installation manual

INSTALLATION MANUAL
SPLIT SYSTEM Air Conditioners
MODELS
Ceiling-mounted Cassette type (Multi flow model)
FCQ18PVJU
FCQ24PVJU
FCQ30PVJU
English
Français
Read these instructions carefully before installation.
Keep this manual in a handy place for future reference.
This manual should be left with the equipment owner.
Español
Lire soigneusement ces instructions avant l’installation.
Conserver ce manuel à portée de main pour référence ultérieure.
Ce manuel doit être donné au propriétaire de l’équipement.
Lea cuidadosamente estas instrucciones antes de instalar.
Guarde este manual en un lugar a mano para leer en caso de tener alguna duda.
Este manual debe permanecer con el propietario del equipo.
00_CV_3PN06240-13Q.indd 1
2/6/2009 11:38:56 AM
SPLIT SYSTEM Air Conditioners
CONTENTS
1.
2.
3.
4.
5.
6.
7.
8.
9.
10.
11.
12.
13.
1.
SAFETY CONSIDERATIONS ........................................... 1
BEFORE INSTALLATION .................................................. 2
SELECTING INSTALLATION SITE ................................... 3
PREPARATIONS BEFORE INSTALLATION ..................... 4
INSTALLATION PROCEDURES FOR FRESH AIR
INTAKE DUCT CONNECTION.......................................... 5
INDOOR UNIT INSTALLATION ......................................... 6
REFRIGERANT PIPING WORK ....................................... 7
DRAIN PIPING WORK ...................................................... 8
ELECTRIC WIRING WORK .............................................. 9
WIRING EXAMPLE AND HOW TO SET THE REMOTE
CONTROLLER ................................................................ 10
FIELD SETTING.............................................................. 12
INSTALLATION OF THE DECORATION PANEL ............. 12
TEST OPERATION ......................................................... 13
SAFETY CONSIDERATIONS
Please read these “SAFETY CONSIDERATIONS” carefully
before installing air conditioning equipment and be sure to
install it correctly. After completing the installation, make sure
that the unit operates properly during the start-up operation.
Please instruct the customer on how to operate the unit and
keep it maintained.
Also, inform customers that they should store this installation
manual along with the operation manual for future reference.
This air conditioner comes under the term “appliances not
accessible to the general public”.
Meaning of danger, warning, caution and note symbols.
DANGER ................ Indicates an imminently hazardous
situation which,if not avoided, will
result in death or serious injury.
WARNING .............. Indicates a potentially hazardous
situation which, if not avoided, could
result in death or serious injury.
CAUTION ............... Indicates a potentially hazardous
situation which, if not avoided, may
result in minor or moderate injury. It
may also be sued to alert against
unsafe practices.
NOTE ..................... Indicates situation that may result in
equipment or property-damage-only
accidents.
DANGER
• Do not ground units to water pipes, telephone wires or
lightning rods because incomplete grounding could
cause a severe shock hazard resulting in severe injury
or death, and to gas pipes because a gas leak could
result in an explosion which could lead to severe injury
or death.
1
01_EN_3PN06240-13Q.indd 1
Installation manual
• Do not install unit in an area where flammable materials
are present due to risk of explosion resulting in serious
injury or death.
• Refrigerant gas in heavier than air and displaces oxygen. A massive leak could lead to oxygen depletion,
especially in basements, and an asphyxiation hazard
could occur leading to serious injury or death.
• If the refrigerant gas leaks during installation, ventilate
the area immediately.
Refrigerant gas may produce toxic gas if it comes in contact
with fire such as from a fan, heater, stove or cooking device.
Exposure to this gas could result in severe injury or death.
• After completing the installation work, check that the
refrigerant gas does not leak.
Refrigerant gas may produce toxic gas if it comes in contact
with fire such as from a fan, heater, stove or cooking device.
Exposure to this gas could result in severe injury or death.
• Safely dispose of the packing materials.
Packing materials, such as nails and other metal or wooden
parts, may cause stabs or other injuries. Tear apart and
throw away plastic packaging bags so that children will not
play with them. Children playing with plastic bags face the
danger of death by suffocation.
WARNING
• Ask your dealer or qualified personnel to carry out
installation work. Do not try to install the unit by yourself.
Improper installation may result in water leakage, electric
shocks or fire.
• Perform installation work in accordance with this installation manual.
Improper installation may result in water leakage, electric
shocks or fire.
• Be sure to use only the specified accessories and parts
for installation work.
Failure to use the specified parts may result in water leakage, electric shocks, fire or the unit falling.
• Install the air conditioner on a foundation strong
enough to withstand the weight of the unit.
A foundation of insufficient strength may result in the equipment falling and causing injuries.
• Carry out the specified installation work after considering strong considering winds, typhoons or earthquakes.
Improper installation work may result in the equipment
falling and causing accidents.
• Make sure that a separate power supply circuit is provided for this unit and that all electrical work is carried
out by qualified personnel according to local laws and
regulations and this installation manual.
An insufficient power supply capacity or improper electrical
construction may lead to electric shocks or fire.
• Make sure that all wiring is secured, the specified wires
are used, and no external forces act on the terminal
connections or wires.
Improper connections or installation may result in fire.
English
2/6/2009 11:44:11 AM
• When wiring the power supply and connecting the
remote controller wire and transmission wire, position
the wires so that the control box lid can be securely
fastened.
Improper positioning of the control box lid may result in
electric shocks, fire or the terminals overheating.
• Before touching electrical parts, turn off the unit.
• Do not touch the switch with wet fingers.
Touching a switch with wet fingers can cause electric shock.
• Be sure to install an earth leakage breaker.
Failure to install an earth leakage breaker may result in
electric shocks, or fire.
• Do not install the air conditioner in the following locations:
(a) where a mineral oil mist or an oil spray or vapor is
produced, for example in a kitchen
Plastic parts may deteriorate and fall off or result in
water leakage.
(b) where corrosive gas, such as sulfurous acid gas, is
produced
Corroding copper pipes or soldered parts may result in
refrigerant leakage.
(c) near machinery emitting electromagnetic waves
Electromagnetic waves may disturb the operation of the
control system and result in a malfunction of the equipment.
(d) where flammable gases may leak, where there are
carbon fiber or ignitable dust suspensions in the air, or
where volatile flammables such as thinner or gasoline
are handled.
Operating the unit in such conditions may result in fire.
• Heat exchanger fins are sharp to cut.
To avoid injury wear gloves to cover the fins when working
around them.
• Refrigerant pipes may be very hot or very cold during
or immediately after operation.
Touching them could result in burns or frostbite. To avoid
injury give the pipes time to return to normal temperature
or, if you must touch them, be sure to wear proper gloves.
CAUTION
• While following the instructions in this installation
manual, install drain pipe in order to ensure proper
drainage and insulate pipe in order to prevent condensate.
Improper drain pipe may result in water leakage and property damage.
• Be very careful about product transportation.
Some products use PP bands for packaging. Do not use
any PP bands for a means of transportation. It is dangerous.
• Safely dispose of the packing materials.
Packing materials, such as nails and other metal or wooden
parts, may cause stabs or other injuries.
Tear apart and throw away plastic packaging bags so that
children will not play with them. If children play with a plastic
bag which was not torn apart, they face the risk of suffocation.
• Do not turn off the power immediately after stopping
operation.
Always wait at least 5 minutes before turning off the power.
Otherwise, water leakage and trouble may occur.
English
01_EN_3PN06240-13Q.indd 2
• Make sure to provide for adequate measures in order to
prevent that the outdoor unit be used as a shelter by
small animals.
Small animals making contact with electrical parts can
cause malfunctions, smoke or fire. Please instruct the
customer to keep the area around the unit clean.
NOTE
• Install the indoor and outdoor units, power supply wire
and transmission wire at least 3.5ft. away from televisions or radios in order to prevent image interference
or noise.
(Depending on the radio waves, a distance of 3.5ft. may not
be sufficient enough to eliminate the noise.)
• Remote controller (wireless kit) transmitting distance
can result shorter than expected in rooms with electronic fluorescent lamps. (inverter or rapid start types)
Install the indoor unit as far away from fluorescent lamps as
possible.
• In a domestic environment this product may cause
radio interference in which case the user may be required to take adequate measures.
• Dismantling of the unit, treatment of the refrigerant, oil
and eventual other parts, should be done in accordance with the relevant local and national regulations.
2.
BEFORE INSTALLATION
• When moving the unit while removing it from the packing case, be sure to lift it by the four hanger brackets.
Avoid putting any pressure on other parts especially
the refrigerant piping.
• Be sure to check the type of R410A refrigerant to be used
before installing the unit. (Using an incorrect refrigerant will
prevent normal operation of the unit.)
• The accessories needed for installation must be retained in
your custody until the installation work is completed. Do not
discard them!
• Decide upon a line of transport.
• Leave the unit inside its packaging while moving, until
reaching the installation site. Where unpacking is unavoidable, use a sling of soft material or protective plates together with a rope when lifting, to avoid damage or scratches to
the unit.
• When moving the unit at or after opening, hold the unit by
the hanger brackets (× 4). Do not apply force to the refrigerant pipe, drain pipe or plastic parts.
• For the installation of an outdoor unit, refer to the installation manual attached to the outdoor unit.
• Do not install or operate the unit in rooms mentioned below.
• Laden with mineral oil, or filled with oil vapor or spray
like in kitchens. (Plastic parts may deteriorate which
could eventually cause the unit to fall out of place, or
could lead to leaks.)
• Where corrosive gas like sulfurous gas exists.
(Copper tubing and brazed spots may corrode which
could eventually lead to refrigerant leaks.)
• Where machines can generate electromagnetic
waves. (Control system may malfunction.)
• Where the air contains high levels of salt such as that
near the ocean and where voltage fluctuates greatly
such as that in factories. Also in vehicles or vessels.
2
2/6/2009 11:44:11 AM
• This unit, both indoor and outdoor, is suitable for installation
in a commercial and light industrial environment.
If installed as a household appliance it could cause electromagnetic interference.
Table 2
Remote controller
Wired type
Wireless type
BRC1C71
BRC7C812
WARNING
• Entrust installation to the place of purchase or a qualified
person. Improper installation could lead to leak and, in
worse cases, electric shock of fire.
• Use of unspecified parts could lead to the unit falling, leaks
and, in worse cases, electric shock or fire.
• Be sure to read this manual before installing the indoor unit.
• Be sure to mount an air filter (part to be procured in the field) in
the suction air passage in order to prevent water leaking, etc.
ACCESSORIES
Check the following accessories are included with your unit.
Name
(1) Drain
hose
(2) Metal
clamp
Quantity
1 pc.
1 pc.
(3) Washer for
hanger
bracket
8 pcs.
(6) Screws
(M5)
(7) Washer
fixing plate
Insulation
for fitting
4 pcs.
4 pcs.
1 each
(4) Clamp
4 pcs.
Shape
Name
Quantity
a. Items to be checked after completion of work
If not properly done, what is
likely to occur.
Are the indoor and outdoor unit The units may drop, vibrate or
fixed firmly?
make noise.
It may result in insufficient
Is the gas leak test finished?
cooling.
Is the unit fully insulated?
Condensate water may drip.
Does drainage flow smoothly? Condensate water may drip.
Does the power supply voltage
The unit may malfunction or the
correspond to that shown on
components burn out.
the name plate?
The unit may malfunction or the
Are wiring and piping correct?
components burn out.
Is the unit safely grounded?
It may result in electric shock.
Is wiring size according to
The unit may malfunction or the
specifications?
components burn out.
Is something blocking the air
It may result in insufficient
outlet or inlet of either the
cooling.
indoor or outdoor units?
Are refrigerant piping length
The refrigerant charge in the
and additional refrigerant
system is not clear.
charge noted down?
Items to be checked
NOTE
2-1
FOR THE FOLLOWING ITEMS, TAKE SPECIAL CARE
DURING CONSTRUCTION AND CHECK AFTER
INSTALLATION IS FINISHED.
(5) Paper
pattern for
installation
1 pc.
Also used
as packing
material
Shape
For paper
pattern for
installation
b. Items to be checked at time of delivery
Also review the “1. SAFETY CONSIDERATIONS”
(8) for gas
pipe
(9) for liquid
pipe
Name
Quantity
Check
Items to be checked
Did you explain about operations while showing the operation
manual to your customer?
Did you hand the operation manual over to your customer?
2-3
Sealing pad
1 each
2 pcs.
(Other)
Check
NOTE TO INSTALLER
• Be sure to instruct customers how to properly operate the
unit (especially cleaning filters, operating different functions,
and adjusting the temperature) by having them carry out
operations themselves while looking at the manual.
• Installation manual
Shape
(10) Large
(12) Small
• Operation manual
(11) Medium
2-2
OPTIONAL ACCESSORIES
• The optional decoration panel and remote controller are
required for this indoor unit.
Table 1
Model
FCQ18 · 24 · 30PVJU
3
01_EN_3PN06240-13Q.indd 3
Optional decoration panel
Color
White
BYC125K-W1
3.
SELECTING INSTALLATION SITE
Please attach additional thermal insulation material to the unit
body when it is believed that the relative humidity in the ceiling
exceeds 80%. Use glass wool, polyethylene foam, or similar
with a thickness of 3/8 in.. or more as thermal insulation material.
(1) Select an installation site where the following conditions
are fulfilled and that meets with your customer’s approval.
• In the upper space (including the back of the ceiling) of the
indoor unit where there is no possible dripping of water
from the refrigerant pipe, drain pipe, water pipe, etc.
• Where optimum air distribution can be ensured.
• Where nothing blocks the air passage.
English
2/6/2009 11:44:11 AM
• If the supporting structural members are not strong enough
to take the unit’s weight, the unit could fall out of place and
cause serious injury.
PREPARATIONS BEFORE INSTALLATION
Refrigerant
pipe
30 11/16 (Suspension bolt pitch)
WARNING
4.
(1) Relation of ceiling opening to unit and suspension
bolt position
33 1/16 (Indoor unit)
• Do not install unit in an area where flammable materials are
present due to the risk explosion resulting in serious injury
or death.
H
11 3/4 or more
(length: in.)
34 5/8 (Ceiling opening)
DANGER
Model
FCQ18 · 24 · 30PVJU
37 3/8 (Decoration panel)
• Where condensate can be properly drained.
• Where the false ceiling is not noticeably on an incline.
• Where sufficient clearance for maintenance and service
can be ensured.
• Where piping between indoor and outdoor units is
possible within the allowable limit. (Refer to the installation manual of the outdoor unit.)
NOTE
Suspension
bolt (×4)
26 3/4 (Suspension bolt pitch)
• Install the indoor and outdoor units, power supply wire and
connecting wires at least 3.5ft. away from televisions or
radios in order to prevent image interference or noise.
(Depending on the radio waves, a distance of 3.5ft. may not
be sufficient enough to eliminate the noise.)
33 1/16 (Indoor unit)
34 5/8 (Ceiling opening)
37 3/8 (Decoration panel)
A
(2) Ceiling height
This indoor unit may be installed on ceilings up to 10.5 ft.
in height.
[View as seen from A]
(length: in.)
 Installation is possible when ceiling opening dimensions is
as follows.
• When installing the unit within the frame for fixing false
ceiling.
(Dimension inside frame)
Air Air discharge 59
inlet
or more
35 13/16
33 1/16 (Indoor unit)
Air
discharge
H
59
or more
39 3/8 or more
H
[Space required for installation]
False
ceiling
(5 15/16)
(3) Use suspension bolts for installation. Check whether
the ceiling is strong enough to support the weight of
the unit or not. If there is a risk, reinforce the ceiling
before installing the unit.
(Installation pitch is marked on the paper pattern for
installation. Refer to it to check for points requiring reinforcing.)
Hanger
bracket
33 1/16 (Indoor unit)
35 13/16
(Dimension inside frame)
59
or more
English
01_EN_3PN06240-13Q.indd 4
Air
Air inlet
discharge
Air
discharge
(length: in.)
59
or more
4
2/6/2009 11:44:12 AM
Installation example ®
33 13/16
(Opening dimension inside
the frame for ceiling)
Ceiling slap
1 15/16 3 15/16
Anchor
Long nut or turn-buckle
Frame
False
ceiling
Suspension bolt
False ceiling
NOTE) All the above parts are field supplied.
13/16 or more
33 13/16-*35 13/16
(Ceiling opening dimension)
13/16 or more
(Ceiling-panel
overlapping
dimension)
(length: in.)
5.
Ceiling material
1 3/8 or less
1 3/8 or less
INSTALLATION PROCEDURES FOR
FRESH AIR INTAKE DUCT CONNECTION
(1) Cut off the knockout hole on the side plate.
Then, cut the inner insulation of the hole portion.
(Refer to Fig. 1)
(2) Adhere the insulation for opening of unit to the opening.
(Refer to Fig. 2)
Refrigerant pipe
Drain pipe
(length: in.)
NOTE) Installation is possible with a ceiling dimension of
35 13/16 in. (marked with *). However, to achieve a
ceiling-panel overlapping dimension of 13/16 in., the
spacing between the ceiling and the unit should be
1 3/8 in. or less. If the spacing between ceiling and the
unit is over 1 3/8 in., attach false ceiling to
part or
recover the ceiling.
(2) Make the ceiling opening needed for installation
where applicable. (For existing ceilings)
• Refer to the paper pattern for installation (5) for ceiling
opening dimensions.
• Create the ceiling opening required for installation. From
the side of the opening to the casing outlet, implement
the refrigerant and drain pipe and remote controller wire
(unnecessary for wireless type) and indoor-outdoor unit
casing outlet. Refer to the “REFRIGERANT PIPING
WORK (Page 7), DRAIN PIPING WORK (Page 8) and
ELECTRIC WIRING WORK (Page 9)”.
• After making an opening in the ceiling, it may be necessary to reinforce ceiling beams to keep the ceiling level
and to prevent it from vibrating. Consult the builder for
details.
Inner insulation
Side plate
Cut it off with cutter.
Cut it off with nipper.
Inner
insulation
Slit
Side plate
Fig. 1
(3) Install the suspension bolts.
(Use either a W3/8 or M10 size bolt)
Use a hole-in anchor for existing ceilings, and a sunken
insert, sunken anchor or other field supplied parts for new
ceilings to reinforce the ceiling to bear the weight of the
unit. Adjust clearance from the ceiling before proceeding
further.
5
01_EN_3PN06240-13Q.indd 5
English
2/6/2009 11:44:12 AM
6-1
Insulation
(field supply)
Put the insulation tightly around the hole of the unit as
shown. The ends of the side plate and the inner
insulation must be completely adhered without leaving
any clearance along the circumference of the hole.
Inner insulation
For new ceilings
(2) • Refer to the paper pattern for installation (5) for ceiling
opening dimension.
Consult the builder or carpenter for details.
• The center of the ceiling opening is indicated on the
paper pattern for installation.
The center of the unit is indicated on the label attached
to the unit and on the paper pattern for installation.
• After removing the packaging material from the 4 corners of the paper pattern for installation (5), fix the
paper pattern to the unit with screws (6) (×4).
• Ceiling height is shown on the side of the paper pattern
for installation (5). Adjust the height of the unit according
to this indication.
Side plate
Only the corner where the pipes go out, the
screw is already fixed at the drain pan.
Edge
Insulation
Center of ceiling opening
Approx. 3/8
(length: in.)
Make sure the inner surface of insulation tightly contacts
with the inner insulation edge and the side plate.
Paper pattern for
installation (5)
Fig. 2
(accessory)
6.
Screw (6)
INDOOR UNIT INSTALLATION
Installing optional accessories (except for the decoration
panel) before installing the indoor unit is easier. However,
for existing ceilings, install fresh air inlet component kit
and branch duct before installing the unit.
(1) Install the indoor unit temporarily.
• Attach the hanger bracket to the suspension bolt. Be
sure to fix it securely by using a nut and washer from
the upper and lower sides of the hanger bracket.
The washer fixing plate (7) will prevent the washer from
falling.
Part to be procured in the field
Washer (3) (accessory)
Hanger bracket
(accessory)
Screw (6)
(accessory)
〈Ceiling work〉
(3) Adjust the unit to the right position for installation.
(Refer to “PREPARATIONS BEFORE INSTALLATION-(1)”.) (Page 4)
(4) Check the unit is horizontally level.
• The indoor unit is equipped with a built-in drain
pump and float switch. At each of the unit’s 4 corners, verify that it is level by using a water-level or a
water-filled vinyl tube.
(If the unit is inclined against condensate flow, the
float switch may malfunction and cause water to
drip.)
(5) Remove the washer fixing plate (7) used for preventing the
washer from falling and tighten the upper nut.
(6) Remove the paper pattern for installation (5).
Tighten
(double nut)
[Securing the hanger bracket]
Water level
Insert
Vinyl tube
6-2
Washer fixing plate (7)
(accessory)
[Securing the washer]
English
01_EN_3PN06240-13Q.indd 6
For existing ceilings
(2) Adjust the height and position of the unit.
(Refer to “PREPARATIONS BEFORE INSTALLATION-(1)”.)
(3) Perform steps (4), (5) in “6-1 For new ceilings”.
6
2/6/2009 11:44:13 AM
7.
REFRIGERANT PIPING WORK
7-1
NOTE
GENERAL INSTRUCTIONS
• For refrigerant pipe of outdoor units, see the installation
manual attached to the outdoor unit.
• Before refrigerant piping work, check which type of refrigerant is used. Proper operation is not possible if the types of
refrigerant are not the same.
• The outdoor unit is charged with refrigerant.
DANGER
• Refrigerant gas may produce toxic gas if it comes in contact
with fire such as from a fan heater, stove or cooking device.
Exposure to this gas could cause severe injury or death.
NOTE
• Use a pipe cutter and flare suitable for the type of refrigerant.
• To prevent dust, moisture or other foreign matter from
infiltrating the tube, either pinch the end or cover it with tape.
• Do not allow anything other than the designated refrigerant
to get mixed into the refrigerant circuit, such as air, etc. If
any refrigerant gas leaks while working on the unit, ventilate
the room thoroughly right away.
7-2
• Apply ester oil or ether oil around the flare portions before
connecting.
• The flare nuts used must be those included with the main
body.
• Over-tightening may damage the flare and cause a refrigerant leakage.
Not recommended but in case of emergency
You must use a torque wrench but if you are obliged to
install the unit without a torque wrench, you may follow the
installation method mentioned below.
After the work is finished, make sure to check that there
is no gas leak.
When you keep on tightening the flare nut with a spanner,
there is a point where the tightening torque suddenly increases. From that position, further tighten the flare nut the
angle shown below:
Table 4
Pipe size
(in.)
φ 3/8
φ 5/8
Connecting the refrigerant pipe
• When connecting the flare nut, coat the flare with ester oil
or ether oil and initially tighten by hand 3 or 4 turns before
tightening firmly.
Ester oil or ether oil.
• To prevent flare nut cracking and gas leaking, be sure to
use both a spanner and torque wrench together, as shown
in the drawing below, when connecting or disconnecting
pipes to/from the unit.
Torque wrench
Spanner
Pipe union
7-3
Further tightening
angle
60 to 90 degrees
30 to 60 degrees
Recommended arm length of
tool (in.)
Approx. 7 7/8
Approx. 11 13/16
Piping insulation
• Execute heat insulation work completely on both sides of
the gas pipe and the liquid pipe. Otherwise, a water leakage
can result sometimes.
• The temperature of the gas pipe can reach up to approximately 250°F, so use insulation which is sufficiently resistant.
• Also, in cases where the temperature and humidity of the
refrigerant pipe sections might exceed 86°F or RH80%,
reinforce the refrigerant insulation. (13/16 in. or thicker)
Condensate may form on the surface of the insulating
material.
• Check the pipe connector for gas leaking, then insulate it as
shown in the drawing below.
• Make absolutely sure to execute heat insulation works on
the pipe-connecting section after checking gas leakage by
thoroughly studying the following figure and using the
attached heat insulating materials for fitting. (Fasten both
ends with the clamps (accessory).)
• Wrap the sealing pad (accessory) only around the insulation for the joints on the gas pipe side.
Medium sealing
pad (11) (accessory)
Flare nut
• Refer to the Table 3 for the dimensions of flare shape.
• Refer to the Table 3 to determine the proper tightening torque.
(Wrap the piping union
with the sealing pad.)
Table 3
φ 5/8
45.6-55.6
0.760-0.776
0
7
01_EN_3PN06240-13Q.indd 7
R0.0160.031
0
0.504-0.520
0
24.1-29.4
Insulation for
fitting (9) (accessory)
(for liquid line)
A
φ 3/8
Clamp (4) ×4
(accessory)
Flare shape (in.)
45 ±2
Flare
dimensions
A (in.)
0
Tightening torque
(ft.lbf)
90 ±2
Pipe
size
(in.)
Liquid pipe
Gas pipe
Insulation for fitting (8)
(accessory)
(for gas line)
English
2/6/2009 11:44:13 AM
CAUTION
1/100 gradient
or more
3.28 - 4.92ft.
• Be sure to insulate any field piping all the way to the piping
connection inside the unit. Any exposed pipe may cause
condensate or burns if touched.
7-4
Brazing refrigerant piping
• Before brazing local refrigerant pipe, nitrogen gas shall be
blown through the pipe to expel air from the pipe.
If your brazing is done without nitrogen gas blowing, a large
amount of oxide film develops inside the pipe, and could
cause system malfunction.
• When brazing the refrigerant pipe, only begin brazing after
having carried out nitrogen substitution or while inserting
nitrogen into the refrigerant pipe. Once this is done, connect
the indoor unit with a flared or a flanged connection.
• Nitrogen should be set to 2.9psi. with a pressure-reducing
valve if brazing while inserting nitrogen into the pipe.
Refrigerant
pipe
Pressurereducing valve
Part to be
brazed
Taping
Hands
valve
Nitrogen
• Use the attached drain hose (1) and metal clamp (2).
Insert the drain hose into the drain socket, up to the white
tape. Tighten the clamp until the screw head is less than
3/16 in. from the hose.
• Be sure to insulate the 2 below indicated spots.
If uninsulated, there is always the possibility of condensate forming and leaking.
• The drain pipe inside the building
• Drain socket
• Wrap the attached sealing pad (10) (Large) over the clamp
and drain hose to insulate, as shown in the drawing below.
Metal clamp (2)
Nitrogen
(accessory)
DANGER
• Use of oxygen may cause an explosion resulting in serious
injury or death. Only use nitrogen gas.
Drain hose (1)
(accessory)
Tape (White)
NOTE
• Do not use flux when brazing refrigerant pipe. Therefore,
use the phosphor copper brazing filler metal (BCuP) which
does not require flux.
(Flux has an extremely negative effect on refrigerant piping
systems. For instance, if chlorine based flux is used, it will
cause pipe corrosion. If the flux contains fluorine, it will
damage the refrigerant oil.)
Metal clamp (2)
(accessory)
Large sealing pad (10)
(accessory)
3/16 or less
DRAIN PIPING WORK
English
01_EN_3PN06240-13Q.indd 8
〈NOTE FOR DRAIN RAISING PIPE〉
• Install the drain raising pipe at a height of less than 21 5/8 in.
• Install the drain raising pipe at a right angle to the indoor
unit and no more than 11 13/16 in. from the unit.
Ceiling slab
11 13/16 or less
3.28-4.92ft.
Adjustable
Suspention bolt (21 5/8 or less)
Clamp metal (2) (accessory)
Drain raising pipe
Rise
Drain hose (1) (accessory)
29 1/2 or less
〈〈Rig the drain pipe as shown below and take measures
against condensate. Improperly rigged pipe could lead to
leak and eventually wet furniture and belongings.〉〉
(1) Rig drain pipe
• The diameter of the drain pipe should be greater than or
equal to the diameter of the connecting pipe (vinyl tube;
pipe size: 1 in.; outer dimension: 1 1/4 in.). (This does not
apply to rise.)
• Keep the drain pipe short and sloping downwards at a
gradient of at least 1/100 to prevent air pockets from forming.
• If the drain pipe cannot be sufficiently set on a slope, execute the drain raising pipe.
• To keep the drain pipe from sagging, space hanging wires
every 3.28 ~ 4.92ft.
(length: in.)
7 7/8
8.
(length: in.)
8
2/6/2009 11:44:14 AM
Power supply
terminal block
NOTE
• The incline of attached drain hose (1) should be 2 15/16 in.
or less so that the drain socket does not have to stand
additional force.
2 15/16
or less
29 1/2 or less
Drain hose (1) (accessory)
(length: in.)
Select converging drain pipe whose gauge is suitable for
the operating capacity of the unit.
• Drain pipe connections
Do not connect the drain pipe directly to sewage pipes that
smell of ammonia. The ammonia in the sewage might enter
the indoor unit through the drain pipe and corrode the heat
exchanger.
• Keep in mind that it will become the cause of getting drain
pipe blocked if water collects on drain pipe.
(2) After piping work is finished, check if drainage flows
smoothly.
• Open the water inlet lid, add approximately 37 in³ of
water slowly and check drainage flow.
WHEN ELECTRIC WIRING WORK IS FINISHED
• Check drainage flow during COOL running, explained under
“TEST OPERATION”.
WHEN ELECTRIC WIRING WORK IS NOT FINISHED
• Remove the control box lids, connect a power supply wire and
remote controller wire to the terminals.
(Refer to the “HOW TO CONNECT WIRES” (Page 10))
Next, press the INSPECTION/TEST OPERATION button
“
” on the remote controller. The unit will engage the test
operation mode. Press the OPERATION MODE SELECTOR
button “
” until selecting FAN SPEED CONTROL button
“ ”. Then, press the ON/OFF button “ ”. The indoor unit
fan and drain pump will start up. Check that the water has
drained from the unit. Press “
” to go back to the first mode.
Control box lid (2)
9.
9-1
ELECTRIC WIRING WORK
GENERAL INSTRUCTIONS
• All field supplied parts and materials, electric works must
conform to local codes.
• Use copper wire only.
• Follow the “WIRING DIAGRAM” attached to the unit body to
wire the outdoor unit, indoor unit and the remote controller.
For details on hooking up the remote controller, refer to the
“INSTALLATION MANUAL OF REMOTE CONTROLLER”.
• All wires must be performed by an authorized electrician.
• A circuit breaker capable of shutting down the power supply
to the entire system must be installed.
• Be sure to ground the air conditioner.
DANGER
• Do not ground units to water pipes, telephone wires or
lightning rods because incomplete grounding could cause a
severe shock hazard resulting in severe injury or death, and
to gas pipes because a gas leak could result in an explosion which could lead to severe injury or death.
9-2
ELECTRICAL CHARACTERISTICS
Power
supply
Units
Model
Portable pump
Inspection
opening
FCQ18PVJU
FCQ24PVJU
FCQ30PVJU
Hz Volts
60
208230V
Fan motor
Voltage
range
MCA
MFA
W
FLA
Max. 253
Min. 187
1.3
1.3
1.3
15
15
15
90
90
90
1.0
1.0
1.0
MCA: Min. Circuit Amps (A) MFA: Max. Fuse Amps (A)
KW: Fan Motor Rated Output (kW) FLA: Full Load Amps (A)
Bucket
(Adding water from
inspection opening)
Plastic watering can
(Tube should be about
3 15/16 long.)
Power supply
terminal block
Control box lid (1)
The water inlet lid
Drain pipe
3 15/16 or more
208V–230V
Single phase
power supply
Indoor unit
PC board
Service condensate outlet
(with rubber plug)
(Use this outlet to condensate
from the drain pan)
(length: in.)
Adding water through air discharge outlet ®
[Method of adding water]
9
01_EN_3PN06240-13Q.indd 9
English
2/6/2009 11:44:16 AM
9-3
SPECIFICATIONS FOR FIELD SUPPLIED
FUSES AND WIRES
Power supply wiring
Field fuses
Size
Model
FCQ18PVJU
FCQ24PVJU
FCQ30PVJU
15A
Clamp A
Transmission wiring
Wire
Size
Wire size
must comply Sheathed wire
with local
(2 wires)
codes.
P1 P2
10. WIRING EXAMPLE AND HOW TO SET
THE REMOTE CONTROLLER
10-1 HOW TO CONNECT WIRES
〈Methods of wiring power supply, units and connecting
remote controller wires〉
• Power supply wire
Remove the control box lid (2) and connect wires to the
power supply terminal block (3P) inside. In doing this, pull
the wires inside through rubber bush A and clamp the wires
along with other wires using clamp A, untightening the clip
of clamp A by pressing. After the connection, tighten clamp
A as before.
• Transmission wire and remote controller wire
Remove the control box lid (1) and pull the wires inside
through rubber bush B and connect to the transmission
terminal block (6P).
• After connection, attach sealing pad
(Be sure to attach it to prevent water from infiltrating the unit
from the outside.)
Sealing pad (Small)
(Wrap around the wire)
(Inside)
(Outside)
Rubber bush A
Lock nut
F1 F2
Remote
controller wire
T1
T2
Transmission
terminal block (6P)
Transmission wire
CAUTION
• Even if the control box lid (1)(2) is removed, pull the remote
controller wire, transmission wire and the power supply wire
inside the unit so that the wires do not come into contact
with the opening section of the metal casing.
• Pass conduits through the wall and secure along with the
refrigerant pipe in order to prevent external pressure being
applied to transmission wire and power supply wire.
• Arrange the wires and fix a lid firmly so that the lid does not
float during wiring work.
• Do not clamp remote controller wire and transmission wire
together with power supply wire. Doing so may cause
malfunction.
• Remote controller wire, transmission wire and power supply
wire should be located at least 5 in. from other electric
wires. Not following this guideline may result in malfunction
due to electrical noise.
WARNING
• Never connect power supply wiring to the terminal block for
remote controller wiring as this could damage the entire
system.
• Use only specified wire and connect wires to the terminal
tightly. Be careful wires do not place external stress on
terminals. Keep wires in neat order so as to not obstruct
other equipment. Make sure that the electric box lid fits
tightly. Incomplete connections could result in overheating
and, in worse case, result in electric shock or fire.
NOTE
Conduit
Field wire
NOTES®
s)FUSINGORMOREWIRESBREAKTHESMALL
sealing pad (Small) and wrap each wire.
L1 L2
Power supply
Power supply
terminal block (3P)
AWG
18-16
Allowable length of transmission wire and remote controller
wire are as follows.
(1) Outdoor unit – Indoor unit:
Max. 3280 ft.
(2) Indoor unit – Remote controller:
Max. 1640 ft.
"ESURETOATTACHITTOPREVENTTHEINFILTRATION
OFWATERASWELLASANYINSECTSANDOTHER
SMALLCREATURESFROMOUTSIDE
Otherwise a short-circuit may occur inside
the control box.
Rubber
Wrap pad tightly enough
bush
to prevent gapping.
Clip
Clamp A
Conduit
mounting
plate
Grounding
terminal
1. Use round crimp-style terminals for connecting wires to the
power supply terminal block.
If unavailable, observe the following points when wiring.
• Do not connect wires of different gauge to the same
power supply terminal.
(Looseness in the connection may cause overheating.)
Attach insulation sleeve
Power supply terminal
block (3P)
Rubber
bush A
Round crimp-style terminal
Rubber
bush B
Transmission
terminal block (6P)
Electric wire
Wiring diagram
Control box lid (2)
Control box lid (1)
English
01_EN_3PN06240-13Q.indd 10
10
2/6/2009 11:44:17 AM
1. When using 1 remote controller for 1 indoor unit.
(Normal operation)
Connect wires of
the same gauge to
both sides.
Power Supply
208-230V
~
Outdoor unit
Control box
60Hz
IN/D OUT/D
F1 F2 F1 F2
L1 L2
2. Tightening torque for the terminal screws.
• Use the correct screwdriver for tightening the terminal
screws. If the blade of screwdriver is too small, the head
of the screw might be damaged, and the screw will not be
properly tightened.
• If the terminal screws are tightened too hard, screws
might be damaged.
• Refer to the table below for the tightening torque of the
terminal screws.
Terminal
Size
Transmission terminal block (6P)
Power supply terminal block (3P)
M3.5
M4
10-2 WIRING EXAMPLE
• Fit the power supply wire of each unit with a switch and
fuse as shown in the drawing.
COMPLETE SYSTEM EXAMPLE
P1 P2 F1 F2 T1 T2
Indoor unit
P1 P2
Remote
controller
2. When using 2 remote controllers for 1 indoor unit.
Power Supply
208-230V
Outdoor unit
~
Control box
60Hz
Tightening torque
(ft.lbf)
0.58 - 0.72
0.87 - 1.06
3. Do not connect wires of different gauge to the same ground
terminal. Looseness in the connection may deteriorate
protection.
4. Outside of the unit, keep transmission wire at least 5 in.
away from power supply wire. The equipment may malfunction if subjected to electrical (external) noise.
5. For remote controller wire, refer to the “INSTALLATION
MANUAL OF REMOTE CONTROLLER” attached to the
remote controller.
IN/D OUT/D
F1 F2 F1 F2
L1 L2
L1 L2
P1 P2 F1 F2 T1 T2
Indoor unit
P1 P2
P1 P2
For use with
2 remote
controllers
NOTE
1. A single switch can be used to supply power to units on the
same system. However, branch switches and branch circuit
breakers must be selected carefully.
2. Do not ground the equipment on gas pipes, water pipes or
lightning rods, or crossground with telephones. Improper
grounding could result in electric shock.
Power supply wire
Power supply
Main
switch
L1 L2
Outdoor unit
Transmission wire
Switch
Fuse
10-3 CONTROL BY 2 REMOTE CONTROLLERS
(Controlling 1 indoor unit by 2 remote controllers)
• When using 2 remote controllers, one must be set to
“MAIN” and the other to “SUB”.
MAIN/SUB CHANGEOVER
(1) Insert a screw driver into the recess between the upper
and lower part of remote controller and, working from the
2 positions, pry off the upper part.
The remote controller PC board is attached to the upper
part of remote controller.
Indoor unit
Upper part of
remote controller
Remote controller
Insert the screwdriver here and
gently work off the upper part of
remote controller
11
01_EN_3PN06240-13Q.indd 11
Lower part of
remote controller
English
2/6/2009 11:44:17 AM
(2) Turn the MAIN/SUB changeover switch on one of the two
remote controllers PC boards to “S”.
(Leave the switch of the other remote controller set to “M”.)
(Factory setting)
S
M
Remote controller
PC board
Only one remote
controller needs to be
changed if factory
settings have remained
untouched.
S
M
11. FIELD SETTING
Make sure the control box lids are closed on the indoor
and outdoor units.
Field setting must be made from the remote controller in
accordance with the installation condition.
• Setting can be made by changing the “Mode No.”, “FIRST
CODE NO.”, and “SECOND CODE NO.”.
• For setting and operation, refer to the “FIELD SETTING” in
the installation manual of the remote controller.
SECOND
CODE NO.
Mode No.
FIRST
CODE NO.
FIELD SET
MODE
SETTING
10-4 COMPUTERISED CONTROL (FORCED OFF
AND ON/OFF OPERATION)
See “FIELD SETTING” on page 12 for local settings.
(1) Wire specifications and how to perform wiring
• Connect the input from outside to terminals T1 and T2
of the transmission terminal block.
F2
T1
T2
FORCED
OFF
Input A
Wire specification
Gauge
Length
External terminal
Sheathed vinyl wire or cable (2 wires)
AWG 18-16
Max. 328ft.
Contact that can ensure the minimum
applicable load of 15V DC, 10mA.
(2) Actuation
• The following table explains FORCED OFF and ON/
OFF OPERATIONS in response to Input A.
FORCED OFF
Input “ON” stops operation (impossible by
remote controllers.)
Input OFF enables control by remote
controller.
ON/OFF OPERATION
Input OFF → ON turns
ON unit.
Input ON → OFF turns
OFF unit.
(3) How to select FORCED OFF and ON/OFF OPERATION
• Turn the power on and then use the remote controller to
select operation.
10-5 CENTRALIZED CONTROL
• For centralized control, it is necessary to designate the
group No. For details, refer to the manual of each optional
controllers for centralized control.
• Set the remote controller to the field set mode. For details, refer to the “HOW TO SET IN THE FIELD”, in the
remote controller manual.
• When in the field set mode, select mode No. 12, then set
the first code (switch) No. to “1”. Then set second code
(position) No. to “01” for FORCED OFF and “02” for ON/
OFF OPERATION. (FORCED OFF at factory set)
SETTING AIR FILTER SIGN
• Remote controllers are equipped with liquid crystal display
air filer signs to display the time to clean air filters.
• Change the SECOND CODE NO. according to Table 5
depending on the amount of dirt or dust in the room.
(SECOND CODE NO. is factory set to “01” for filter contamination-light)
Table 5
Setting
Air filter
contaminationlight
Air filter
contaminationheavy
Spacing time of
display air
filter sign
(long life type)
Mode
No.
FIRST
CODE
NO.
Approx. 2500
hrs
01
10 (20)
Approx. 1250
hrs
SECOND
CODE NO.
0
02
〈When using wireless remote controllers〉
• When using wireless remote controllers, wireless remote
controller address setting is necessary. Refer to the installation manual attached to the wireless remote controller for
setting instructions.
12. INSTALLATION OF THE DECORATION
PANEL
Refer to the installation manual attached to the decoration
panel.
After installing the decoration panel, ensure that there is no
space between the unit body and decoration panel.
English
01_EN_3PN06240-13Q.indd 12
12
2/6/2009 11:44:18 AM
13. TEST OPERATION
Refer to the section of “FOR THE FOLLOWING ITEMS,
TAKE SPECIAL CARE DURING CONSTRUCTION AND
CHECK AFTER INSTALLATION IS FINISHED.” on page 3.
• Make sure if the service lids are closed on the indoor and
outdoor units.
• After finishing the construction of refrigerant pipe, drain pipe
and electric wire, conduct the check operation referring to
the installation manual of the outdoor unit.
• The operation lamp of the remote controller will flash when a
malfunction occurs. Check the malfunction code on the liquid
crystal display to identify the point of trouble. An explanation
of malfunction codes and the corresponding trouble is provided in the installation manual of the outdoor unit.
If any of the items in Table 6 are displayed, there may be a
problem with the wiring or power, so check the wiring again.
Table 6
Remote control display
“
” (under
centralized control) is lit up.
“U4” is lit up
“UH” is lit up
No display
Content
• There is a short circuit at the
FORCED OFF terminals (T1, T2)
• The power on the outdoor unit is off.
• The outdoor unit has not been wired
for power supply.
• Incorrect wiring for the transmission
wiring and / or FORCED OFF wiring.
• The transmission wiring is cut.
• The power on the indoor unit is off.
• The indoor unit has not been wired for
power supply.
• Incorrect wiring for the remote
controller wiring, the transmission
wiring and / or the FORCED OFF
wiring.
• The remote controller wiring is cut.
• If “U3” is lit up, the malfunction code shows the check
operation has not been performed yet.
(2) With the wireless remote controller.
(Refer also to the operation manual attached to the wireless remote controller)
When the operation stops due to trouble, the display on
the indoor unit flashes. In such a case, diagnose the fault
contents with the table on the Malfunction code list looking
for the Malfunction code which can be found by following
procedures. (NOTE 2)
(1) Press the INSPECTION /TEST OPERATION button,
“
” is displayed and “ 0 ” flashes.
(2) Press the PROGRAMMING TIME button and find the
unit No. which stopped due to trouble.
Number of beeps 3 short beeps Perform all the following operations
1 short beep
Perform (3) and (6)
1 long beep
No trouble
(3) Press the OPERATION MODE SELECTOR button
and upper figure of the Malfunction code flashes.
(4) Continue pressing the PROGRAMMING TIME button
unit it makes 2 short beeps and find the upper code.
(5) Press the Operation selector button and lower figure
of the Malfunction code flashes.
(6) Continue pressing the PROGRAMMING TIME button
unit it makes a long beep and find the lower code.
• A long beep indicate the Malfunction code.
NOTE)
1. In case wired remote controller. Press the INSPECTION /
TEST OPERATION button on remote controller, “
” starts
flashing.
2. Keep down the ON/OFF button for 5 seconds or longer in
the inspection mode and the above trouble history disappears, after the trouble code goes on and off twice, followed
by the code “ 00 ”(normal).
The display changes from the inspection mode to the
normal mode.
13-3 MALFUNCTION CODE LIST
13-1 TEST OPERATION
(1) Make sure if the gas side and the liquid side stop valves
are open.
(2) Electrify crank case heater for 6 hours.
(3) Confirm function of unit according to the operation manual.
NOTE
• Refer to the diagnoses below if the unit does not operate
properly.
13-2 CAUTIONS FOR SERVICING
With the power on. Troubles can be monitored on the
remote controller or the LED’s on the PC board of the
indoor unit.
 Trouble shooting with the display on the liquid crystal display
remote controller.
(1) With the wired remote controller. (NOTE 1)
When the operation stops due to trouble, operation lamp
flashed, and “
” and the Malfunction code are indicated
on the liquid crystal display. In such a case, diagnose the
fault contents by referring to the table on the Malfunction
code list it case of group control, the unit No. is displayed
so that the indoor unit no with the trouble can be recognized. (NOTE 2)
13
01_EN_3PN06240-13Q.indd 13
• For places where the Malfunction code is left blank, the
“
” indication is not displayed. Though the system continues operating, be sure to inspect the system and make
repairs as necessary.
• Depending on the type of indoor or outdoor unit, the malfunction code may or may not be displayed.
Code
A1
A3
A6
A7
A9
AJ
C4
C5
C9
CJ
E3
E4
Malfunction/Remarks
Indoor unit’s PC board faulty
Drain water level abnormal
Indoor fan motor overloaded, overcurrent or locked.
Air flow direction adjust motor is fault.
Drive for electronic expansion valve is fault.
Type set improper
Capacity data is wrongly preset. Or there is nothing
programmed in the data hold IC.
Sensor R2T for heat exchanger temperature is fault.
Sensor R3T for heat exchanger temperature is fault.
Sensor R1T for suction air temperature is fault.
Sensor for remote controller is fault.
The remote controller thermistor does not function, but
the system thermo run is possible.
High pressure abnormal (outdoor unit)
Low pressure abnormal (outdoor unit)
English
2/6/2009 11:44:18 AM
E5
E7
E9
F3
F6
H9
J3
J5
J6
J9
JA
JC
L4
L5
L8
L9
LC
P1
P3
P4
PJ
U0
U2
U3
U4
UF
U9
UA
English
01_EN_3PN06240-13Q.indd 14
Compressor motor lock malfunction
Outdoor fan motor lock malfunction
Outdoor fan instantaneous overcurrent malfunction
Electronic expansion valve faulty (outdoor unit)
Discharge pipe temperature abnormal (outdoor unit)
The refrigerant is overcharged.
Outdoor air thermistor faulty (outdoor unit)
Discharge pipe thermistor faulty (outdoor unit)
Suction pipe thermistor faulty (outdoor unit)
Heat exchanger thermistor faulty (outdoor unit)
Sensor for heat exchanger is fault.
Sensor for high pressure is fault.
Sensor for low pressure is fault.
Overheated heat-radiating fin (outdoor unit)
Inverter cooling defect.
Instantaneous overcurrent (outdoor unit)
Possible earth fault or short circuit in the compressor
motor.
Electric thermal (outdoor unit)
Possible electrical overload in the compressor or cut
line in the compressor motor.
Stall prevention (outdoor unit)
Compressor possibly locked.
Transmission malfunction between the outdoor control
units’ inverters (outdoor unit)
Open-phase (outdoor unit)
PC board temperature sensor malfunction (outdoor
unit)
Heat-radiating fin temperature sensor malfunction
(outdoor unit)
Type set improper (outdoor unit)
Capacity data is wrongly preset. Or there is nothing
programmed in the data hold IC.
Suction pipe temperature abnormal
Power source voltage malfunction
Includes the defect in K1M.
The check operation has not performed.
Transmission error (indoor unit – outdoor unit)
Miswiring between indoor and outdoor units or
malfunction of the PC board mounted on the indoor
and the outdoor units.
If UF is shown, the wire between the indoor and
outdoor units is not properly wired. Therefore,
immediately disconnect the power supply and correct
the wire. (The compressor and the fan mounted on the
outdoor unit may start operation independent of the
remote controller operation.) The power is not supplied
to outdoor unit.
Same transmission for in / outdoor unit is fault.
Miss setting for multi system
Setting is wrong for selector switch of multi-system.
(see switch SS2 on the main unit’s PC board)
14
2/6/2009 11:44:19 AM
3PN06240-13Q EM08A095A
00_CV_3PN06240-13Q.indd 2
(0902) HT
2/6/2009 11:38:57 AM