Notify me when back in stock

Applications:
Provides permanent waterproof barrier & environmental seal for electrical connections
Used as an alternative to moulded parts and cable breakouts. High shrink ratio enables insulation of cables with connectors of various sizes.Suitable for use in telecommunication, industrial equipment, automotive and avionics applications.

General:

Shrink ratio 3:1

Flame retarded and self extinguishing

Dielectric strength 15kV/mm

Resistance to chemical, copper corrosion and fungus

UV stabilised

Operating temperature range -55°C to +85°C

ROHS compliance

Heat Shrink Tube to Lay Flat Internal Dimensions

Tube ID

Lay Flat ID

Tube ID

Lay Flat ID

4.8mm

7.7mm

18mm

28mm

6mm

10mm

24mm

37mm

9mm

15mm

39mm

61mm

12mm

18mm

52mm

80mm

Heat Shrink Diameter for Copper Lug or Link Barrel Insulation

Red2Go Sleeve Part Number

Red2Go Lug Part Number

Heat Shrink Part Number

CS1.5

CL1.5

RDW4.8

CS2.5

CL2.5

RDW6

CS4

CL4

RDW6

CS6

CL6

RDW9

CS10

CL10

RDW9

CS16

CL16

RDW12

CS25

CL25

RDW12

CS35

CL35

RDW18

CS50

CL50

RDW18

CS70

CL70

RDW18

CS95

CL95

RDW24

CS120

CL120

RDW24

CS150

CL150

RDW24

CS185

CL185

RDW39

CS240

CL240

RDW39

CS300

CL300

RDW39

CL400

RDW39

CL500

RDW39

CL630

RDW52

Bus Bar

12mm

19mm

25mm

38mm

51mm

Thickness

3.2mm

RDW12

RDW24

RDW24

RDW39

RDW52

4.8mm

RDW18

RDW24

RDW24

RDW39

RDW52

6.4mm

RDW24

RDW24

RDW39

RDW52

9.5mm

RDW24

RDW39

RDW52

12.7mm

RDW24

RDW52

(RDW3Reels)

Wall Thickness Data RDW3

Shrink Range / Ratio 3:1

Total Thickness After Recovery

Adhesive After Recovery

Inside Ø 3mm to 1mm

1.03mm ± 0.8mm

40 to 50% of Total Thickness

Product Technical Data RDW3

Properties

Test Method

Typical value

Tensile strength

ASTM-D-638

12 N/mm²

Water Absorption

ASTM-D-570

0.15% Max

Elongation

ASTM-D-638

300%

Low Temperature Flexibility

ASTM-D-2671

-55°C

Specific Gravity

ASTM-D-792

1.4

Longitudinal Change

ASTM-D-638

+/- 5%

Flammability

UL224 VW1

3 (Outer Wall)

Operating Temperature

IEC216

-55°C to +125°C (Outer Wall)

Heat Shock @ 250°C 4 hours

No dripping, cracking or flowing

(Outer Wall)

Fungus Resistance

MIL-1-7444

Inert

Copper Corrosion

ASTM-D-2671 B

Good

Chemical Resistance

Good

Dielectric Strength

ASTM-D-2671

>15kV/mm

Dielectric Constant

ASTM-D-150

3.0 Max

Volume Resistance

ASTM-D-257

1014 Ohm/cm

SKU

RDW3Reels

Brand

RADIFORM

Be The First To Review This Product!

Help other Red2go Pty Ltd users shop smarter by writing reviews for products you have purchased.