Single Conductor Polyethylene-Covered Line Wire is rated for a 75°C normal conductor temperature&comma; and is intended for use in overhead distribution circuits operating at primary or secondary voltages&period; The covering provides circuit protection against momentary contact with other conductors or trees&period; Because the covering carries no voltage rating&comma; the conductors must be installed on insulators adequate for the intended service voltage&period; The user should consider the dielectric compatibility of the covering&comma; insulator and conductor&sol;insulator tie&period;

Covering MaterialThe standard covering on the conductor is black linear low-density polyethylene &lpar;LLDPE&rpar;&period; Alternatively&comma; a covering of black low-density crosslinked polyethylene &lpar;XLPE&rpar; with a 90°C temperature rating is available upon request&period;

For LLDPE insulation&comma; remove "XLP" from code word&period;Overall Diameter is the approximate circumscribed diameter of the assembly&period;&ast; Based on 40°C ambient temperature&comma; crosswind at 2 ft&sol;s&comma; no sun&period; For ampacity values at 75°C&comma; contact our Sales Office&period;

TRIPLEX SERVICE DROP AL 1350 NEUTRAL

Code Word

Phase Conductor

Neutral

Complete Cable

DC Resistance at 20°C&lpar;ohm&sol;kft&rpar;

Inductive Reactance &lpar;ohm&sol;kft&rpar;

Ampacity&ast;&lpar;90°C&rpar;

Size&lpar;&num; of wires&rpar;

InsulationThickness&lpar;inch&rpar;

Size&lpar;Stranding&rpar;

OverallDiameter&lpar;inch&rpar;

CableWeight&lpar;lb&sol;kft&rpar;

Patella&sol;XLP

6 &lpar;7&rpar;

0&period;045

6 &lpar;7&rpar;

0&period;53

107

0&period;661

0&period;033

95

Albus&sol;XLP

6 &lpar;7&rpar;

0&period;060

6 &lpar;7&rpar;

0&period;57

123

0&period;661

0&period;035

95

Oyster&sol;XLP

4 &lpar;7&rpar;

0&period;045

4 &lpar;7&rpar;

0&period;63

157

0&period;416

0&period;031

125

Argo&sol;XLP

4 &lpar;7&rpar;

0&period;060

4 &lpar;7&rpar;

0&period;67

174

0&period;416

0&period;033

125

Clam&sol;XLP

2 &lpar;7&rpar;

0&period;045

2 &lpar;7&rpar;

0&period;76

234

0&period;261

0&period;030

165

Hyas&sol;XLP

1 &lpar;19&rpar;

0&period;060

1 &lpar;7&rpar;

0&period;89

311

0&period;207

0&period;029

180

Murex&sol;XLP

1&sol;0 &lpar;7&rpar;

0&period;060

1&sol;0 &lpar;7&rpar;

0&period;97

378

0&period;164

0&period;030

220

Purpura&sol;XLP

1&sol;0 &lpar;19&rpar;

0&period;060

1&sol;0 &lpar;7&rpar;

0&period;97

379

0&period;164

0&period;029

220

For LLDPE insulation&comma; remove "XLP" from code word&period;Overall Diameter is the approximate circumscribed diameter of the assembly&period;&ast; Based on 40°C ambient temperature&comma; crosswind at 2 ft&sol;s&comma; no sun&period; For ampacity values at 75°C&comma; contact our Sales Office&period;

TRIPLEX SERVICE DROP AL 6201 NEUTRAL

Code Word

Phase Conductor

Neutral

Complete Cable

DC Resistance at 20°C&lpar;ohm&sol;kft&rpar;

Inductive Reactance &lpar;ohm&sol;kft&rpar;

Ampacity&ast;&lpar;90°C&rpar;

Size&lpar;&num; of wires&rpar;

InsulationThickness&lpar;inch&rpar;

Size&lpar;Stranding&rpar;

OverallDiameter&lpar;inch&rpar;

CableWeight&lpar;lb&sol;kft&rpar;

Hippa&sol;XLP

6 &lpar;7&rpar;

0&period;045

6 &lpar;7&rpar;

0&period;54

111

0&period;661

0&period;033

95

Barnacles&sol;XLP

4 &lpar;7&rpar;

0&period;045

4 &lpar;7&rpar;

0&period;64

163

0&period;416

0&period;031

125

Shrimp&sol;XLP

2 &lpar;7&rpar;

0&period;045

2 &lpar;7&rpar;

0&period;78

244

0&period;261

0&period;030

165

Gammarus&sol;XLP

1&sol;0 &lpar;7&rpar;

0&period;060

1&sol;0 &lpar;7&rpar;

0&period;99

394

0&period;164

0&period;030

220

Leda&sol;XLP

1&sol;0 &lpar;19&rpar;

0&period;060

1&sol;0 &lpar;7&rpar;

1&period;00

395

0&period;164

0&period;029

220

For LLDPE insulation&comma; remove "XLP" from code word&period;Overall Diameter is the approximate circumscribed diameter of the assembly&period;&ast; Based on 40°C ambient temperature&comma; crosswind at 2 ft&sol;s&comma; no sun&period; For ampacity values at 75°C&comma; contact our Sales Office&period;Neutral sizes are diameter equivalent to ACSR&period;