Nicholas L.

Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiency was found on order 13945672
- One cylinder was found to be "flat" and in need of maintenance to restore pressure
- 5 additional cylinders have now come due for 6yr service to meet compliance
- 5 cylinder will be due for the 6yr service in 2019. Included in this proposal to have cylinders due at same time and to save cost of second trip next year.
- Due to 11 cylinders needing to be serviced this proposal may be scheduled over 2 trips
**- All (96) nozzle caps should be replaced - price not included in proposal per client request **
- Electrician needed to review credit card machine connections as this shuts down when suppression system is tested. 8hrs of troubleshooting/service included in proposal. If fix is over labor and material requested an additional proposal will be provided. Removed from proposal 10-24-18 per client