prosoft-technology.com uses cookies for analytics and functionality purposes.
To change your cookie settings or find out more, click here.
If you continue browsing our website or close this banner, you accept these cookies.

Featured Articles

Make sure you connect to your radio with an Ethernet cable (Cat5, Cat5e, Cat6, etc) either directly or through a switch.
*Radio's have auto detect port so straight-through or crossover are fine.
Make sure that any firewalls including the Windows firewall are turned OFF.**When us...

For our PLX3x gateways that feature 2 Ethernet-based protocols (such as EtherNet/IP, Modbus/TCP, Profinet, and SIE) we offer 2 variants: the PLX31 and the PLX32. They are essentially identical except for one critical distinction.The PLX31 variant has a single Ethernet port, and s...

It can be difficult at times to get USB-to-serial adapters working properly. They are not an ideal replacement for proper DB-9 ports as found on older computers. Even modern computers that do have DB-9 ports can have issues. The issue is that USB-to-serial adapters (and most DB-9...

The requirements for Prosoft's CompactLogix InRAx modules are:
* 1769 I/O bus
* 450-800ma @5v from the bus, depending on the MVI module* Placement within 2-4 slots of a CompactLogix power supply, depending on the MVI moduleThe power and Distance Rating (proximity to power supply)...

Prosoft gateways and in-chassis PLC modules which are configured via Ethernet use UDP port 50000 for discovery and UDP port 3000 for configuration and online diagnostics.Web based services for products including AN-X2 and Fieldserver gateways require TCP port 80Some of the more c...

The database addresses of all ProSoft modules and gateways consist of 16 bit integers. Therefore when dealing with 32 bit floating point data, or REAL values, they are stored as two consecutive 16 bit integers. Converting from Integers into FloatsIn all versions of RS...