An Inside Look at Hazardous (Classified) Locations

When you're looking for answers on hazardous (classified) location questions, where should you turn? Think of Articles 500 through 517 as a mini codebook dedicated specifically to that subject. Article 500 is the foundation within it you'll find the definitions and general requirements that apply to all hazardous locations. More specifically, the properties of materials present (or likely to be present)

Advertisement

When you're looking for answers on hazardous (classified) location questions, where should you turn? Think of Articles 500 through 517 as a mini codebook dedicated specifically to that subject. Article 500 is the foundation — within it you'll find the definitions and general requirements that apply to all hazardous locations.

More specifically, the properties of materials present (or likely to be present) determine the hazard classification — and which 501-503 Article(s) apply. Article 504 provides the requirements for a certain protection technique known as “Intrinsically Safe Systems.” Articles 505 and 506 provide requirements for the “Zone” method of area classification, which is an alternative method to Articles 500-503. The NEC classifies specific hazardous locations by use in Articles 511 through 517. Article 500 is also loaded with Fine Print Notes. While not Code requirements [90.5(C]), they are immensely helpful in making a hazardous location safe.

The Fire Triangle (Fig. 1) helps clarify the rationale behind hazardous (classified) location requirements. The three components are fuel, oxygen, and a source of ignition. Fire needs all three.

Locating wiring and equipment outside of the classified location provides the safest electrical installation — usually at the least cost [500.5(A) FPN].

As an installation standard [90.2(A)], the NEC doesn't cover battery-operated equipment. OSHA regulates the use of battery-operated equipment in hazardous (classified) locations.

“Explosionproof” means the device contains the explosion so external temperature won't ignite the surrounding flammable atmosphere. It does not mean the device protects against explosion [500.2].

Proper documentation is a requirement for all hazardous (classified) locations. It must be available to those who are authorized to design, install, inspect, maintain, or operate the electrical equipment [500.4].

Classification. Classification is not set by the entire facility. Rather, it is determined by individual room, section, or area [500.5(A)]. In fact, the same structure might contain a mix of different classifications. Although detailed descriptions of these classifications may seem overwhelming, they can be simplified by Class:

I: Presence of flammable gases or vapors that may be present in the air and in quantities sufficient to produce explosive or ignitible mixtures [500.5(B)].

II: Presence of combustible dust that may be suspended in the air with quantities sufficient to ignite or explode [500.5(C].

III: Presence of easily ignitible fibers or flyings that aren't likely to be suspended in the air in quantities sufficient to produce ignitible mixtures [500.5(D)].

Division. Confusion may also result when we append a “Division” to the Classification. We can cut through the fog there, as well.

Class I:

Class I, Division 1. Ignitible concentrations of flammable gases or vapors may exist in the course of normal operations [500.5(B)(1)].

Class I, Division 2. Volatile flammable gases or vapors would become hazardous only in case of an accident or some unusual operating condition — or under certain conditions [500.5(B)(2)]:

Where volatile flammable liquids or gases are handled, processed, or used, but are normally confined within closed containers and the gases would escape only in the case of accidental rupture or breakdown — or by abnormal operation of equipment.

Where ignitible concentrations of flammable gases or vapors are normally prevented by positive mechanical ventilation, but might become hazardous through abnormal operation of ventilating equipment.

May be present in the air, due to abnormal operations, in quantities sufficient to produce explosive or ignitible mixtures.

Accumulation is normally insufficient to interfere with the normal operation of electrical equipment or apparatus, but where equipment malfunction may result in combustible dust being suspended in the air.

Accumulations on, in, or near electrical equipment could be sufficient to interfere with the safe dissipation of heat from electrical equipment, or could be ignitible by abnormal operation of electrical equipment.

Class III:

Class III, Division 2. Ignitible fibers or flyings are stored or handled other than in the manufacturing process [500.5(D)(2)].

Material group. The material group designates what the atmosphere in a given location contains. Groups A through D apply to Class I. Groups E, F, and G apply to Class II [500.6]. Class III hazardous locations do not have material groups. Here's a quick overview:

These are incapable of releasing sufficient electrical or thermal energy to cause ignition of flammable gases or vapors [500.2]. None of the requirements in Articles 501 through 503, or 510 through 516 apply to intrinsically safe system installations, except as required by Article 504.

You can install these in a general-purpose enclosure in an area that doesn't contain explosive or ignitible mixtures under normal conditions [500.2].

You can implement “other protection techniques used in equipment identified for use in hazardous (classified) locations” [500.7(L)]. The NEC doesn't explain what this means. But the use of the term “identified” provides insight. Article 100 defines it as, “Recognizable as suitable for the specific purpose, function, use, environment, application, and so forth, where described in a particular Code requirement.”

Equipment. Equipment installed in any hazardous location must be identified for the “Class” and explosive, combustible, or ignitible properties of the specific gas, vapor, dust, fiber, or flyings that will be present (Group) [500.6]. But you can still use general-purpose enclosures for:

Thread conduit with a National Pipe Thread (NPT) taper of ¾ inch per foot. Assemble wrenchtight, with at least five threads fully engaged [500.8(D)]. Exception: For listed explosionproof equipment, factory-threaded entries must be made up with at least 4½ threads fully engaged.

So now you've seen the modular structure of the Articles that address hazardous locations. And you can see that breaking down the hazardous location designations by class, division, and material group — in that order — simplifies the task of correctly identifying and implementing the requirements for protecting equipment in hazardous locations. Remember the key concepts, and you'll have little problem correctly applying the other Articles in the Code.

Discuss this Article 2

Randy (not verified)

on Feb 14, 2013

For hazardous locations Who determines the class and division. Is it the plant manager and his team. Do they need forms filled out and submitted to the local buiding department. Whats the process becuase the code book only guides you for wiring methods it dosn't determine the clasification.

When we first mention about hazardous locations, the first thing that comes up to my mind is those areas that have hazardous materials lying around freely out in the open. That is why, at my workplace, we practice safety habits and make them a regular routine. When handling hazardous materials, we make it a habit to put on safety goggles and gloves to protect our body from harmful substances. After finish using them, we always make it a habit to put them away in their original location, which is usually far from sight and far from common walkways. Proper storage methods will help to ensure that a high prevention level can be done to avoid accidents or work hazards.

Photo Galleries

If you’re an electrical engineer striving to earn the highest salary possible, a move to California may be in your future — considering the fact that six of the top 10 highest paying cities for electrical engineers just happen to fall within that state’s borders.

According to in-house research conducted by EC&M in early 2015, nearly two-thirds (64.06%) of the 543 electrical contractors responding to a purchasing practices survey said they currently buy electrical products online.

If you are like most facilities managers, you probably think busway is maintenance-free. There are no moving parts, so what could go wrong — right? Wrong. Check out these 13 photos, view the video online, and watch for the upcoming article in EC&M magazine on “Understanding Electrical Busway Vulnerabilities,” written by John A.

EC&M Webinars

The energy released during an arc flash event can result in severe damage to personnel, equipment, and property. While there are solutions which seek to improve the protection for each, this program will focus on personnel....More

Get more information on the important changes to the 2015 edition of NFPA 70E. More specifically, this event will address hazard analysis and FR clothing performance testing, focusing on the quantification of incident energy and ATPV (or Arc Rating)....More

Are you protected in the event of short circuit fault? Stainless steel cable ties provide a durable method of bundling, identifying and fastening cable in severe and harsh conditions.
Productivity. Reliability. Safety. We’ve Got You Covered....More

Productivity. Reliability. Safety. We’ve Got You Covered.
The connectors and crimping process make the Panduit solution unique. Offering the speed and safety of a compression connection, while exceeding the stringent requirements of IEEE Std 837-2002. Install in ANY weather. No burn permits needed....More

Arlington's TVBU810 delivers the ultimate in versatility for installing wall-mounted TVs in new or retrofit projects. You can install it horizontally or vertically to ensure proper positioning of low voltage connections behind the TV....More