Used in apartment applications where a high quality dependable heater is desired and the wattage is specified on the plans. This heater has all the qualities of the famous Pic-A-Watt®, but without the features of picking the wattage at the time of installation.

Ratings: Heaters shall be available in wattages of 250 to 2,000, at 120, 208, 240, or 277 volts.

Blower and Motor: A tangential cylindrical blower, delivering 65 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater.

Thermal Overload: Heaters shall be equipped with thermal overload protection, which disconnects elements in the event normal operating temperatures are exceeded. The thermal overload protectiondevice shall automatically reset when normal operating temperatures are reached or manual reset by turning the thermostat down for 15 minutes.

Wall Can: The wall can shall be 20 gauge electro-galvanized steel and shall contain a minimum of three (3) knockouts through which power leads are brought. The wall can shall have a depth gauge indicator, and a factory installed, insulated and stranded copper grounding wire. Minimum Clearance to Floors and Sidewalls. Zero clearance to combustibles.

Grill: The grill shall be louvered, one piece design with rounded edges on all four sides, with rounded corners to prevent snags from contact with other materials. The grill shall be epoxy powder coated in the color specified on the plans.

Approval: Heaters shall be listed and approved by Underwriters Laboratories or similar agencies.