outlet pressure can be regulated to 100 bar.Gas specific inlet connection.The outlet is fitted with an Ø 8 mm hose connector.Max. nitrogen capacity at 100 bar 500 Nm³/h, 8333 Nl/min.

GIGANT/R AUTOMATIC CONTROL MODULE

Single stage control panel for medical gases, high flow rate and automatic cange over: composed of two pressure reducers model GIGANT / R with CW614N brass body and aluminum cap, automatic inverter, two High Pressure shut-off valves and two Low Pressure shut off valves for maintenance, stainless steel box.The inlet connection is specific for the gas used, the outlet is fitted with a Ø 22 mm weld-on pipe connector. Its maximum nitrogen capacity at 9 bar outlet pressure is 150 Nm³/h, 2500 Nl/min.The two pressure regulator High Pressure gauges have electrical contacts, are pre-calibrated with a 15 bar alarm threshold and can be connected to an alarm control unit to signal manifold empty.The control module is protected from atmospheric agents by a satin-finished AISI 316 steel box with transparent PLEXIGLAS windows for checking the pressure gauges and an optional alarm if installed.To facilitate wall mounting, all the components are installed on a satin-finish AISI 316 steel plate, which includes also the support for housing the control module alarm.

GIGANT/R THIRD SOURCE MODULE

Control module for medical gases, consisting of one GIGANT/R model regulator, two pressure gauges with CW614N brass body, aluminum cap and a High Pressure shut-off valve.The inlet connection is specific for the gas used, the outlet is fitted with a Ø 22 mm weld-on pipe connector.Its maximum nitrogen capacity at 7.5 bar outlet pressure is 150 Nm³/h, 2500 Nl/min.The pressure regulator High Pressure gauge has electrical contacts, and is pre-calibrated with a 100 bar alarm threshold (30 for NO2 and CO2) and can be connected to an alarm control unit to signal source empty.The module is protected from atmospheric agents by a satin-finish AISI 316 stainless steel box with transparent PLEXIGLAS windows for checking the pressure gauges.For easy wall mounting, all components are installed on a satin-finish AISI 316 stainless steel plate.

451-TYPE CYLINDER PRESSURE REGULATOR

Pressure regulator for cylinders, suitable for medical gases, equipped with dual pressure gauge to show high and low pressure, used on outlet of cylinders to reduce the pressure down to that of the line or equipment.Maximum inlet pressure is 200 bar, the outlet pressure is adjustable up to 12 bar.The gas inlet connection is specific to the gas type, the outlet is fitted with an Ø 8 hose connector.Its maximum nitrogen capacity at 12 bar outlet pressure is 90 Nm³/h, 1500 Nl/min.

EURO/A CYLINDER PRESSURE REGULATOR

Pressure regulator for cylinders, suitable for medical gases, equipped with dual pressure gauge to show high and low pressure, used on outlet of cylinders to reduce the pressure down to that of the line or equipment.Maximum inlet pressure is 200 bar, the outlet pressure is adjustable up to 12 bar.The gas inlet connection is specific to the gas type, the outlet is fitted with an Ø 8 hose connector.Its maximum nitrogen capacity at 12 bar outlet pressure is 60 Nm ³/h, 1000 Nl/min.

SEMIAUTOMATIC HF MANIFOLD

Manifold, suitable for use with pure gases, with automatic switching and manual reset using the lever on the pressure regulator to restore priority of use of the source. If one of the two sources is discharged, the system is fed automatically from the other source.The module includes two HF-type single-pressure gauge pressure regulators made of CW614N chemically nickel-plated brass, one pressure gauge to show the line pressure, two high pressure shut-off valves and two bleed valves.Inlet connection is threaded G1/4" M R, outlet connection is G1/4" F R.Its maximum capacity at 10 bar outlet pressure is 24 Nm³/h, 400 Nl/min.On request the pressure gauge at the pressure regulator's inlet can have electrical contacts to be connected to a central alarm unit to signal if the manifold is empty.For easy wall mounting, all components are installed on an anodized aluminum plate.A helium leak test at 10-4 mbar l/s can be carried out at the customer's request.

HF SINGLE MANIFOLD

Manifold for use of pure gases, consisting of a dual HF-type pressure gauge made of chemically nickel-plated CW614N brass, one high pressure shut-off valve and a bleed valve.Inlet connection is threaded G1/4" M R, outlet connection is G1/4" F R.Its maximum capacity at 10 bar outlet pressure is 24 Nm³/h, 400 Nl/min.On request the high pressure gauge can have electrical contacts to be connected to a central alarm unit to signal if the manifold is empty.For easy wall mounting, all components are installed on an anodized aluminum plate.A helium leak test at 10-4 mbar l/s can be carried out at the customer's request.

About us

Company details

Behringer today

The know-how acquired over many years of experience enables Behringer to always provide the most cost effective solutions, based on advanced technology, top quality and excellent performance. The company operates with a growing international focus in the following sectors: medical gas equipment, welding devices, devices for pure gases, gas equipment for food use and devices for torching. Of note, our newly formed Service department dedicated to medical installations.

Quality

Behringer's products are distinguished by quality and robustness. Each device is tested individually: the strict controls of our quality system ensure a level of reliability among the best in the industry. All Behringer products are designed and manufactured entirely in Italy, in line with UNI EN ISO 9001 quality management system certification.