Technical Data

Capacitive couplings pF/km at 800 Hz
k1 (98%/100% of all values)
k9-12 (98%/100% of all values)

≤ 1333/2666
≤ 333/1000

Operating voltage V

≤ 225

Alternating voltage test 50 Hz
core-core Veff
core-screen Veff

500
2000

Temperature ranges
during laying, installing °C
before and after laying, installing °C

-20 to +50
-40 to +70

Application

As connection cable in subscriber networks and private branch exchanges, for telephony and data transmission. Suitable for laying in the ground and in cable ducts, as well as for threading into cable conduits. The cables are approved by VDE (certificate with production monitoring) and released for use in the area of operation of Deutsche Bahn AG.

Type Designation Codes

A

outdoor cable

02YS

conductor insulation made from cell PE with outer polyolefin layer

F

cable core filled with petroleum jelly, longitudinally watertight

(L)2Y

laminated sheath, transversally watertight

St III

starquad in the local cable

Bd

stranded in bundles

(H42)

Mutual capacitance max value 42 nF/km

Additional Informations

Design according to national and international standards
Design according to customer specifications