Are You a

Builder?

From the Manufacturer

New, quieter PTAC design with improved air distribution

New Two Motor Design
With separate indoor and outdoor motors, the indoor motor can run at slower speeds which reduces sound levels indoors.

New Tangential Blower Wheel
Tangential blower wheel has nearly 5x the surface area of a typical fan used on other pTAcS. The result is more uniform airflow over a wider path for faster, more even air distribution throughout the room and improved sound levels.

Air is blown over the entire length of the tangential wheel into the room in a uniform laminar airflow.

3 Speed Fan
Friedrich is the only major PTAC brand with 3 fan speeds in cooling and heating mode.

Universal Heater/Power Cord
All PTAC units ship complete with the standard power cord for that model (7K, 9K and 12K = 3.0 kW and 15K = 5.0 kW). If you want to adjust the heater size on any PTAC unit simply unplug the attached power cord and connect the desired size. It is important to ensure that all wiring and building connections are sized properly for the power cord as well.

Universal heater allows installers to change the heat output of the pTAc by changing the power cord, simplifying ordering and installation.

Energy Usage & Management
° EERs up to 12.0; COPs up to 3.4 for increased energy savings
° Owners and operators have the flexibility to set separate heat and cool range limits
° Desk control ready allowing hotel owners to control units from a central location
° Electronic defrost control ensures more run time in the efficient heat pump mode

Health & IAQ
° Fresh air damper control to bring in fresh outside air when desired
° Washable, antimicrobial air filters

Energy Info

This air conditioner has an Energy Efficiency Rating of 11.3 and has an estimated yearly operating cost of $66.25.

The estimated yearly operating cost is based on the 2011 national average cost of $.1109 cents per kWh for electricity and an estimated number of operating hours of 750 hours. Your operating cost will depend on your utility rates and usage.

Specifications

Dimensions & Weights

Sleeve Width:

42"

Front Cover Width:

42"

Sleeve Depth:

13 3/4"

Front Cover Depth:

7 3/4"

Sleeve Height:

16"

Front Cover Height:

16"

Cutout Width:

42 1/4"

Cutout Height:

16 1/4"

Package Width:

43 1/2"

Package Depth:

23"

Package Height:

19 3/4"

Net Weight:

111 lbs.

Shipping Weight:

131 lbs.

Performance Data

Cooling:

9,000 BTU/Hr.

Power:

800 Watts

EER:

11.3

Dehumidification:

2.2 Pints/Hr.

Sensible Heat Ratio:

0.81

R-410A Charge:

33.51 Oz.

Electrical Data

Voltage (1 Phase, 60 Hz):

265 Volts

Volt Range:

292-239

Current:

3.7 Amps

Power Factor:

0.99

Compressor LRA:

18.0 Amps

Compressor RLA:

2.9 Amps

Fan Motor:

0.029 HP

Airflow Data

Indoor CFM - High:

360

Indoor CFM - Medium:

330

Indoor CFM - Low:

300

Vent CFM:

75

Electric Heating

Heater Watts:

3,000 Watts

Voltage:

265 Volts

Heating:

10,236 BTU/Hr.

Heating Current:

11.4 Amps

Min. Circuit Ampacity:

14.6

Branch Circuit Fuse:

20 Amps

Features

IMPORTANT NOTE: Sleeves are sold and shipped separately to accommodate new construction and replacement requirements.

The fan start and stop delays prevent abrupt changes in room acoustics due to the compressor energizing or stopping immediately.

Upon call for cooling or heating, the unit fan will run for five seconds prior to energizing the compressor.

Also, the fan off delay allows for "free cooling" by utilizing the already cool indoor coil to its maximum capacity by running for 30 seconds after the compressor.

Remote Thermostat Operation

Some applications require the use of a wall-mounted thermostat.

All new Friedrich PTACs may be switched from unit control to remote thermostat control easily without the need to order a special model or accessory kit.

Internal Diagnostic Program

The new Friedrich digital PTAC features a self diagnostic program that can alert maintenance to component failures or operating problems.

The internal diagnostic program saves properties valuable time when diagnosing running problems.

Service Error Code Storage

The self diagnosis program will also store error codes in memory if certain conditions occur and correct themselves such as extreme high or low operating conditions or activation of the room freeze protection feature.

Storing error codes can help properties determine if the unit faced obscure conditions or if an error occurred and corrected itself.

Electronic Temperature Limiting

By limiting the operating range, the property can save energy by eliminating "max cool" or "max heat" situations common with older uncontrolled systems.

The new electronic control allows owners to set operating ranges for both heating and cooling independently of one another.

Room Freeze Protection

When the PTAC senses that the indoor room temperature has fallen to 40°F, the unit will cycle on the fan (high) and the electric strip heat to raise the room temperature to 46°F, and then cycle off again.

This feature works regardless of the mode selected and can be turned off.

The control will also store the Room Freeze cycle in the service code memory for retrieval at a later date.

This feature ensures that unoccupied rooms do not reach freezing levels where damage can occur to plumbing and fixtures.

Random Compressor Restart

Multiple compressors starting at once can often cause electrical overloads and premature unit failure.

The random restart delay eliminates multiple units from starting at once following a power outage or initial power up.

The digital control monitors indoor conditions to ensure that the room temperature is within five degrees of the setpoint. If necessary, the unit will cycle the electric heat to maintain the temperature.

This feature ensures guest comfort by delivering the heating benefits of an electric heater while maintaining the efficiency benefits of a heat pump.

Separate Heat/Cool Fan Cycle Control

The owner may choose between fan cycling or fan continuous mode based on property preference.

Fan continuous mode is used to keep constant airflow circulation in the room during all times the unit is 'ON'.

Fan cycle will conserve energy by only operating the fan while the compressor or electric heater is operating.

The ability to set the fan cycling condition independently between heating and cooling mode will increase user comfort by allowing the choice of only constantly circulating air in the summer or winter time.

Unlike other PTAC brands that only allow one selection.

Emergency Heat Override

In the event of a compressor failure in heat pump mode, the compressor may be locked out to provide heat through the resistance heater.

This feature ensures that even in the unlikely event of a compressor failure, the room temperature can be maintained until the compressor can be serviced.

Controlling the unit from a remote location like the front desk can reduce energy usage and requires no additional accessories on the PTAC unit.

Indoor Coil Frost Sensor

The frost sensor protects the compressor from damage in the event that airflow is reduced or low outdoor temperatures cause the indoor coil to freeze.

When the indoor coil reaches 30°F, the compressor is disabled and the fan continues to operate based on demand.

Once the coil temperature returns to 45°F, the compressor returns to operation.

Ultraquiet Air System

The new Friedrich PD series units feature an indoor fan system design that reduces sound levels without lowering airflow or preventing proper air circulation.

High Efficiency

The Friedrich PTAC has been engineered so that all functional systems are optimized so that they work together to deliver the highest possible performance.

Dual Motor

With Friedrich's new dual-motor design the indoor motor can run at slower speeds which reduces sound levels indoors.

Rotary Compressor

High efficiency rotary compressors are used on all Friedrich PTACs to maximize durability and efficiency.

Stainless Steel Endplates

Outdoor coil endplates made from stainless steel reduce corrosion on the outdoor coil common with other coil designs.

Top-Mounted Antimicrobial Air Filters

All Friedrich PTAC return air filters feature an antimicrobial element that has proven to prevent mold and bacterial growth in laboratory testing.

PDXFT replacement filter kits feature the same antimicrobial agent.

All filters are washable, reusable and easily accessed from the top of the unit without the removal of the front cover.

Filtered Fresh Air Intake

Friedrich PTAC units are capable of introducing up to 75 CFM of outside air into the conditioned space.

The outdoor air passes through a washable mesh screen to prevent debris from entering the airstream.

R-410A Refrigerant

Friedrich PTAC units use environmentally-friendly refrigerant.

Friedrich PDE09R3SF Reviews

Quick Ship

Items labeled Quick Ship will ship within 2 business days from our East Coast warehouse. Actual delivery times will vary based on your location. If you are ordering multiple items and not all items qualify for Quick Ship, the order will ship when all items are available to ship. Quick Ship may not apply to multiple quantities of the same product.

BTU Calculator

Warranty

Add an extended warranty for full coverage of parts & labor with fast, in-home repairs by certified technicians.

50% Cash Back Offer on 5 Year Warranties:

If no claims are filed during the 5 year period, you are eligible to receive a gift card of 50% off your original arrant purchase price.

Redemption instructions will be sent via mail within a few weeks of your purchase.