Inventory At Nearby Branches

Loading...

Description

System Includes:One RAWL-090CAZ Classic Series® Condenser

CABINET-Galvanized steel with powdercoat paint finish. The powder coat paint finish is high gloss, durable and capable of withstanding a 1000-HR salt spray test per ASTM B117. The unit is of the frame and panel type of construction which allows all access panels to be opened or removed without affecting the structural strength of the unit. Fastening screws are also of the 1000-HR type. Stamped louver panels offer 100% protection for the condenser coil.

BASE PAN-Galvanized steel with powdercoat paint finish.

SERVICE ACCESS-Control box with separation between line and control voltages, as well as compressor and other refrigerant controls are accessible through removable panel without affecting normal operation of unit.

FAN MOTOR-Condenser fan motor(s) are mounted on removable top panel(s) which bring the motor(s) out to you and expose entire condenser coil for cleaning.

COMPRESSOR-The Scroll Compressor is hermetically sealed with internal high temperature protection, and durable insulation on motor windings. The entire compressor is mounted on rubber grommets to reduce vibration and noise. Compressors have an internal pressure relief assembly to protect against excessive pressure differential. There is a separate compressor compartment for easy service access.

CONTACTOR-The contactor is an electrical switch which operates the compressor and condenser fans. Its 24 is activated through the High Pressure Control and Low Pressure Control on a call for cooling.

EQUIPMENT GROUND-Lug for field connection of ground wire.

TESTING-All units are run tested at the factory prior to shipment. Units are shipped with a holding charge of nitrogen.

CONTROL BOX-The control box is located in the top corner of the cabinet providing for easy access through a service panel.

COMPRESSOR TIME DELAY CONTROL-Compressor will remain off for five minutes after power or thermostat interruption, allowing system pressures to equalize. (Model No. RXMD-B01)

FILTER/DRIER-A liquid line filter drier is shipped with each unit for field installation

AndOne RHGL-120ZL Classic Series® Air Handler

CABINET-Powder coat painted. Matching discharge plenums and decorative supply and return air grilles are available for use when units are to be installed within conditioned space.

MOTOR-Inherently protected motors are mounted inside of insulated cabinet to reduce motor noise. A choice of motor horsepower sand drive combinations are available to allow you to meet specified various static pressures up to 2" [.498 kPa] external static pressure.

LOW PROFILE-Allows for horizontal installation in most standard drop ceiling applications, and the movement of units through most standard doorways for addition or replacement work.

THERMAL EXPANSION VALVES-Standard all models.

FILTERS-One inch [25 mm] throwaway filters are standard, but filter racks are designed to accept either one inch [25 mm] or two inch[51 mm] filters.

REFRIGERANT CONNECTIONS-Field piping connections are made through a fixed post between two side access panels on either side of the unit. Allows flexibility to meet most field conditions as well as full accessibility after the installation is complete. Units may be used with two straight cool condensing units or single in the field using the copper fittings shipped with each unit. The RHGL Air Handler has not been tested, rated or certified to operate with dual residential remote heat pumps.

DRAIN PAN-The galvanized steel drain pan is designed to trap condensate in either vertical or horizontal installations. Condensate drain connections are located on both sides of the unit allowing complete flexibility to meet most field conditions.

SERVICE ACCESS-Two removable panels on top and each side of the unit are easily removed for access to motors, blowers, sheaves, and filters.

HORIZONTAL OR VERTICAL-All models are designed for either application and can be installed in either position as supplied from the factory.

TESTING-All units are run tested at the factory prior to shipment. Units are shipped with a holding charge of nitrogen.