Related Links

N-Series TeraFrame® Gen 3 Network Cabinet

Highly flexible frame and ducting provides a universal solution to meet the unique thermal and cable management requirements for network switching equipment. The internal duct can be configured to support side airflow or front to rear switch airflow patterns. Additionally, the duct is designed to simultaneously support equipment of different sizes.

Its unique frame design allows you to mount various sizes and models of switches, whether Cisco, Juniper or other, in the same cabinet. A highly flexible side intake duct can be adjusted onsite to accommodate and manage the airflow regardless of switch style, providing complete separation of hot and cold air within
the cabinet to expand your data center containment strategy to your network
infrastructure. It is designed to be
compatible with Aisle Containment or on a per cabinet basis with a Vertical
Exhaust Duct.

Order pre-configured for front-to-rear, front-to-top, side-to-rear or side-to-top airflow

Vertical Exhaust Duct option provides side-to-top airflow

Includes large cable entry ports on the top panel, T-shaped cable guides on the front mounting rails and a front-to-rear cable manager to organize cables; vertical cable managers are available as accessories

Easy access to cables and equipment with removable doors, top panel and side panels

Includes T-shaped cable guides with openings that align with each U on the rack to divide and organize cable