Dissolver specification

Dissolver Specification

NEW!! – State of the art dissolver

Chemiteq are pleased to announce that this new state of the art solid dissolver will be available to ship from the beginning of December. This new dissolver incorporates technology brought about from heads of different industries to bring an updated piece of equipment to complement the solid technology. The dissolver offers a smaller footprint than the other models, very easy installation and maintenance and is suitable to take either jars or disks.

A non-contact level control uses ultra-sonic sonar, which is the same technology used in parking sensors in cars. A rolling average for solution level evens out peaks and troughs. Please click here for further details.

CQ591W – Single dissolver without backup

Allows a single product to be dissolved automatically giving a constant reservoir of dissolved product which is then pumped into the system via a standard dosing pump connected to the bottom of the sump. This dissolver has no back up chamber, but there is an overflow connection that can be connected to a foul drain in the event of an overflow

Please note: units supplied in white

CQ592 – Dual dissolver with back up

Allows 2 jars of a single product to be dissolved simultaneously and automatically giving a constant reservoir of dissolved product which is then pumped into the system via a standard dosing pump connected to the bottom of the sump. This dissolver has a backup chamber which acts as a bund should the dissolving reservoir overflow. This activates a second float which cuts of the water supply to the dissolver preventing overflows.

CQ593 230vGravity Feed System – Solenoid Activated

A single product dissolver that has no storage chamber. The dissolver is operated by a 230v solenoid valve which sends water to the dissolver which then drops via gravity direct into the system being treated. This dissolver eliminates the need for dosing pumps and can be used to feed large quantities of product directly into a system. Cannot be used on pressurized systems. Solenoid must be connected to a separate timer/controller to enable dosing.

CQ594 Gravity Feed System - Timer Activated

A single product dissolver that has no storage chamber. The dissolver is operated by a battery powered timer controlled solenoid valve which sends water to the dissolver which then drops via gravity direct into the system being treated. The dissolver eliminates the need for dosing pumps and can be used to feed large quantities of product directly into a system. Cannot be used on pressurized systems.

CQ500BF – Biocide Feeder for use with QSOL Bio Brom

The revolutionary design of the CQ500BF allows for a higher solution strength through saturation compared to a standard solid dissolver. The CQ500BF is designed to be used exclusively with BioBrom.

Unlike an in-line brominator, the concentrated solution can be fed to multiple cooling systems.

The unique, integrated lid allows loading of the chemical without direct user contact. There is no exposure to dust.

The CQ500BF is designed to hold an entire case of BioBrom (4 jars)). The hopper does not need to run empty before it is refilled, and the dissolver valve does not need to be off during the refill.