Omega Water Meters for cold water.

Quick Overview

Full bore, Helix Woltmann type meter suitable for cold water. The Omega-WE-SDC is a super dry dial type meter with a 360° rotating display. Pipe diameters from 2" (50mm) up to 20" (500mm) with a PN16 flanged connection and a flow rate ranges of 40m³/h up to 5,000m³/h. Unit is fitted with an interchangeable Mechanism.

Details

Full bore, helix Woltmann type meter suitable for cold water. It's impellar rotates on a stainless steel spindle mounted in the measuring chamber. The impeller is made of self-cleaning synthetic resin which like the rest of the meter is BS 6920 tested.The complete metering insert is easily removed from the meter body if damaged in service. The meter is of modern design and ensures high flow rates with minimum head loss. The Omega-We-Sdc is a "super-dry" dial type meter with a 360° rotating display. The gears and the totalizer operate in a dry Copper-Can compartment, only the helix is submerged in water. Transmission is achieved through a corrosion-proof permanent magnetic drive which is protected by the cast iron meter body from external magnetic fields. A version for warm water up to 90°C is available. The water meter OMEGA WE SDC in pre-equipped for the connection of pulse emitter (reed switch type or opto design for higher frequencies on request. Performance according to MID 2004/22/CE Directive.

Due to the large size of these flow meters, these units are not available to purchase online. If you send an e-mail inquiry to info@omni.uk.com, we will be happy to send you a quotation for your requirements.

Availability: Stock Item

Components / Downloads

For further information, technical advice, or a quotation please call or email us. If you are not sure which product you need one of our technical sales advisors will be happy to discuss your application. We also accept company purchase orders by fax or post. Credit card orders can also be placed over the phone for any product.

REF

DESCRIPTION

DOWNLOADS

PRICE

ORDER ITEM

OMEGA Helix Woltmann Cold Water Meters

OMEGA-WE-SDC50

OMEGA Helix Woltmann Type Bulk Water Meter. Pipe diameter 50mm with PN16 flanged connections, flow range: Qmin 500 l/hr; Qn 40m3/hr; Qmax 50m3/hr. Epoxy coated cast Iron body suitable for up to water up to 30°C with WRAS Approval. All OMEGA Flow meters come prepared for a pulse output of Ltr/pulse. Additional pulse output options from 100 to 1,000 Ltr/pulse are available at the time of order. (Please order pulse modules separately).