Introducing the Bravo Inverter MK2 wall mounted series. The second evolution of these exciting Split Inverter units provide heating and cooling flexibility where you need it most.

Impressive A and A+ rated energy credentials coupled with discreet design and a host of remote controlled functions make temperature control “precise” as well as easier on the pocket.

Presented to you with four outstanding specifications, dependent on your needs. Manage your temperature and environment in a cost effective way, and improve the air that you breathe.

Energy Saving G10 Inverter Technology

Our inverter technology varies the speed of the compressor (the outside unit) delivering fast and precise heating and cooling at your fingertips. It reacts to outside temperatures with variable fan speeds dependent on your required heating and cooling levels. Any fluctuation in temperature will be sensed immediately, so the result is a saving in energy versus “fixed speed” compressor systems. In real terms G10 Inverter Technology makes a difference of between 30%-50% on your energy bill, against a non inverter equivalent and increase start up times via the “quick start” function by 30%.

Choice of Specification to suit your needs

Flexible use within the home and office with a selection of models, differing in heating and cooling capacity but containing the same advanced range features. Chose from models with 9000, 12000, 18000 and 24000 BTU.

Temperature control at your command

Bravo Inverters are available with power output (heating) capacity from 3.0KW to 7.0KW (Models EC0916SD MK2 and ECO2416SD MK2). This against a power input of just 0.9KW and 2.2KW on these models respectively. A smart way to heat. Similar efficiencies also relate to cooling converting power-in to efficient cooling performance. Full details are included in our product sheet which can be downloaded via our “library” tab below.

Features:

G10 Inverter Technology for rapid heating and cooling

Dehumidification

Ultra Quiet Operation

Quick Start Up Function

One Touch Self Cleaning Function

Oscillating Air Louvres

Digital Display

Low Energy Standby (1W)

24 Hour Timer

Auto Clean

Settings Memory

Sleep Mode

Auto Restart

European Energy Ratings between A & A+

Bravo Inverter MK2 Split Air Conditioning Specifications

Model

ECO916SD MK2

ECO1216SD MK2

ECO1816SD MK2

ECO2416SD MK2

Power supply

Ph-V-Hz

1, 220-240V~, 50Hz

1, 220-240V~, 50Hz

1, 220-240V~, 50Hz

1, 220-240V~, 50Hz

Fed to

Indoor

Indoor

Indoor

Indoor

Cooling

Capacity

kW

2.6 (0.45~3.23)

3.52 (0.6~3.96)

5.27 (1.2~6.2)

6.45 (2.53~6.55)

Capacity

BTU

8900 (1500~11000)

12000 (2000~14000)

17998 (4094~21154)

22007 (8632~22349)

Input Power

kW

0.87 (0.2~1.42)

1.15 (0.22~1.55)

1.6 (0.38~2.65)

2.18 (0.6~2.65)

SEER

5.6

5.1

5.4

5.1

Current

A

3.8

5.1

7.1

9.7

Heating

Capacity

kW

3.0 (0.45~4.1)

3.8 (0.6~5.13)

5.6 (1.1~6.0)

7.0 (2.53~7.6)

Capacity

BTU

10200 (1500~14000)

13000 (2000~17500)

19005 (3753~20472)

23884 (8632~25931)

Input Power

kW

0.9 (0.2~1.55)

1.1 (0.22~1.65)

1.75 (0.35~2.6)

2.22 (0.6~2.8)

SCOP

3.8

3.8

3.8

3.8

Current

A

4.0

4.9

7.8

10.5

Rated Input

kW

1.5

1.65

2.65

2.8

Rated Current

A

6.3

7.3

11.8

12.5

Indoor Sound Pressure Level

dB(A)

24/30/38/41

25/31/39/42

35/40/44/49

37/42/47/51

Indoor Sound Power Level

dB(A)

38/44/52/55

39/45/53/56

46/51/55/60

49/53/57/63

Indoor unit

Net Dimension (WxHxD)

mm

770x283x201

770x283x201

865x305x215

1007x315x219

Net/Gross weight

Kg

8/11

9/12

12/15

14.5/17.5

Outdoor Sound Pressure Level

dB(A)

51

53

55

58

Outdoor Sound Power Level

dB(A)

62

62

65

68

Outdoor unit

Net Dimension(WxHxD)

mm

776x540x320

848x540x320

1030x700x396

980x790x427

Net/Gross weight

Kg

28/32

30/33.5

46/50

55.5/60.5

Refrigerant type R410A @ 4 metres

g

700

1000

1300

1800

Refrigerant piping

Liquid side/ Gas side

mm(inch)

6.00(1/4)/9.52(3/8)

6.00(1/4)/9.52(3/8)

6.00(1/4)/12.00(1/2)

6.00(1/4)/15.88(5/8)

Max. refrigerant pipe length

m

15

20

25

25

Max. Elevation

m

10

10

10

10

Dehumidification

litres/h

0.80

1.4

1.8

2.0

Energy Rating (Cooling / Heating)

A+/A

A/A

A/A

A/A

Fuse Rating

A

13

13

20

32

Interconnecting Cable

3C+E

3C+E

3C+E

3C+E

Operating Temperature

°C

16 ~ 30

16 ~ 30

16 ~ 30

16 ~ 30

Ambient Temperature (Heating)

°C

-7 ~ 24

-7 ~ 24

-7 ~ 24

-7 ~ 24

Ambient Temperature (Cooling)

°C

18 ~ 43

18 ~ 43

18 ~ 43

18 ~ 43

Annual Energy Consumption (over 500 hours)

Kw

435

575

800

1090

Note: Due to our policy of innovation some specifications may be changed without notification.

All split air conditioning units contain F-gas, and is governed by F-gas regulations
Under EU regulations: The installation of all split air conditioning units containing F-gas (R410A or R407C) require installation or commissioning by a F-gas certified air conditioning engineer.