Pro-10 Series Cable Trays - Straight Sections
CM10 Cable Tray straight sections(0.120) are designed and have a grid pattern of 2" x 2". They can be used for the support of fiber optics and as tray separators. They are available in industry standard widths of 2", 4", 6" and 8". Available lengths are: 1', 2', 5', 8' and 10'. Height/Depth measurements are 2" or 4". Available colors: Yellow, Chrome, White & Black. Call us with your custom requirement if the above standard dimensions are not suitable for your application. Interconnecting hardware is included. CM10 is not UL classified.

Please Select Your Color:

YellowChromeWhiteBlackOrangeBlueRed

PRO-10TM is available in wire diameter choices CM10 (0.120) - to accommodate various cable tray load capacities. No cutting or bending is required on any of these styles.

The PRO-10TM CM10 cable tray, with a 2"x2" grid pattern, is the lightweight solution for fiber optic cabling that minimizes cable sagging or dropping. CM10 cable trays come in widths of 2", 4", 6", 8" or 12"; lengths of 1', 2', and 5' with depths of 2" or 4". CM10 is not UL-classified®.

Installation

PRO-10TM should be installed from the originatinghead-end i.e., the electrical or telecommunications closet. Once the pathway has been established, it is important the layout of the pre-fabricated junctions be installed first. This allows for field measurements to be taken before installing the cable tray. If the straight sections are installed first, it will cause unnecessary field adjustments. Each section has loops at each end. When the sections are connected, the loop on the bottom aligns under the galvanized masked area of the adjoining section. The loop on the side slides into the outside loop guide. Once the trays are aligned, install the 5/16" carriage bolt (included) through the loops with the threaded end to the outside of the tray. Install and tighten the flanged nuts with a 1/2" socket. This reduces the chances of damage when pulling the cables. It is not recommended that the cable tray be cut as it will interfere with the grounding characteristics and UL classification®.PRO-10'sTM wire grid cabletray systems require only one tool and very few accessory items for installation. Pre-fabricated junctions/intersections reduce 50% or more labor hours by eliminating cutting and fabrication in the field. With center hung, trapeze, wall or floor mount accessories, PRO-10TM is prepared to handle the toughest installations.

Tray Size (D" x W" x L')

Fill Area

Max # cables 50% Fill Ratio

**Approx. Max. Cable Weight lbs./ft

Tested Load Capacity 5ft

***lbs./ft. 10ft.

2 x 2 x 10

4.4

44

1.452

25

15

2 x 4 x 10

8.8

86

2.838

17

14

2 x 6 x 10

17.6

130

4.29

20

10

2 x 8 x 10

17.6

174

5.742

25

12

4 x 6 x 10

25.2

252

8.316

35

17

4 x 8 x 10

33.6

336

11.088

41

20

For more information, or to continue shopping, please visit this products main webpage.