Can I use two cables per lug on an LA or LAL breaker?

Cause:
Need to bring in (2) wires per phase on an LA breaker, want to use lugs listed for this application

Resolution:
Yes. The standard lug is AL400LA. It has been tested and UL listed for two cables per pole, up to 250 kcmil. Some inspectors may tell you it cannot be used, but they are incorrect. It may be applied as listed.