d. Edited and wrote reset schedule for Main Supply Fan Static Pressure control based on Outside Air Temperature and Average Building Temperature. Supply Fan Static Pressure was set at a constant setpoint of 2.5 inches. Program now resets Supply Fan Static Pressure to 1.5 - 2.2 inches. Reduced electrical demand from Main Supply Fans.

Further reduced Floor Heating Enable Setpoint to 70 degrees during period of low heating demand.

g. Editing Floor Heating Fan Coil Unit programming to reset supply air temperature based on OSA and Average Return Temps. Locked out Heating Fan Coil Unit operation if Boilers are not enabled.

Communications:

Unavailable

Testimonial:

Unavailable

Please note: Narrative information in this profile has been provided by Government Properties Income Trust or a representative of this facility. Other building information was verified and submitted to EPA at the time of application. Building energy performance, operating characteristics, and ownership/management may be subject to change over time.