Online Statements

Purchase Electricity

Thank you for your patronage for any help please contact our helpdesk on 086 107 3289

*Notice EFT payments made can take up to 24 hours to process due to banking delays.
The system is managed during business hours only. In order to speed up the process you can e-mail or fax your proof of payment together with meter
number and your contact details for the token to info@pscafrica.co.za or 086 263 2856

Prepaid Gas Meter

The meter is typically installed at a convenient location close to the incoming utility supply where it is easily accessible to the user.
The user interacts directly with the meter via the meter keypad. The meter presents information to the user via the LCD, LED light indicators
and audible alarm.

Technical Specification

Model Number

NEAT GAS

Capacity (m3)

1.6

2.5

4

Parameters

Nominal Flow Rate (m3/h)

1.6

2.5

4

Maximum Flow Rate (Qmax) (m3/h)

2.5

4

6

Minimum Flow Rate (Qmin) (m3/h)

0.016

0.025

0.040

Working Pressure (kPa)

0.5

Basic Error (%)

Qmin≤Q≤0.1Qmax: ±3 ; 0.1Qmin≤Q≤0.1Qmax: ±1.5

Leakage pressure (Pa)

No leakage below 15kPa pressure

Pressure Loss (Pa)

≤250 (inlet to outlet)

Maximum Reading (m3)

99999.9

Minimum Reading (m3)

0.2

Working Temperature (oC)

-10 +40

Power Source:

Lithium battery 3.6V

Average current (standby)

< 18µ A

Average current (steady state)

150µ A/60ms

Valve operational consumption

1mA

Cut off technology

Motorised valve

Minimum display value

0.1m3

Measurement Accuracy

Class B

Body Dimensions

Prepaid Water Meter

As water is used, the meter registers pulses from the measurement element and decrements the remaining credit in meter.
The meter measures units of water and decrements units of water as it flows through the meter. The meter does not store
any tariff information making the meter very simple and cost effective. When all the available credit is consumed, the meter
shuts off the valve, cutting off the consumer‘s water supply. The meter supports advanced features to allow for compliance to
general utility, legislative and World Health Organisation basic water guidelines.

Technical Specifications

Standards

GB/T 778-2007OIMLR49

GB/T 778-2007OIMLR49

CJ/T 133-2007OIMLR49

Diameter (DN)

15mm

20mm

25mm

Unit

0.1m3

0.1m3

0.1m3

Maximum Flow (Q4)

3 m3/h

5 m3/h

7 m3/h

Nominal Flow (Q3)

1.5 m3/h

4 m3/h

6.3 m3/h

Transitional Flow (Q2)

0.05 m3/h

0.08 m3/h

0.126 m3/h

Minimum Flow (Q1)

0.03 m3/h

0.05 m3/h

0.07 m3/h

Minimum Reading

0.0001 m3

Maximum Reading

99999 m3

Credit Alarm Level

Customised

Working Temperature

0.1 C ~ 40 C

Permissible Water Pressure

0.03 MPa ~ 1 MPa

Method of Alarm

Valve Close

Flow Profile Sensitivity Level

U10,D5

Accuracy class

Class B

Reverse flow meaurement

Yes

Dimensions

Smart Meter Portal

Our system is compatible with most existing meters available in South Africa and can quickly integrated into a client's existing
metering infrastructure. Using our software portal clients are able to view accurate and transparent near real-time electricity
consumption and be able to view historical monthly consumption, demand and compare month to month consumption and maximum demand
at the click of a button. Our full suite offering gives the client the ability to manage their primary and sub meters and help
make informed decisions.

The meters are installed by our qualified and skilled staff after an initial site visit to ensure that the correct area is being
measured by the specific meter.

Important features offered by our solution:

Individual client access to info via the internet with a secure password.

View reporting information on each building.

Typical reporting information:

Unique meter number

Meter consumption - updated daily

Maximum demand measurement

Graphical half hourly profile data

Historical profile and billing data (from date of installation)

Current and historical tariff details of applicable meter

Total rand value for energy consumption and demand per meter, group of meter or area.

Communication between meters and our servers is through a private secure data connection.

*** You pay a once off cost for the electricity meters and communication equipment which becomes your property. From here onwards we carry all the
operational and system maintenance cost. You just pay us a low nominal monthly fee.