KEY FEATURES

SHRMi Specifications

1) Simultaneous heating and cooling
The SHRM-i allows freely selectable heating and cooling from each indoor unit on a single refrigerant piping system.

Flexible refrigerant flowThe flow selector unit can automatically shift the flow of refrigerant carried to the indoor unit, thereby switching between heating and cooling modes. Recovered energy from one unit can be used to supply another unit on the same system.

More efficient heat recovery operation than individual heating and cooling only
SHRM-i achieves the highest energy efficiency when both heating and cooling are provided simultaneously, as recovered energy from one zone is recycled for use in another. Highest efficiencies are achieved when heating and cooling capacities are near equal.

World-class EER and COP at partial load
Adopting the new super-efficient DC twin-rotary compressors and advanced vector-controlled inverters realizes a partial load COP of 5.63 and EER of 6.02 on the BHP model.

Rotary compressor
Unlike scroll compressors that have to initially exceed capacity in order to achieve target partial load, the rotary compressors can efficiently achieve the same target load with little energy loss.

Precision comfort
What truly makes the SHRM-i one the most flexible solutions available is its ability to provide simultaneous heating and cooling. Temperatures can be controlled and maintained precisely throughout the day. Room temperature is monitored and the air conditioning mode is switched to maintain the ideal temperature. As a result, temperature fluctuations are maintained within just± 1.5c.

3) Flexible piping configurations mean ease of installation and flexible designA key advantage of the SHRM-i system is its installation flexibility. Flexible piping configurations allow unsurpassed installation ease. With only a small footprint outdoors, indoor air conditioning units can be placed at a farthest equivalent distance of 200m.