OVENTROP-Station for hot water preparation "Regumaq X-30-B" (fresh water station)

Electronically controlled product assembly with heat exchanger for the hygienic heating of potable water on the flow principle. The potable water is only heated when it is needed ,e.g "just in time". For connection to buffer storage cylinders. Depending on the temperature and the flow volume on the potable water side, the circulation pipe on the heating side is speed regulated.

The plate heat exchanger complies with the specifications of the European Pressure Equipment Directive (PED). Due to the turbulent flow, a good self-cleaning effect avoiding a contamination is achieved.

The plate heat exchanger can be flushed using the fill and drain cocks integrated in the primary and secondary circuit. The potable water circuit is protected by a 10 bar safety valve. The components of the heat exchanger system have flat sealing connections, are pre-assembled on a mounting board and leak tested.

The controller "Regtronic RQ-B" is wired up with the internal electric components and features a data bus (S-bus) for the connection to the data logger "CS-BS".

-Heat exchanger: 30 plates -Discharge capacity: 20-45 l/min., depending on the set potable water temperature and the existing buffer water temperature -Connections: G 1 flat sealing for the connection to the buffer and potable water circuit