Transcription

1 2/18/EN/2 Air Handling Lights Type LR Recommended for use in rooms with ceiling heights of approx m

2 Contents Description Description... 2 Supply Air Construction LR-Z... 3 Extract Air Construction LR-A... 4 Combined Construction LR-K... 5 Installation Details... 6 Materials... 6 Nomenclature... 8 Acoustic Data... 9 Aerodynamic Data...10 Order Details... 1 In air-conditioned buildings supply air and exhaust air is ducted into and out of rooms, suspended ceilings are installed which mask this equipment from the working space. From cost considerations the depth of ceiling void is kept to a minimum ensuring sufficient space for ducts, plenum boxes, light fittings etc. Openings are required in the ceiling for air diffusers and flush lights. As the visual impression of a ceiling depends not only on the ceiling elements but also on the air diffusers and lights used, it is useful to combine the two. By combining the two components, the architect can optimise the design of the ceiling further. In this technical brochure, we introduce Trox Air Handling Lights Type LR. In a combined air and light fitting, the customer can specify the manufacturer and type of light fitting to be integrated with the Trox diffuser. The opening size in the diffuser is designed to accept the most common light diameters produced by Staff GmbH and Co. KG. The Trox air diffuser is designed so that the light ordered can easily be fitted on site. Trox air lights are available in 5 sizes for supply air, extract air or as a combination of the two. They are all characterised by sophisticated design, excellent air conditioning functions, low noise level and a flat construction. Trox also offer other Air/Light Combinations. 2

3 Supply Air-Construction LR-Z-... The air handling light type LR-Z is suitable for supply air. The air flows evenly out through the diffuser annulus and discharges horizontally along a ceiling. If required, an airflow control damper can be fitted in the entry spigot. The light fitting is enclosed in a sheet metal cylinder. The heat from the bulb can dissipate into the false ceiling void through an opening in the top of the cylinder. k1 / k Ø 198 Ø D Ø R Size D K 1 K 2 R

4 Extract Air-Construction LR-A-... Air handling light type LR-A is designed for extract air application. The air is exhausted through the diffuser annulus. The heat from the bulb is also removed with the extract air. If required, an airflow control damper can be fitted in the connecting spigot. k 1 / k 2 H1 H2 Ø 123 Ø D Ø R Size D H 1 H 2 K 1 K 2 R

5 Combined Construction LR-K-... The air handling light type LR-K is designed for a combination of supply and extract air. The supply air flows evenly out through the outer annulus of the diffuser and discharges horizontally along a ceiling when flush mounted. The extract air is exhausted through the inner annulus. There is no risk of contact between the supply and extract air, as the connections and internal fittings have been designed to prevent this. The extract air volume flow should never be set higher than the supply air flow. The heat from the bulb is removed with the extract air. If required, an airflow control damper can be fitted in the entry spigot for the supply air. k 1 / k Ø 198 Ø 198 Ø D Ø R Size D K 1 K 2 R

6 Installation Details Materials Installation details The plenum box hangs from the support brackets such that the bottom of the diffuser spigot lies flush with the ceiling line. The push-in mounting frame is then fitted and screwed in place. The diffuser face with the light already fitted, is mounted using special quick release fasteners. Fasten the safety cable provided and insert the plastic plugs. The elctrical connection cable is pushed through the grommet in the top of the box. The reflector and bulb (s) are then fitted. When the diffuser face is removed, the control damper in the inlet or outlet spigot can be adjusted using a screwdriver. Materials The diffuser face is pressed galvanised sheet steel to DIN The surface is phosphate treated and white stove enamel finish (RAL 9002). The plenum box is made from sendzimir galvanised sheet steel to DIN Suspension by others Connection spigot Ø DA Ceiling Plenum Box fitting flush with ceiling 4 of f sheet metal fixing screws Push in mounting frame Cable connection for light Light fitting frame Special quick release fastener Dif fuser face 6

11 Order Details Order Code These codes do not need to be completed for standard products. LR -Z -M S1 RAL 9010 Supply Z Extract A Combination K (supply and extract) Air flow control M 1) damper 1) For combination units (supply and extract) control damper only available in the supply air spigot Size (installation ø of light) Not used State colour S1Painted to RAL... 0 Standard finish RAL 9002 Note : For a given nominal size the overall face size of LR-Z and LR-K are the same but LR-A is different. However all air handling lights accomodate the same size light fitting, see pages 3-5. Specification Text Air handling lights in circular construction for horizontal air discharge, comprising the diffuser face with concentric annuli for supply and exhaust air, spacing 14 mm, and plenum box fitted at rear with internal special air control elements, circular side mounted spigots (with optional flow control damper), mounting brackets and adjustable height push-in mounting frame to compensate for ceiling irregularities. Diffuser face fixed with two quick release fasteners for easy removal, and designed fro the installation of circular light fittings by the customer (down lighters). Material : The diffuser face is made from sheet steel. The surface is phosphate treated and white (RAL 9002) stove enamel finish using the electro-dipcoat process, resistant to saturated environment for a minimum 100 hours without deterioration (DIN)50017). The plenum box is made from sendzimir galvanised sheet steel to DIN Order example: Make : TROX Type : LR-Z-M/

X X testregistrierung Non-return dampers Type For installation into ductwork Non-return dampers prevent unwanted airflows against the intended airflow direction when the system is not in operation Maximum

Type VSD35 Nominal length up to 1500 mm: one spigot NUMEROUS VARIANTS FOR MANY DIFFERENT INSTALLATION SITUATIONS Slot diffusers with 35 mm diffuser face (nominal width) and adjustable air control elements

Technical information Ceiling air diffuser INDULCLIP INDUDRALL KOMBICLIP Draught-free air distribution Differences in supply air temperature of up to K 7 sizes from 0 to 800 mm, round or square Many different

Plenum for diffusers Halton reserves the right to alter products without notice 07/15 Plenum ensuring proper function of supply air ceiling diffuser and connecting to ductwork Flexibility for levelling

Issue Date June 2009 Quick Selection Guide Quick Selection This selection guide has been designed to allow quick and simple selection for a broad range of TROX Grille and Diffuser product. Full product

SQUARE AND RECTANGULAR DIFFUSERS introduction The IC diffuser is a versatile form of air terminal offering the facility of multi directional throw patterns in a wide range of frame sizes. Each core style

Homepage > Products > Fire and Smoke Protection > Fire dampers > Type KA-EU Type KA-EU FOR THE EXTRACT AIR OF COMMERCIAL KITCHENS Rectangular fire damper for use in extract air and exhaust air ducts of

Slot diffusers Type Slot diffuser Slot diffuser for ceiling installation type. The frontal face of the diffuser has an attractive design with extruded aluminum sections. diffusers can be installed in rooms

Activent is a ventilation system for supplying and distributing air. The system has been proven to function effectively in both small and large areas and is used in all types of premises ranging from offices

Swirl diffusers with adjustable air control blades NSDZ The diffusers NSDZ are intended to use in low- and medium-pressure ventilation systems. They allow for obtaining the swirl air flow and are especially

Model : OSTL GI 341 Description: OPTIMA make Sand Trap Louver is used as pre-filter for the protection of air conditioning plants in area exposed to extreme levels of industrial pollution. It has a high

Introduction ASLI VAV diffusers, VVD are variable air volume diffuser for supply air in variable air volume system. In many conventional HVAC systems, multiple work spaces are controlled by a single thermostat.

Technical Data Donn Features The DONN brand air diffuser provides air delivery and return for the ceiling system. Air is supplied through the lay-in diffuser, which is placed on the 2 x 2, narrow-suspension

Chassis panelwork is all In House manufactured from nominally 1.2mm Galvanised steel. Where at all possible, flanges are formed inward facing to prevent exposure to bare metal edges. Sufficient forms and