This site uses cookies so that we can provide you with the best user experience. If you continue your browsing, we assume that you accept our use of cookies. Find out on how we use cookies and how to change your settings to refuse them by clicking on the link on the right hand side.

Contact

Description

The cable is intended to be used for inside couplings in switch cabinet boxes and similar applications.

Standards

International :
EN 50525-2-31Declaration of Performance :
Reaction to fire: Ecaaccording to EN50575:2014+A1:2016

Description

H07V2-K is a lead free, PVC insulated, connecting cable with one circular, multi stranded copper conductor. The cable is designed according to EN 50525-2-31. The conductor has resistance according to EN 60228 class 5. The insulation is marked ”NEXANS GS H07V2-K 0,75 SEMKO (HAR) E. H07V2-K meets the requirements for CPR class E.

Certification

Certifeid by INTERTEK SEMKO.

Quality system

Certified according to ISO 9001, IRIS, ISO/TS 16949 and ISO 14001.

Characteristics

Construction characteristics

Colour

Grey

Conductor material

Bare copper

Insulation

PVC

Halogen free

No

Dimensional characteristics

Number of cores

1

Conductor cross-section

1.5mm²

Number of core wires (nb x mm Ø)

32 x 0.23 mm Ø

Conductor diameter

1.6mm

Average insulation thickness

0.7mm

Nominal outer diameter

3.0mm

Approximate weight

20kg/km

Electrical characteristics

Max. DC resistance of the conductor at 20°C

13.3Ohm/km

Rated Voltage Uo/U (Um)

450 / 750 V

Usage characteristics

Length

200m

Packaging

Reel

Flame retardant

IEC 60332-1

Operating temperature, range

0 .. 90°C

Bending factor when installed

4 (xD)

Docs and info

Selling information

H07V2-K will be delivered in lengths of 100 to 500 m. The drum is marked with manufacturer, type of cable and length.