TKK3

Nominal heat output is given for wood logs of caloric value 15 MJ/kg. It can also efficiently burn wood pellets with an additional Biotermec pellet burner attached to the lower door.

Boiler is made of 5mm thick steel. Parts which are less exposed to the heat are made of 4mm thick steel.

The boiler comes with a manual cast-iron-made cleaning system located above the ash-tray. It also comes with a a cleaning kit and a boiler thermometer.

Combustion is controlled via draught regulator (which is not a component part of boiler, must be ordered extra).

Type

25

30

35

40

50

70

90

Overall power (KW)

25

30

35

40

50

70

90

Weight (kg)

274

290

304

319

352

400

440

Necessary draught (mbar)

19

21

22

23

25

28

31

Max working temperature (°C)

90

90

90

90

90

90

90

Max working pressure (bar)

2,5

2,5

2,5

2,5

2,5

2,5

2,5

Water content (lit)

76

83

90

102

115

155

178

Height (mm)

1225

1225

1225

1225

1225

1325

1325

Width (mm)

540

590

640

690

690

690

750

Length (mm)

1050

1050

1050

1050

1150

1270

1270

Flue diameter (mm)

ø134

ø134

ø134

ø160

ø160

ø160

180

Flue height (mm)

1015

1015

1015

1015

1015

1015

1087

Flow / Return (inch)

5/4

5/4

5/4

5/4

6/4

6/4

2

Inner chimney diameter* (mm)

200

200

200

200

200

250

250

Chimney height* (m)

7-8

7-8

8-9

9-10

10-11

11-13

13-15

Heating area* (m²)

<150

150-180

180-210

210-240

240-270

270-420

420-560

* Data given in the chart represents is a rough estimate only.

Termomont Šimanovci is one of the major solid fuel boilers producers in the Balkan region. The biggest slice of our turnover belongs to export activities. We are present in all former Yugoslav republics. We have strong partners in the Russian Federation, Ukraine, Romania, Bulgaria, Albania, Greece, Czech Republic, Estonia, Latvia, Belarus, Poland, France, Belgium, Spain and Portugal. ”