MA-RC Series chiller combine one or more refrigeration circuits to chill fluid. A separate reservoir and pumping system is required to circulate chilled fluid to the use points.

Air-Cooled chillers use ambient air to dissipate the heat from the refrigeration system.

The refrigeration system and controls remain inside while the remote air-cooled condenser is located outside.

Specifications

Indoor Chiller Unit (1)

Refrigerant Zones

Quantity : 3

Compressor

Quantity : 3

HP : 40

Type : Scroll

(2) Total Capacity : 120

Refrigerant

Type : R-410A

Connection Sizes

To Process : 4"

From Process : 4"

Full Load Amperage (3)

230/3/60 : 426.0

460/3/60 : 213.0

575/3/60 : 170

Dimensions (5)

Height : 85"

Width : 73"

Depth : 130"

Weight (6)

Shipping : 3,600 lbs

Remote Air-Cooled Condenser (1)

Quantity

Temptek Model : RCSZ-40-LK

Numbers of Units : 3

Capacity (2)

R410A @ 1° TD : 29.85 MBTU/hr

R410A @ 20° TD : 39.8 tons

Fans (3)

Quantity : 3

RPM : 1,140

Connections (4)

Gas : 2-1/8"

Liquid : 2-1/8"

Full Load Amperage

460/3/60 : 10.5

Construction

Tube Material : Copper

Fin Material : Aluminum

Fins Per Inch : 14

Coating : None

Dimensions

Height : 49.13"

Width : 45.43"

Depth : 180"

Weight (5)

Weight : 1,000 lbs

Circuits Served

Maximum : 1

Reference #

Reference : LNH-S03-A026(14)

EC Reference : LNH-S03-A026(14)-AdvEng

Specification Notes:

1. Since product innovation and improvement is our constant goal, all features and specifications are subject to change without notice or liability. Selection of certain optional features may change listed specifications.

3. Full load amps are higher than run load amps and must be used for sizing disconnects and supply wiring. Not for construction. Consult factory for power requirements of unit as configured and on selected options.

Temptek, Inc. 525 East Stop 18 Road, Greenwood, IN 46142 Phone: 317-887-6352 Fax: 317-881-1277
Product innovation and improvement is our constant goal. All features and specifications are subject to change without notice or liability. Products are
assembled in the United States of America. Site Map

2019 TEMPTEK, INC

Close

This site uses cookies to offer you a better browsing experience. Learn more about how Temptek, Inc. uses cookies by contacting the site administrator at
admin@temptek.com. By closing this banner, scrolling this page, clicking a link or continuing to browse otherwise, you agree to the use of cookies.
Please refer to the Privacy Policy for more information.