Feature Products

6-10KVA High Frequency UPS (1:1)

INQUIRY DETAILS *

Product Detail

Specification

Applications

Documents

Solution

Venus series is double-conversion high frequency online UPS with a output power factor 0.8. Specifically designed for operation in poor power areas. They provides high power density with long backup time in compact size. It’s ideal for ATMs, banking and other business critical applications. Users also can adjust charging current from 1A to 6A according to different applications.Venus Series also have USB and RS-232 communication ports as standard, with a built-in intelligent slot for additional adapters, protocol converters and relate contact cards.

Main Features

1.True double-conversion online UPS

A true double conversion UPS will provide clean, high level quality power to fully protect mission-critical devices such as sensitive networks, small computer centers, servers, telecom applications, as well as for industrial applications.

2. Output power factor 0.8

Compared to the online UPS in the current market, Venus series UPS provides better output power factor up to 0.8. It offers higher performance and effciency for critical applications.

3. Wide input voltage range (110V-300V)

Venus series can still provide stable power to connected devices under unstable power environments.

4. 50/60 Hz Frequency Converter Mode

Lock output frequency at 50Hz or 60Hz to suit power sensitive equipments.

6.Emergency Power Off (EPO) Function

This feature can secure the personnel and equipment in case of fires or other emergencies.

7. DSP technology applied for 6-10K models

A DSP controller provides an improved and cost-effective solution with high performance.

Monitoring Software

• UPS can be connected to the computer via USB or Rs232 interface. So it can be realized LAN monitoring single or many sets of UPS, it also can monitor the other ups which connected to the computer via LAN.

• UPS monitoring software has more than 10 kinds of language for choice.

• Humanized operation interface, which is powerful and can shows the battery voltage, frequency, load, temperature and other data by real-time monitoring through the charts.

• Alarm of different power incident could be set by radio, mobile phone text messages, e-mails and SNMP etc.

Technical Specification

High Frequency UPS

MODEL

PHT1106

PHT1110

PHT1106B

PHT1110B

CAPACITY

6000VA / 4800W

10000VA / 8000W

6000VA / 4800W

10000VA / 8000W

Battery Voltage

192V

Size, D X W X H (mm)

369 x 190 x 318

442x 190 x 318

369 x 190 x 688

442x 190 x 688

Net Weight (kgs)

21

23

72

82

INPUT

Voltage Range

Low Line Transfer

110 VAC ± 3 % at 50% Load; 176 VAC ± 3 % at 100% Load

Low Line Comeback

Low Line Loss Voltage + 10V

High Line Transfer

300 VAC ± 3 %

High Line Comeback

High Line Loss Voltage – 10V

Frequency Range

46Hz ~ 54 Hz @ 50Hz

56Hz ~ 64 Hz @ 60Hz

Phase

Single phase with ground

Power Factor

≧ 0.99 at 100% Load

OUTPUT

Output voltage

208/220/230/240VAC

AC Voltage Regulation

± 1%

Frequency Range

(Synchronized Range)

46Hz ~ 54 Hz @ 50Hz

56Hz ~ 64 Hz @ 60Hz

Frequency Range (Batt. Mode)

50 Hz ± 0.1 Hz or 60Hz ± 0.1 Hz

Overload

AC mode

100%~110%: 10min、110%~130%: 1min、>130% : 1sec

Battery mode

100%~110%: 30sec、110%~130%: 10sec、>130% : 1sec

Current Crest Ratio

3:1 max

Harmonic Distortion

≦ 3 % @ 100% Linear Load; ≦ 6 % @ 100% Non-linear Load

Transfer Time

AC Mode to Batt. Mode

0 ms

Inverter to Bypass

0 ms

Waveform (Batt. Mode)

Pure Sine Wave

EFFICIENCY

AC Mode

> 89%

> 90%

> 89%

> 90%

Battery Mode

> 88%

> 89%

> 88%

> 89%

BATTERY

Battery Type

Depending on applications

12V7AH

12V9AH

Battery Numbers

Depending on applications

16

Recharge Time

Depending on applications

9 hours recover to 90% capacity

Charging Current

Default: 4 A ± 10%; Max.: 6A ± 10%

Default : 1 A ± 10%; Max.: 2A ± 10%

Charging Voltage

218.4 VDC ± 1%

ENVIRONMENT

Operation Temperature

0 ~ 40°C (battery life cycle will be shorten when temperature is above 25°C)