FEATURES

1. All components are integrated on a rugged steel base. It is ready for use by only connecting with
supply piping and to the power source.
2. Layout is very compact and much lighter than conventional units. It occupies lesser space and requires
easier installation than conventional units.
3. The flow control system which prevent frequent start and stop of pumps, requires small hydropneumatic
pressure tank and ensures constant fresh water supply
4. Pumps are in parallel operation for high demand and alternating in low demand, suitable for energy
saving

CONTROL SYSTEM

Step 1) both pumps are stopped when water tank is fully charged. In
this condition water is supplied from the pressure tank and
water pressure in tank gradually decreases.
Step 2) No. 1 pump start at pressure P1 (point 1) and water supplied
from pump and pressure tank.
Step 3) When more water is required and water pressure decreases to
P2 (point 2), no. 2 pump also starts, operation point shifts to
point 3 and system shifts to parallel operation.
Step 4) When water consumption decreases, water pressure in tank
increase and when pressure reaches P3 (point 4) no. 2 pump
is stopped and operation point shifts to point 5.
Step 5) when water consumption further decreases, water pressure in
tank increases and pressure switch is turned off and the flow
switch used to detect small flow is turned off. When both
pressure and flow switch are off, no. 1 pump stops (point 6).
Flow switch setting point is at small capacity point; therefore
pump continuous operation range is much wider. Accordingly
pump start frequency is greatly decreased