Abstract In present days, structures exceeding 45m in length are designed with one or more expansion joint, where the building are split into two or more and behaves independent. In this study as per the code IS 456-2000 or IS 3414(1968), the building is modeled with expansion joint over a podium in ETABS. Now, while entering the time period for static earthquake forces, in the multiblock tall buildings over podium, structural engineers face challenge to select the building from which the time period has to be selected. Structural engineers had different perspectives on choosing the appropriate time period. But, usual practice was to take the entire buildings plan ignoring the expansion joint. This study discusses how to determine an appropriate time period considering the expansion joint, which time period is to be used in analysing the multi-block tall buildings with an expansion joint over a podium. The time period obtained from the larger size plan should be considered for earthquake analysis of the building

INTRODUCTION Atimeperiod(denotedby'T')isthetimerequired for one complete cycle of vibration to pass in a given point. As the frequency of a wave increases, the time period of the wave decreases. The unit for time period is 'seconds'. Frequencyand timeperiod are in a reciprocal relationship that can be expressed mathematically as: T = 1/f or as: f

=1/T

An expansion joint or movement joint is an assembly designed to safely absorb the temperature-induced expansion and contraction of construction materials, to absorb vibration, to hold parts together, or to allow movement due to ground settlement or earthquakes.They are commonly found between sections of buildings, bridges, sidewalks, railway tracks, piping systems, ships, and otherstructures.

Building faces, concrete slabs, and pipelines expand and contract due to warming and cooling from seasonal variation, or due to other heat sources. Before expansion joint gaps were built into these structures, they would crack under the stress induced.

THE OBJECTIVES OF THIS STUDY CAN BELISTED AS FOLLOWS:

TostudytheEarthquakeresponseofRCC Tall Building with variation of time period inX directionfordifferenttypesofplansbyresponsespectrum analysis.(Individual modelanalysis)

TostudytheEarthquakeresponseofRCC Tall Building with variation of time period in y directionfordifferenttypesofplansbyresponse spectrum analysis. (Individual modelanalysis)

TostudytheEarthquakeresponseofRCC Tall Building with variation of time period in x & y direction for different types of plans by response spectrum analysis. (Individual model analysis)

To Identify the worst time period, when two different building are at samepodium.

PRESENT STUDY

In present days, the design industries face design failures. The structural engineers go through many possible works identifying the worsttimeperiodwhilemodelingtwodifferent model in a single plane. For instance, when we consider two buildings, where the height of the building remains same, but their plan size is different. Initially, considering two models in a single podium assuming anyone of the models time period was the usual method. Since, considering two buildings we obtain fourinputs of time period. Whereas, ETABS has optionsof only two input. Hence, we sequentially analyse individual model and compare the earthquake response of both the models. We have to identify worst earthquake response among the two models. Once identified, the worst earthquake response of a model, that is given as the input time period from that model and has to be taken for furtheranalysis.

RESPONSE SPECTRUMANALYSIS

The procedure to compute the peak response of structureduringtheearthquakedirectlyfromthe earthquake response spectrum without the need of time history analysis iscalled response spectrum analysis. A typical design response spectrum(IS-1893) is shown below inFigure 1.

Fig 1: Design Response spectrum

MODEL 1

MODEL 3

(PLAN SIZE) X=24m Y=40m

T=.

(sec)

(PLAN SIZE) X=24m Y=40m

as per IS 1893-2016 PART1 X=0.854

Y=0.661 MODEL 4

T=.

(sec)

as per IS 1893-2016 PART1 X=0.854

Y=0.661 MODEL 2

(PLAN SIZE) X=24m Y=48m

T=.

(sec)

(PLAN SIZE) X=28m Y=40m

as per IS 1893-2016 PART1 X=0.854

Y=0.604

T=.

(sec)

as per IS 1893-2016 PART1 X=0.790

Y=0.661

(PLAN SIZE) X=24m Y=40m

T=.

(sec)

as per IS 1893-2016 PART1 X=0.854

Y=0.661

MODEL 6

(PLAN SIZE) X=28m Y=48m

(24 x 40 m) and (28 x 40 m) With 0.100m expansion joint

MODEL 8

T=.

(sec)

(24 x 40 m) and (28 x 48 m)

as per IS 1893-2016 PART1 X=0.790

Y=0.604

With 0.100m expansion joint

building Plan view combined model 7

Building elevation view combined model 7

Building isometric view combined model 7

Building plan view combined model 8

Building elevation view combined model 8

Building isometric view combined model 8

SEISMIC LOADING ZONE AS PER IS:1893- 2016(PART 1)

MODEL TYPE

ALL MODELS

R

3

I

1

Z

.10

Sa/G

Type2

MA MODEL TYPE MATERIAL PROPERTIES

TERIAL PROPERTI ALL MODELS

Column

M40

Beam

M25

Slab

M25

MA MODEL TYPE MATERIAL PROPERTIES

TERIAL PROPERTI ALL MODELS

Column

M40

Beam

M25

Slab

M25

directional combination

SRSS

SRSS

input response spectra

1.2×9.81/2 x3

1.2×9.81/2x 3

eccentricity ratio

0.05

0.05

directional combination

SRSS

SRSS

input response spectra

1.2×9.81/2 x3

1.2×9.81/2x 3

eccentricity ratio

0.05

0.05

ES

Density of concrete: 25 KN/m3

Density of brick masonry: 21.20 KN/m3 Slab thickness: 120 mm

Wall thickness: 230 mm

STATIC LOAD ASSIGNMENT

The loads considered are Dead Load, Live Load, Floor Finish, and Earth Quake Load. All models consist of these loads.

Dead Load: The dead load of the structure is obtained from Table 1, Page 8, of IS 875 Part 1 1987. The permissible vaue for unit weight of reinforced concrete varies from 24.80kN/m3 to 26.50 kN/m3. From the table, the unit weight of concrete is taken as 25kN/m3. The software has a inbuilt DL calculator

Self weight of the structural elements Floor finish = 1.5 kN/m2 and

Wall load on all beams is 11 kN/m

Imposed Load: The imposed load on the floor is obtained from Table 1 of IS 875 (Part 2) 1987. The uniformly distributed load on the floor of the building is assumed to be 4.0 kN/m2 (for assembly areas, corridors, passages, restaurants business and office buildings, retail shops etc). On roof 1.5 kN/m2, and

On floors 3.5 kN/m2

Earth Quake Load: The structure is assumed to be in Zone- II as per IS 1893 2016 (PART 1). So the zone factor is taken as per Table 2 of IS 1893 2002. The damping is assumed to be 5%, for concrete as per Table 3 of IS 1893- 2016 (PART 1).. Importance factor is taken as 1 as per Table 6 of IS 1893 2016 (PART 1).

Behaviour of earthquake in first phase shows that, as the dimensions of the building increases the time period will decrease but the modal time period increases. The earthquake response of the buildings like displacement, storey drift, and storey shear will increase.

In second phase it is observed that as the dimensions of the building increases the time period will decrease but the modal time period also decreases as the orientation of columns are in horizontal direction. The earthquake response of the buildings like displacement, storey drift, and storey shear will increase.

In third phase it is observed that as the dimensions of the building increases the time period will decrease but the modal time period increases. The earthquake response of the buildings like displacement, storey drift, and storey shear will increase.

Considering the first three phases, it is concluded that the time period of the building with larger horizontal dimension is considered as the appropriate time period for the combined models in fourth phase.

C. G. Konapure , M. S. Muddiddi, 2018,Determination Of Time Period And Evaluation Of Seismic Response Of Framed Structure With Different Approaches, International Research Journal Of Engineering And Technology (Irjet), Volume: 05 Issue: 04,pp 956-960

IS 1893, 2016. Indian Standard criteria for earthquake resistant design of structures (part 1): general provisions and buildings (fifth revision, Bureau of Indian Standards, New Delhi).

IS 3414, 1968. Indian Standard code of practice for design and installation of joints in buildings (second reprint April 1978, Bureau of Indian Standards, New Delhi).

IS 456-2000. Indian Standard plain and reinforced concrete-code of practice (fourth revision, Bureau of Indian Standards, New Delhi).

LarilLawlineCutinha, Pradeep Karanth,2018, Study On Time Period As Per Is Code Using Etabs Software, International Journal Of Current Engineering And Scientific Research (Ijcesr),

Young-Soo Chun, And Moo-Won Hur,Effects Of Isolation Period Difference And Beam-Column Stiffness Ratio On The Dynamic Response Of Reinforced Concrete Buildings,2015, International Journal Of Concrete Structures And Materials, Vol.9, No.4, pp.439451