Applications and Features:

Southwire’s 600 Volt Type TC-ER flexible power cables are made with class C copper stranding for extra flexibilty suited for use in wet and dry areas, conduits, ducts, troughs, trays, direct burial, aerial supported by a messenger, and where superior electrical properties are desired. These cables are capable of operating continuously at the conductor temperature not in excess of 75°C in wet locations and 90°C in dry locations, 130°C for emergency overload, and 250°C for short circuit conditions. For uses in Class I, II, and III, Division 2 hazardous locations per NEC Article 501 and 502. Constructions with 3 or more conductors are listed for exposed runs (TC-ER) per NEC 336.10.

Specifications:

ASTM B3 Standard Specification for Soft or Annealed Copper Wire

ASTM B8 Concentric-Lay-Stranded Copper Conductors

UL 83 Thermoplastic Insulated Wires and Cables Type THHN

UL 1277 Electrical Power and Control Tray Cables

UL 1581 Electrical Wires, Cables and Flexible Cords

UL 1685 FT4 Vertical-Tray Fire Propagation and Smoke Release Test

ICEA S-58-679 Control Cable Conductor Identification Method 1 Table 2

ICEA S-93-639 (NEMA WC 74) 5-46 KV Shielded Power Cable

ICEA S-95-658 (NEMA WC70) Power cables rated 2000 volts or less for the distribution of electrical energy