Water requirements:1)Operating water temperature:The temperature between (18˚C-23˚C)is best. If do not use
temperature regulation, please allow the temperature between
(10˚C-27˚C),or a heating exchanger or chiller equipment to be used
for adjust the water temperature.2)Operating water pressure:Minimum 0.2 MPa, Maximum 0.35 Mpa, if not in this scope, need to
increase a he pressure or vacuum equipment3)water quality requirements:pH 6.5 to 8.5hardness[in calcium carbonate] < 5 ppm (soft water equipment
outlet)COD(Mn) < 1.5 ppmFe < 0.2 ppmMn < 0.01 ppmNi < 5 ppmF <2 ppmCu < 5 ppb

Product introduction:

Generation principle:

The revolutionary CNJS-S series sodium hypochlorite generator is a
newly and for on-site product of NaClO equipment and use for all
kinds of needed NaClO disinfected. Its working principle is :the
sodium chloride solution under the certain voltage effect of the
cell, a series of electrochemical reaction within the cell and the
resulting solution is the NaClO solution. The main process can be
simplified as follows:

The electrode reaction:anode:2Cl--2e→Cl2cathode:2H++2e→H2solution:2NaOH+Cl2→NaCl+NaClO+H2O

Work flow chart:

Product components system

A,inlet water distribution systemMain components: water pressure gauge, water softener, soft water
pump, water meter, salt tank, salt water pump and related piping
and valves.

B,The power control system:Including control cabinet, rectifier and cable connection.

SAFETY:Material safety: Salt, Water and Electricity as raw materials, no
need for transportation of dangerous chemicals;Process safety: No risk of chlorine leakage and reactor explosion,
safety for operator;Product safety: Product-0.8% NaCIO solution, has the advantage of
stable and safety, cost effective in operation and no attenuation
in storage.ENERGY-SAVING:Make use of electricity in the off-peak period to generate the
NaCIO solution.ENVIRONMENTAL PROTECTION:Avoid of usage, transportation of dangerous chemical material.High current efficiency ,few by-product, safe H2 ventilation.ECONOMY:JIASHANG equipment can largely reduce the operation cost compared
to the bulk hypochlorite