Experiences with pre-precipitation of phosphorus in a vertical flow constructed wetland in Austria

Using constructed wetlands (CWs) with vertical flow and intermittent loading, high organic matter and ammonium removal can be achieved. In the case of additional requirements for phosphorus removal, which in Austria often occurs if the treated wastewater is discharged into small sensitive receiving waters, additional measures have to be taken. The objective of this work was to investigate the applicability of conventional phosphorus pre-precipitation with sodium aluminate for a CW system. The experiment was carried out at a full-scale CW in Oberwindhag in Lower Austria, a two-stage vertical flow CW with intermittent loading designed for a size of 60 person equivalents (PE). The goal was to reach the required value of 1.6 mg/L PO4-P for the effluent of the system. Prior to the experiments the plant was in operation for 3 years without measures for phosphorus removal. After pre-precipitation with sodium aluminate was activated, three different dosages were investigated. Satisfying results in the preliminary treatment chambers were not obtained until a high dosage (ß = 3.5, i.e. 3.5 times the dose required from stoichiometry) was applied. After an adaptation time of several months the required effluent concentration of 1.6 mg PO4-P/L could be reached and maintained. However, the additional phosphorus pre-precipitation increases the yearly operating costs of a vertical flow CW system significantly, e.g. for 60 and 25 PE, by 15 and 38%, respectively, thus indicating the need for optimizing the dosing of the chemical.

Related articles

The goal of this paper was to evaluate the possibility of using terrestrial laser scanning (TLS) for inventorying of a hybrid constructed wetland (CW) wastewater treatment plant. The object under study was a turtle-shaped system built in 2015 in Eastern Poland. Its main purpose is the treatment of wastewater from the Museum and Education Centre of Polesie National Park. The study showed that the CW system had been built in compliance with the technical documentation, as differences between values obtained from...

Septage is wastewater stored temporarily in cesspools. A periodic supply of its significant quantities to small municipal wastewater treatment plants (WWTPs) may cause many operational problems. In the frame of the research, it has been proposed to utilize vertical flow constructed wetlands for pre-treatment of septage prior to its input to the biological stage of a WWTP. The aim of the work was to assess the effectiveness of pre-treatment in relation to factors such as: seasonality, hydraulic load, pollutants...

Despite the fact that several authors consider the available measurement methods of hydraulic conductivity (ks) suitable for a good representation of the bed condition and clogging potential in horizontal subsurface flow constructed wetlands, others have questioned their adequacy. In this work, hydraulic conductivity measurements with conventional and modified methods were undertaken in two small full-scale units, one planted with cattail (Typha latifolia) and the other unplanted. Both units had already been...

Pharmaceutical residues in wastewater pose a challenge to wastewater treatment technologies. Constructed wetlands (CWs) are common wastewater treatment systems in rural areas and they discharge often in small water courses in which the ecology can be adversely affected by the discharged pharmaceuticals. Hence, there is a need for studies aiming to improve the removal of pharmaceuticals in CWs. In this study, the performance of a full-scale aerated sub-surface flow hybrid CW treating wastewater from a healthcare...

Customer comments

No comments were found for Experiences with pre-precipitation of phosphorus in a vertical flow constructed wetland in Austria. Be the first to comment!

Add your comment

Great! comment successfully added!

Contact

Your message:

Your email

Your first name

Your last name

I would like to receive periodic email updates and special offers from select suppliers.