Operating Mode Some products are only capable of cooling, while others can either heat or cool a space. Some products heat via "heat pump" technology while others use electric heating elements. Learn More

Cooling + Heating

Number of Zones A zone is a room or area within a building that has it's own temperature control.

5

Indoor Unit Size(s) Mini split systems can have one or more indoor units connected to a single outdoor unit. Indoor Unit Size(s) specifies what indoor unit sizes are used in a system. For example (09 + 12) means the system includes a 9k BTU unit and a 12k BTU unit.

06 + 06 + 06 + 06 + 12

DOE Regional Compliance In 2015, the US Department of Energy broke the country into three regions - North, Southeast, and Southwest - and set legal standards for energy efficiency within each region. Learn More

Nationwide

Model

L5H48C0707070712

Performance

Cooling Capacity

40000 BTU

Heating Capacity

44000 BTU

SEER SEER (Seasonal Energy Efficiency Ratio) is a measurement of cooling efficiency over a typical cooling season. It is useful for comparing energy efficiency of cooling systems. The higher the SEER, the more energy efficient the system. Learn More

20.0

EER EER (Energy Efficiency Ratio) is a measurement of cooling efficiency under fixed conditions. It is useful for comparing units that will operate consitantly under one set of conditions (e.g. server room). The higher the EER, the more efficient the system. Learn More

13.1

HSPF HSPF (Heating Seasonal Performance Factor) is a measure of heating efficiency for heat pumps. It is useful for comparing energy efficiency of heat pumps. The higher the HSPF, the more efficient the system. Learn More

10.3

Cooling Power Input

3060 Watts

Heating Power Input

3613 Watts

Dimensions

Product Weight

290 Pounds

Shipping Weight

332 Pounds

Warranty Information

Parts Warranty

5 Years

Compressor Warranty

7 Years

Certifications

UL Listed

Yes

ETL Listed

Yes

AHRI Certified

Yes

ISO Certified

Yes

AHRI Reference Number

8111357

PT-UQC Specs

General Information

Type

Grille

Product Line

Multi F

Product Sub-line

Four-Way Ceiling Cassette

Installation Location

Indoor

Dimensions

Product Height

2.4375 Inches

Product Width

27.5625 Inches

Product Depth

27.5625 Inches

Product Weight

7 Pounds

Shipping Weight

9 Pounds

Warranty Information

Parts Warranty

5 Years

LMCN077HV-NOGRILLE Specs

General Information

Type

Ceiling Cassette Unit

Product Line

Multi F

Product Sub-line

Four-Way Ceiling Cassette

Operating Mode Some products are only capable of cooling, while others can either heat or cool a space. Some products heat via "heat pump" technology while others use electric heating elements. Learn More

Cooling + Heating

Multi-Zone Compatible

Yes

Remote Control

Wireless

Installation Location

Indoor

Grille

Not Included

Required Grille Model

PT-UQC

Performance

Nominal Capacity

7000 BTU

Minimum Air Flow

177 CFM

Maximum Air Flow

265 CFM

Maximum Sound Level

31 dB

Minimum Sound Level

24 dB

Electrical Data

Voltage

208/230 Volts

Phase

1

Frequency

60 Hz

Dimensions

Liquid Connection Size

0.25 Inches

Suction Connection Size

0.375 Inches

Product Height

8.4375 Inches

Product Width

22.4375 Inches

Product Depth

22.4375 Inches

Product Weight

31 Pounds

Shipping Weight

34 Pounds

Warranty Information

Parts Warranty

5 Years

Certifications

UL Listed

Yes

ETL Listed

Yes

AHRI Certified

Yes

ISO Certified

Yes

LMU480HV Specs

General Information

Type

Outdoor Condenser

Product Line

Multi F

Product Sub-line

MAX

Operating Mode Some products are only capable of cooling, while others can either heat or cool a space. Some products heat via "heat pump" technology while others use electric heating elements. Learn More

Cooling + Heating

Maximum Number of Zones

8

Multi-Zone Compatible

Yes

Installation Location

Outdoor

Performance

Nominal Capacity

48000 BTU

Maximum Sound Level

56 dB

Electrical Data

Voltage

208/230 Volts

Phase

1

Frequency

60 Hz

Recommended Breaker Size

40 Amps

Dimensions

Maximum Line Length

475.7 Feet

Liquid Connection Size

.375 Inches

Gas Connection Size

.75 Inches

Product Height

54.34375 Inches

Product Width

37.60625 Inches

Product Depth

15.75 Inches

Product Weight

214 Pounds

Shipping Weight

236 Pounds

Warranty Information

Parts Warranty

5 Years

Compressor Warranty

7 Years

Certifications

UL Listed

Yes

ETL Listed

Yes

ISO Certified

Yes

LCN127HV4-NOGRILLE Specs

General Information

Type

Ceiling Cassette Unit

Product Line

Multi F

Product Sub-line

Four-Way Ceiling Cassette

Operating Mode Some products are only capable of cooling, while others can either heat or cool a space. Some products heat via "heat pump" technology while others use electric heating elements. Learn More

LG's devotion to providing efficient ductless solutions can be seen across the Multi F line. This ceiling cassette ductless heat pump system pairs a powerful LMU480HV outdoor condenser with very efficient ceiling cassette indoor units. LG's Multi F ceiling cassette indoor units feature four air outlets which allow them to provide consistent air flow to the farthest reaches of large rooms. In addition to providing excellent coverage, the ceiling cassette indoor units also feature an exceptionally low profile. When installed, a grille less than 1" thick is the only visible clue that your room is receiving efficient heating and cooling from a ductless heat pump system.

Low Ambient OperationsThis outdoor unit supports cooling operations down to 14 degrees Fahrenheit and with a wind baffle, 0 degrees Farenheit. In heating operations, the unit can handle down to -4 degrees Fahrenheit.

Quiet DesignThanks to a brushless direct current fan motor, both the outdoor and indoor units in this system produce less mechanical and electrical noise, allowing them to provide comfort that doesn't disrupt your home.

Jet CoolThese LG mini split indoor units feature a Jet Cool operation mode for rapid cooling. In this mode, an indoor unit observes a set point of 64 degrees Fahrenheit while the fan operates at maximum speed for 30 minutes to quickly cool your zone.

Swirl Wind ModeExclusive to ceiling cassette models is Swirl Wind, which automates both air flow direction and fan speed to produce steady comfort throughout any zone.

Improved Air QualityThese mini split indoor units include anti-fungal filters to keep your air clean. These filters capture contaminants like dust and bacteria, and they are washable to ensure long term air quality.

DehumidifyLG's multi-zone indoor units include a dehumidifying operation mode. In this mode, the unit's internal sensors monitor temperature and modify the set point and fan speed to remove moisture from the air.

Hot StartWhen the hot start function is enabled on a mini split indoor unit, the fan will not engage until the outdoor condenser has had the opportunity to warm the indoor coil. This prevents the unit from blowing cold air during heating operations.

eComfort will not give or sell your individual information to non-related companies for its use in marketing or solicitations.

Receive Weekly How-To Tips & Specials

eComfort will not give or sell your individual information to non-related companies for its use in marketing or solicitations.

(*) Required Information

Submit Your Question

1 Question Answered

Q: Can the LG system deliver heat down to 5 degrees? If so, are the BTU ratings listed the same at this temp?by Andrew S. from Massachusetts on July 24, 2016

A: LG outdoor units do not shut down based on outdoor temperature*. They will deliver heat at 5 degrees, and lower. However, their output will decrease as temperature drops toward freezing and below. For specific details on capacities at different outdoor temperatures, you can reference the Engineering Manual. If you need any help interpreting the manual, feel free to email or call us.

*The units will shut down if operating pressures in the systems are unsafe. Once pressures return to safe levels, the units will resume operation. by Chris, Product Expert