ANIKRON T-07

Digital excitation regulator for synchronous motor ANIKRON T-07 (for static excitation system) is intended to provide power for the excitation winding and automatic control of the excitation currents during startup, synchronous operation and emergency mides of synchronous motors.

Main characteristics:
· Additional control system of the bridge thyristor power rectifier allowing to detect and prevent any possible trouble in thyristor operation
· Opportunity of manual selection and correction of the required control algorithms
· Graphic 10" LCD for viewing of preset and operational parameters of motor and excitation including oscillograms of the main events
· Crate location of the controlling boards that simplifies the maintenance
· Advanced system of data collection and analysis
· Fully identical, interchangeable, galvanically decoupled main and backup excitation control units each provided with its own set of power supply units, pickups, and actuation circuits with automatic immediate switch from main to backup unit
· Reactive current control according to the set value and managing of reactive current production or consumption
· Wide range of protection algorithms
· Immediate field suppression after the motor is disabled by forcing the thyristor rectifier to the inverter mode
· Testing (pre-startup) mode that enables to observe the main parameters of the motor and the excitation system
· Wide range of climatic versions and degrees of protection of cabinet assembling
· Rated operation period - 15 years
· Events log capacity no less than 12 000 events
· Oscilloscope capacity no less than 500 oscillograms

PARAMETERS

UNITS

VALUES

Nominal excitation current

А

100-320

Nominal excitation voltage

V

20-230

Resistance of starting resistor

r. u.

0,4-0.8

Field-forcing to current ratio, at least

о.е.

1,8

Current consumption in chains 220 V AC , no more than

А

1

Current consumption in chains 220 V DC , no more than

А

1

Stator current and voltage consumption in measuring chains

W

2

Maximum current for output signal chains

А

5

Accuracy of Cos φ control, at least

r. u.

0,0015

Diapason of settings for Cos φ

r. u.

± 0.2

Operation period

years

15

Weight

kg

350

Overall size

mm

2135х806х852

ANIKRON B-04

Digital excitation regulator for synchronous motor ANIKRON B-04 is intended to provide power for the excitation winding and automatic control of the excitation currents during startup, synchronous operation and emergency mides of synchronous motors.