Where the eyes of any person may be exposed to injurious orcorrosive materials, suitable facilities for quick flushing andcleansing of the eyes must be provided within the work areafor immediate emergency use. Emergency eyewash facilitiesshall be in unobstructed and accessible locations that requireno more than 10 seconds for the injured person toreach.Model 7261-7271 is certified by CSA to meet the ANSIZ358.1 Standard for Emergency Eyewash and ShowerEquipment.

Valve is designed to make the flushing of fluid occur withthe push of a stainless steel flag, and is equipped with astainless steel ball and stem to provide added protectionagainst corrosion and breakage.

STRAINERS/FILTERS

Chrome-plated brass in-line 50 x 50 mesh water strainerprevents debris from reaching the eyewash so the unitstays functioning at its best. Strainer is easily serviceable.

Dust Cover: Model 9102 is a stainless steel cover thatprotects the eyewash heads as well as the bowl. Pushingthe stainless steel flag will activate the unit while raising thedust cover. (Picture shows cover mounted to an eyewash.)