Ordering Information

The CyberPower Smart App Online OL6000RT3UPDUTF rack/tower uninterruptible power supply (UPS) with Maintenance Bypass Switch, LCD Control Panel and pure sine wave output safeguards mission-critical servers, data center and telecom equipment, VoIP and internetworking hardware that require seamless power correction. Its Online Double Conversion topology is generator compatible and delivers consistent and clean 120V and 200-240VAC power with zero transfer time to protect connected equipment and prevent costly business interruptions. Auto-bypass insures connected equipment continues to operate seamlessly when an overload or internal fault is detected. Maintenance Bypass Switch allows for the UPS power module to be hot-swapped for service or replacement without cutting power to the connected equipment.

The LCD Control Panel provides (43) information status and configuration settings to customize the operating parameters for the OL6000RT3UPDUTF, plus it can be removed and mounted separately from the UPS for ease of use regardless of where the UPS is installed. Functions include menus for checking power status on (19) different parameters, (24) settings for setup, control and testing of the UPS, and (3) selections for event logging. With a DB26 cable (available separately) the LCD Control Panel can be removed from the UPS and relocated up to 10ft away from the UPS for ease of viewing when installed in hard to reach locations.

The UPS incorporates microprocessor-based digital control and includes PowerPanel Business Edition providing the user unsurpassed flexibility and control. An optional SNMP/HTTP Remote Management card (RMCARD302/303) supports networked management and control of the OL6000RT3UPDUTF through a standard web browser. The RMCARD303 additionally supports the connection of the optional ENVIROSENSOR to monitor temperature & humidity, receive notifications and monitor 3rd party sensors via dry contacts.

The OL6000RT3UPDUTF unit has a capacity of 10,000VA/9,000W (0.9 power factor) that can be configured for an output of 200V, 208V, 220V, 230V, 240V +/-2% and 120Vac. It features thirteen (13) outlets with two (2) NEMA L6-20R, four (4) NEMA L6-30R, one (1) hardwired terminal block, six (6) NEMA 5-20R and maintenance-free, hot swappable, user-replaceable batteries. This unit offers connectivity via one (1) HID USB, one (1) DB9 serial and one (1) emergency power off (EPO) port. 2,670 Joules of IEC 61000-4-5 Level 3 compliant surge suppression and EMI/RFI filters increase the immunity of the load to noise disturbances. The runtimes are expandable by adding a hot swappable, user replaceable BP240V30ART3U External Battery Module (EBM, available separately).

Online Double Conversion and Pure Sine Wave Output – The OL6000RT3UPDUTF with Online Double-Conversion topology provides continuous pure sine wave output with zero transfer time by converting utility AC power to DC power and inverting it back to pure sine wave AC output. The output power is identical to or cleaner than the power from the utility company power grid, free of harmonic distortion and electrical noise, resulting in optimal line clarity.

Maintenance Bypass Switch – The maintenance bypass switch provides IT managers the ability to service or replace the UPS without powering down the connected equipment. With the patented interlock bracket the UPS automatically switches to internal bypass mode making the hot-swap process easier and quicker to complete.

Removable LCD Control Panel – The LCD Control Panel on the OL6000RT3UPDUTF can be removed and relocated for easy viewing by using a DB-26 cable (available separately) that can be attached to the front or back of the UPS. This feature provides easy access to view, up to 10 ft. away, status or change settings on the UPS when it is installed in a hard to reach area such as the bottom of a rack, in a crowded IT closet or on the floor.

GreenPower UPS ECO Mode – The OL6000RT3UPDUTF can be placed into an ECO mode that places the UPS into a bypass state with a user selectable voltage range for switching back to traditional double-conversion online mode. This mode improves the UPS efficiency from 90% to 95%. Cost savings are not only achieved by reducing energy consumption, but also by lowering the heat generated by the UPS.

Extended Battery Module (EBM) – The runtime of the OL6000RT3UPDUTF can be extended by integrating additional EBMs (BP240V30ART3U, available separately). The OL Series UPS can have up to ten modules connected without additional software or hardware required. With the easy to use LCD Control Panel, you can select the number of additional EBMs and it will provide the correct estimated run-time for your configuration.

Fast Charge Technology – Each EBM (BP240V30ART3U) has its own built in charger that enables the UPS to recover its charge rapidly when utility power is restored. As a result, your charging time remains under 4 hours whether you add one EBM or ten.

Smart Battery Management (SBM) – SBM uses a 3-cycle charging mode that improves battery life and reduces heat generated. The first cycle charges the battery to full capacity, the second cycle enters float mode, and the final cycle turns the charger off and allows the battery to naturally discharge or "rest" until it reaches a set point. After the slight discharge, the UPS will restart the process ensuring runtimes are maintained.

PowerPanel Business Edition UPS Management Software – This software suite manages the power for all servers and computers supported by the UPS on a network. Features include application/OS shutdown, event logging (power, load and voltage variations), internal reports and analysis, as well as remote management capability for comprehensive power control.

Linux and Virtual Machine OS Compatibility – PowerPanel power management software has been fully tested and is compatible with most mainstream Linux builds and many of the popular versions of Virtual Machine Operating Systems such as VMware ESX/ESXi, Windows Hyper-V Server, and Citrix XenServer.

Critical and Non-Critical Loads – The UPS has two banks of outlets that can be configured so that the non-critical loads shut off after a set time frame to provide additional runtime for the critical load outlets. Users can prioritize their equipment runtimes to maximize the capacity of the UPS to meet their power requirements.

Emergency Power Off (EPO) – The EPO port can be connected to a master EPO switch allowing the output power of the UPS to be cut in the event of an emergency.

Backfeed Protection – The UPS can be connected to mains power with Backfeed Protection to prevent the risk of electric shock from any electric current feeding back from the UPS through the input terminals when utility power is lost. This isolates the UPS and allows service engineers to safely work on the utility power.

Generator Compatible – When connected to a generator, the UPS can have the generator mode enabled so the UPS continues to receive input power, even when the generator output frequency is less than stable. The UPS will take the unstable input power and transform it into pure sine wave output that is free of harmonics and distortion to power connected equipment.

Converter Mode – With OL6000RT3UPDUTF, IT managers have the flexibility to set the output frequency, regardless of the input frequency, to match their connected equipment by selecting a 50Hz or 60Hz output on the LCD control panel.

Multiple Language Options – The OL6000RT3UPDUTF LCD Control Panel can be configured in English, Spanish, French and German for ease of use.

USB and Serial Connectivity – HID compliant USB port and Serial port enables full integration with built-in power management and auto shutdown features of Windows, Linux and VMware.

3-Year Warranty – Stringent manufacturing processes and innovative product design enables CyberPower to offer one of the strongest warranties in our industry. CyberPower will repair or replace damaged units within three (3) years of purchase date.

Technical Support – CyberPower will assist customers with any product, installation or warranty concerns.

Our Accessibility Policy

We endeavor to make our website accessible to any and all users. Please contact us toll-free at 800-998-4388 if you need assistance with navigating our blog, website, or placing an order. We appreciate your business and are happy to answer any questions that you may have.