Burn Down Transformer - ATG Series

Burn down transformers enable the user to change a high-resistive fault into a low-resistive fault. This then allows a TDR to be used for low resistance fault pre-location.

BAUR ATG 2 Burn Down Transformer

Portable, Easy to use

Output voltage up to 10 kV DC

Optimized power matching by 6 output voltage ranges; switchable even at full load (2,3 kVA )

Individual electronic voltage and current control

Integrated terminal for connection of external ohmmeter

AC output for use in low voltage system

Safety control circuit according to VDE 0104

The portable burn down transformer is enclosed in a sturdy 19 “steel housing. The well-proven power electronics allows individual control of output voltage and current. A vital step to a practical burn down technique.

BAUR ATG 6000 Burn Down Generator

Powerful, High Power Fault Burner

Output voltage up to 15 kV DC, 6 kVA

Max. output current 90 A

Optimized power matching by 8 output voltage ranges; switchable at full load

Safety control circuit according to VDE 0104

Individual electronic voltage and current control

Operation on maximum power (short circuit proof) up to one hour

The high-power burn down transformer ATG 6000 is oil-cooled and therefore capable of full power output up to one hour. Even during the burn down procedure the output voltage is switchable in 8 ranges. Continuous regulation of voltage and current from 0 to 100 % within the selected range enables a precise regulation of desired output values. The 19“ rack version ATG 6000 is ideally designed for use in a cable fault location system, but can also be used as a portable unit.