BTK

BTK

Boiler is constructed according to the EN 303-5. Steel materials used apply to EN 10025, EN 10028-2, EN 10120 i EN 10088-2.

Due its increased volume the heating chamber can be fed with more fuel – apart of biomass, longer wood stocks (up to 1 m) or the coal with lower calory value can be used as well.

The whole boiler is insulated with appropriate mineral wool protection and its door with vermiculite.

Specific construction allows double pass (draught) of heating air – efficiency depends on the type of the fuel used, but lies above 75% in any case (up to 80% for soya straw).

In order to allow constant and most efficient working circle, use of an additional tank AT (heat accumulator) is strongly recommended.

Boiler is easy to clean with included cleaning kit. Boiler has a thermometer included as well.

Draught regulator is not included.

Type

BTK 40

BTK 65

BTK 100

Overall power (KW)*

40

65

100

Water content (lit.)

162

184

295

Heating chamber volume (dm3)

335

415

830

Exit flue gas temperature (oC)

250

250

250

Temperature range (oC)

60-90

60-90

60-90

Min Working Temperature (oC)

60

60

60

Efficiency (%)

70-80

70-80

70-80

Max working pressure (bar)

2,5

2,5

2,5

Chimney height** (m)

7-8

7-8

9-10

Height (mm)

1060

1060

1060

Width (mm)

785

815

1080

Length (mm)

1720

1870

2200

Flue diameter (mm)

ø220

ø220

ø220

Flue height (mm)

710

710

800

Flow / Return line (inch)

5/4“

5/4“

2“

Weight (kg)

470

545

780

* Values are for 18000 KJ/kg coal.

** Data given in the chart represents is a rough estimate only.

Termomont Šimanovci is one of the major solid fuel boilers producers in the Balkan region. The biggest slice of our turnover belongs to export activities. We are present in all former Yugoslav republics. We have strong partners in the Russian Federation, Ukraine, Romania, Bulgaria, Albania, Greece, Czech Republic, Estonia, Latvia, Belarus, Poland, France, Belgium, Spain and Portugal. ”