EZD 44T

When it comes to traditional firestopping methods, you never stop paying. You pay to put it in and every time you make cable changes, you do it again. The more changes you make, the more it costs you both in time and money… Not to mention disruption!

Implementing Ez-Path®

Firestopping is No Longer the Problem with he Only Truly Automatic Firestop System!

EZ-Path® customers benefit from greatly enhanced cable management. The EZ-Path® System allows cable installations to be easily organized by type, use, or trade… Or any other way that you might like to do it. Pathways installed in walls provide managed portals through which cables can easily be routed.

To ensure your firestop installation is a success, simply follow the steps below:

1. Define the type and number of pathway in accordande with the estimated number of cables provided by the cable management (see calculation tool ) .

3. Check the existing framework or reservation , if there is none, select suitable tools the the material involved and make the opening (check table below) .

4. Select the finishing plates in accordance with the table below :

Horizontal installation

Module 44T

Number
of
modules

Installation

Plates*

Code

Dry partitions

Concrete wall

Cables
already
in place

EZD 44
Code: 250058
78 97

1

EZP144WT

250230

120X105 mm 152 mm

120X105 mm 152 mm

1 to 5

EZP544WT

250250

120X105 mm

120X206 mm

120X308 mm

120X410 mm

120X511 mm

120X105 mm

120X206 mm

120X308 mm

120X410 mm

120X511 mm

* Plates sold in pairs

Module 44

Number
of
modules

Installation

Plates*

Code

Dry partitions

Concrete wall

Cables
already
in place

EZD 44
Code: 250058
78 97

4

EZG444WT

250360

120X415 mm

8

EZG844WT

250390

275X415 mm

Please note! Not all steel wire cable trays are the same. The mechanical and electrical characteristics, tests, certifications, overall quality management aspects and recommendations referred to in this technical guide are relevant to CABLOFIL® only and cannot, under any circumstances, be applied to other similar or imitation products.

Vertical installation

Module

Number
of
modules

Installation

Plate

Code

FLOOR
Framework
0 Coring

EZD 44
Code: 250058
78 97

1

EZG144T

250260

120X105 mm 152 mm

Module

Number
of
modules

Installation

Plate

Code

FLOOR
Framework

EZD 44
Code: 250058
78 97

4

EZG444T

250370

155X445 mm

8

EZG1644

250380

155X1010 mm

* Plate sold separately

Framework: A frame or structure for various types of opening (doors, windows, pipes, etc.). These are put in place as part of a building's main construction work and may take the form of polystyrene blocks or wooden frames.Coring: A procedure for cutting out a test specimen from an area undergoing work. A diamond crown is generally used for this procedure.

Please note! Not all steel wire cable trays are the same. The mechanical and electrical characteristics, tests, certifications, overall quality management aspects and recommendations referred to in this technical guide are relevant to CABLOFIL® only and cannot, under any circumstances, be applied to other similar or imitation products.

Module

Number
of
modules

Installation

Acessories

Code

Length

EZD 44
Code: 250058
78 97

1

EZD 44E

250178

150 mm

1

RCM 44

250306

25mm

bend radius

Maximum module capacity

of cables (mm)

3.5

4.5

5.5

6

7.5

8

10

15

16

18

20

22

25

26

29

32

38

48

60

70

75

Modules

Maximum number of cables

EZD44

648

399

255

210

140

110

75

30

23

20

16

11

9

7

6

4

3

2

1

1

1

The table above provides an estimate of the maximum number of cables that each module can accommodate.* Within the context of renovation work, if cables are already in place in the duct, modules can be caulked directly into the wall.