Overhead secondary service drop attachment to customer-owned service and meter pole to underground service entrance
Single phase or Three Phase 240 volt maximum, self-contained meter
400 ampere maximum

Typical Connectors to be provided by the customer for serving a single point of connection for multiple enclosed service entrance conductors

Distribution Block Connectors when used for Service Drop connections to service entrance conductors shall be covered to avoid inadvertent contact. Except the neutral connection of service cable assemblies may be bare.