This is the amount of thermal incident energy to which the worker's face and chest could be exposed at working distance during an electrical arc event. Incident energy is measured in joules per centimeter squared (J/cm2) or calories per centimeter squared (cal/cm2). Minimum reported incident energy is 0.25 cal/cm2 which is the accuracy limit of the test equipment.

A value in cal/cm^2 to determine arc flash boundary (AFB) distance at that Incident Energy. The Incident Energy of 1.2 cal/cm^2 for bare skin is used in solving equation for arc flash boundary in IEEE 1584 Guide for Performing Arc Flash Hazard Calculations. However, the Guide equation for arc flash boundary can be solved with other incident energy levels as well such as the rating of proposed personal protective equipment (PPE). The Incident Energy at Arc Flash Boundary value should be equal or above incident energy to second degree burn for bare skin exposure.

The arc flash boundary is an approach limit at a distance from exposed live parts or enclosed live parts if operation, manipulation, or testing of equipment creates a potential flash hazard, within which a person could receive a second degree burn if an electrical arc flash were to occur. A worker entering the arc flash boundary must be qualified and must be wearing appropriate PPE. The arc flash boundary is required to be calculated by NFPA 70E.

This is the minimum level of Personal Protective Equipment in calories per centimeter squared, as evaluated in IEEE Standard 1584, with the intent to protect the worker from the thermal effects of the arc flash at working distance from the source of the arc.

Equipment bus gap in mm. Gaps of 3 to 40 mm were used for low voltage testing to simulate gaps between conductors in low voltage equipment and cables. Gaps 13, 104 and 152 mm. were used in 5 and 15kV equipment testings. For cases where gap is outside the range of the Empirical model, the theoretically derived Lee method can be applied and it is now included in ARCAD's arc flash assessment software.

Typical working distance is the sum of the distance between the worker standing in front of the equipment, and from the front of the equipment to the potential arc source inside the equipment.

Arc-fash protection is always based on the incident energy level on the person's face and body at the working distance, not the incident energy on the hands or arms. The degree of injury in a burn depends on the percentage of a person's skin that is burned. The head and body are a large percentage of total skin surface area and injury to these areas is much more life threatening than burns on the extremities. Typical working distances are shown in table below:

Use protective device characteristics, which can be found in manufacturer's data. For fuses, the manufacturer's time-current curves may include both melting and clearing time. If so, use the clearing time. If they show only the average melt time, add to that time 15%, up to 0.03 seconds, and 10% above 0.03 seconds to determine total clearing time. If the arcing fault current is above the total clearing time at the bottom of the curve (0.01 seconds), use 0.01 seconds for the time.

For circuit breakers with integral trip units, the manufacturer's time-current curves include both tripping time and clearing time.

For relay operated circuit breakers, the relay curves show only the relay operating time in the time-delay region. For relays operating in their instantaneous region, allow 16 milliseconds on 60 Hz systems for operation. The circuit breaker opening time must be added. Opening times for particular circuit breakers can be verifed by consulting the manufacturer's literature.

Available 3 phase bolted fault current for the range of 700A to 106kA at the point where work is to be performed is entered into this box in kA. Example: if 42,350 amps are available, enter 42.35 into this box. If 16,000 amps are available, enter 16 into this box. Please consider ARCAD's short circuit calculation software to determine the available fault currents in your power distribution system.

The arcing current depends on the available 3 phase bolted fault current for the range of 700A to 106kA at the point where work is to be performed, configuration, system voltage and gap between conductors. Leave the field blank, the program calculates the value based on the system parameters. The arc duration should be determined based on the predicted arcing current.

System Line to Line Voltage for the range of 208V to 15000V is entered into the box in Volts. For cases where voltage is over 15kV, the theoretically derived Lee method can be applied and it is now included in ARCAD's arc flash assessment software.

For protective devices operating in the steep portion of their time-current curves, a small change in current causes a big change in operating time. Incident energy is linear with time, so arc current variation may have a big effect on incident energy. The solution is to make two arc current and energy calculations; one using the calculated expected arc current and one using a reduced arc current that is 15% lower.

ARCAD's arc flash assessment software makes possible both calculations for each case considered. It requires that an operating time be determined for both the expected arc current and the reduced arc current. Incident energy is calculated for both sets of arc currents and operating times and the larger incident energy is taken as the model result. This solution was developed by comparing the results of arc current calculations using the best available arc current equation with actual measured arc current in the test database.