The dry-type transformers are casted with epoxyresin,which are made of high quality materials by means of a strict process with advanced production and testing devices.The product features high reliability and long service life.In accordance with different operation environment,it can be equipped with different protection casings or without casing.It can replace the oil-immersed transformer and be used in the high buildings,business centers,airports,tunnels,chemical plants,nuclear power stations and watercrafts ect.

Normal service conditions 1)Altitude should not be over 1000m:indoor type2)Highest ambient temperature should not over:+40oC;Highest daily average should not over temperature:+30oC3)Highest annual average temperature should not over +20oC,lowest temperature should not below -5oC.We can provide transformer operated in special conditions according to user's requirement.

1.The product is safe,fire-proof,pollution free,and can be used in the load center directly.2.High mechanical strength,strong shour-circuit proof capacity,small partial discharge,excellent thermal stability,high reliability,and long service life.3.Low loss,low noise,energy saving and maintenance free.4.Excellent heat dissipation,great overload capacity and a large operating capacity is available when ONAF is applied.5.Good humidity resistance,it's suitable for operating in the highly humid and harsh environment.6.An intelligent signal and temperature control system is adopted,which can automatically monitor and display all working temperature of the three-phase windings.The blowing fan can give an alarm,switch on and off automatically and conduct tripping operation to protect the transformer.7.Dur to the structure is compact and weight is light,it can save space and decrease the cost of installation.

Method of incoming and outgoing line:1.Incoming line to lower part and outgoing line from upper part2.Incoming line to upper part and outgoing line form upper part3.Incoming line to upper part and outgoing line form side part4.other*If customer has no requirement,the color of outer casing is light grey(the standard color of ANDELI),or you sould indicate color code that you want

About us

Rated capacity(KVA)

Voltage combination(KV)

Connecting groupid

No-load lossess(W)

Load-loss(W)(120 o C)

Load-loss(W)(75 o C)

Short circuit impedance(%)

No-load current(%)

Yawp grade(Db)

IP00(no crust)

IP20(IP23)

High voltage connection end(mm)

Low voltage connectionend(mm)

High voltage(KV)

Tapping(%)

Low voltage(KV)

Length(mm)

Width(mm)

Height(mm)

Gauge(mm)

Gross weight(kg)

Length(mm)

Width(mm)

Height(mm)

Gross weight(kg)

30

6
6.3
10

±5
±2×2.5

0.4

Yyn0 or Dyn11

210

745

650

4.0

2.8

45

670

500

700

400

280

1100

1000

1200

380

M10

30×3

50

300

1050

915

2.5

45

720

500

770

400

400

1200

1000

1200

510

M10

30×3

80

410

1460

1275

2.4

46

760

500

950

400

500

1200

1000

1200

650

M10

30×3

100

450

1665

1455

2.2

46

980

600

1060

500

580

1300

1100

1400

820

M10

30×3

125

530

1950

1700

2

47

1030

650

1100

500

660

1300

1100

1400

880

M10

30×3

160

610

2250

1965

2

48

1050

650

1130

550

720

1500

1100

1400

940

M10

(a)40×4

200

700

2670

2330

1.8

48

1100

650

1150

550

920

1500

1100

1600

1120

M10

(a)40×4

250

810

2920

2550

1.8

49

1150

760

1200

660

1100

1500

1250

1600

1310

M10

(a)40×6

315

990

3670

3205

1.6

49

1210

760

1250

660

1250

1500

1250

1600

1460

M10

(a)40×6

400

1100

4220

3685

1.6

50

1270

760

1420

660

1600

1700

1250

1800

1850

M10

(b)60×6

500

1300

5170

4515

1.6

51

1320

760

1500

660

1850

1700

1250

1800

2100

M10

(b)60×6

630

1500

6220

5430

1.5

52

1360

760

1520

660

2200

1700

1250

1800

2450

M10

(c)80×8

630

1460

6310

5510

6

1.5

52

1430

760

1360

660

2100

1700

1250

1800

2350

M10

(c)80×8

800

1710

7360

6425

1.5

53

1470

1000

1460

820

2300

1900

1500

1800

3000

M10

(c)80×8

1000

1990

8600

7510

1.3

54

1540

1000

1560

820

2800

1900

1500

1800

3100

M10

(d)100×10

1250

2350

10260

8955

1.3

55

1610

1000

1620

820

3200

1900

1500

2000

3510

M10

(d)100×10

1600

2750

12420

10840

1.3

56

1710

1250

1700

1070

3800

2100

1800

2000

4150

M10

(d)120×10

2000

3735

15300

13355

1.1

56

1830

1250

1930

1070

4800

2100

1800

2200

5180

M16

(e)120×12

2500

4500

18180

15870

1.1

57

1850

1250

1970

1070

5400

2100

1800

2300

5800

M16

(e)120×15

Main technical parameters of SC(B)10-30~2500/10 series of transformers