A stylish elegant design and a plethora of remote controlled functions for precise temperature control.

Impressive A+ and A++ Energy Ratings, with even smarter savings. A luxury within reach to help you improve the air quality within your home.

Features:

SEER up to 6.4

Low Energy Standby (1W)

Warm Air Start Function

Intelligent Defrosting

G10 Energy Saving Inverter Technology

Ultra Quiet Operation

Auto Clean

24 Hour Timer

Settings Memory

Intelligent Defrosting

Sleep Mode

Auto Restart

CE Marking To UK & EU

Z Series Inverter Split Air Conditioning Specifications

Model

ECO950SD

ECO1250SD

ECO1850SD

Power supply

Ph-V-Hz

1, 220-240V~, 50Hz

1, 220-240V~, 50Hz

1, 220-240V~, 50Hz

Fed to

Indoor

Indoor

Indoor

Cooling

Capacity

kW

2.6 (0.9~3.0)

3.5 (0.9~3.8)

5.275 (1.0~6.3)

Capacity

Btu

8871.2 (3070.8~10236)

11942 (3070.8~12965.6)

18000 (3412~21495)

Input Power

kW

0.72 (0.17~1.2)

1.1 (0.18~1.4)

1.62 (0.35~2.45)

SEER

Btu, w/w

6.4

6.4

5.6

Current

A

3.5

5.0

7.19

Heating

Capacity

kW

2.75 (1.0~3.2)

3.65 (1.0~3.9)

5.275 (1.2~6.8)

Capacity

Btu

9383 (3412~10918.4)

12453.8 (3412~13303.8)

18000 (4100~23200)

Input Power

kW

0.72 (0.18~1.55)

1.1 (0.19~1.58)

1.6 (0.4~2.50)

SCOP

W/W

4.0

3.8

3.8

Current

A

3.5

5.0

7.1

Rated Input

kW

1.55

1.58

2.50

Rated Current

A

5.3

6.2

10.87

Indoor Sound Pressure Level

dB(A)

23/30/34/41

23/32/35/42

33/37/46/48

Indoor Sound Power Level

dB(A)

38/44/49/58

38/46/50/58

44/48/53/57

Indoor unit

Net Dimension (WxHxD)

mm

845×275×180

845×275×180

945×298×208

Net/Gross weight

Kg

10/12

10/12

13/17

Outdoor Sound Pressure Level

dB(A)

50

55

56

Outdoor Sound Power Level

dB(A)

63

63

65

Outdoor unit

Net Dimension(WxHxD)

mm

776×540×320

848×540×320

955×700×396

Net/Gross weight

Kg

32/34

35/37

46/51

Refrigerant type R410A @ 4 metres

g

900

1150

1300

Refrigerant piping

Liquid side/ Gas side

mm(inch)

6.00(1/4)/9.52(3/8)

6.00(1/4)/9.52(3/8)

6.00(1/4)/12.00(1/2)

Max. refrigerant pipe length

m

15

20

25

Max. Elevation

m

10

10

10

Dehumidification

litres/h

0.80

1.4

1.8

Energy Rating (Cooling / Heating)

A++/A+

A++/A

A+/A

Fuse Rating

A

13

13

20

Interconnecting Cable

3C+E

3C+E

3C+E

Operational Temperature

°C

16 ~ 30

16 ~ 30

16 ~ 30

Ambient Temperature (Heating)

°C

-5 ~ 24

-5 ~ 24

-5 ~ 24

Ambient Temperature (Cooling)

°C

18 ~ 40

18 ~ 40

18 ~ 40

Note: Due to our policy of innovation some specifications may be changed without notification.

All split air conditioning units contain F-gas and is governed by F-gas regulations under EU regulations: The installation of all split air conditioning units containing F-gas (R407C, R410A & R32) require installation or commissioning by a F-gas certified air conditioning engineer. It is illegal to handle gas without the required F-gas qualification. Therefore, any installation by non-qualified F-gas engineer will render your warranty void.