Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Airstack with Fieldserver Lonworks????

Need to know if any one has used the Airstack chiller with the provided fieldserver to Lonworks. I would like to know if it went well and if you had any issues? I am using a Jace BTW. I pulled in the points with a soft jace on my first visit and could read some points. ON the next day all the points were -17. Any one had this issue? I know you must set points up as critical, I did not do this yet, as I was just testing the point data to see if I could see it. Also I converted the XIF to the lnml file extension, but where do I need to load this in the Jace once I get it mounted. Any help?

Well I got it to work, all but one point, The nviON/OFF will not come through. The factory said the csv file was correct and it should but they could not help so I had to hard wire the remote start stop. Other than that it seems to be working. Just in case any one else has an issue check the node address set up in the carel contoller and make sure it matches the field server node address.