Just updating my notes and find that App.4 no longer has grouping for similar circuits enclosed in trunking ( F=1/(rt(N)). I assume that this one has been dropped? (It would make sense)

2.3.3.1 legh ?

and

5.1.1 and 5.1.2

It>= In/(Cg.Ca.Cs.Cd.Ci.Cf.Cc)

Leaving out Cs, Cd, Cf, there appears to be no mention of non-concurrency.

There never was Legh, if it's grouped in a hot environment and surrounded by insulation and protected by a BS 3036 fuse then all the factors apply - not just the "worst" one

If different parts of the run have different conditions you can evaluate on the "worst condition" for each factor but you can't ignore lesser factors if they apply - they weren't derived collectively - only in isolation

I don't fancy installing a 9kW shower with 35mm2 conductors.

Don't use a 3036 fuse, with lots of other grouped circuits run through a heating chamber then

2.3.3.1 How did I miss tha t- I'm going to resist the temptation and say that the pages were stuck together.....

Its amazing how these little regulations disappear when you look for them and then like magic reappear again.

As far as non-currency goes. and as a design consideration, I would have thought a note to say where there is no concurrency of correction factors it would be acceptable to use the worst factor rather than all of them.