World's smallest dry contact switch

FLUSH 1D RELAY

The Qubino Flush 1D Relay is ideal as a dry contact switch for lights, fans, ovens, washing machines, irons, power sockets, garage doors, electric radiators, water heaters, etc. The output contact is voltage free (dry contact), so different power supply loads can be connected to the module. It also supports the connection of a digital temperature sensor.

The smallest of them all.

The Qubino Flush 1D Relay occupies a smaller volume than comparable modules of any other brand and will fit easily in any flush mounting box.

Energy wizard.

The Qubino Flush 1D Relay has an extremely low power consumption of just 0.4 W.

Remarkably versatile.

The Qubino Flush 1D Relay can operate across a wide temperature range, from a chilly -10˚C to a scorching 40˚C (14˚–104˚F). It supports the connection of a digital temperature sensor, which is also useful for creating complex scenes. Every module also acts as a repeater in order to improve the range and stability of the Z-Wave network.

The simplest installation.

Extremely small size and a specially designed casing mean that connecting the module inside a flush mounting box is simplicity itself. The installation process, tested and approved by professional electricians, consists of just three simple steps:

Remove the switches from the box and disconnect the wires.

Connect the wires to the Qubino module and insert it in the box.

Fix the switches to the box.

Incredibly fast support. Free.

We know that when you need information you need it quickly. That is why we offer a live customer service helpline, where you can get instant answers to all your questions. Free. All our support and training is personalized and free of charge.

The most tested and most reliable module.

Qubino modules are "install-and-forget" products. Our products are made to last, so we only select and use top-quality electronic components. Our modules are also the most tested Z-Wave microcontrollers on the market. The Slovenian Institute of Quality and Metrology (SIQ), an independent testing body, tests safety parameters including temperature rise, construction, insulation resistance, power consumption and overload in accordance with the EN 60669-2-1 standard.

Technical specifications

Power supply

110 - 230 VAC ±10%
50 / 60 Hz, (24–30 VDC)

Rated load current of AC output (resistive load)*

1 X 10 A / 230 VAC

Rated load current of DC output (resistive load)

1 X 10 A / 30 VDC

Output circuit power of AC output (resistive load)

2300 W (230 VAC)

Output circuit power of DC output (resistive load)

240 W (24 VDC)

Digital temperature sensor range
(sensor must be ordered separately)

-50° ~ +125°C

Operation temperature

-10° ~ +40°C

Distance

up to 30 m indoors
(depending on building materials)

Dimensions (WxHxD)

41.8 x 36.8 x 15.4 mm

(packaging)

(79 x 52 x 22 mm)

Weight (including packaging)

28 g (34 g)

Electricity consumption

0.4 W

For installation in boxes

Ø ≥ 60 mm or 2 M, depth ≥ 60 mm

Switching

Relay

* In the case of loads other than resistive, pay attention to the value of cosφ and if necessary use a load lower than the rated load. Max current for cosφ = 0.4 is 3 A at 250 VAC, 3 A at 24 VDC L/R = 7 ms.

Supported Z-Wave Frequencies

ORDERING CODE

FREQUENCY

ZMNHND1

868.42 MHz

ZMNHND2

921.42 MHz

ZMNHND3

908.42 MHz

ZMNHND4

869 MHz

ZMNHND5

916 MHz

ZMNHND8

865.2 MHz

Additional parameters for pros.

There are 11 additional parameters for expert users. Some of the most useful are:

Parameter no. 2 – Input I2 contact type

Parameter no. 11 - Automatic turning off output after set time

TVs, Hi-Fi systems and other home appliances have already integrated automatic turn off functionality, this module also offers this functionality. Automatic turning off function allows energy saving, without doing scenes on Z-Wave controller.

This function, for example also allows automatic re-locking door after defined time.

When Relay is ON it goes automatically OFF after time defined by this parameter. Timer is reset to zero each time the module receives ON command regardless from where it comes (push button, associated module, gateway, controller, etc.).

Parameter no. 12 - Automatic turning on output after set time

When Relay is OFF it goes automatically ON after time defined by this parameter. Timer is reset to zero each time the module receive OFF command regardless from where it comes (push button, associated module, gateway, controller, etc.).

Enabling I2 means that Endpoint (I2) will be present on UI. Disabling it will result in hiding the endpoint according to the parameter set value. Additionally, a Notification Type and Event can be selected for the endpoint. Available configuration parameters (data type is 1 Byte DEC):Endpoint device type selection:- notification sensor (1 - 6):
GENERIC_TYPE_SENSOR_NOTIFICATION,
SPECIFIC_TYPE_NOTIFICATION_SENSOR

NOTE: After parameter change, module has to be re included into the network in order setting to take effect!

NOTE 1: After parameter change, first exclude module (without setting parameters to default value) then wait at least 30 s and then re-include the module!

NOTE 2: When the parameter is set to value 9, the notifications are sent for Home Security.

Temperature Sensor Setting

Parameter no. 110 – Temperature sensor offset settings

If the temperature sensor is connected to the module, the temperature sensor widget is shown automatically in UI (user interface).

If the measured temperature with an additional temperature measuring device is different from the one measured by the connected digital temperature sensor, the temperature can be compensated by this parameter.

Available configuration parameters (data type is 2 Byte DEC):

default value 32536

32536 – offset is 0.0 °C

From 1 to 100 – value from 0.1 °C to 10.0 °C is added to actual measured temperature.

From 1001 to 1100 – value from -0.1 °C to -10.0 °C is subtracted to actual measured temperature.