WPT Series chillers combine one or more refrigeration circuits to chill fluid. A separate reservoir and pumping system is required to circulate chilled fluid to the use points.

Water-cooled chillers require a secondary water source (typically cooling tower water) to dissipate the heat from the refrigeration system.

PRODUCT PRICING

SPECIFICATIONS

Model: CCC-150WPT (1)

Refrigerant Zones

Quantity: : 3.0

Compressor

Quantity : 6.0

HP : 25.0

Type : Scroll

(2) Total Capacity : 150.0

Refrigerant

Type : R-410A

Water-Cooled Condenser

(3) City Water : 225.0 GPM

(4) Tower Water : 450.0 GPM

Connection Sizes

To Process : 6.0"

From Process : 6.0"

Full Load Amperage (5)

230/3/60 : 612.0

460/3/60 : 306.0

575/3/60 : 245.0

Dimensions (7)

Height : 85.0"

Width : 73.0"

Depth : 130.0"

Weight (8)

Shipping : 3,900 lbs

Specification Notes:

1. Since product innovation and improvement is our constant goal, all features and specifications are subject to change without notice or liability. Selection of certain optional features may change listed specifications.

3. Flow rate (GPM) is based on 60°F city water source with a clean condenser.

4. Flow rate (GPM) is based on 85°F tower water source with a clean condenser.

5. Full load amps are higher than run load amps and must be used for sizing disconnects and supply wiring. Not for construction. Consult factory for power requirements of unit as configured and on selected options.