An insulator shall be
installed in each truss guy which is required to be sectionalized by Rule
56.6-A, so that such insulator is located not less than 8 feet above the ground
and not less than 8 feet below the level of the lowest supply conductor passing
within 8 feet of the guy (see App. G, Fig. 51).These requirements can normally be met by insulation at one
portion; however, in certain unusual conditions the two 8-foot distances may
overlap, in which case insulation will be necessary at two positions.

Strikeout
and Underline Version

Rule 56.7-C

56.7-C.
Truss Guys

An insulator shall be
installed in each truss guy which is required to be sectionalized by Rule
56.6-A, so that such insulator is located not less than 8 feet above the
ground and not less than 8 feet below8 feet or more above the ground
and 8 feet of more the level of the lowest supply conductor passing within
8 feet of the guy (see App. G, Fig. 51Fig. 56-10).These requirements can normally be met by
insulation at one portion; however, in certain unusual conditions the two
8-foot distances may overlap, in which case insulation will be necessary at two
positions.

Final Version

Rule 56.7-C

56.7-C.
Truss Guys

An insulator shall be installed in each truss
guy which is required to be sectionalized by Rule 56.6-A, so that such
insulator is located 8 feet or more above the ground and 8 feet of more the
level of the lowest supply conductor passing within 8 feet of the guy (see Fig.
56-10).These requirements can normally
be met by insulation at one portion; however, in certain unusual conditions the
two 8-foot distances may overlap, in which case insulation will be necessary at
two positions.