HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

This unit just had a PM!!

And nothing was quoted except a few shorted to ground compressors. It was the first time anyone from my outfit was on site here & it was obvious that heat rejection was a major issue. i tend to run my hands over everything as i know many of you do & immediately noticed this .. How it was missed is beyond me. I believe 9 of 13 were this bad. I found so much wrong on this inspection i don't think it's all been addressed yet and it was 2 months ago.

It's obvious these coils weren't ever split. The discharge temps were through the roof .... I had 3-10 ton circuit severe burn outs, 1 header restriction, few flat systems to name some of the issues. One thing i didn't understand is why they were so focused on getting this building switched over to EMS including brand new VFDs in all units before addressing/spending on the major problems.