Heating - Combi Boiler in Mine Hill, NJ

Pipeworks will provide and install three way automatic valve in HTP combi boiler, will have do drain down entire system, will then remove primary central circulating pump, get to three way valve, replace o-ring baskets and assembly everything back together.

Installed three way valve and tested for proper operation and function, system now heating up and three way valve diverting heat to hydronic system as needed, also no need to replace gauge as liquid in gauge is actually meant to protect gauge from thermal overload.