Cooling system designed to operate in ambient conditions up to 50°C (122°F).

Performance 50 Hz 60 Hz

Engine Speed: RPM 1500 1800

Gross Engine Power: kW (hp)

-Standby: 31.0 (42.0) 36.5 (49.0)

-Prime: 28.2 (38.0) 33.1 (44.0)

BMEP: kPa (psi)

-Standby: 752.0 (109.0) 738.0 (107.0)

-Prime: 684.0 (99.2) 669.0 (97.0)

Regenerative Power: kW 7.0 9.0

Lubrication System

Oil Filter Type: Spin-On, Full Flow

Total Oil Capacity l (US gal): 8.3 (2.2)

Oil Pan l (US gal): 7.8 (2.1)

Oil Type: AP1 CG4 15W-40

Cooling Method: Water

Fuel System

Fuel Filter Type: Replaceable

Element Recommended Fuel: Class A2 Diesel

Fuel Consumption: l/hr (US gal/hr)

110% 100% 75% 50%

Load Load Load Load

P30P1

50 Hz 7.6 (2.0) 6.9 (1.8) 5.2 (1.4) 3.8 (1.0)

60 Hz 8.9 (2.4) 8.0 (2.1) 6.2 (1.6) 4.7 (1.2)

P33E1

50 Hz 7.6 (2.0) 5.7 (1.5) 4.1 (1.1)

60 Hz 8.9 (2.4) 6.8 (1.8) 5.0 (1.3)

(based on diesel fuel with a specific gravity of 0.85 and conforming to BS2869, Class A2)

Exhaust System 50 Hz 60 Hz

Silencer Type: Level 1

Silencer Model & Qty: SD50 (1) Pressure Drop Across

Silencer System: kPa (in Hg) 1.80 (0.532) 2.00 (0.591)

Silencer Noise Reduction

Level: dB 20 19

Max. Allowable Back

Pressure: kPa (in. Hg) 15.0 (4.4) 15.0 (4.4)

Exhaust Gas Flow:

m³/min (cfm) -Standby: 6.2 (219) 7.5 (265)

-Prime: 5.2 (184) 6.3 (222)

Exhaust Gas Temperature: °C (°F)

m³/min (cfm) -Standby: 490 (914) 510 (950)

-Prime: 472 (882) 501 (934)

P30P1 / P33E1

Alternator Performance Data

Data Item

50 Hz 60 Hz

415/240V

400/230V

230/115V

200/115V

380/220V

220/110V

220/127V

480/277V

240/139V

380/220V

220/110V

240/120V

208/120V

230/115V

440/254V

220/127V

Motor Starting Capability* kVA

64

60

55

71

70

47

55

52

61

Short Circuit Capacity** %

0

0

0

0

0

0

0

0

0

Reactances: Per Unit

Xd X'd X''d

1.970

0.100

0.052

2.120

0.110

0.056

2.350

0.120

0.062

1.750

0.090

0.046

1.990

0.110

0.053

3.170

0.170

0.084

2.650

0.140

0.070

2.860

0.150

0.076

2.370

0.130

0.063

Reactances shown are applicable to prime ratings

Based on 30% voltage dip. Improved motor starting capability is available with optional Permanent Magnet generator or AREP excitation.

** With optional Permanent Magnet generator or AREP excitation.

Alternator Technical Data

Physical Data Operating Data

Manufacturer: FG WILSON

Overspeed: RPM 2250

Model: LL1014S

Voltage Regulation (steady state) (%): + /- 0.5

No. of Bearings: 1

Wave Form NEMA = TIF: 50

Insulation Class: H

Wave Form IEC = THF: 2.0%

Winding Pitch Code: 2/3 - 6

Total Harmonic Content LL/LN:4.0%

Wires: 12

Supression is in line with European Standard

Radio Interference: EN61000-6

Ingress Protection Rating: IP23

Radiant Heat: kW (Btu/min)

-50 Hz 3.3 (188)

-60 Hz: 3.8 (216)

Excitation System: SHUNT

AVR Model: R230

P30P1 / P33E1

Technical Data

3 Phase Ratings and Performance at 50 Hz, 1500 RPM

3 Phase Ratings and Performance at 60 Hz, 1800 RPM

Voltage Prime Model Standby Model Voltage Prime Model Standby Model

P30P1 P33E1 P30P1 P33E1

kVA kW

kVA kW

kVA kW

kVA kW

415/240V

30.0 24.0

33.0 26.4

480/277V

33.8 27.0

37.5 30.0

400/230V

30.0 24.0

33.0 26.4

220/127V

33.8 27.0

37.5 30.0

380/220V

30.0 24.0

33.0 26.4

380/220V

33.8 27.0

37.4 29.9

230/115V

30.0 24.0

33.0 26.4

240/120V

33.8 27.0

37.5 30.0

220/127V

30.0 24.0

33.0 26.4

230/115V

33.8 27.0

37.5 30.0

220/110V

30.0 24.0

33.0 26.4

440/254V

33.8 27.0

37.5 30.0

200/115V

30.0 24.0

33.0 26.4

220/110V

33.8 27.0

37.4 29.9

208/120V

33.8 27.0

37.5 30.0

230/115V

33.8 27.0

37.5 30.0

Definitions

Standby Rating

These ratings are applicable for supplying continuous electrical power (at variable load) in the event of a utility power failure. No overload is permitted on these ratings. The alternator on this model is peak continuous rated (as defined in ISO 8528-3).

Prime Rating

These ratings are applicable for supplying continuous electrical power (at variable load) in lieu of commercially purchased power. There is no limitation to the annual hours of operation and this model can supply 10% overload power for 1 hour in 12 hours.