The Sigma CP-R Repeater is compatible with all Sigma CP Fire Detection panels which have operating software version V2.0 or above.Repeaters are available with 2, 4 or 8 zones.24V DC versions require an additional two cores for power either from the Fire Detection panel or from another 24V DC source.A mixture of Repeaters, Ancillary boards or Sounder Boards up to a maximum of 7 of each type can be connected to a Fire Detection panel and each is allocated an address from 1 to 7 using a binary coded DIL switch. The total length of the data cable from the main panel to the last repeater must not exceed 1200 metres.

FEATURES & BENEFITS

- Two wire serial connection- Up to 7 panels per system- Full control over main panel- Volt free fire and fault contact outputs