Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

My wife and I moved into a house in January...immediately I started having air quality symptoms. I thought his might have had something to do with the heat pump itself. However, I have been convinced that that wasn't the issue.

Well we had an air quality test done. The results were...outdoor environment B...Chemical pollutants were 820 ug/m3....Particle Allergens were at 27 ug/m3...Carbon dioxde was 771 ppm....Temperature was 70 degrees...all results are given in overall averages....some of the daily and hourly averages were much higher.

So...the air quality guy said to do a blow test or something like that to measure the leakage. Since this is a $$$$ test and our house is only 5 years old, I'm thinking about passing on it. It seems to me we would be really unlikely to be pulling air from outside. Not just that the air quality outside is pretty good...so if I was pulling air in from outside it seems like it would help the indoor air quality. In fact with seconds of going outside my symptoms usually go away.

He also recommended installing an additional return...perhaps one for each bedroom...so +3 more than what we have now. He seem to think this would help the particle count and the humidity. He also said it might be necessary to seal up the vents, canned lights, plugs and switches to keep them from leaking attic air into the house...another hvac guy confirmed this particular thing.

At this point, I have a few questions. Is putting an addtional/additional return/s likely to be effective for the particles and humidity(which would in turn deal with the need to have the thermostat down to 70)? I was thinking of starting with one return at a time to see how it did.

Also, will that deal with the high carbon dioxide levels in the house? If not, would it be possible/adviseable to put a return that sucks air from my patio to pull in fresh air. I got this idea from my dad's house. I have no symptoms at his house...his house is old...has very old vent work but has a return that sucks air from under the house as well as another return sucking air from inside the house. I know my patio isn't as cool as under my dad's house but wouldn't the unit cool and dehumidify the air coming from a patio return?

Any advice about which way to go would be greatly appreciated...I have one more guy coming tomorrow. Just trying to make the best decision I can for my health....my home...and also making this decision with my wife...she thinks a lot of this in my head....and the available funds I have to tackle this issue.

Thanks comfortcontrolac...Does the theory of pulling attic air into the house seem valid? If so, any external filter would seem to be useless given that the attic particles are getting sucked from the vents and other receptacles.

I change the filter regularly...regularly. It seems like 3 month filters only last one month or less with this system.

The coils have been inspected and are clean. Don't know what the p-trap is. I do know it has one plenum that feeds all the supply vents..it is a closed plenum. The one supply doesn't have a plenum. It goes straight into the side of the unit.

Could it be that if the return (25x20x1 1600 square foot house) is undersized for the unit, it could be sucking too hard and pulling attic particles into the house?

That's what I was thinking too...I didn't know if there was some other variable of which I wasn't aware causing that...perhaps if the system was pulling attic air into the house. Is there a cheaper way to do something like that?...I was thinking of pulling air from outside through an addtional return...I'm really wanting to pay someone to do all this. I just want to make a good decision.

I live in Fort worth TX...the air outside right now is less humid than the air in the house....One day not too long ago I looked and it was about 10% dryer than the air in the house.

THe relative humidity is probably lower, but the dewpoint (I hope) is mcuh higher outside. Right now its' 95F and 69F dewpoint in Ft .Worth. Indoors, if it was 70F and a dewpoint of 69F, you would have condensation and mold forming inside the home. I'm guessing if it feel "muggy" the RH is around 60% which is a 55F dewpoint.

40% RH is fairly humid... when its' over 90F. Dewpoints in the mid 40's to mid 50's are the most comfortable generally over a wide range of temperatures.

I think you need a good HVAC company to evaluate your system, chekc the blower speed, check how well sealed the ducts are and maye recommendations such as a MERV 11 or 13 media filter and/or an ERV for fresh air.