Background: HVAC systems are often designed to supply a constant discharge air

temperature from an air handling system to maintain comfort in

the space. Some HVAC systems, especially those that have strict

space humidity requirements, should be controlled for a constant

discharge air dew point temperature (or maximum discharge air

dew point) in addition to controlling to a set discharge dry bulb

temperature. Wrap-around heat pipe systems, especially

controllable wrap-around heat pipe systems, can be an effective

tool to help meet these strict space humidity requirements.

Wrap-around heat pipe systems are air-to-air heat exchangers that

are installed in the airstream upstream and downstream of a

cooling coil. The upstream precool heat pipe shifts the excess

sensible cooling capacity off the cooling coil while the downstream

heat pipe provides reheat. Wrap-around heat pipes are passive devices that are driven by the difference

in thermal energy between the entering hot air and the cold air leaving the cooling coil. This thermal

energy affects a phase change of the refrigerant in the tubes which drives the flow of refrigerant

between the two heat pipe sections. As warm air enters the precool heat pipe, refrigerant changes

phase from liquid to vapor extracting heat from the air stream thus lowering the air temperature.

Refrigerant then flows naturally to the reheat section where it condenses and releases the energy it

absorbed from the precool section to the airstream in the form of sensible heat.

The Challenge: HVAC systems with strict space humidity requirements typically need to provide air with a dew point

that is lower than the dry bulb temperature. Operating rooms and many other applications fall under

this category. For this article, lets consider another example:

HVAC Products

Systems Design

Service

AA/EOE

A space with chilled beams is being served by a dedicated outdoor air system (DOAS). A typical DOAS

unit uses an air-to-air heat exchanger to transfer energy between the supply and exhaust air streams,

followed by a preheat coil, a cooling coil and supply fan(s). The chilled beams in this example require 55

degree air (the supply air dry bulb set point, SASP) with a maximum dew point of 48 degrees (the supply

air dew point set point, SADP). In the typical DOAS system, the chilled water coil will cool the air down to

the SADP (48 degrees) to remove the necessary moisture. However, reheat is then required to bring the

dry bulb temperature up to 55 degrees, as 48 degrees is too cold for the space. By introducing a wrap-

around heat pipe, the heat pipe can be selected to help precool the incoming air, relieving sensible load

from the cooling coil, then reheat the air from 48 degrees to 55 degrees, which is exactly what the space

requires.

Since the wrap-around heat pipe system is a passive device, there is no means to control the amount of

reheat applied to the supply air stream. The heat pipe can only reheat with as much energy as is

extracted from the air on the precool side. Therefore, if a heat pipe system is selected for a hot day, the

heat pipe will underperform on a cool day when the entering heat energy is lower and supply colder air

than is needed to the space. If a heat pipe system is selected for a cool day, the heat pipe will over-

perform on a hot day when the entering heat energy is higher, and supply warmer air than is needed to

the space.

The Solution: Enter the controllable wrap-around heat pipe. By installing solenoid valves on the refrigerant circuits of

the wrap-around heat pipe, the building management system (BMS) can control the amount of

refrigerant flow in individual circuits between the precool and reheat heat pipes, and thus effectively

control the amount of reheat being applied to the airstream.

In our example, if we select the heat pipe to supply 55 dry bulb/48 dew point air with a 65 degree

entering air temperature, for any entering air temperature above 65 degrees, the BMS will stage the

solenoid valves closed to prevent overheating of the discharge air. What about other entering outdoor

HVAC Products

Systems Design

Service

AA/EOE

air/humidity scenarios? How would the system be controlled then? The following psychrometric charts

portray all possible air condition scenarios and explain how each should most effectively be handled.

Note: The air-to-air heat exchanger is assumed to transfer total enthalpy for ease of illustration; however the same principles could be applied to a sensible-only energy recovery device. OADP: Entering outdoor air dew point temperature OAT: Entering outdoor air dry bulb temperature SADP: Supply air dew point set point SASP: Supply air dry bulb set point RAT: Return air dry bulb temperature from the space to the DOAS

1. Cold and dry (OAT < SADP): This is normal heating mode, and the air-to-air heat exchanger and hot water coil will work to reach the supply air dry bulb set point temperature. The heat pipe will do nothing under these conditions.

HVAC Products

Systems Design

Service

AA/EOE

2. Cool and dry (OAT < SASP and OAT > SADP and OADP < SADP): This case is for when the

outdoor air temperature is between the supply air dew point and dry bulb temperatures, and the air is sufficiently dry to not require dehumidification. As in case 1, the air-to-air heat exchanger and hot water coil will work to reach the supply air dry bulb set point temperature. The heat pipe will do nothing under these conditions.

air temperature between the supply air set point and the return air temperature. Because the dew point is sufficiently low, dehumidification is not required, the heat pipe and air-to-air heat exchanger can be turned off, and the cooling coil brings the entering air down to the supply air set point.

HVAC Products

Systems Design

Service

AA/EOE

4. Cool to warm, but humid (OAT< RAT and OAT > SADP and OADP > SADP): The outdoor air

temperature is between the return air temperature and the supply air dew point set point, but contrary to cases 2 and 3, the entering dew point temperature is sufficiently high to require dehumidification. In this scenario, cooling mode is enabled, but the air-to-air heat exchanger operates to bring the entering air temperature as close as possible to the return air temperature to maximize reheat effectiveness. Though this increases the cooling load, the additional reheat savings will outweigh that additional cooling penalty. The cooling coil will work to cool/dehumidify, and the heat pipe can be staged to meet the supply air dry bulb set point.

HVAC Products

Systems Design

Service

AA/EOE

5. Hot and dry (If OAT > RAT and OADP < SADP): The outdoor air temperature is greater than

the return air temperature, but because the outdoor air dew point is below the supply air dew point set point, dehumidification is not required. Cooling mode is enabled and the air-to-air heat exchanger precools outdoor air. The heat pipe can be staged off and the cooling coil is used to cool down the air to the supply air dry bulb set point.

HVAC Products

Systems Design

Service

AA/EOE

6. Hot and humid (If OAT > RAT and OADP > SADP): This scenario is for a typical summer day,

when full cooling mode is enabled. The air-to-air heat exchanger precools outdoor air and the heat pipe/cooling coil work to cool/dehumidify/reheat supply air. Stage heat pipe solenoid valves closed as required to maintain supply air dry bulb set point.

Conclusions: With proper application and control of wrap-around heat pipe systems, the example illustrated can be

expanded to nearly any system with strict space humidity requirements. Even more common systems

where humidity requirements arent as strict can be accomplished the same way by simply raising the

dew point line that separates Cases 1-2-3 from Cases 4-5-6. Although the example did not include

mention of humidification requirements, the system can be used in conjunction with a humidification

system to effectively raise the humidity in the airstream and space as required. Furthermore, it is worth

noting that the larger the outdoor air (ventilation) requirement for the particular air handling system,

the more effective the controllable wrap-around heat pipe system will be, as less return air means less

opportunity to condition the air by mixing.

HVAC Products

Systems Design

Service

AA/EOE

About Flow Tech, Inc.:

Flow Tech, Inc.s mission is to provide the highest quality and most energy-efficient HVAC systems and products that directly affect how buildings operate. Serving the commercial, healthcare, education, research, pharmaceutical, and water and wastewater markets, we strive to maintain the utmost professional and educated team offering sales, support and on-call, 24/7 service.

We are a full-service heating, ventilating and air conditioning (HVAC) equipment manufacturers representative celebrating over 25 years of business and serving CT, Western Massachusetts and counties in New York. We pride ourselves in offering:

The premier source of new VFD applications, retrofits and servicing all brands of existing VFDs The finest critical airflow control solution in the market providing a safe and energy efficient

environment for the occupants to work. The highest quality custom built air handlers providing a dependable means for building owners

to provide conditioned air to occupants. Multiple technologies of heat recovery allowing owners to run their buildings at peak

efficiencies. A service department that is educated and experienced and provides a level of service that goes

HEAT PIPE TECHNOLOGY, INC. (HPT) is the innovation leader in energy recovery and dehumidification systems for commercial applications around the globe. Employing the very latest in passive heat transfer technology, HPT designs and supplies the core systems to the world's leading commercial air handling equipment manufacturers.

Heat Pipe Technology, Inc. is recognized worldwide for our innovation and expertise. Our heat pipes are made right here in Tampa, Florida; they save energy and dramatically reduce heating and cooling costs.

With a network of more than 70 representatives and licensees in North and South America, Europe, The Middle East, Asia, and Australia, HPT is a true global operator. Learn more at www.heatpipe.com.