THERMIC FLUID HEATERS

Product Specification

This system is forced circulation fully automatic thermic fluid heater where thermic fluid is circulated in a closed loop through heater and user equipment circuit where the heat is dissipated to process. The same thermic fluid is re-circulated through heater for heating. The thermic fluid heater gives high temperature upto 300 oC using thermic fluid oil at near atmospheric pressure as compared to steam heating which requires 85 Kg/Cm2 pressure.

Parameter

Unit

Model

TFHV-400

TFHV-600

TFHV-1000

TFHV-1500

TFHV-2000

Heat Output

Kcal/Hr

4,00,000

6,00,000

10,00,000

15,00,000

20,00,000

Max.Fluid Outlet Temperature

oC

300

Max. Head at heater Outlet

M/c

27

Efficiency on GCV

With APH+

%

75

Without APH+

%

70

Rated fuel consumption

Steam Coal

Kg/hr

116

175

290

435

580

Lignite

Kg/hr

150

226

376

564

752

Agro-waste

Kg/hr

174

260

433

650

866

Thermic Fluid Pump Motor

Kw

7.5

9.30

11.0

18.5

30

I.D.Fan Motor

Kw

3.7

5.5

9.3

11.0

15.0

Over fire fan motor

Kw

-

1.50

2.20

3.70

5.50

Total Load

Kw

11.20

16.30

22.50

33.20

50.70

Expansion Tank Capacity

Liters

800

800

1000

1000

1250

Overall Dimensions

Length

mm

4600

6000

7500

7800

10000

With

mm

3800

4000

4500

5400

6200

FEATURES

Multifuel Concept

Highest Efficiency

The combustion chamber dimension and grate area are suitably designed for maximum combustion efficiency on low grade fuel. This system is easily accessible and large heating surface of Thermo Energy Systems heater and air pre-heater assures on unmatched efficiency f 76% (on GCV of coal having 5000 Kcal/Kg.)

Low Power Consumption

Unique design of Thermo Energy Systems heater ensures lowest power consumption over any other competing system available today.

Absolute Safety

External Combustion chamber ensures longer life of heater coil and thermic fluid. No radiation energy is transferred to heater coil in case of power failure ensuring complete safety. Diesel engine driven pump is not required for Fluid tech heater as compared to vertical systems.

External Furnace

Coal/Lignite is burnt in an external furnace which results in an elimination of any possible hazard to the thermic fluid heater coil. A flue by-pass system is attached for the protection against power failure. The entire furnace is provided with steel casing and the combustion chamber is constructed with best quality high heat duty fire bricks and insulation bricks. Mineral wool insulating panels help minimum heat loss.

Thermic Fluid Heater

Here a nest of concentric helical tube coils is placed within sturdy mild steel shell. The special arrangement of concentric coils ensures optimum heat transfer. The system along with the standard accessories is conveniently mounted on the sturdy steel skid for easy installation.

Optional Features

Coal cum oil firing system to change over from one fuel to another with minimum down time, Automatic by-pass damper with electromagnetic or pneumatic device. Modulating damper or variable speed drive to control combustion under all operating conditions.

Clients Testimonials

Thermo Energy System has a strong engineering background and a deep understanding of the challenges facing industry. We are very happy with the company and provided products.

Thermo Energy System is challenging and innovative company, work to the highest standards and always go the extra mile, not only delivering quality but also working with us to identify new opportunities and markets.

The TEST team are extremely professional, we are a pleasure to work with and I would recommend them to any business.