The P-5215 Differential Pressure Transmitter accurately measures differential pressure and converts the measurement into a proportional 3 to 15 PSIG (21 to 105 kPa) output signal. This instrument can be used in a variety of control applications including static, velocity, and differential pressure control.

Operation

The P-5215 is used with the low input acting as a reference less than, greater than, or equal to atmospheric pressure. As the differential between the low and high inputs increases, an internal mechanism will proportionally increase the output signal of the P-5215. The output at zero differential is 3 PSIG (21 kPa). When the differential reaches its maximum, as defined by the range, the output will be 15 PSIG (105 kPa).