250 kW at 400 V (connection to the motor delta terminals) for standard applications220 kW at 400 V (connection to the motor delta terminals) for severe applications160 kW at 400 V (connection in the motor supply line) for standard applications160 kW at 230 V (connection to the motor delta terminals) for standard applications132 kW at 400 V (connection in the motor supply line) for severe applications132 kW at 230 V (connection to the motor delta terminals) for severe applications90 kW at 230 V (connection in the motor supply line) for standard applications75 kW at 230 V (connection in the motor supply line) for severe applications

Power dissipation in W

902 W for standard applications695 W for severe applications

Utilisation category

AC-53A

Type of start

Start with torque control (current limited to 5 In)

Icl nominal current

554 A (connection to the motor delta terminals)for standard applications433 A (connection to the motor delta terminals)for severe applications320 A (connection in the motor supply line)for standard applications250 A (connection in the motor supply line)for severe applications