3 FIRE RISK ASSESSMENT FIRE RISK ASSESSMENT 1. PREMISES PARTICULARS Premises Name: Gatehouse School Use of Premises: Educational establishment Address: Sewardstone Rd, Victoria Park, London E2 9JG Tel : Owner/Employer/Person in control of Workplace: Mr Robert Francis Headmaster Mr James Bishop Bursar Date of Risk Assessment: 6th October 2014 Date of Review: October 2015 Name and relevant details of the person who carried out the Fire Risk Assessment and/or standard used for assessment: Mr Ron Britten Health and safety consultant, Universal Safety Management Ltd, IFE- Fire Risk Assessment & Fire Emergency Plans/Fire Safety in the Workplace HM Government Guide to Fire Safety Risk Assessment for Educational Premises has been used as the standard for this assessment. 2. GENERAL STATEMENT OF POLICY Statement: A Health & Safety policy is issued to each employee. This includes a section on Fire Safety. It is the policy of Gatehouse School to protect all persons including employees, pupils, contractors and members of the public from potential injury and damage to their health which might arise from work activities. Gatehouse School will provide and maintain safe and healthy working conditions, equipment and system of work for all employees and provide such information, training and supervision as they need for this purpose. Gatehouse School will give a high level of commitment to health and safety and will comply with all statutory requirements. Signed: Print Name: Date:

4 3. MANAGEMENT SYSTEMS Commentary: The Fire Safety Management Plan is contained with the Health and Safety file and it kept in the Bursar's office. The plan confirms that a fire risk assessment will be completed to ensure adequate fire safety and will be reviewed as necessary. The fire risk assessment will follow the five step approach detailed in the HM Government fire safety risk assessment guide. The significant findings will be recorded. Any deficiencies identified by the fire risk assessment process will be prioritised and rectified accordingly. Although having overall responsibility for fire safety matters, the employer has made the Bursar (as a competent person) responsible for fire safety matters, which include the fire risk assessment and all matters appertaining to it. The Bursar is responsible for: Deciding the fire safety protective and preventative measures Ensuring they are implemented and communicated to other employees Routine periodic checks of all systems Fire Safety is an agenda item for the health and safety committee meetings. The other appointed persons are shown on the attached schematic. They will be responsible for the fire safety measures as shown. There are no other occupiers to inform of fire safety issues or to co-operate and co-ordinate with. The Bursar is responsible for monitoring the effectiveness of the fire risk assessment process and its implementation. Fire Drills are carried out every term. All fire training, routine checks and engineers tests of fire safety equipment are recorded in the Fire Log Book.

5 4. GENERAL DESCRIPTION OF PREMISES Description: The school comprises 2 buildings, one main building with a ground floor, plus 2 additional floors and 1st floor mezzanine in the staff room & caretaker store room. There is a basement/under-croft used as classrooms. Construction was completed 1901, constructed of stone, brick, concrete and timber with slate and bitumen roofing. Refurbishment/internal improvements took place on the following dates, summer 2014 internal office refurbishment, summer 2013 staff room mezzanine installed, 1st floor alterations and 2nd floor extension The second building referred to as New House, is a modern single floor prefabricated modular construction, located in the school grounds adjacent to the main building, constructed of brick and lightweight materials common to the building type. The premises are considered to be of low risk taking into account the likelihood of fire and likely consequences. In the event of fire there is little chance of anyone being placed at risk due to the fire safety measures in place. The main building has 3 internal stairways which are protected from all rooms on each floor by fire resisting walls, partitions and self-closing fire doors. This excludes WC accommodation as there is no fire risk in the WCs. There 3 external stairways from the under-croft The under-croft ceiling is finished with sound, fire-resisting concrete. Occupancy: Size: Times the Premises are in use: Building footprint approx. 600 M2 per level. The Total Number of Persons within Number of Floors: 4 (including the Premises at any one time: 380 mezzanine) pupils + 50 staff (numbers may increase when school performances are held and family members are Number of Stairs: 6 present) 5. FIRE SAFETY SYSTEMS WITHIN THE PREMISES Fire Warning System: Alarm control model: series 8000 (complies with BS55839 pt ) 12 zone addressable system linked to automatic smoke and heat detection plus manual break-glass call points. Additional smoke detection should be installed in the void above the main hall. Electrical wiring supplying the hall lighting, runs through this space and the smoke detectors installed on the ceiling below, will not give sufficient early warning in the event of fire in the ceiling void. Provide additional smoke detection in the ground floor classrooms in the main building (including the 2 adjacent to the Premises Managers room) and at the far end of the corridor nearest the main entrance and in the art room where the kiln is located. Emergency Lighting: Maintained 3hr duration (complies with BS55266) Other: Portable Fire-Fighting Equipment to BS EN3 provided in accordance with the Guide.

6 6. (Single line) PLAN DRAWING OF PREMISES

7

8 7. IDENTIFY FIRE HAZARDS Source of Ignition: The ignition sources are mainly those commensurate with school premises, being office electrical equipment such as computers, printers, photocopiers and laminator etc. and classroom IT equipment, including laptops, PCs and LCD projectors There are also gas boilers in the main building and New House and air conditioning units in various classrooms in both. The staff room contains items including toaster, kettle and microwave and convection oven and fridges. There are additional fridges and microwave ovens and convection oven and cooking range in the main building nursery and after school club kitchen. The only additional equipment of note is a kiln in the basement art room which runs on electricity. Smoking is not allowed on the premises. There are no other significant ignition sources within the workplace. Source of Fuel: The sources of fuel are those commensurate with school premises being furniture, stationery and combustible office equipment. Majority of the office work is completed on computers so there are not vast amounts of paper. Spare paper for printers etc is stored away in stationery cupboards. In addition there are school text books located in cupboards and on shelves (including the library) Waste paper bins are emptied every night and the waste is stored outside away from the building in metal bins. There is mains gas supplying the gas boilers. There were many bin bags full of plastic bottles stacked up against the 2 airconditioning units on the outside wall of New House. The emergency isolation switches cannot be accessed and the bottles are a source of fuel which could be ignited by any electrical fault arising from the air-conditioning units. Remove immediately. Source of Oxygen: Air-conditioning is self-contained in each supplied room and is not ducted through the building. There is therefore, no relevant hazard with oxygen supply for a potential fire. There are no additional sources of oxygen other than normal air. Work Processes: The work processes are commensurate with normal school and office premises. There are no processes that pose a significant fire hazard. There is no deep fat frying and large scale cooking processes. There are no hazardous science experiments taking place. The kiln may run at night, but is controlled by a timer. A competent electrician maintains all the portable electrical equipment by PAT testing and the installed electrical systems are inspected periodically in accordance with Institute of Electrical Engineers (IEE) recommendations. IT equipment is serviced by a resident engineer. The school policy is to close down

9 all unnecessary electrical equipment at night. Structural features that could promote spread of fire: This is an old building, completed in All services and compartments have been inspected by a building surveyor following and confirmed as adequately fire stopped at wall/floor penetrations. There are 2 mezzanine floors with false ceilings above the staff room kitchen area, after school club kitchen and to the New House. There is a large ceiling void above the main hall which is not partitioned. Arrange for inspection by an architect to assess if remedial works are required. Update the fire risk assessment following the inspection. 8. IDENTIFY PEOPLE AT RISK Identify and specify the location of people at significant risk in case of fire, indicating why they are at risk, and what controls are or need to be in place: Employees and pupils are distributed throughout the buildings. All staff are given an induction including all safety procedures on first being employed on the premises. This is acknowledged and recorded in their personnel file. Cleaning staff who work after normal working hours may be isolated in the building. These persons are given a safety induction including all fire safety procedures on first being employed on the premises, a copy of this is provided to the cleaning company who employs them. An agreement is in place that the cleaners employer will provide the staff with general fire safety training including the use of fire extinguishers. Evidence is supplied to confirm this. Visitors and contractors are signed in at reception. All contractors who may be working on the site have been accepted as approved contractors. General visitors are always accompanied by an employee who will brief them on the fire evacuation procedures and the alarm signal which is a siren/klaxon. Employees are made responsible for their guests during any evacuation. It was noted that at the time of carrying out this risk assessment, that there is not any formal permit to work or hot works policy currently in operation. At the present time there are no employees with disabilities. Visitors and contractors are invited by a clear notice at the premises signing-in book to inform reception of any disabilities that would prejudice their evacuation in an emergency. The Bursar is informed and suitable measures put in place to ensure their safe evacuation in the event of fire, in cases where it is obvious how to help them. Any unusual disability, where it is not so obvious what assistance may be needed, is checked by consulting the Government Fire Safety Risk Assessment Guide to Means of Escape for Disabled People. Some employees work late and may find themselves isolated in parts of the building during these times. Automatic fire detection provides early warning of fire. There fire evacuation drills every term, carried out at varying times of the day to ensure all staff and pupils take part at least twice a year and remain familiar with

10 the emergency procedures. Records are maintained in the fire log-book.

11 11. FIRE SAFETY SIGNS AND NOTICES Commentary: There are adequate fire safety signs and notices in the premises in accordance with the Guide. All emergency exit routes and doors are adequately signposted with green running-man. Fire Action tices are displayed beside each break glass. All self-closing fire doors display Fire Door Keep Shut signs. Fire doors to cupboards/store display Fire Door Keep Locked Shut signs. Fire extinguisher positions are marked by appropriate signs showing the type. 12. FIRE WARNING SYSTEM Commentary: The system is described in section 5 of this assessment and is a continuous siren/klaxon. It is a manual / electric fire warning system comprising manual call points and automatic smoke detection. It is audible in all areas and will warn all persons resorting to the building when operated. This is serviced 6 monthly by Chubb Ltd in accordance with British Standard It is tested weekly using a different break-glass point for each test. This is all in accordance with the Guide. 13. EMERGENCY LIGHTING SYSTEM Commentary: The system is described in section 5 of this assessment. It is an adequate maintained type emergency lighting system in accordance with the Guide. It is serviced annually by Chubb Ltd. It is checked monthly by simulating a lighting power failure / using test keys to make sure all lighting units work correctly. Tests are recorded by Lee Jenkins Premises Manager. 14. FIREFIGHTING EQUIPMENT Commentary: There are a sufficient number of fire extinguishers correctly mounted on wall brackets and located throughout the premises in accordance with the Guide. They are adequate for the risks within the premises and have been serviced within the last twelve months. Service contract with Chubb Ltd. who also advise as necessary if there are any issues with numbers or type of extinguishers provided. An extinguisher schedule is kept with the fire log-book to assist in monthly location and condition checks. 15. MANAGEMENT MAINTENANCE Is there a maintenance programme for the fire safety provisions in the premises: Commentary: All plug-in type electrical equipment is PAT tested annually by an external contractor and a register of all

12 equipment tested is kept in the fire safety file. PAT testing was last carried out February Building electrical installation last tested in 2010 and the report was seen. It is next due in The gas boilers are serviced annually by Gas-Safe registered contractor and reports are kept on file and were seen. Are regular checks of fire resisting doors, walls and partitions carried out: Commentary: There is no formal system for maintenance checks on fire doors, but there are daily visual checks. Arrange for a fire door specialist contractor to carry out checks every 6 months (This service may be available through your current fire safety maintenance contractor) Are regular checks of escape routes and exit doors carried out: Commentary: Monthly checks carried out by the Premises Manager and recorded. Are regular checks of fire safety signs carried out: Commentary: Checks are carried out by the Premises Manager but it wasn't confirmed at the time of the assessment on frequency. The current provision of signs indicated that effective checks are maintained. Is there a maintenance regime for the fire warning system: Commentary: Weekly check carried out by Weekly the Premises Manager and recorded. Six monthly test carried out by contractors Six monthly and recorded. Is there a maintenance regime for the emergency lighting system: Commentary: Monthly checks carried out by the Premises Manager and recorded. Annual check carried out by contractors and recorded. Monthly Annually Is there maintenance of the fire fighting equipment (by competent person?) and condition checks: Commentary: Monthly check carried out by the Monthly Premises Manager and recorded. Annual inspection carried out by contractors and recorded. Are records kept and their location identified; Commentary: Annually

13 The Fire Log Book for all aspects relating to maintenance issues is kept in the Premises Manager s office. A duplicate file is kept in the Bursars Office. All engineers testing paperwork is also kept in the Fire Log Book. 16. METHOD FOR CALLING THE FIRE SERVICE Specify: The Fire Brigade will be phoned by the Headmaster, Bursar or reception staff, or any other member of staff who has immediate access to the phone. The Headmaster will be informed immediately. There are plans to connect the alarm system to a call centre monitoring service provided by the alarm maintenance company (Chubb). The Bursar also mentioned the possibility of linking the alarm system to the local fire station. 17. EMERGENCY ACTION PLAN (EAP) Commentary: There is an Emergency Action Plan for fire, bomb threat and gas leak emergencies. The Emergency Action Plan for fire is attached at the end of this report. 18. TRAINING Commentary: There are 11 members of staff who have been allocated the role of fire wardens. This was carried out in Refresher training should take place every 3 years (due 2015) Fire extinguisher training (practical) was carried out April 2014 by an external trainer (the ex Bursar). Training records were available. Fire evacuation drills are carried out every term. Evacuation date, time of day, duration and outcomes are recorded in a log book.

14 19. FIRE SAFETY DEFICIENCIES TO BE RECTIFIED See Section:- Deficiency / Rectification Priority 5 Arrange for the installation of additional detection in the void above the main hall and in the classroom and corridor locations identified in section 5 7 Remove the large accumulation of bin bags containing plastic bottles, from around the airconditioning units on the outside wall of New House. 7 Arrange for the inspection of the roof void above the main hall by an architect to assess if it is necessary to install partitions, to prevent fire spread. 15 To be Completed within To be Completed by - name 3 3 months Premises Manager/ Bursar 1 1 week Premises Manager/ Bursar 3 3 months Premises Manager/ Bursar 3 3 months Currently no formal maintenance/servicing of fire door self-closing mechanisms. Checks to intumescent seals (where fitted). Contact fire door specialist contractor. 20. Date Rectified. Name and Signature Premises Manager GENERAL COMMENTS AND/OR OBSERVATIONS Item Control Measure/Action Deficiencies identified (see Section 19). Action required by Manager and Bursar. the Premises Additional hazards identified during the fire risk assessment, not included in the previous sections are listed in section 21. and require immediate action. Action required by Manager and Bursar. the Premises

15 21. ADDITIONAL HAZARDS Specify: Many classroom doors are wedged open by teaching staff which compromises the protected means of escape, by preventing fire doors from closing and therefore allowing the spread of fire and smoke. All wedges should be discarded with immediate effect and teaching staff made aware of the the fire safety hazard, resulting from the use of door wedges. Include door wedge removal and disposal as part of daily fire safety checks. Teaching staff need to be briefed on the importance of discontinuing the use of door wedges. Where classroom doors need to be kept open for child protection reasons, fit Chubb Dorgard (or equivalent) door holding units, to enable fire doors to be held open and then close on the activation of the alarm system. (Remove door wedges with immediate effect. Install Dorgard units within 3 months) Some classroom doors connecting on to the protected means of escape, do not have self closing mechanisms., such as 3T opposite the school office/reception and to the post room/bursars office entrance. Arrange for self closing mechanisms to be fitted to all other doors which connect to the protected means of escape. (Install self closing mechanisms within 3 months) Some of the children's lockers in New House and the main building were noted as being overfilled, resulting in their contents spilling onto the floor which are on main evacuation routes, presenting a tripping hazard which could impede escape. Some of the locker doors cannot be shut and are projecting into the evacuation routes. Ensure all lockers have unnecessary and oversized items removed to prevent items falling onto the fire escape routes and allow all locker doors to be closed securely. (Complete within 1 week) Need to consult Fire Service

17 EMERGENCY ACTION PLAN ASSEMBLY POINT PLAYGROUND ACTION ON DISCOVERY OF FIRE SOUND THE ALARM USING THE NEAREST FIRE ALARM CALL POINT LEAVE THE BUILDING BY THE NEAREST FIRE EXIT DO NOT RE-ENTER THE BUILDING REPORT TO THE ASSMBLY POINT CALL THE FIRE BRIGADE BY MOBILE PHONE (AFTER LEAVING THE BUILDING) LIAISE WITH THE FIRE BRIGADE ON THEIR ARRIVAL ONLY ATTEMPT TO TACKLE SMALL FIRES IF CONFIDENT TO DO SO DO NOT PUT YOURSELF AT RISK ACTION ON HEARING ALARM LEAVE THE BUILDING BY THE NEAREST EXIT DO NOT RE-ENTER THE BUILDING REPORT TO THE ASSEMBLY POINT CALL THE FIRE BRIGADE BY MOBILE PHONE (AFTER LEAVING THE BUILDING) LIAISE WITH THE FIRE BRIGADE ON THEIR ARRIVAL VISITORS ENSURE ALL VISITORS AND CONTRACTORS ARE TAKEN TO THE ASSMBLY POINT ASSIST ANY DISABLED PERSONS WITH THEIR EVACUATION AS NECESSARY ALTERNATIVE ACCOMMODATION IN THE EVENT OF BEING UNABLE TO RETURN TO THE BUILDING IN A SHORT TIME, ARRANGEMENTS HAVE BEEN MADE WITH ** ** TO PROVIDE TEMPORARY SHELTER AND OFFICE FACILITIES. BACK-UP COMPUTER RECORDS AND PHONE DIVERSIONS ARE AVAILABLE THERE TO ASSIST WITH BUSINESS CONTINUITY.

CITY OF LONDON SCHOOL FOR GIRLS FIRE SAFETY, PROCEDURE AND RISK ASSESSMENT POLICY This policy was written in July 2014 and will be agreed by the Board of Governors in October 2014. To be reviewed by June

Fire risk assessment a guide for businesses Disclaimer Cornwall Fire and Rescue Service provide this guide to assist businesses to improve fire safety in their premises, but stress the person completing

1 Sources of ignition The main sources of ignition in Cass building are: PAF arrange for the fixed electrical installation to be tested in accordance with the British Standards. Test certificates are kept

fire risk assessment For use by landlords of small premises Premises Address FIRE RISK ASSESSMENT for use by landlords of small premises Person having control of the premises: Name of landlord (if different):

RECORD OF FIRE SAFETY RISK ASSESSMENT Building Name & Use: Address: Postcode: Name of person(s) with fire safety duties: Name and contact details of assessor: Date of Assessment: 6 th February 2011 Laurel

Fire Safety Risk Assessment This form is to aid you in carrying out a fire safety risk assessment of a property. The form is separated in to two parts: Part 1 initial assessment form and guidance notes

Fire Risk Assessment For Simple Premises Responsible Person (Employer or other person having control of the relevant premises) Company / Premises Name Address of Premises Postcode Primary Use of Premises

fire risk assessment For use by landlords of small premises Premises Address FIRE RISK ASSESSMENT for use by landlords of small premises Person having control of the premises: Name of landlord (if different):

Checklist for Residential Care Premises Name of Premises: Address of Premises: Name of Responsible Person: What area / location does the assessment cover? Does the assessment cover the whole site YES or

Checklist for Educational Premises Name of Premises: Address of Premises: Name of Responsible Person: What area / location does the assessment cover? Does the assessment cover the whole school YES or NO?

The Clare School South Park Avenue Norwich Norfolk NR4 7AU Regulatory Reform (Fire Safety) Order 2005 FIRE RISK ASSESSMENT Name and address: Use of premises: Owner: Responsible person: The Clare School

HMO Information Sheet No 1 FIRE DETECTION AND ALARM SYSTEMS 1. Introduction When a property is in multiple occupation, the risk of fire breaking out is greater than in an ordinary single family home. Some

Fire Risk Assessment Safety Checklist This checklist has been prepared to help you comply with The Regulatory Reform Fire Safety Order 2005 What is the Regulatory Reform (Fire Safety) Order 2005? The Regulatory

SBR FIRE RISK ASSESSMENT Report of audit and inspection Premises Details Occupier Premises Address Premises Description Times premises are in use Use and maximum no. people present The British School of

Fire Risk assessment 1.0 APPOINTMENTS 1.1 Responsible Person. In compliance with the Regulatory Reform (Fire Safety) Order 2005 (FSO) the School s Head, Mrs J M Miles is appointed as the Responsible Person

London Borough of Barnet Fire Safety in Houses in Multiple Occupation A Guide to Landlords March 2016 Contents Introduction p.3 Summary of main requirements p.3 Fire Safety Precautions p.4 Protecting the

Fire Risk Assessment for Simple Premises Guidance Notes The UK s national fire safety organisation Protecting people, property, business and the environment Introduction This guide and the accompanying

FIRE SAFETY RECORD OF TESTS LOGBOOK PREMISES ADDRESS: Responsible person AN INTRODUCTION TO YOUR LOG BOOK The Regulatory Reform (Fire Safety) Order 2005 requires the responsible person for a premises to

AVAILABLE TO DOWNLOAD ON THE APOLLO APP a guide to Fire Alarm Systems Design BS5839 Part1:2013 The Regulatory Reform (Fire Safety) Order (FSO) became law on 1 October 2006 Legally you must comply! What

REGULATORY REFORM (FIRE SAFETY) ORDER 2005 FIRE RISK ASSESSMENT This template has been provided to assist the Responsible Person with the preparation of a Fire Risk Assessment and is not intended for commercial

NORTH BIRMINGHAM ACADEMY FIRE AND EVACUATION PROCEDURES FIRE DRILLS: These are carried out once a term. Observations and details of each drill are recorded in the logbook, which is kept by the Assistant

PART 3/8 PRESTON CITY COUNCIL GUIDANCE OF MEANS OF ESCAPE FROM FIRE in HOUSES IN MULTIPLE OCCUPATION (HMO s) This guidance summarises the current standards for fire protection in HMO s which will satisfy

FIRE SAFETY PROCEDURES, ST MARY S CAMPUS MEDICAL SCHOOL BUILDING These notes supplement the Imperial College London Fire Safety Policy and Code of Practice and give details of local fire safety management

Schedule of works for a three storey + HMO with a typical entrance hallway, single staircase layout with rooms leading off the main hallway and landing areas To provide Adequate Means of Escape in case

Conditions of Hire (Rooms 20.1.1.1 and Halls) Grou Page 1 of 6 Conditions of Hire 1. Hirer: The Hirer is you the person who completes the agreement and signs the conditions of hire. 2. Availability The

Fire Safety Requirements for Child Care Centre A. Restrictions on Location Child care centre shall not be located : - (a) (b) in any premises designed for residential use; in any industrial building, warehouses,

FIRE ACTION PLAN COLLEGE OF PHYSICAL SCIENCES May 2014 CONTENTS Introduction... 2 Definitions... 2... 3 1. How people are warned if there is a fire... 3 2. Action on discovering a fire... 3 3. Action on

PAGE: 1 OF 14 Maidenhead and District Housing Association Fire Safety Policy and Management System Page 1 of 15 PAGE: 2 OF 14 FOREWORD This document details the system for the management of fire safety

Fire Log Book Provided by Norfolk Fire & Rescue Service Name and address of premises:... Storage location of fire risk assessment: This logbook should be kept in a secure location on the site or building

The British Section SHAPE International School Aims Security Policy and Procedures The aim of this policy is to ensure that the school can operate on a day-to-day basis in an environment that is safe and

Fire Safety Guidance Private Sector Housing Including HOUSES IN MULTIPLE OCCUPATION 1 HOW THIS GUIDANCE DOCUMENT IS TO BE USED This document is intended to give guidance on relevant fire safety provisions

The Imperial College Healthcare NHS Trust A guide to your onsite key worker accommodation Welcome to the accommodation at the Imperial College Healthcare NHS Trust. We hope you enjoy your stay. This guide

Fire Risk Assessment A Guide A Fire Risk Assessment is a tool to identify potential fire hazards and enable actions to be taken to remove or reduce these hazards to as low a level as practically possible

HYDE PARK SCHOOL, Marble Arch CRISIS MANAGEMENT PLAN Statement In the event of an emergency at Hyde Park School, the safety of everyone in the school community and preservation of life will override all

FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS The attached self-inspection form is intended for staff use at regular, frequent intervals. It should not take the place of two other vital measures

General Inspection FIRE SAFETY SELF-INSPECTION FORM FOR CULTURAL INSTITUTIONS 1. All Floors (inspect from top floor to basement): Yes are fire exits and directional signs properly illuminated? is the emergency

BRITISH SCHOOL OF GENEVA HEALTH AND SAFETY POLICY The Health and Safety Policy of the British School of Geneva aims to safeguard the health and safety of all its pupils and employees as well as visitors

NFG27 FIRE RISK ASSESSMENT PRINCIPLES A GUIDE FOR LICENSED PREMISES The Workplace Fire Precautions Legislation brings together existing Health & Safety and Fire Legislation to form a set of dedicated Fire

Document F SPECIFIC GUIDANCE FOR A HOUSE IN MULTIPLE OCCUPATION (HMO) CONVERTED ENTIRELY INTO SELF CONTAINED FLATS This document is intended as a specific guide for persons who own, manage or control Houses

THE REQUIREMENTS This section of this Complying Document/Complimentary Guide? deals ways of meeting the following requirements in Part B of Schedule 1 to the Building Regulations 2000 (as amended) when

Law No. (9) of 2012 Amending some provisions of Law No. (13) of 1997 Concerning the Civil Defense We, Hamad Bin Khalifa Al-Thani, Emir of the State of Qatar Having pursued the Constitution, And the Law