95DSS3

Insight II Flame scanner | SIL3

The only flame scanner on the market with 2 completely programmable Flame Relays!

Best in class for biomass conversions and new build

InSight II incorporates the superior detection and discrimination elements of the popular InSight product with additional enhanced capability, features and benefits.

The scanner measures the amplitude of the modulations (the flame “flicker”) that occur within the targeted flame. During the scanner set-up procedure, the modulation frequency that yields the best flame ON/OFF discrimination is selected. The appropriate modulation frequency and sensor gain can be either manually or automatically selected.

Standard features include two independently adjustable Flame Relays that can be selected to operate from the UV sensor, the IR sensor, or both sensors, 21 choices of modulation frequency, adjustable sensor gain, adjustable flame relay ON/OFF thresholds, two 4-20 mA analog signal strength outputs (one for FR1 and one for FR2), Fault Relay, four selectable programmable files (e.g. for different fuels or firing rates), and Auto Config capability with manual override. Remote communication capability is available via optional “Fireye Explorer” PC software (CU-109).

Fuel Types

All

Markets Served

All

Special features

2 relays means 2 scanners in 1 box. Use 1 relay for pilot, the other for mains. Or set each relay for different fuels. With 4 user files to choose from the firing combinations are endless. This industrial flame detector also has a feature to allow you to ignore fireballs in opposed and corner fired boilers. Can be remotly commissioned using the Fireye Explorer software (FEX) Click here