Description

The Xtender series is comprised of three groups by power level corresponding to the XTS, XTM and XTH models. Whether configured individually, in parallel, split-phase, or three-phase, these devices allow for complete flexibility with respect to the desired energy system concept.

With its sophisticated software, the Xtender can be used in a wide range of applications. The Xtender series products are ideal devices for specific markets that need revolutionary solutions with all types of battery technologies.

Ease of useThe Xtender fulfils the requirements of the majority of applications with its factory settings, which makes it a plug & play device. Energy flows automatically and the auxiliary contacts are configured to provide genset auto-start and alarm functions.

The LEDs on the Xtender front panel allow the user to see in a quick glance how the device is working.

5 in 1The Xtender is a true energy manager, unique and compact, that has 5 main functions. It can be an off-grid inverter, battery charger, current injector, transfer system and provide support to an AC source. With these functions, the available energy can be managed and used in an intelligent and efficient manner.

Specification

Product No.

I1142

Inverter:

Nominal battery voltage

24Vdc

Input voltage range

19 - 34Vdc

Continuous power @ 25°C

2000VA

Power 30 min. @ 25°C

2400VA

Power 5 sec. @ 25°C

6kVA

Maximum load

Up to short-circuit

Maximum asymmetric load

Up to Pcont.

Load detection (stand-by)

2 to 25 W

Cos j

0.1-1

Maximum efficiency

94%

Consumption OFF/Stand-by/ON

1.4W/1.6W/9W

Output voltage

Pure sine wave 230Vac (+/- 2%) / 120Vac (1)

Output frequency

50Hz / 60Hz (1) +/- 0.05% (crystal controlled)

Harmonic distortion

<2%

Overload and short-circuit protection

Automatic disconnection with 3 time restart attempt

Overheat protection

Warning before shut-off - with automatic restart

Battery charger:

Charge Characteristic

6 steps : Bulk-Absorption-Floating-Equalization-reduced floating-periodic absorption
Number of steps, thresholds, end current and times completely adjustable with the RCC-02/-03

* Adjustable with the RCC-02/-03** These features are valid only when using the cooling module ECF-01.(1) With -01 at the end of the reference, means 120V/60Hz. Available for all Xtenders except XTH 8000-48