The Radian Series GS7048E Grid/Hybrid™ (full-flexibility grid-interactive/off-grid) Inverter/Charger is engineered toward one goal: making system design and installation easier and faster in grid-interactive and comprehensive off-grid applications. The Radian Series simplifies the configuration, distribution, and implementation of energy storage through a standardized approach when integrated with an OutBack GS Load Center, making it easier than ever to provide successful solutions for virtually any residential, commercial or institutional power requirement.

The all-new 230V 50Hz Radian reflects OutBack’s ongoing commitment to clean, reliable power for homes, businesses and other facilities around the world, delivering 7,000 Watts. This model combines pure sine wave power output technology with unsurpassed surge capability to start the most demanding appliances, and are built around a unique dual-power module design which ensures high efficiency in both low and full power operation as well as redundancy in mission-critical applications.

The Radian Grid/Hybrid inverter incorporates OutBack’s FLEXgrid™ technology for full operational flexibility. Modular system architecture and simplified parallel design supports three-phase systems up to 21kW and multiple inverter arrays of up to 70kW. System integration and programming are easy with OutBack’s powerful MATE3 Control and HUB Communications Management devices. An advanced, front-vented layout provides optimum cooling in zero-clearance installations (i.e. where units are stacked next to each other). Field-serviceable design simplifies maintenance if needed, and firmware updates can be easily made in the field without specialized equipment.

GS7048E

Nominal DC Input Voltage

48 VDC

Continuous Output Power at 25 °C

7000 VA

AC Output Voltage

230 VAC (212-250 VAC)

AC Output Frequency

50 or 60 Hz

Continuous AC Output Current at 25 °C

30 AAC

Continuous AC output Current at 25° C

30 AAC

Idle Consumption - Invert mode, no load

34 Watts

CEC Weighted Efficiency

N/A

Total Harmonic Distortion (Typical)

><5% THD, Max single voltage harmonic <2%

Output Voltage Regulation

± 2%

Maximum Output Current (1 ms peak)

100 AAC

Maximum Output Current (100 ms RMS)

70.7 AAC

Overload Capability (100 ms surge)

16.3 kVA

Overload Capability (5 second)

11.5 kVa

Overload Capability (30 minute)

7.9 kVa

AC Input Voltage Range (Adjustable)

170 to 290 VAC

AC Input Frequency Range

45 to 55Hz or 55 to 65Hz

Grid-Interactive Voltage Range

208 to 252VAC (EN50438)

Grid-Interactive Frequency Range (Default)

57Hz to 61Hz (EN50438)

AC Input Current (Maximum)

50 AAC

Continuous Battery Charge Output

100 ADC

DC Input Voltage Range

40 - 64 VDC

Temperature Range (rated)

0°C to 50°C (power derated above 25°C)

Temperature Range (maximum)

-40°C to 60°C (functions, but does not necessarily meet all component specifications)