PRODUCTS

NM-B SuperSlick Elite®

Type NM-B (Non-metallic sheathed cable) has a broad range of usage as defined in Article 334 of the National Electrical Code (NEC). Type NM-B cable is commonly used for residential fixtures, switches, and loads rated for at least 90°C. Type NM-B ampacity limitation shall be in accordance with the 60°C conductor temperature rating, as specified in the National Electrical Code. Type NM-B is rated for 600 volts for both exposed and concealed work in normally dry locations. Type NM-B may be installed or fished in air voids and joints and in masonry block or tile walls where such walls are not exposed to, nor subject to, excessive moisture or dampness.

UF-B

Type UF-B (Underground Feeder Cable) has a broad range of usage as defined in Article 340 of the National Electrical Code (NEC). Type UF-B may be installed as interior wiring in wet, dry, or corrosive locations at temperatures not to exceed 90°C (with ampacity limited to that for 60°C conductors) as specified by the National Electrical Code. Type UF-B may be used where exposed to direct rays of the sun or underground, including direct burial. Type UF-B may also be used in applications permitted for Type NM-C construction as specified in Article 334.10 B of the NEC. Maximum voltage rating for UF-B is 600 volts.

SE-STYLE U 600V

For above ground electrical service use from the electric utility power service point to the meter or service entrance panel. Under special conditions as permitted, the NEC Type SE Style U can be used for interior wiring as branch circuits to ranges, ovens, cooking units, or clothes dryers. Type SE Style U is manufactured in accordance with Article 338 of the NEC and also the requirements of Underwriters Laboratories Standard 854 and is approved for installation in accordance with Article 230 of the NEC and has a rating of 600 volts.

SE-STYLE R 600V

For above ground electrical service use from the electric utility power service point to the meter or service entrance panel. Under special conditions as permitted, the NEC Type SE Style R can be used for interior wiring as branch circuit to ranges, ovens, cooking units, or clothes dryers. Type SE Style R is manufactured in accordance with Article 338 of the NEC and the requirements of Underwriters Laboratories Standard 854 and is approved for installation in accordance with Article 230 of the NEC and has a rating of 600 volts.