Copper Conductor Stranded Copper THW Wire Electric Cable

1. Main application THW electric cable is suitable for various commercial and industrial applications. These cables may be installed in wet or dry locations, indoors or outdoors, in raceways, underground ducts (ask about our preinstalled cable-in-conduit products), aerial or direct buried. THW...

Product Details

1. Main application

THW electric cable is suitable for various commercial and industrial applications. These cables may be installed in wet or dry locations, indoors or outdoors, in raceways, underground ducts (ask about our preinstalled cable-in-conduit products), aerial or direct buried.

THW electric cable is NEC-compliant for continuous operations at 75° C in wet and dry locations.

2.Specifications and Ratings

- UL Type THW

- The insulation is suitable for use in wet or dry locations at a temperature not exceeding 75° C

INSULATION: Heat and moisture resistant polyvinyl chloride (PVC) meeting the requirements of ICEA S-95-658 (NEMA WC 90) UL 83 for Type THW and wires. The insulation is suitable for use in wet or dry locations at a conductor temperature not exceeding 75° C for normal operation.

ASSEMBLY: Single conductor cables can be paralleled or multiplexed for more efficient installations. Single conductor cables can also be pre-installed in conduit.

Size

No. of Strands

Nominal Thickness of

PVC Insulation

Approximate Overall Diameter

Approximate Weight of Cable

AWG or MCM

mm

mil

mm

inch

kg/km

lbs/ 1000ft

14

solid

0.76

30

4.30

0.169

33

22.2

12

solid

0.76

30

4.8

0.189

47

31.6

10

solid

0.76

30

5.4

0.213

68

45.7

8

solid

1.14

45

6.1

0.240

100

67.2

6

solid

1.52

60

7

0.276

151

101.4

14

7

0.76

30

4.50

0.177

36

24.2

12

7

0.76

30

5.10

0.201

50

33.6

10

7

0.76

30

5.80

0.228

73

49.0

8

7

1.14

45

7.40

0.291

118

79.3

6

7

1.52

60

8.50

0.335

174

116.9

4

7

1.52

60

9.80

0.386

256

172.0

2

7

1.52

60

11.30

0.445

391

262.7

1

7

2.03

80

13.50

0.531

505

339.3

1/0

19

2.03

80

14.6

0.575

622

417.9

2/0

19

2.03

80

15.8

0.622

767

515.3

3/0

19

2.03

80

17.2

0.677

950

638.2

4/0

19

2.03

80

18.8

0.740

1179

792.1

250

37

2.41

95

20.9

0.823

1404

943.2

300

37

2.41

95

22.4

0.882

1664

1117.9

350

37

2.41

95

23.8

0.937

1923

1291.9

400

37

2.41

95

25

0.984

2180

1464.5

500

37

2.41

95

27.4

1.079

2694

1809.8

600

61

2.79

110

30.4

1.197

3241

2177.3

700

61

2.79

110

32.3

1.272

3751

2519.9

750

61

2.79

110

33.2

1.307

4007

2691.9

800

61

2.79

110

34.1

1.343

4260

2861.9

900

61

2.79

110

35.8

1.409

4769

3203.8

1000

61

2.79

110

37.4

1.472

5265

3537.1

GUANGDONG CABLE FACTORY CO. LTD. is one of the TOP 10 BRAND CABLE in China, which was eastablished in 1968, is the production of cable products, research and development, sales in the integration of professional, modern enterprise. Our factory is located in Foshan, Guangdong Province, a famouse city with convenient transportation in China.

Main products: We are specialized in manufacturering different kinds of cable, such as: copper cable wire, power cable, electric cable wire, XLPE cable, rubber cable, control cable and so on

Why chose us

01.All used materials are high-quality materials.

02.All products produced and delivered according to the national standards.

03.All products are provided in adequate length.

04.We guarantee to return and replace any sold products that are incompatible with the above commitments.