XLPE Insulated Aerial Bunched Cables Bare AAC In Air 25 35 50mm is applied to overhead power line with rated voltage 0.6/1kv and
10KV.XLPE Insulated Aerial Bunched Cables Bare AAC In Air 25 35 50mm is mainly used for electric power transmission, rebuiding of urban
and forest regions. They can improves safety and reliance of
electrified wire netting.

ABC aerial Cable are overhead power lines using several insulated phase conductors
bundled tightly together, usually with a bare neutral conductor. They can improves safety and reliance of electrified wire netting.

a Duplex Service DropApplications:To supply 120 volt aerial service for temporary
service at construction sites,outdoor or street lighting . For
service at 600 volts or lower at a conductor temperature of 75
maximum.

b Triplex Service DropApplications: To supply power from the ulility`s lines to the
consumer`s weatherhead. For service at 600 volts or less(phase to
phase ) at a conductor temperature of 75 maximum for PE insulation
or 90 maximum for XLPE insulation .

c Quadruplex Service DropApplications: Used to supply 3 phase power , usually from a
pole-mounted transformer to the use`s servic head where connection
to the service entance cable is made . To be used at voltages of
600 volts or less phase to phase and at conductor temperature not
to exceed 75 for PE insulated conductors or 90 for XLPE insulated
conductors.

Duplex ABC Cable

Code Word

Phase conductor

Bare Neutral Message

Nominal lay Length

Weight Per 1000 ft.(lbs.)

Allo wable Amp acitles

Size (A WG)

Stranding

Insul Thick(Mils)

Size (AWG)

Stranding

Rated Strength (lbs.)

inches

XLP

POLY

XLP

POLY

AAC Neutral-messenger

Pekingese

6

1

45

6

7

563

10.36

61

61

85

70

Collie

6

7

45

6

7

563

10.36

64

64

85

70

Dachshund

4

1

45

4

7

881

10.36

92

92

115

90

Spaniel

4

7

45

4

7

881

10.36

96

96

115

90

Doberman

2

7

45

2

7

1350

14.88

147

147

150

120

Malemute

1/0

9

60

1/0

7

1990

14.88

234

234

205

160

Triplex ABC Cable

Code Word

Phase conductor

Bare Neutral Message

Nominal lay Length

Weight Per 1000 ft.(lbs.)

Allo wable Amp acitles

Size (A WG)

Stranding

Insul Thick(Mils)

Size (AWG)

Stranding

Rated Strength (lbs.)

inches

XLP

POLY

XLP

POLY

AAC Neutral-messenger

Pateela

6

7

45

6

7

563

14.88

103

103

85

70

Oyster

4

7

45

4

7

881

14.88

154

154

115

90

Clam

2

7

45

2

7

1350

20.58

233

233

150

120

Murex

1/0

7

60

1/0

7

1990

20.58

374

374

205

160

Purpura

1/0

9

60

1/0

7

1990

20.58

368

368

205

160

Nassa

2/0

7

60

2/0

7

2510

25.42

462

462

235

185

Melita

3/0

17

60

3/0

19

3310

29.97

562

562

275

215

Portunus

4/0

18

60

4/0

19

4020

29.97

696

696

315

245

Nannynose

336.4

19

60

336.4

19

6146

38.79

1118

1118

420

325

*Code words for XLP insulated products are formed by adding "/XLP"
to the conventional code words above (e.g.-Chihuahua/XLP)
+Conductor temperature of 90 for XLP,75 for Poly;ambient
temperature of 40;emissivity 0.2;2ft./sec.Wind in sun.

Quadruplex ABC Cable

Code Word

Phase conductor

Bare Neutral Message

Nominal lay Length

Weight Per 1000 ft.(lbs.)

Allo wable Amp acitles

Size (A WG)

Stranding

Insul Thick(Mils)

Size (AWG)

Stranding

Rated Strength (lbs.)

inches

XLP

POLY

XLP

POLY

AAC Neutral-messenger

Clydessdale

4

1

45

4

7

881

20.58

198

198

100

80

Pinto

4

7

45

4

7

881

20.58

211

211

100

80

Mustang

2

7

45

2

7

1350

25.42

318

318

135

105

Criollo

1/0

9

60

1/0

7

1990

25.42

503

503

180

140

Percheron

2/0

11

60

2/0

7

2510

29.97

619

619

205

160

Hanovarian

3/0

17

60

3/0

19

3310

35.18

764

764

235

185

Oldenburg

4/0

18

60

4/0

19

4020

35.18

945

945

275

210

Lippizaner

336.4

19

80

336.4

19

6146

38.79

1519

1519

370

280

*Code words for XLP insulated products are formed by adding "/XLP"
to the conventional code words above (e.g.-Chihuahua/XLP)
+Conductor temperature of 90 for XLP,75 for Poly;ambient
temperature of 40;emissivity 0.2;2ft./sec.

5 Advantages

In comparison to bare overhead distribution lines, ABC Cables have
very high reliability during the services. As the power and neutral
conductors are insulated with the best dielectric material,
resulting in the following advantages:

Less fault rate on account of good protection against line and
ground fault by high winds or falling trees or birds especially in
hilly areas & forests as encountered in Rural distribution
networks

High Insulation resistance to earth in all polluted atmosphere.
Negligible currents and low losses

Multiple circuits of Power and Telephone Cables could be strung in
the same set of poles or any other supports like walls etc