• For Micrologic 5 and 6, SDx can be configured for different alarms.
Note that the SDX can be used for ground fault alarm on non configurable 6 (LSIG) trip units, but it will not provide ground fault alarm on a Micrologic 5 (LSI) trip unit. Therfore, GF alarm without tripping is not possible.
All alarms on a trip, failure, and maintenance event and all alarms associated with a measurement previously activated in the Alarms tab can be assigned to an SDx Module output.
For complete list, refer to Alarms section of manual 48940-312-01.
To set alarms, access the SDx Module output settings using the RSU software under the Output tab.