Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

What do you do when a TXV is hunting?

What is going on w/ the system when a txv is hunting for correct superheat? I charged a split system w/ a txv to the correct subcooling but checked the superheat and the txv was opening way up and closing going frm 10 to 20 degrees superheat. Would I just have to adjust the txv manually until its correct?

What is going on w/ the system when a txv is hunting for correct superheat? I charged a split system w/ a txv to the correct subcooling but checked the superheat and the txv was opening way up and closing going frm 10 to 20 degrees superheat. Would I just have to adjust the txv manually until its correct?

ya it was on a lieberte in a huge server room that they keep super clean and change the filters like once a month. There was a leak in the system and I repaired the leak and was recharging the unit, charged it to subcooling, got correct subcooling then checked the superheat and the unit was at a steady 15 degrees superheat then started going between 10 to 20 degrees hunting and was just wondering if I messed up the charge.

ya it was on a lieberte in a huge server room that they keep super clean and change the filters like once a month. There was a leak in the system and I repaired the leak and was recharging the unit, charged it to subcooling, got correct subcooling then checked the superheat and the unit was at a steady 15 degrees superheat then started going between 10 to 20 degrees hunting and was just wondering if I messed up the charge.

Is the TXV bulb secure to the sucition line and insulated? you might try changing the bulb placement of the bulb.

If I had to guess you use to have 1000,0000000000,00000000,0000K of heat generated by vacuum tube electronics and since modern technology came by and we use solid state electronics now and produce 10k of heat and they kept that enormous unit. What happens it's under no load and with no load the txv hunts.