Product Description

Complete pump end and motor set. Control box (control panel) is not mandatory, but a three phase power switch with overload protection is required. Complete Instructions.

HP: 10 HP

Voltage: 460V Three Phase

Cycle: 60 Hz

Operating Amperage: 13.8 A

Motor RPM: 3450 RPM

Stages: 6

Maximum Flow: 88 GPM

Maximum Head: 453 ft

Typical Flow: 79GPM @ 267ft; 62GPM @ 350ft; 40GPM @ 410ft

Suction Port: Center Suction

Discharge Port: 2.5 inch NPTF

Built-in Check-valve: Yes

Housing Material: Stainless Steel

Impeller Material: Thermal Plastic

Motor Enclosure: Stainless steel

Duty: Continuous or up to 30 restarting cycles / hour

Control Box: Three phase power switch with overload protection is required.

Weight: 112 lbs

Dimensions/Length: 49.75"

Minimum requirement for operating the motor is a non-fused 3-phase power switch and a 3-phase overload protector / Circuit breaker. The protector / breaker must be the type of those that shut off all 3-phase when one or more phase is overloaded. Do NOT use a fused switch that could burn out one of the phase. Do NOT use three individual 1-Phase breakers. You must use a real 3-phase protector / breaker or a protection device that does not cause missing phase problem.