ASTM A861 - 04(2017) en

Over deze norm

1.1 This specification covers high-silicon iron pipe and pipe fittings intended for corrosion-resistant service for both above- and below-grade construction.

1.2 The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.

1.3 Pipe and pipe fittings shall be the no-hub (MJ) or the hub and plain end design.

1.4 Pipe and pipe fittings shall be of the sizes specified in Table 1 and Table 2 and Figs. 1-71 or other sizes that shall be permitted to conform to the requirements given herein.

TABLE 1 Tolerances for High-Silicon Iron Hub/Plain-End Pipe

Note 1:1 in. = 25.4 mm.

Size, in.

Wall Thickness, in.

ID Tolerance, in.

OD Tolerance, in.

2

±1/32

±1/32

±1/32

3

±1/32

±1/32

±1/32

4

±1/32

±1/32

±1/32

6

±1/32

±1/32

±3/64

8

±1/32

±1/8

±1/8

10

±1/8

±1/8

±1/8

12

±1/8

±1/8

±1/8

15

±1/8

±1/8

±1/8

TABLE 2 Tolerances for High-Silicon Iron Fittings

Note 1:1 in. = 25.4 mm.

Size, in.

ID Tolerance, in.

OD Tolerance, in.

Stop Lug Depth Tolerance, in.

11/2

±1/16

±1/16

±1/16

11/2 × 11/2

±1/16

±1/16

±1/16

2

±1/16

±1/16

±1/16

2 × 11/2

±1/16

±1/16

±1/16

2 × 2

±1/16

±1/16

±1/16

3

±1/16

±1/16

±1/16

3 × 11/2

±1/16

±1/16

±1/16

3 × 2

±1/16

±1/16

±1/16

3 × 3

±1/16

±1/16

±1/16

4

±1/16

±1/16

±1/16

4 × 11/2

±1/16

±1/16

±1/16

4 × 2

±1/16

±1/16

±1/16

4 × 3

±1/16

±1/16

±1/16

4 × 4

±1/16

±1/16

±1/16

TABLE 3 Chemical Composition

Element

Composition, Weight %

Grade 1

Grade 2

Carbon

0.65–1.10

0.75–1.15

Manganese

1.50 max

1.50 max

Silicon

14.20–14.75

14.20–14.75

Chromium

0.50 max

3.25–5.00

Molybdenum

0.50 max

0.40-0.60

Copper

0.50 max

0.50 max

FIG. 1 No-Hub Pipe (MJ)

Size, in.

J, in.

F, in.

t, in.

11/2

23/16 (2.19)

84

5/16

2

211/16 (2.69)

84

5/16

3

349/64 (3.77)

84

5/16

4

449/64 (4.77)

84

5/16

Note 1:1 in. = 25.4 mm.

FIG. 2 Quarter Bends

Size, in.

D, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

41/4

11/2

23/16 (2.19)

11/32

2

41/2

2

25/8 (2.62)

11/32

2 × 11/2

43/16 × 41/2

2 × 11/2

25/8 × 23/16

11/32

3

5

3

33/4 (3.75)

11/32

4

51/2

4

43/4 (4.75)

11/32

Note 1:1 in. = 25.4 mm.

FIG. 3 Sixth Bends

Size, in.

D, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

3

11/2

23/16

11/32

2

31/4

2

25/8

11/32

3

31/2

3

33/4

11/32

4

33/4

4

43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 4 Return Bends

Size, in.

C, in.

D, in.

F, in.

R, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 2

4 43/4

2 2

53/32 511/16

2 23/8

11/22

23/16 25/8

11/3211/32

Note 1:1 in. = 25.4 mm.

FIG. 5 Double-Branch Quarter Bend

Size, in.

D, in.

E, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

37/8

33/4

11/2

23/16

11/32

Note 1:1 in. = 25.4 mm.

FIG. 6 Eight Bends

Size, in.

D, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

21/2

11/2

23/16

11/32

2

23/4

2

25/8

11/32

3

3

3

33/4

11/32

4

31/4

4

43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 7 Sixteenth Bends

Size, in.

D, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

2

11/2

23/16

11/32

2

21/8

2

25/8

11/32

3

21/4

3

33/4

11/32

4

23/8

4

43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 8 Long-Sweep Quarter Bends

FIG. 9 Sanitary Y Branches

Size, in.

D, in.

F, in.

G, in.

ID, in

OD, in.

Stop Lug Depth (P), in.

1/2 × 11/2

45/8

61/2

17/8

11/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

47/8

61/2

15/8

2 × 11/2

25/8 × 23/16

11/32

2 × 2

45/8

63/8

2

2 × 2

25/8 × 25/8

11/32

3 × 11/2

55/8

61/2

11/4

3 × 11/2

33/4 × 23/16

11/32

3 × 2

57/8

71/8

11/2

3 × 2

33/4 × 25/8

11/32

3 × 3

63/8

85/8

21/4

3 × 3

33/4 × 33/4

11/32

4 × 11/2

65/8

71/2

13/8

4 × 11/2

43/4 × 23/16

11/32

4 × 2

65/8

71/2

13/8

4 × 2

43/4 × 25/8

11/32

4 × 3

71/8

83/4

13/4

4 × 3

43/4 × 33/4

11/32

4 × 4

75/8

101/4

25/8

4 × 4

43/4 × 43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 10 Double-Branch Sanitary Y

Size,

D,

F,

G,

ID,

OD,

Stop Lug

in.

in.

in.

in.

in.

in.

Depth (P), in.

11/2 × 11/2

45/8

61/2

17/8

11/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

47/8

61/2

15/8

2 × 11/2

25/8 × 23/16

11/32

2 × 2

45/8

63/8

2

2 × 2

25/8 × 25/8

11/32

3 × 11/2

55/8

61/2

11/4

3 × 11/2

33/4 × 23/16

11/32

3 × 2

57/8

71/8

11/2

3 × 2

33/4 × 25/8

11/32

3 × 3

63/8

85/8

21/4

3 × 3

33/4 × 33/4

11/32

4 × 2

65/8

71/2

13/8

4 × 2

43/4 × 25/8

11/32

4 × 3

71/8

83/4

13/4

4 × 3

43/4 × 33/4

11/32

4 × 4

75/8

101/4

25/8

4 × 4

43/4 × 43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 11 Sanitary Combination Y and 1/8 Bend

Size, in.

D, in.

E, in.

F, in.

G, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 × 11/2

43/4

53/8

61/2

17/8

1/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

43/4

53/4

61/2

15/8

2 × 11/2

25/8 × 23/16

11/32

2 × 2

5

57/8

65/8

17/8

2 × 2

25/8 × 25/8

11/32

3 × 11/2

4

51/4

61/2

15/8

3 × 11/2

33/4 × 23/16

11/32

3 × 2

5

61/4

71/8

11/2

3 × 2

33/4 × 25/8

11/32

3 × 3

61/4

7

81/2

21/4

3 × 3

33/4 × 33/4

11/32

4 × 11/2

45/16

61/8

65/8

13/8

4 × 11/2

43/4 × 23/16

11/32

4 × 2

5

63/8

73/8

13/8

4 × 2

43/4 × 25/8

11/32

4 × 3

6

71/4

83/4

13/4

4× 3

43/4 × 33/4

11/32

4 × 4

73/8

8

101/4

25/8

4× 4

43/4 × 43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 12 Double-Branch Sanitary Combination Y and 1/8 Bend

Size, in.

D, in.

E, in.

F, in.

G, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 × 11/2

43/4

53/8

61/2

77/8

11/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

43/4

53/4

61/2

15/8

2 × 11/2

25/8 × 23/16

11/32

2 × 2

5

57/8

65/8

15/8

2 × 2

25/8 × 25/8

11/32

3 × 11/2

41/4

51/4

61/2

15/8

3 × 11/2

33/4 × 23/16

11/32

3 × 2

5

61/4

71/8

11/2

3 × 2

33/4 × 25/8

11/32

3 × 3

61/4

7

81/2

21/4

3 × 3

33/4 × 33/4

11/32

4 × 2

5

63/8

73/8

13/8

4 × 2

43/4 × 25/8

11/32

4 × 3

6

71/4

83/4

13/4

4 × 3

43/4 × 33/4

11/32

4 × 4

73/8

8

101/4

25/8

4 × 4

43/4 × 43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 13 Sanitary T Branches

Size, in.

E, in.

F, in.

G, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 × 11/2

41/4

63/4

41/4

11/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

41/2

63/4

41/4

2 × 11/2

25/8 × 23/16

11/32

2 × 11/2 × 11/2

41/2

63/4

41/4

2 × 11/2 × 11/2

25/8 × 23/16 × 23/16

11/32

2 × 2

41/2

67/8

41/2

2 × 2

2 5/8 × 25/8

11/32

3 × 11/2

5

63/4

41/4

3 × 11/2

33/4 × 23/16

11/32

3 × 2

5

71/4

41/2

3 × 2

33/4 × 2 5/8

11/32

3 × 3

5

83/8

5

3× 3

33/4 × 33/4

11/32

4 × 11/2

59/16

67/8

47/32

4× 11/2

43/4 × 23/16

11/32

4 × 2

51/2

71/4

41/2

4 × 2

43/4 × 25/8

11/32

4 × 3

51/2

81/4

5

4 × 3

43/4 × 33/4

11/32

4 × 4

51/2

93/8

51/2

4 × 4

43/4 × 43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 14 Double-Branch Sanitary T

Size, in.

E, in.

F, in.

G, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 × 11/2

41/4

63/4

41/4

11/2 × 11/2

23/16 × 23/16

11/32

2 × 11/2

41/2

63/4

41/4

2 × 11/2

25/8 × 23/16

11/32

2 × 2

41/2

67/8

41/2

2 × 2

25/8 × 25/8

11/32

3 × 11/2

5

63/4

41/4

3 ×11/2

33/4 × 23/16

11/32

3 × 2

5

71/4

41/2

3 × 2

33/4 × 25/8

11/32

3 × 3

5

83/8

5

3 × 3

33/4 × 33/4

11/32

4 × 2

51/2

71/4

41/2

4 × 2

43/8 × 25/8

11/32

4 × 3

51/2

81/4

5

4 × 3

43/4 × 33/4

11/32

4 × 4

51/2

93/8

51/2

4 × 4

43/8 × 43/8

11/32

Note 1:1 in. = 25.4 mm.

FIG. 15 Sanitary Running Traps

Size, in.

A, in.

B, in.

C, in.

D, in.

J, in.

R, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

23/4

15/8

5

10

4

13/4

11/2

23/16

11/32

2

31/2

115/16

51/2

11

4

2

2

25/8

11/32

3

4

25/16

61/2

13

51/2

21/2

3

33/4

11/32

4

41/2

3

71/2

15

61/2

3

4

43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 16 Sanitary P Traps

Size, in.

A, in.

B, in.

C, in.

D, in.

J, in.

R, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

33/4

15/8

31/2

63/4

4

13/4

11/2

23/16

11/32

2

4

115/16

4

71/2

4

2

2

25/8

11/32

3

41/2

25/16

5

9

51/2

21/2

3

33/4

11/32

4

5

3

6

101/2

61/2

3

4

43/4

11/32

Note 1:1 in. = 25.4 mm.

FIG. 17 Swivel Trap P-Style, Short

Size, in.

C, in.

D, in.

E, in.

F, in.

G, in.

H, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 2

83/4 93/4

4 41/2

615/16 73/4

57/16 53/4

13/32 13/8

121/2 12

11/2 2

23/16 25/8

11/3211/32

Note 1:1 in. = 25.4 mm.

FIG. 18 Swivel Trap P-Style, Long

Size, in.

CA, in.

D, in.

E, in.

F, in.

G, in.

HA, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

123/4

4

615/16

57/16

13/32

121/2

11/2

23/16

11/32

(A)For shorter C or H dimension, snap-cut to desired length.

Note 1:1 in. = 25.4 mm.

FIG. 19 Swivel Type-S Style, Long

Size, in.

C, in.

F, in.

G, in.

H, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2 2

6 63/8

8 101/2

143/8 12

223/4 175/8

11/2 2

23/16 25/8

11/3211/32

Note 1:1 in. = 25.4 mm.

FIG. 20 Centrifugal Drum Trap P Swivel Type

FIG. 21 Centrifugal Drum Trap S Swivel Type

Size, in.

C, in.

D, in.

E, in.

F, in.

J, in.

ID, in.

OD, in.

Stop Lug Depth (P), in.

11/2

4

53/32

63/4

123/4

4

11/2

11/8

11/32

11/2

4

1515/32

63/4

123/4

4

11/2

11/8

11/32

2

43/4

511/16

79/16

141/4

43/4

2

2

11/32

Note 1:1 in. = 25.4 mm.

FIG. 22 Combination Cleanout and Test Tees

Size, in.

B, in.

E, in.

F, in.

G, in.

2

27/16

33/4

67/8

37/16

3

33/8

411/16

83/8

43/16

4

37/8

57/16

93/8

411/16

Note 1:1 in. = 25.4 mm.

FIG. 23 Coupling

Size, in.

A, in.

B, in.

11/2

33/8

27/8

2

4

33/8

3

47/16

43/16

4

415/16

53/16

Note 1:1 in. = 25.4 mm.

FIG. 24 Pipe Plugs

Size, in.

F, in.

1/2

2

2

21/2

3

21/2

4

21/2

Note 1:1 in. = 25.4 mm.

FIG. 25 Cleanout Plugs

Size, in.

A, in.

D, in.

E, in.

F, in.

11/2

23/16

21/4

15/16

39/16

2

221/32

21/4

15/16

39/16

3

33/4

21/2

13/8

37/8

4

43/4

23/4

17/16

43/16

Note 1:1 in. = 25.4 mm.

FIG. 26 Adapter/Hub to No-Hub

Size, in.

A, in.

B, in.

E, in.

F, in.

11/2 × 11/2

323/32

21/4

9/16

45/8

11/2 × 2

313/16

221/32

9/16

45/8

11/2 × 3

313/16

313/16

9/16

45/8

11/2 × 4

313/16

413/16

9/16

47/8

2 × 2

45/16

223/32

5/8

51/8

2 × 3

45/16

313/16

5/8

43/4

2 × 4

45/16

413/16

5/8

5

3 × 3

55/16

313/16

11/16

53/8

4 × 4

69/32

47/8

11/16

59/16

Note 1:1 in. = 25.4 mm.

FIG. 27 Reducers-Increasers

Size, in.

B, in.

F, in.

2 × 11/2

11/2

8

3 × 11/2

11/2

8

3 × 2

11/2

8

4 × 11/2

11/2

8

4 × 2

11/2

8

4 × 3

11/2

8

Note 1:1 in. = 25.4 mm.

FIG. 28 Sink Outlet

Size, in.

A, in.

B, in.

C, in.

D, in.

E, in.

F, in.

11/2

0 to 2

101/4

17/8

35/16

1/4

23/16

Note 1:1 in. = 25.4 mm.

FIG. 29 Sink Overflows

A, in.A

B, in.A

C, in.

4

61/8

1

6

81/8

1

8

101/8

1

(A)Dimension A and B will vary depending upon the sink strainer in which overflow is placed, depth of counterbore, and so forth, Dimension B is given only as a guide.

Note 1:1 in. = 25.4 mm.

FIG. 30 Threaded Adapters

Type

Size, in.

AD-7

11/2 Outlet to 11/2 MJ

AD-8

11/2 Outlet to 2 MJ

AD-10

2 Outlet to 2 MJ

Note 1:1 in. = 25.4 mm.

FIG. 31 Trap Cleanout Details

Note 1:1 in. = 25.4 mm.

FIG. 32 Adapter – No-Hub and Split Flange

Size, in.

A, in.

J, in.

2

53/4

6

3

7

71/2

4

8

9

Note 1:Flange dimensions are 150 lb ANSI standard.

Note 2:1 in. = 25.4 mm.

FIG. 33 MJ to Lead Adapter

Type

Size, in.

B, in.

C, in.

D, in.

AD-11 AD-12

11/2 2

21/4 223/32

11/211/2

125/32 29/32

Note 1:1 in. = 25.4 mm.

FIG. 34 Floor Drains

Note 1:1 in. = 25.4 mm.

FIG. 35 Hub and Plain End Pipe

Size, in.

A, in.

B, in.

C, in.

D, in.

E, in.

F, in.

2

49/16

43/16

35/16

21/32

211/16

25/8

3

55/16

53/16

45/16

31/8

325/32

25/8

4

63/8

63/16

55/16

41/8

425/32

25/8

6

817/32

811/32

75/16

515/16

611/16

3

8

111/4

103/4

95/8

81/4

9

3

10

141/4

133/4

121/4

10

111/4

37/8

12

163/4

16

141/2

12

131/4

4

15

201/4

193/4

173/4

15

163/4

41/8

Size, in.

t, in.

Weight, lb

Working Length, ft

Overall Length

2

5/16

0.31

7

7 ft 25/8 in.

3

5/16

0.31

7

7 ft 25/8 in.

4

5/16

0.31

7

7 ft 25/8 in.

6

13/32

0.40

7

7 ft 3 in.

8

13/32

0.40

7

7 ft 3 in.

10

5/8

0.62

7

7 ft 37/8 in.

12

5/8

0.62

5

5 ft 4 in.

15

7/8

0.75

5

5 ft 41/8 in.

Note 1:1 in. = 25.4 mm.

FIG. 36 Straight Tees

Size, in.

Weight, lb

A, in.

B, in.

C, in.

2 × 11/2

11

81/2

17/8

65/8

2 × 2

12

9

2

7

3 × 2

17

9

21/2

613/16

3 × 3

19

10

21/2

71/2

4 × 2

20

9

3

7

4 × 3

221/2

10

3

71/4

4 × 4

26

11

3

8

Note 1:1 in. = 25.4 mm.

FIG. 37 Sanitary T Branches

Size, in.

Weight, lb

A, in.

B, in.

C, in.

2 × 11/2

11

81/2

31/2

63/4

2 × 2

12

9

31/2

7

3 × 11/2

16

81/2

4

63/4

3 × 2

18

9

4

7

3 × 3

20

10

4

71/2

4 × 11/2

18

81/2

41/2

63/4

4 × 2

19

9

41/2

7

4 × 3

26

10

41/2

71/2

4 × 4

28

11

41/2

8

6 × 2

31

9

51/2

7

6 × 3

33

10

51/2

71/2

6 × 4

35

11

51/2

8

6 × 6

50

13

51/2

9

8 × 4

62

105/8

61/4

8

8 × 6

65

141/2

65/8

101/2

8 × 8

113

19

65/8

131/2

10 × 6

130

141/4

75/8

101/2

10 × 10

180

21

73/4

141/2

12 × 8

187

19

83/4

131/2

Note 1:1 in. = 25.4 mm.

FIG. 38 Sanitary Y Branches

Size, in.

Weight, lb

A, in.

B, in.

C, in.

2 × 11/2

11

85/8

43/8

43/8

2 × 2

12

9

41/4

43/4

3 × 11/2

16

85/8

51/16

37/8

3 × 2

17

9

5

43/16

3 × 3

21

101/2

51/2

5

4 × 11/2

17

91/8

513/16

37/8

4 × 2

21

9

53/4

311/16

4 × 3

26

101/2

61/4

41/2

4 × 4

30

12

63/4

51/4

6 × 2

28

9

71/8

211/16

6 × 3

35

101/2

75/8

31/2

6 × 4

45

121/4

81/4

41/4

6 × 6

60

143/4

91/8

53/4

8 × 2

60

167/8

9

41/2

8 × 3

63

121/8

9

33/4

8 × 4

65

131/2

10

41/2

8 × 6

79

161/2

11

61/16

8 × 8

117

191/2

121/4

71/4

10 × 4

160

131/2

111/2

31/2

10 × 6

165

165/8

131/2

37/8

10 × 8

170

193/4

143/8

43/8

10 × 10

180

221/2

15

75/8

12 × 4

173

181/4

153/16

41/2

12 × 6

196

181/4

161/2

41/2

12 × 8

200

233/8

151/2

5

12 × 10

275

27

191/2

6

12 × 12

288

251/2

183/8

71/4

15 × 15

455

321/8

223/4

81/8

Note 1:1 in. = 25.4 mm.

FIG. 39 Double-Branch Sanitary Tee

FIG. 40 Double-Branch Sanitary Y

Size, in.

Weight, lb

A, in.

B, in.

C, in.

2 × 11/2

14

85/8

43/8

43/8

2 × 2

15

9

41/4

43/4

3 × 11/2

19

85/8

51/16

37/8

3 × 2

20

9

5

43/16

3 × 3

28

101/2

51/2

5

4 × 11/2

21

91/8

513/16

37/8

4 × 2

23

9

53/4

311/16

4 × 3

26

101/2

61/4

41/2

4 × 4

33

12

63/4

51/4

6 × 2

31

9

71/8

211/16

6 × 3

46

101/2

75/8

31/2

6 × 4

52

12

81/8

41/4

6 × 6

65

143/4

91/8

53/4

8 × 4

71

131/2

10

101/2

8 × 6

86

161/2

11

61/16

Note 1:1 in. = 25.4 mm.

FIG. 41 Double-Branch Sanitary Combination Y and 1/8 Bend (T-Y)

Size, in.

Weight, lb

A, in.

B and B, in.

C, in.

E, in.

2 × 11/2

15

85/8

91/4

43/8

73/8

2 × 2

17

9

101/2

43/4

81/4

3 × 11/2

17

85/8

101/4

37/8

73/8

3 × 2

22

9

111/2

43/16

83/16

3 × 3

27

101/2

13

5

99/16

4 × 11/2

24

91/8

113/4

37/8

81/8

4 × 2

24

9

121/2

311/16

83/16

4 × 3

28

101/2

14

41/2

99/16

4 × 4

40

12

151/2

51/4

1013/16

6 × 3

45

101/2

16

31/2

99/16

6 × 4

57

12

171/2

41/4

1013/16

6 × 6

83

15

201/2

53/4

137/16

Note 1:1 in. = 25.4 mm.

FIG. 42 Short-Sweep Quarter Bends

Size, in.

Weight, lb

B, in.

C, in.

2

11

51/4

8

3

20

6

9

4

25

61/2

10

Note 1:1 in. = 25.4 mm.

FIG. 43 Long-Sweep Quarter Bends

Size, in.

Weight, lb

B, in.

C, in.

2

14

81/2

12

3

24

9

121/2

4

29

91/2

13

6

47

101/2

14

8

98

111/8

15

Note 1:1 in. = 25.4 mm.

FIG. 44 Sanitary Combination Y and 1/8 Bend (T-Y)

Size, in.

Weight, lb

A, in.

B, in.

C, in.

E, in.

2 × 11/2

11

85/8

45/8

43/8

73/8

2 × 2

13

9

51/4

43/4

81/4

3 × 11/2

14

85/8

51/8

37/8

73/8

3 × 2

18

9

53/4

43/16

83/16

3 × 3

24

101/2

61/2

5

99/16

4 × 11/2

17

91/8

57/8

37/8

81/8

4 × 2

21

9

61/4

311/16

83/16

4 × 3

23

101/2

7

41/2

99/16

4 × 4

31

12

73/4

51/4

103/16

6 × 2

33

9

71/4

211/16

83/16

6 × 3

37

101/2

8

31/2

99/16

6 × 4

47

12

83/4

41/4

1013/16

6 × 6

63

15

101/4

53/4

137/16

10 × 6

185

163/4

121/2

47/16

43/8

10 × 8

192

213/8

151/8

61/2

181/2

Note 1:1 in. = 25.4 mm.

FIG. 45 Quarter Bends

Size, in.

Weight, lb

B, in.

C, in.

2

9

31/2

7

3

16

4

71/2

4

20

41/2

8

6

36

51/2

9

8

54

61/8

10

10

116

85/8

12

12

195

103/8

14

Note 1:1 in. = 25.4 mm.

FIG. 46 Sixth Bends

Size, in.

Weight, lb

B, in.

C, in.

2

8

21/4

53/4

3

11

21/2

6

4

15

23/16

65/16

6

27

33/8

67/8

8

71

41/8

9

Note 1:1 in. = 25.4 mm.

FIG. 47 Eighth Bends

Size, in.

Weight, lb

B, in.

C, in.

2

7

13/4

51/4

3

13

115/16

57/16

4

16

23/16

511/16

6

25

29/16

61/16

8

46

311/16

813/16

10

95

41/4

91/4

12

132

5

95/8

Note 1:1 in. = 25.4 mm.

FIG. 48 Sixteenth Bends

Size, in.

Weight, lb

B, in.

C, in.

2

6

11/8

45/8

3

8

13/16

411/16

4

11

15/16

413/16

6

21

11/2

5

8

44

21/16

71/8

10

80

2

67/8

Note 1:1 in. = 25.4 mm.

FIG. 49 Sanitary Increasers

Size, in.

Weight, lb

A, in.

2 × 3

9

9

2 × 4

13

9

2 × 6

17

9

3 × 4

17

9

3 × 6

16

9

4 × 6

17

9

4 × 8

33

115/8

6 × 8

50

117/8

8 × 10

85

16

Note 1:1 in. = 25.4 mm.

FIG. 50 Hub Strainers

Size, in.

Weight, lb

2

21/2

3

3

4

5

6

10

8

18

Note 1:1 in. = 25.4 mm.

FIG. 51 Sanitary Reducers

Size, in.

Weight, lb

A, in.

3 × 11/2

6

5

3 × 2

7

5

4 × 11/2

7

5

4 × 2

9

5

4 × 3

11

5

6 × 2

12

5

6 × 3

13

5

6 × 4

14

5

8 × 4

22

6

8 × 6

25

6

10 × 6

39

6

10 × 8

51

6

12 × 6

55

61/2

12 × 8

65

6

12 × 10

83

6

15 × 6

79

6

15 × 12

109

6

Note 1:1 in. = 25.4 mm.

FIG. 52 Double Hubs

Size, in.

Weight, lb

A, in.

2

61/2

1

3

9

1

4

12

1

6

18

1

8

40

2

10

82

2

Note 1:1 in. = 25.4 mm.

FIG. 53 Pipe Plugs

Size, in.

Weight, lb

2

2

3

3

4

5

6

10

8

17

12

56

Note 1:1 in. = 25.4 mm.

FIG. 54 Cleanout Plugs

Size, in.

Weight, lb

2

31/2

3

61/2

4

11

6

14

8

26

10

39

Note 1:1 in. = 25.4 mm.

FIG. 55 Adapter – Plain End and Split Flange

Size, in.

Weight, lb

A, in.

J, in.

2

5

53/4

6

3

11

7

71/2

4

12

8

9

6

22

91/2

11

8

44

103/4

131/2

Note 1:1 in. = 25.4 mm.

FIG. 56 Adapter – Hub and Split Flange

Size, in.

Weight, lb

A, in.

J, in.

2

5

21/2

6

3

7

21/2

71/2

4

12

23/4

9

6

16

3

11

8

36

31/2

131/2

Note 1:1 in. = 25.4 mm.

FIG. 57 Combination Cleanout and Test Tees

Size, in.

Weight, lb

A, in.

B, in.

C, i n.

D, in.

E, in.

F, in.

2

12

21/2

9

313/16

35/8

31/16

27/8

3

22

27/8

10

5

45/8

41/4

313/16

4

29

39/16

11

57/16

55/8

41/2

413/16

Note 1:1 in. = 25.4 mm.

FIG. 58 Insertable Joints

Plate No.

Size, in.

Weight, lb

A, in.

B, in.

5045

2

11

73/4

61/2

5070

3

17

83/8

73/8

5095

4

21

91/8

77/8

5144

6

37

91/8

77/8

Note 1:1 in. = 25.4 mm.

FIG. 59 Backwater Valves

Size, in.

3

4

6

8

Note 1:1 in. = 25.4 mm.

FIG. 60 Sanitary P Traps

Size, in.

Without Vent Weight, lb

Hub Vent Weight, lb

A, in.

B, in.

C, in.

D, in.

E, in.

G, in.

H, in.

Vent, in.

2

12

16

11

3

61/4

41/2

21/4

313/16

15/8

2

3

25

32

121/2

41/4

61/4

51/2

3

41/2

25/16

3

4

37

45

14

51/2

7

61/2

31/4

53/16

3

4

6

68

80

17

81/2

8

81/2

4

61/2

315/16

4

Note 1:Depth of seal on all traps shall be 21/2 in.

Note 2:1 in. = 25.4 mm.

FIG. 61 Sanitary S Traps

Size, in.

Without Vent, Weight, lb

Hub Vent, Weight, lb

A, in.

B, in.

C, in.

D, in.

E, in.

F, in.

G, in.

H, in.

Vent, in.

2

16

18

91/4

3

8

41/2

33/4

43/4

313/16

15/8

2

3

24

29

101/2

41/4

10

51/2

41/4

61/4

41/2

25/16

3

4

33

39

111/4

51/2

12

61/2

41/4

7

53/16

3

4

6

82

89

14

81/2

16

81/2

5

9

61/2

315/16

4

Note 1:Depth of seal on all traps shall be 21/2 in.

Note 2:1 in. = 25.4 mm.

FIG. 62 Sanitary Running Traps

Size, in.

Without Vent, Weight, lb

Single Hub Vent, Weight, lb

Double Hub Vent, Weight, lb

A, in.

B, in.

D, in.

E, in.

F, in.

G, in.

H, in.

Vent, in.

2

14

17

22

131/2

21/2

41/2

21/2

51/4

85/16

15/8

2

3

29

36

42

151/2

3

51/2

31/4

61/4

10

25/16

3

4

41

49

57

171/2

31/2

61/2

31/2

71/4

1111/16

3

4

6

78

87

168

211/2

41/2

81/2

41/4

81/4

15

315/16

4

8

162

165

208

267/8

51/2

11

37/8

12

187/16

51/4

6

10

330

334

346

317/8

71/8

13

51/8

16

221/4

611/16

6

Note 1:Single hub vent is located on the inlet side. Depth of seal on 8- and 10-in. traps is 3 in. All others 21/2 in.

Note 2:1 in. = 25.4 mm.

FIG. 63 Outside Caulk

Plate No.

Outlet Size, in.

Weight, lb

1

2, 3, 4 and 6

45

2

2, 3, 4 and 6

45

3

2, 3, 4 and 6

53

4

2, 3, 4 and 6

53

5

2, 3, 4 and 6

41

6

2, 3, 4 and 6

42

7

2, 3, 4 and 6

48

8

2, 3, 4 and 6

49

Note 1:1 in. = 25.4 mm.

FIG. 64 Outside Caulk with Basin

Plate No.

Size, in.

A, in.

B, in.

C, in.

5, 6, 7, 8

2

27/8

31/2

5/16

3

37/8

41/2

5/16

4

47/8

51/2

3/8

6

7

73/4

3/8

Note 1:1 in. = 25.4 mm.

FIG. 65 Inside Caulk

Note 1:1 in. = 25.4 mm.

FIG. 66 Floor Drains

Plate No.

Outlet Size, in.

Weight, lb

1

3

70

2

4

73

3

2

37

4

2

45

Plate No.

Size, in.

A, in.

B, in.

C, in.

D, in.

E, in.

F, in.

1 2

3 4

8 8

9 9

57/863/8

11/211/2

14 14

141/2141/2

Note 1:1 in. = 25.4 mm.

FIG. 67 Method of Installation

FIG. 68 Floor Drain Funnel Attachment

Note 1:1 in. = 25.4 mm.

FIG. 69 No. 1, 2, 3, 4, and 5 Overflows

Plate No.

A, in.A

B, in.A

C, in.

1

2

41/8

1

2

4

61/8

1

3

6

81/8

1

4

8

101/8

1

5

0

21/8

1

(A)Dimensions A and B will vary depending upon the sink strainer in which overflow is placed, depth of counterbars, and so forth. Dimension B is given only as a guide.

Note 1:1 in. = 25.4 mm.

FIG. 70 Sink Outlet

Plate No.

Size, in.

A, in.

B, in.

C, in.

D, in.

E, in.

1

11/2 or 2

3/4 to 11/4

10

31/2

43/8

1/8

2

11/2 or 2

1 to 2

10

21/2

37/8

7/16

3

11/2 or 2

1 to 2

10

21/2

3

1/4

4

11/2

0 to 2

101/4

35/16

1/4

Note 1:Furnished with flat loose strainer plates.

Note 2:1 in. = 25.4 mm.

FIG. 71 Detailed Cross Section of Cleanout

Size, in.

Diameter of Drain, in.

A, in.

Under 6

11/2

23/16

6 and over

21/4

29/16

Note 1:Traps can be supplied without cleanouts, as shown in the figure.

Note 2:1 in. = 25.4 mm.

1.4.1Pipe:

1.4.1.1No-Hub (MJ) (Fig. 1):

Size (in.)

Length (ft)

11/2

7

2

7

3

7

4

7

1.4.1.2Hub/Plain End (Fig.35):

Size (in.)

Length (ft)

2

7

3

7

4

7

6

7

8

7

10

5

12

5

15

5

1.4.2Fitting (No-Hub) (MJ):

Figs.

Quarter Bends

2

Sixth Bends

3

Return Bends

4

Double-Branch Quarter Bend

5

Eighth Bends

6

Sixteenth Bends

7

Long-Sweep Quarter Bends

8

Sanitary Y Branches

9

Double-Branch Sanitary Y

10

Sanitary Combination Y and 1/8 Bend

11

Double-Branch Sanitary Combination Y and 1/8 Bend

12

Sanitary T Branches

13

Double Branch Sanitary T

14

Sanitary Running Traps

15

Sanitary P Traps

16

Swivel Trap P-Style, Short

17

Swivel Trap P-Style, Long

18

Swivel Trap S-Style, Long

19

Centrifugal Drum Trap P Swivel Type

20

Centrifugal Drum Trap S Swivel Type

21

Combination Cleanout and Test Tees

22

Coupling

23

Pipe Plugs

24

Cleanout Plugs

25

No-Hub (MJ) Adapter

26

Reducers-Increasers

27

Sink Outlet

28

Sink Overflows

29

Threaded Adapters

30

Trap Cleanout Details

31

No-Hub (MJ) Adapter

32

(MJ) (No-Hub) to Lead Adapter

33

Floor Drains

34

1.4.3Fitting (Hub/Plain End):

Figs.

Hub Plain End Pipe

35

Straight Tees

36

Sanitary T Branches

37

Sanitary Y Branches

38

Double-Branch Sanitary Tee

39

Double-Branch Sanitary Y

40

Double-Branch Sanitary Combination Y and 1/8 Bend (T-Y)

41

Short-Sweep Quarter Bends

42

Long-Sweep Quarter Bends

43

Sanitary Combination Y and 1/8 Bend (T-Y)

44

Quarter Bends

45

Sixth Bends

46

Eighth Bends

47

Sixteenth Bends

48

Sanitary Increasers

49

Hub Strainers

50

Sanitary Reducers

51

Double Hubs

52

Pipe Plugs

53

Cleanout Plugs

54

Adapter – Plain end to Split Flange

55

Adapter – Hub to-Split Flange

56

Combination Cleanout and Test Tees

57

Insertable Joints

58

Backwater Valves

59

Sanitary P Traps

60

Sanitary S Traps

61

Sanitary Running Traps

62

Floor Drains

63, 64, 65

Floor Drains

66

Floor Drains/Installation – Funnel Attachment

67, 68

Overflow

69

Sink Outlet

70

Detailed Cross Section of Cleanout

71

Chemical Composition

Table 3

Transverse Bend Test Minimum Requirements

Table S1.1

1.5This international standard was developed in accordance with internationally recognized principles on standardization established in the Decision on Principles for the Development of International Standards, Guides and Recommendations issued by the World Trade Organization Technical Barriers to Trade (TBT) Committee.