Continuous or periodic exhaust ventilation of bathroom, showers, kitchens and other utility spaces.

Ventilation shaft mounting or duct connection.

Low to medium air flow motion for short distances at low air resistance..

Compatible with 100, 125 and 150 mm air ducts.

DESIGN

Modern design and aesthetic look.

The casing and the impeller are made of high-quality durable ABS plastic, UV resistant.

The intellectual impeller design makes the fan efficiency high and the service life long.

Protection rating IP 34.

MOTOR

Reliable and low-watt electric motor.

Designed for continuous operation and requires no maintenance.

Equipped with overheating protection.

CONTROL

Manual:

The fan is controlled by a room light switch. It is not included in the delivery package.

The fan is controlled by the built-in pull cord switch V. Not applied in case of ceiling mounting.

Speed control is possible through a thyristor speed controller (see Electrical Accessories). Several fans may connected to the same controller. Speed controllers can not be connected to the fans with T, TH, TP, VT, VTH modification.

Automatic:

By the electronic control unit BU-1-60 (see Electrical Accessories). The control unit is supplied separately.

By the timer T (the built-in run-out timer enables the fan operation within 2 to 30 minutes after the fan switching off).

By the humidity sensor and timer TH (if the humidity level in the room exceeds the sensor threshold adjustable value within 60-90% the fan switches automatically on and operates until the humidity level drops to the standard level, after that the fan continues operating within the time period according to the timer setting, then shuts down).

By the motion sensor and the timer TP (in case of motion detection the fan switches automatically on and operates within the set time period from 2 to 30 minutes. The motion sensitivity area is up to 4 meters and the maximum detection angle is 100°.

MOUNTING FEATURES

The fan is mounted directly into the ventilation shaft or used for ceiling mounting with the connection to the duct.

Flexible duct application is recommended in case of remote location of the ventilation shaft. The air duct is connected to the fan exhaust flange through a clamp.

Fixed to the wall by self-tapping screws.

For 12 V low-voltage motor fan connection to 220 V / 50 Hz power mains use the step-down transformer TRF 220/12-25 that is available upon separate order.

The motor is equipped with ball bearings for long service life (appr. 40 thousand hours) and fan mounting at any angle. The bearings are maintenance-free and contain enough grease for the entire operating period.