Nicholas L.

Gas Station Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection
GAS STATION SYSTEM - QTY 1
IND50 x 4 -2014GS TO BE DONE WITH FX
FIRE EXTINGUISHERS - QTY 3FX TO BE DONE WITH GS
EMERGENCY LIGHT SPOT CHECK - QTY 3
REPAIR AS NEEDEDEL TO BE DONE WITH GS
Deficiency for Kidde/Badger IND-50 4: Standard canopy, XV control head and all IND50 cylinders are mounted to the pillars, no fire alarm at this location, pumps reset when devices go back into normal state (not with control head). Also control head is not listed for outdoor use. Needs to be moved into a weather tight enclosure. Will need an electrician.

Nicholas L.

Gas Station Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection
GAS STATION SYSTEM - QTY 1
IND50 x 4 -2014GS TO BE DONE WITH FX
FIRE EXTINGUISHERS - QTY 3FX TO BE DONE WITH GS
EMERGENCY LIGHT SPOT CHECK - EL QTY 3
REPAIR AS NEEDEDEL TO BE DONE WITH GS
Deficiency for Kidde/Badger IND-50 4: Gas station: previous deficiency still exists.
Electrical shutdown is incorrect. pumps restart after heats and pull station return to normal state.
Pull station is obstructed. see pictures
Control head is not listed for out door use per manufacturer. will need a weather tight enclosure.