Below 1000M. It have to rise the rate power when the altitudeis more than 1000M.

Temperature

-30 +55oC

Humidity

90%RH without dew condensation.

Vibration

<0.5G

Structure

Protection Class

IP20

Cooling Pattern

Natural wind cooling.

Products Selection

1, 220V Series

Model

Current (A)

Standard (kW)

Heavy load (kW)

Model

Current (A)

Standard (kW)

Heavy load (kW)

ST-GS2-5d5

22

5.5

4

ST-GS2-075

320

75

55

ST-GS2-7d5

30

7.5

5.5

ST-GS2-090

370

90

75

ST-GS2-011

45

11

7.5

ST-GS2-115

400

115

90

ST-GS2-015

60

15

11

ST-GS2-132

500

132

115

ST-GS2-018

75

18.5

15

ST-GS2-160

560

160

132

ST-GS2-022

90

22

18.5

ST-GS2-185

630

185

160

ST-GS2-030

110

30

22

ST-GS2-200

800

200

185

ST-GS2-037

150

37

30

ST-GS2-220

900

220

200

ST-GS2-045

180

45

37

ST-GS2-250

1000

250

220

ST-GS2-055

230

55

45

ST-GS2-280

1200

280

250

2, 380V Series

Model

Current (A)

Standard (kW)

Heavy load (kW)

Model

Current (A)

Standard (kW)

Heavy load (kW)

ST-GS3-5d5

11

5.5

4

ST-GS3-132

260

132

115

ST-GS3-7d5

15

7.5

5.5

ST-GS3-160

320

160

132

ST-GS3-011

23

11

7.5

ST-GS3-185

370

185

160

ST-GS3-015

30

15

11

ST-GS3-200

400

200

185

ST-GS3-018

37

18.5

15

ST-GS3-022

45

22

18.5

ST-GS3-250

500

250

220

ST-GS3-030

60

30

22

ST-GS3-280

560

280

250

ST-GS3-037

75

37

30

ST-GS3-320

630

320

280

ST-GS3-045

90

45

37

ST-GS3-355

710

355

320

ST-GS3-055

110

55

45

ST-GS3-400

800

400

355

ST-GS3-075

150

75

55

ST-GS3-450

900

450

400

ST-GS3-090

180

90

75

ST-GS3-500

1000

500

450

ST-GS3-115

230

115

90

ST-GS3-600

1200

600

500

3, 480V Series

Model

Current(A)

Matching motor power

Model

Current(A)

Matching motor power

Standard(kW)

Heaavy load(kW)

Standard(kW)

Heaavy load(kW)

ST-GS4-5d5

11

5.5

4

ST-GS4-132

260

132

115

ST-GS4-7d5

15

7.5

5.5

ST-GS4-160

320

160

132

ST-GS4-011

23

11

7.5

ST-GS4-185

370

185

160

ST-GS4-015

30

15

11

ST-GS4-200

400

200

185

ST-GS4-018

37

18.5

15

ST-GS4-250

500

250

200

ST-GS4-022

45

22

18.5

ST-GS4-280

560

280

250

ST-GS4-030

60

30

22

ST-GS4-320

630

320

280

ST-GS4-037

75

37

30

ST-GS4-355

710

355

320

ST-GS4-045

90

45

37

ST-GS4-400

800

400

355

ST-GS4-055

110

55

45

ST-GS4-450

900

450

400

ST-GS4-075

150

75

55

ST-GS4-500

1000

500

450

ST-GS4-090

180

90

75

ST-GS4-600

1200

600

500

ST-GS4-115

230

115

90

Size Information

Soft starter installation diagram

The soft start (5.5KW~600KW) selection list of peripheral appliances are as follows:

Model

Rated power (KW)

Rated current (A)

Breaker (A)

By-pass contactor(A)

Cable size (mm2)

XX-XX3-5d5

5.5

11

16

16

4 mm2

XX-XX3-7d5

7.5

15

20

16

4 mm2

XX-XX3-011

11

23

32

25

6 mm2

XX-XX3-015

15

30

40

40

10 mm2

XX-XX3-018

18

37

50

40

10 mm2

XX-XX3-022

22

43

63

63

16 mm2

XX-XX3-030

30

60

80

63

25 mm2

XX-XX3-037

37

75

100

100

35 mm2

XX-XX3-045

45

90

125

100

35 mm2

XX-XX3-055

55

110

160

160

35 mm2

XX-XX3-075

75

150

180

160

30×3 mm2

XX-XX3-090

90

180

225

250

30×3 mm2

XX-XX3-115

115

230

315

250

30×3 mm2

XX-XX3-132

132

264

315

400

30×4 mm2

XX-XX3-160

160

320

350

400

30×4 mm2

XX-XX3-185

185

370

400

400

30×4 mm2

XX-XX3-200

200

400

400

400

50×5 mm2

XX-XX3-250

250

500

630

630

50×5 mm2

XX-XX3-280

280

560

630

630

50×5 mm2

XX-XX3-320

320

640

630

630

50×5 mm2

XX-XX3-355

355

710

1000

1000

60×6 mm2

XX-XX3-400

400

800

1000

1000

60×6 mm2

XX-XX3-450

450

900

1000

1000

60×6 mm2

XX-XX3-500

500

1000

1250

1000

80×6 mm2

XX-XX3-600

600

1200

1600

1600

80×6 mm2

Note:

The rated power and rated current indicate the maximum rated value of the soft start. The matching specification of breakers and bypass contactors should match with the motor.

Soft starter is for six terminal inputs and three terminal outputs, it is still with the online protection function at the state of bypass contactor sucking, do not need to add additional motor protection device.

Real SolutionQuality Guarantee

Our Service:

1. Can I get some samples?Yes, Sample order is available for quality check and market test .But you have to pay for it .2. What's delivery time?It usually takes about 3-5 working days for small order and 10-15 days for big order .3. What's your payment terms?We usually accept all kinds of payment terms .Such as T/T,L/C, Western Union.Cash.4. What's your warranty terms?We offer 24 months warranty time .5. Do you have the products in stock?Depends on your request ,We have standard models in stock. Some special products and big order will be newly produced according to your order .6. Can I mix different power in one container .Yes ,Different models can be mixed up in one container ,even one order .7. How does your factory do the quality control?Quality is priority ,we always attach the importance to quality control from the beginning to the end of the production .every product will be fully assembled and carefully tested before packing and shipping .8. Can you sell spare parts ?If you are using our products .we can sell spare parts to you . But we couldn't sell the half-finished products.9.I would like to know if you have a partner for export?Yes .We have the right to export and can sell electrical product all over the world..10. Can you make the inverter and soft starter control boards (switchgear)?Yes. We have a lot of experience to design frequency inverter and soft starter cabinet according to your request . 11.Can the inverter connect with computer?Yes .All inverters have built-in RS485 port .andsupport Modbus communication protocol.12.How can I trust you ?Our company has been audited and approved ISO9001,CE.CCC. Assessment report will could be sent to you by e-mail. and we will take all the responsibility once problem during warranty time.