3 English Assembly and operating instructions Type AWD3D5WM Three-phase active power energy meter with M-Bus interface, Pic. 1 Description Energy meter with M-Bus interface enables the reading of all relevant data like meter reading, electricity, voltage and power (active and reactive). Technical data Connection Pic. 2 diagram Dimensions Pic. 3 Accuracy class B according to EN , 1 according to IEC Reference, Maxi- Iref = 5 A, Imax = 6 A, Ist = 10 ma mum, initial current operating voltage 3 230/400 VAC, 50 Hz Tolerance 20%/+15% Counting range , kwh LED-Ouptut 10 Imp/kWh Connections Conductor cross-section 1,5 16 mm 2, Main circuit screwdriver pozi no. 1, slot no. 2, torque 1,5 2Nm Connections Conductor cross-section max. 2,5 mm 2, Control circuit screwdriver pozi no. 0, slot no. 2, torque 0,8 Nm Operating C (noncondensing temperature Environment Indicating elements (Pic. 4) according standard EN50470) Mechanical M2 Electromagnetic E2 (kwh) Shows total consumption T1part. (kwh) Shows partial consumption, this value is resettable CT Shows the sett current transformer ratio Select The transformer ratio can be selected in Menu item Select, in the open bridge Z1-Z2 Shows the instantaneous power per phase or all phases Shows the voltage per phase Shows the current per phase kwh Shows the unit kwh when the consumption is displayed / / For P-, U-, I- or display, the corresponding phase is displayed In case of missing phase or wrong current direction. The corresponding phase is additionally displayed. Notes before connecting 1. Do not connect, or to N 2. In order to avoid moisture in the meter due to condensate build-up, acclimatise the meter at room temperature for about half an hour before connecting. 3. N must always be connected. Attention! These devices must only be installed by a professional electrician, otherwise there is the risk of fire or the risk of an electric shock. Wiring diagram The secondary, mains current transformer connection is to be connected to the phase to be measured and therefore the transformer don t have to be grounded. This connection is to be fused according to the local installation instructions. Operation of the LCD display See page with LCD menu navigation. The bridge Z1-Z2 should be removed for adjusting the transformer ratio. Installation instructions The three-phase energy meter can be attached to a 35 mm rail (EN60715TH35). The meter can be used only in installation cabinets. Declaration of Conformity CE We, Saia-Burgess Controls AG, CH 3280 Murten (Switzerland), herewith declare, on our own responsibility that the products: AWD3D5WM00C3A00 which this certificate refer to, are in accordance with the directive 2004/22/EG (MID) and the following standards: EN50470 parts 1 and 3 (electronic meter), of October Murten, Conformity Assessment Body: METAS-Cert, Nr CH-3003 Bern-Wabern Signed: Urs Tanner, Site Quality Leader e Subject to change without notice

4 English Technical data M-Bus Bus system Standard Bus length Transmission rates Response time (system response) M-Bus EN13757 According to M-Bus specification. 300, 2400, 9600 Bd. The transmission rate is automatically detected. Write: up to 60 ms Read: up to 60 ms Data transmission When reading out the values, all values are transferred in a telegram It supports the following telegrams: Initialisation SND_NKE Response: ACK Reading meter REQ_UD2 Response: RSP_UD Changing primary address SND_UD Response: ACK Reset T part SND_UD Response: ACK Slave selection for secondary addressing SND_UD Response: ACK (Further information you will find on the website under the document PP ) The device does not respond to unknown queries The transmission rate is automatically detected The device has a voltage monitor. In the case of a power failure, all the registers in the EEPROM are saved. Changing the M-Bus primary address In order to change the M-Bus primary address, hold down touch for 3 sec. In the following menu, increases the address by 10, increase the primary adress by 1 When the desired address is set, wait until the main display appears again Secondary addressing It is possible to communicate with the energy meter usint the secondary address, according to EN13757 The use of Wild Cards is possible Saia-Burgess Controls AG Bahnhofstrasse 18 I CH-3280 Murten I Schweiz T I F

Conformity Declaration according to the Directive on the Restriction of Hazardous Substances (RoHS) 2011/65/EU We hereby declare that the following products and their associated spare parts and accessories

CABLE TESTER Manual DN-14003 Note: Please read and learn safety instructions before use or maintain the equipment This cable tester can t test any electrified product. 9V reduplicated battery is used in

Filing system designer FileDirector Version 2.5 Novelties FileDirector offers an easy way to design the filing system in WinClient. The filing system provides an Explorer-like structure in WinClient. The

Kuhnke Technical Data The following page(s) are extracted from multi-page Kuhnke product catalogues or CDROMs and any page number shown is relevant to the original document. The PDF sheets here may have

p^db=`oj===pìééçêíáåñçêã~íáçå= Error: "Could not connect to the SQL Server Instance" or "Failed to open a connection to the database." When you attempt to launch ACT! by Sage or ACT by Sage Premium for

Application of EN ISO 13849-1 in electro-pneumatic control systems Hazards and measures against hazards by implementation of safe pneumatic circuits These examples of switching circuits are offered free

Exercise (Part XI) Notes: The exercise is based on Microsoft Dynamics CRM Online. For all screenshots: Copyright Microsoft Corporation. The sign ## is you personal number to be used in all exercises. All

BEDIENUNGSANLEITUNG To comply with the published safety standards, the following must be observed when using this power supply. Um den zur Zeit gültigen Sicherheitsbestimmungen zu genügen, müssen die nachstehenden