DiBiase Heating and Cooling Company

Rated 4.9 out of 344 reviews

CALL NOW: 610-873-1244

Your Comfort is Our #1 Priority!

Haverford PA Heating Air Conditioning Service Repair

2018-02-15T17:38:17+00:00

DiBiase Heating & Cooling Company proudly serves our neighbors in Haverford, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience. We do this by providing the fastest services from the most qualified technicians in the Haverford, PA area. See what your neighbors are saying about our unshakable customer-first service!

Joseph D.

Visually inspected ductwork in 2nd floor closet and inspected basement for humidity concerns. Ductwork in closet was insulated well. Basement wall does show signs of moisture that should be further investigating by water proofing company.

Near Ivy Ln, Haverford, PA19041

120 days ago

Joseph D.

Biological growth present above light fixture in closet. Attempted to remove hatch to expose attic but could not get hatch down, it was sealed with sparkle. Attempted to view from behind in attic space. No indicators of mold present. Growth only evident above light fixture. Recommend having electrician remove light and seal any penetrations coming through ceiling and clean area while light is removed.

Near Ivy Ln, Haverford, PA19041

146 days ago

Joseph D.

Inspected air handlers and checked air filters on all units. All filters were ok. Serviced the 3 humidifiers in the basement and replaced water panels. Turned humidifiers on for season and tested operation. Checked dehumidifier settings and inspected air filter for dehumidifier.

Near Ivy Ln, Haverford, PA19041

215 days ago

Joseph D.

Found water on floor on arrival coming from overflowing condensate pump. Found GFCI tripped and causing pump not to operate. Reset GFCI and pump ran but GFCI tripped again. INstalled new condensate pump and interlocked pump to break 24 v power source to board if pump stops working. Tested pump operation and had vacuum plugged into GFCI to vacuum up water and GFCI never tripped again. Tested unit and pump operation. If GFCI trips again replace GFCI. Vacuumed and cleaned up pools of water.

Near Ivy Ln, Haverford, PA19041

320 days ago

Christopher B.

Service call that the Air Conditioning was not working properly. Upon arriving, found Thermostat was set to 63 Degrees and the Temperature within the home was 77 Degrees. Temperature differential was at 10 Degrees. After troubleshooting system, found Compressor was completely frozen and the Indoor Coil was frozen. Defrosted both the Indoor Coil and the Compressor. Put system back in operation and tested Refrigerant. System was low on refrigerant which was causing it to freeze. Added 3lbs of 410-A Refrigerant to system. Monitored system, and charged unit using Superheat Guidelines. Upon completion temperature Split was 18 Degrees. Replaced the 20x20x1 Air Filter. Set Thermostat to 72 Degrees.Performed a quick leak search using the UV Light, and was unable to find a source of the leak at this time. Due to no one being home at this time, the Office will follow up for payment.

Near College Ave, Haverford, PA19041

328 days ago

Joseph D.

Performed ac tune up on 4 systems. Replaced filters on all units in basement. Replaced 2 capacitors on outdoor units.

Near Ivy Ln, Haverford, PA19041

363 days ago

Christopher B.

Performed Precision Heat Tune Up on system. Replaced 20x20x1 Air Filter. Found Blower Compartment and Blower Motor was very dirty and dusty. While testing system, 7.5 Mfd Blower Capacitor was testing below the recommended rating at 6.7 Mfd. Replaced Blower Capacitor and tested operation. Visual inspection of the Hat Exchanger shows that rust is forming. This could compromise the integrity of the Heat Exchanger over time. Performed Smoke Test to check the Heat Exchanger, Smoke Test passed. Tested Combustion Levels of Furnace.Was informed that the Daughters Bedroom and the Sons Bedroom were colder than the other rooms upstairs. Daughters bedroom only has one register. The sons bedroom has two vents, but one of the vents was closed. Need to keep both registers open in the Sons bedroom. Recommend Air Balancing of the system and adjustment of the registers. If Air Balacing and Adjustment of the registers does not work, the next possible solution would be a Duct Booster.Due to age and

Near College Ave, Haverford, PA19041

497 days ago

Joseph D.

Cleaning Of the condensate pump reservoir is only one step in our preventive maintenance procedures.

Near Booth Ln, Haverford, PA19041

680 days ago

Joseph D.

Injecting dye into a Goodman air conditioner to find the refrigerant leak for a homeowner in Haverford PA

Near College Ave, Haverford, PA19041

702 days ago

Joseph D.

Performing air conditioning maintenance on 4 Carrier air conditioning systems in Haverford PA