Which events can be triggered from an either an input contact or output relay on the AP9613 Dry Contact Relay I/O SmartSlot Card?

Product Line

UPS Device Management

AP9613 Dry Contact I/O SmartSlot Card

AP9335T/TH Environmental Sensors

AP9810 Dry Contact I/O Accessory Dongle

Environment

All firmware versions

All serial numbers

Cause

General information - if a user is interested in which events can be mapped to an input contact or output relay on the AP9613, refer to the list below. Legacy Configuration options (those available with the older AP9610 SmartSlotCard) are available via dip switch configuration (outlined in the user's guide) or also as a template in the configuration utility the AP9613 offers.

If you would like to customize which inputs or outputs map to which commands and/or relay numbers, please refer to the user's guide for the AP9613 in using the "Custom" dip switch configuration in order to utilize the Dry Contact I/O SmartSlot Card Configuration Utility to do the customization.

Resolution

The available targets on the standalone AP9613 for input contacts include:

UPS

UPS Outlet Group 1*

UPS Outlet Group 2*

UPS Outlet Group 3*

Output Relay 1

Output Relay 2

Output Relay 3

Output Relay 4

Output Relay 5

Output Relay 6

UIO Port 1 Output Relay (if optional AP9810 is connected)

UIO Port 2 Output Relay (if optional AP9810 is connected)

If you choose the UPS or an Outlet Group as the target, the following (control) Actions are available:

On

On With Delay

Off

Off Gracefully

Shutdown

Shutdown with Delay (With outlet groups only)

Reboot

Reboot Gracefully

Self Test (Not available with outlet group target)

Bypass* (Not available with outlet group target)

The available events on the standalone AP9613 for output relays include: