HOW CAN WE HELP?

Residential Pool / Spa - Electrical Inspections

Residential Pool / Spa - Electrical Inspections

Equipment

Inspector will verify code compliance by assuring that a minimum size #8 solid copper conductor is attached to the pool steel shell. Proper connectors are used for all bond wire connections; all connections are tight and correctly made. # 8 solid copper is attached to the rear exterior of the pool light wet niche. Internal wet niche bond is secure and proper encapsulating compound is used to completely cover termination of # 8 insulated wire. Metal within 5? of waters edge is connected to the equipotential bonding grid, and a # 8 solid copper conductor is run completely around pool walk area between 18? and 24? from waters edge and 4? to 6? below grade.