Text for tender

The unit includes motor and fan, cool -and/or heating coil, filter, main condensate tray and electrical connection. Al parts in contact with conditioned air are insulated. Total insulated main driptray with condensate connection. Side panels provided of knock-out system for quick and easy connecting of accessories. On the back provided of small opening for easy installation of the units.

The coils are made of copper tubes and alu fins, provided of a male connection (GAS) and an air nipple. Water connection are left or right and easy be changed on site. The fans are depending of the size made of different quantities of turbines. The total of the fan deck (motor and turbine) is dynamic balanced to avoid noise and are low in consumption. De motors are totally closed, split-condensator type including an overheating safety. Single phase 230 V / 50 Hz. The standard filter of polyester with metal frame is EU3.

The unit includes motor and fan, cool -and/or heating coil, filter, main condensate tray and electrical connection. Al parts in contact with conditioned air are insulated. Total insulated main driptray with condensate connection. Side panels provided of knock-out system for quick and easy connecting of accessories. On the back provided of small opening for easy installation of the units.

The coils are made of copper tubes and alu fins, provided of a male connection (GAS) and an air nipple. Water connection are left or right and easy be changed on site. The fans are depending of the size made of different quantities of turbines. The total of the fan deck (motor and turbine) is dynamic balanced to avoid noise and are low in consumption. De motors are totally closed, split-condensator type including an overheating safety. Single phase 230 V / 50 Hz. The standard filter of polyester with metal frame is EU3.

Specifications

2 PIPES (4R)

Cooling capacity1

Total cooling capacity [W]

Sensible cooling capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

2

3

4

FRESH-1

2581

2785

2856

1926

2092

2147

457

493

506

8.3

9.2

9.9

FRESH-2

5618

5924

6058

4048

4284

4388

988

1041

1065

12.8

14.1

14.6

FRESH-3

6966

7825

9016

4926

5585

6506

1229

1380

1590

11.8

14.5

18.6

FRESH-4

9140

11274

12010

6490

8144

8720

1614

1994

2127

12.4

18

20.2

FRESH-5

13329

15131

16014

9649

11081

11784

2373

2695

2859

16.8

21

22.8

FRESH-6

17979

22568

24480

13039

16688

18260

3182

4003

4348

12.1

18.2

21.1

FRESH-7

24818

27851

29589

18308

20801

22249

4430

4976

5298

22.8

22.8

32

Heating capacity2

Total heating capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

FRESH-1

2700

2900

2980

470

506

519

7

8.4

9

FRESH-2

6050

6410

6570

1054

1116

1144

11.9

13.2

13.8

FRESH-3

7350

8310

9630

1280

1447

1686

10.5

13.1

17

FRESH-4

9740

12240

13140

1696

2131

2289

11.1

17

18.9

FRESH-5

14640

16840

-

2550

2934

3132

15.8

20.2

22.6

FRESH-6

19840

25540

28020

3454

4449

4881

11.6

18.1

21.3

FRESH-7

27930

31820

34170

4865

5544

5952

22.7

28.6

32.4

Heating capacity3

Total heating capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

FRESH-1

3240

3480

3570

457

493

506

6.7

7.9

8.3

FRESH-2

7220

7640

7830

988

1041

1065

10.4

11.5

11.9

FRESH-3

8790

9930

11560

1229

1380

1590

9.6

11.8

15.2

FRESH-4

11640

14600

15660

1614

1994

2127

10.1

14.6

16.4

FRESH-5

17440

20030

21370

2372

2695

2859

13.6

17.1

18.9

FRESH-6

23620

30310

33210

3182

4003

4348

9.9

14.8

17.1

FRESH-7

33190

37740

40470

4430

4976

5298

18.9

23.2

25.9

Air flow [m³/h]

Static pressure [Pa]

Sound power level inlet [dB(A)]

Sound power level outlet [dB(A)]

Speed

2

3

4

2

3

4

2

3

4

2

3

4

FRESH-1

381

469

484

39

46

50

56

59

60

55

58

59

FRESH-2

939

1007

1039

44

50

55

67

67

68

64

64

65

FRESH-3

1092

1267

1528

37

50

73

55

59

63

57

60

66

FRESH-4

1470

1946

2128

50

88

106

58

64

68

59

66

70

FRESH-5

2349

2806

3052

50

72

86

67

70

73

66

71

75

FRESH-6

3161

4357

4916

26

50

63

61

69

72

61

70

74

FRESH-7

4776

5668

6232

50

72

86

70

74

76

69

75

78

Specifications

4 PIPES (4R + 2)

Cooling capacity1

Total cooling capacity [W]

Sensible cooling capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

2

3

4

FRESH-1

2662

2837

2896

1876

2002

2047

471

502

513

7.9

8.7

9.1

FRESH-2

5408

5634

5728

3888

4064

4138

952

991

1009

12

12.9

13.3

FRESH-3

6896

7725

8786

4876

5505

6326

1217

1363

1551

11.6

14.2

17.8

FRESH-4

8970

10924

11521

6370

7864

8331

1586

1934

2044

12

17

18.8

FRESH-5

13009

14511

15214

9389

10581

11134

2318

2589

2721

16.1

19.5

21.3

FRESH-6

17549

21768

23350

12689

16038

17320

3117

3878

4167

12.1

18.4

20.2

FRESH-7

23958

26171

27349

17608

19401

20369

4282

4687

4912

22.2

26.4

28.7

Heating capacity2

Total heating capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

FRESH-1

3660

3860

3930

321

338

345

10.5

11.5

11.9

FRESH-2

7180

7460

7580

630

654

665

15.1

16.1

16.6

FRESH-3

9080

10070

11380

797

883

997

7.7

9.2

11.4

FRESH-4

11760

14170

14930

1031

1242

1309

5.7

7.9

8.6

FRESH-5

17130

19040

19970

1502

1669

1751

12.7

15.2

16.6

FRESH-6

23600

29080

31190

2069

2550

2735

20.5

29.6

33.5

FRESH-7

31460

34360

35980

2758

3012

3155

19.6

22.8

24.8

Heating capacity3

Total heating capacity [W]

Water flow [l/h]

Water pressure drop [kPa]

Speed

2

3

4

2

3

4

2

3

4

FRESH-1

4130

4350

4430

362

382

390

12.7

14

14.5

FRESH-2

8110

8420

8560

712

740

752

18.4

19.7

20.3

FRESH-3

10260

11380

12860

901

1000

1130

9.4

11.2

13.9

FRESH-4

13300

16030

16900

1169

1408

1484

6.9

9.6

10.6

FRESH-5

19360

21520

22590

1702

1890

1984

15.5

18.6

20.3

FRESH-6

26640

32840

35230

2341

2885

3095

25

36.1

40.8

FRESH-7

35570

38850

40690

3124

3413

3574

23.9

27.9

30.3

Air flow [m³/h]

Static pressure [Pa]

Sound power level inlet [dB(A)]

Sound power level outlet [dB(A)]

Speed

2

3

4

2

3

4

2

3

4

2

3

4

FRESH-1

369

447

459

39

46

50

56

59

60

55

58

59

FRESH-2

894

944

966

44

50

55

67

67

68

64

64

65

FRESH-3

1079

1245

1478

37

50

73

55

59

63

54

60

66

FRESH-4

1437

1868

2014

50

88

106

58

66

68

59

67

70

FRESH-5

2275

2651

2844

50

72

86

67

70

72

66

71

74

FRESH-6

3062

4144

4598

26

50

63

61

69

72

61

70

74

FRESH-7

4548

5187

5562

50

72

86

70

74

76

69

75

78

1 Cooling capacity at inlet water temperature 7°C and outlet water temperature 12°C