3 WARNING: When servicing or replacing components to the FLUSHMATE Flushometer-Tank System, make certain that the water supply is turned OFF and the toilet is then flushed to relieve pressure in the vessel. NEVER use lubricants on any of the components unless otherwise noted in this manual. NEVER use corrosive chemicals or household cleaners on FLUSHMATE products. NEVER use corrosive disinfectants, bowl cleaners or deodorant blocks on FLUSHMATE Products or in the china tank. Note: It is normal for less than one inch of water to remain in the bottom of the china tank. INSTALLATION The Sloan FLUSHMATE Flushometer-Tank System Fixture installs in the same manner as other water closets. Please follow the instructions provided by the fixture manufacturer. Using the gasket, washer and nuts provided with the fixture, assemble the tank to the bowl. Before connecting the supply to the tank, be sure the supply line is flushed clean. Do this by running water from the supply stop into a bucket until water flows clear. After connecting the supply line to the tank, turn on the water again and check for leaks. You may be required to make adjustments to the actuator for either pushbutton type or trip lever type units. Please follow the instructions provided by the fixture manufacturer. TROUBLESHOOTING CONDITION: Water runs on and will not shut off. A newly installed toilet that does not shut off may be caused by inadequate or low pressure, and is usually the result of an insufficient water supply flow rate into the FLUSHMATE Vessel. (NOTE: The recommended static pressure range by code is 20 psi to 80 psi). If sufficient supply pressure has been verified and the toilet continues to run, the following steps may be required: FIGURE 1 FIGURE 2 Step 1. Step 2. Step 3: Step 4. Step 5. Make sure supply stop is fully open. Check the Supply Shank Screen for any obstruction that would restrict the supply. Check the Actuator adjustment (see Installation Procedure). The linkage rod or push button should not interfere with the flush. On Pushbutton type units, loosen the setscrew on the actuator (See Number 4F on the component list) and rotate the Actuator up or down until proper clearance is obtained (1/8 ). For trip lever units, gently lift the actuator rod and observe proper clearance is maintained (approximately 1/8 gap between rod and actuator). See Figure 1. Check the Flush Valve Cartridge Assembly for proper installation. Proceed as follows: a) Turn off the water supply and flush the toilet. b) Remove the Flush Valve Cartridge Assembly using pliers handles as shown in Figure 2. NOTE: You may be required to disconnect the Actuator Linkage Rod to remove the Flush Valve Cartridge Assembly. c) Inspect the O Rings on the Flush Valve Cartridge and the seating area inside the tank for wear and/or improper seating. Reinstall the Flush Valve Cartridge Assembly. First, insert the cartridge into vessel and, while gently pushing down on the Cartridge, turn the Cartridge counterclockwise until you hear an audible click, indicating that the threads are now aligned. Screw Cartridge clockwise into place until two black threads of the Vessel are showing. Next, turn on the water and continue to turn cartridge until the water stops running. Do not over-tighten.

4 Step 6. If the Tank continues to run on, push down lightly on the Flush Valve Actuator. If the water stops running, it is an indication that the Flush Valve Cartridge requires tightening (clockwise). If water still runs on while pushing down on the Actuator, the Flush Valve Cartridge requires loosening (counter-clockwise). NOTE: Adjust the Flush Valve Cartridge Assembly in quarter- to half-turn increments until the water stops running. Always turn the water supply off for all adjustments. Flush Valve Cartridge turns the water off. Step 7. If replacement of the Flush Valve Cartridge is necessary, follow the instructions in Step 5. TROUBLESHOOTING CONDITION: Weak or Sluggish Flush. IMPORTANT: Before doing any of the steps below, it is highly recommended that you inspect the metal endcaps for rust and pin holes. If you detect th ese conditions, it is recommended that your 501-A FLUSHMATE be replaced with a 501-B Model M FA for American Standard toilets, or Model M F for all other FLUSHMATE -equipped toilets. Air Inducer Cap Step 1. Check the water pressure (20psi - 80psi recommended). If OK, then check the Flush System by removing the Tank Cover and tripping the Actuator. While the unit is flushing, gently raise the Actuator. Water should flow freely and wash away any debris in the supply line and Vessel. Step 2. Check the Air Inducer for sufficient air draw. The Air Inducer is designed to draw air during the refill cycle. To test the Air Inducer, place a small amount of water (2 to 3 drops) in the orifice of the Air Inducer cap and flush the toilet. If the Air Inducer is functioning properly the water will be drawn in. If not, it will need to be cleaned and tested again. FIGURE 3 TO CLEAN AIR INDUCER: (Figures 3 & 4) a) Turn off the water supply and trip the Actuator. b) Unscrew the Air Inducer Cap, clean thoroughly and remove any obstructions. Reassemble. (Hand tighten ONLY) c) Turn on water supply. Wait for the Vessel to refill (30 to 60 seconds). Repeat Step 2 above. If the Air Inducer does not function properly, replace the Upper Supply Assembly. Step 3. Check the Flush Valve Cartridge for leaks. Turn the water supply off and drain the Vessel by tripping the Actuator and holding it down until completely drained. Next, pour a cup of water onto the Cartridge Housing area as shown in Figure 5. Turn on the water supply. If a leak is detected (a steady flow of bubbles from the center of the Cartridge Area), the Cartridge should be replaced. FIGURE 4 Step 4. Check Lower Supply. Turn the water off and relieve the Vessel pressure by flushing the toilet. Remove the supply line connection to the shank. Remove any obstruction in the supply shank screen. If necessary, you can use a small brush to gently brush the screen. Reattach the supply line to the supply shank and observe connections to assure no leakage. IMPORTANT: If you are still experiencing a weak or sluggish flush after this point, it is recommended you replace the entire lower supply group. Step 5. Check the following: 1. water line pressure (20-80 psi) 2. obstruction in the bowl trapway 3. obstruction in the drain 4. proper drain ventilation Consult a professional for their recommendations if any of these conditions exist. If the drain and drain vent are clear, and the flush has not been improved, replace the Lower Supply Assembly. FIGURE 5

5 TROUBLESHOOTING CONDITION: No Flush Step 1. Check the water pressure (20 psi to 80 psi). Step 2. Check the Air Inducer for sufficient air draw. Refer to Step 2 of Weak or Sluggish Flush. Step 3. Review all of Step 3 and Step 4 covered in Weak or Sluggish Flush Condition. Step 4. Replace the Flush Valve Cartridge. NEVER use lubricant on the O Ring (Arrow - Figure 6). FIGURE 6 CONDITION: Relief Valve Discharging This is a sign that the Lower Supply Group (Number 1 from list of components) is not working properly and should be replaced. Follow the procedure outlined below: FIGURE 7 Step 6. Insert new Lower Supply into Hose and secure with new Hose Clamp. REPLACE PROCEDURE FOR LOWER SUPPLY: Step 1. Turn the water supply off. Flush the fixture to relieve pressure in the Vessel. Step 2. Disconnect the water supply from the Shank. Step 7. Follow Step 3 above and in reverse to re-connect water and check for leaks. Step 3. Unscrew the plastic locknut that holds the Shank to the bottom of the China Tank. Step 4. Carefully pull the entire Lower Supply up and out of the Tank. Step 5. Cut the Hose just above the Barbed Fitting (about 1/4 above clamp) on the Lower Supply. Discard old Lower Supply. WINTERIZING The Sloan FLUSHMATE, when installed in a summer home, cottage or cabin, can be winterized to allow for periods for nonuse especially when the dwelling is subject to frigid conditions. Follow the procedures outlined below. NOTE: A sponge, a pail and adjustable channel locks will be useful. Tank Procedure: Bowl Procedure: Step 1. Turn off the water supply line valve and remove the Toilet Tank Cover. Step 2. Push the Actuator on top of the Vessel to flush and discharge the water. Step 3. Disconnect the supply line coupling nut from the Lower Supply located under the Toilet Tank Housing. NOTE: A small amount of water will drip out of the Shank. Be prepared to collect it in a bucket or sponge it up. Remove the Supply Shank and drain the water from the bottom of the china tank into a bucket. Step 4. Push down on the Actuator one more time, then pull it up momentarily to allow air into the Vessel. After flushing out the Vessel, remove the remaining water from the bowl or add from 1 pint to 1 quart of antifreeze or RV antifreeze to the water remaining in the bowl. NOTE: Refer to fixture manufacturer s instructions for procedures to winterize bowl.

6 POINTS TO REMEMBER When servicing any component, the water supply should be turned OFF and the Actuator tripped to relieve the pressure in the Vessel. The Flush Valve Cartridge Assembly can be removed by inserting the handles of a pair of pliers into the top of the Cartridge and turning counter-clockwise. It is normal for less than an inch of water to remain in the bottom of the outside China Tank. The FLUSHMATE System will automatically recirculate this water with each flush to eliminate any stagnant condition. NEVER use corrosive disinfectants, bowl cleaners or deodorant blocks on FLUSHMATE Products or in the china tank. Cold water use only. The Sloan FLUSHMATE Flushometer-Tank System has been engineered to provide reliable performance year after year. However, if servicing is ever required, it is recommended that you follow the instructions included in this brochure. If you would like additional information or require technical assistance, write or call us at the address or telephone number below. FLUSHMATE A DIVISION OF SLOAN VALVE CO Research Drive New Hudson, MI U.S.A Installation Date Serial Number 2015 Sloan Flushmate FLU

Before repairing your toilet, you must determine which type of toilet you have. Pressurized Toilets If you have a pressurized toilet, it is recommended that you call a licensed plumbing contractor to repair

DAZZLE Installation Instructions 08.80 Spread Lavatory Faucet with Speed Connect Drain* Congratulations on purchasing your American Standard faucet with Speed Connect drain, a feature found only on American

HOME & BATH INSTALLATION & CARE GUIDE ONE PIECE TOILET January 2012 2 BEFORE YOU BEGIN Please read these instructions carefully to familiarize yourself with the required tools, materials, and installation

CYLINDER OPERATED G-SERIES ACTUATOR USED ON PEC ECCENTRIC VALVES Instruction D10022 August 2012 Instructions These instructions provide information about G-Series Cylinder Actuators. They are for use by

For RV and Marine Use Only No more tank taste! Purifies Instantly and Naturally, Without Adding Chemicals Compact, Convenient and Complete Installs in Minutes Reliable and Simple to Use Just Turn on the

Aquverse Water Cooler Installation and Troubleshooting Instructions For any needed assistance please call 1-866-872-5722 ****Warning do not plug water cooler in until water line is in place and dispensing

PLUMBING CARE AND REPAIR No special skills are required for any of the repairs described in this section. Plumbing repairs are seldom dangerous unless leaking water is soaking areas where there are electrical

INSTR3010 0406 Installation and Operating Instructions Installation Instructions for SS EPE-316L Series Congratulations on your purchase of this Aqua-Pure high flow, single housing filtration system. This

INSTALLATION INSTRUCTIONS BEFORE YOU BEGIN NOTES Shut off the main water supply. Observe local plumbing codes. If possible, install this faucet before installing the bidet. Inspect the supply tubing for

A High Bill Usually Means a Leak Did you know that approximately 50 percent of all households have some kind of plumbing leak? Most of these leaks are due to worn out washers, flappers or faulty tank valves,

HAND SHOWERS AND HAND SHOWER ACCESSORIES BEFORE YOU BEGIN HOW TO USE THESE INSTRUCTIONS Please read these instructions carefully to familiarize yourself with the required tools, materials, and installation

14 / WASTE SYSTEM The waste water system in your trailer is made up of sinks, tub, shower, toilet, plumbing drain and vent lines. Waste water from the sinks and shower is contained in a gray water holding

Installation Instructions.00 SINGLE CONTROL KITCHEN FAUCET Thank you for selecting American-Standard...the benchmark of fine quality for over 00 years. To ensure that your installation proceeds smoothly--please

BOWIE PUMPS OPERATION - MAINTENANCE PUMPING PRINCIPLE: The meshing owieeof the gears cause a slight depression, with the resulting enmeshing of the gears causing a vacuum drawing the fluid being pumped

14 / WASTE SYSTEM The waste water system in your trailer is made up of sinks, tub, shower, toilet, plumbing drain and vent lines. Waste water from the sinks and shower is contained in a gray water holding

Watts Pure Water Systems WM-120-PT Installation and Operation Manual Premier Water Systems Do not use with water that is microbiologically unsafe or of unknown quality without adequate disinfection before

Backpack Sprayer Use and Care Manual Model MS-41BP 4G/ 15L WARNING Carefully Read These Instructions Before Use 013529 R0514 WARNING WARNING: Improper use or failure to follow instructions can result in

125/160/185 UD SULLAIR POWERTECH SECTION 7 7.1 GENERAL A good maintenance program is the key to long compressor life. Below is a program that when adhered to, should keep the compressor in top operating

++ 24 Replacing a Toilet Replacing a toilet is simple, and the latest generation of 1.6-gallon watersaving toilets has overcome the performance problems of earlier models. YOU CAN REPLACE A POORLY FUNCTIONING

Maintenance Diamond High Efficiency Filter Systems are designed for low maintenance. The following maintenance procedures outline recommended minimum frequency to help ensure continued trouble-free operation

6. Cooling System XCITING 400i Cooling System This chapter covers the location and servicing of the cooling system components for the KYMCO XCITING 400i. Coolant... 6-3~6-11 Radiator... 6-12~6-23 Thermostat...

Backpack Sprayer Use and Care Manual BACKPACK SPRAYER CAUTION: Read and follow all instructions Do Not Return This Backpack To The Store For Help, Information or Parts, Call : 1-800-311-9903 The Fountainhead

Prior to installing the Butler Faucet, locate and record the serial number on your Zuvo Water Purator. This serial number appears on the lower back of the device. Zuvo Water Purator Butler Faucet Kit Installation

Fuel Tank Pickup Modifications-Dmax The Duramax Fuel sending unit pickup assembly is very restrictive and not designed to provide the large volume of fuel required to support high horsepower numbers. It

Adjustable Fuel Pressure Regulator Kit for 2008+STI 2014-10-16 Thank you for purchasing this PERRIN product for your car! Installation of this product should only be performed by persons experienced with

FUEL PUMP/FUEL GAUGE SENDING UNIT 4.4 GENERAL s0660x8xx Stop the engine when refueling or servicing the fuel system. Do not smoke or allow open flame or sparks near gasoline. Gasoline is extremely flammable