Summary of Contents for Vanguard VMH3000TPA

VENT-FREE PROPANE/LP GAS MINI-HEARTH OWNER’S OPERATION AND INSTALLATION MANUAL VMH3000TPA 15,000 to 30,000 Btu/Hr with Thermostat WARNING: If the information in this manual is not followed exactly, a fire or explosion may result caus- ing property damage, personal injury, or loss of life.

FRESH AIR FOR COMBUSTION AND VENTILATION WARNING: This heater shall not be installed in a confined space or unusually tight construction unless provisions are provided for adequate combustion and ven- tilation air. Read the following in- structions to insure proper fresh air for this and other fuel-burning appliances in your home.

® PROPANE/LP GAS RESIDENTIAL HEATERS AIR FOR COMBUSTION AND VENTILATION Continued DETERMINING FRESH-AIR FLOW FOR HEATER LOCATION Determining if You Have a Confined or Unconfined Space Use this worksheet to determine if you have a confined or unconfined space. Space: Includes the room in which you will install heater plus any adjoining rooms with doorless passageways or ventilation grills between the rooms.

AIR FOR COMBUSTION AND VENTILATION Continued VENTILATION AIR Ventilation Air From Inside Building This fresh air would come from an adjoining unconfined space. When ventilating to an adjoining unconfined space, you must pro- vide two permanent openings: one within 12" of the ceiling and one within 12" of the floor on the wall connecting the two spaces (see options 1 and 2, Figure 7).

® PROPANE/LP GAS RESIDENTIAL HEATERS INSTALLATION NOTICE: This heater is intended for use as supplemental heat. Use this heater along with your pri- mary heating system. Do not in- stall this heater as your primary heat source. If you have a central heating system, you may run system’s circulating blower while using heater.

INSTALLATION Continued Mounting Heater to Optional Hearth Base 1. Lay heater on its back on a table with the bottom of heater overhanging the edge of the table. 2. Remove 2 shipping screws in bottom of heater. Discard shipping screws. 3.

INSTALLATION Continued CHECKING GAS CONNECTIONS WARNING: Test all gas pip- ing and connections for leaks after installing or servicing. Cor- rect all leaks at once. WARNING: Never use an open flame to check for a leak. Apply a mixture of liquid soap and water to all joints.

® PROPANE/LP GAS RESIDENTIAL HEATERS OPERATING HEATER FOR YOUR SAFETY READ BEFORE LIGHTING WARNING: If you do not fol- low these instructions exactly, a fire or explosion may result caus- ing property damage, personal injury or loss of life. A. This appliance has a pilot which must be lighted by hand.

OPERATING HEATER Continued THERMOSTAT CONTROL OPERATION The thermostatic control used on this heater differs from standard thermostats. Standard thermostats simply turn on and off the burner. The thermostat used on this heater senses the room temperature. The thermostat adjusts the amount of gas flow to the burner.

® PROPANE/LP GAS RESIDENTIAL HEATERS TROUBLESHOOTING Note: For additional help, visit DESA International’s technical service web site at www.desatech.com. Note: All troubleshooting items are listed in order of operation. OBSERVED PROBLEM When ignitor button is pressed, there is no spark at ODS/pilot When ignitor button is pressed, there is spark at ODS/pilot but no ignition ODS/pilot lights but flame goes out when...

® PROPANE/LP GAS RESIDENTIAL HEATERS TROUBLESHOOTING Continued WARNING: If you smell gas • Shut off gas supply. • Do not try to light any appliance. • Do not touch any electrical switch; do not use any phone in your building. •...

CLEANING AND MAINTENANCE WARNING: Turn off heater and let cool before cleaning. CAUTION: You must keep control areas, burner, and circu- lating air passageways of heater clean. Inspect these areas of heater before each use. Have heater inspected yearly by a quali- fied service person.

ACCESSORIES Purchase these heater accessories from your local dealer. If they can not supply these accessories call DESA International’s Sales Department at 1-800-458-2472 for infor- mation. You can also write to the address listed on the back page of this manual. EQUIPMENT SHUTOFF VALVE - GA5010 Equipment shutoff valve with 1/8"...

WARRANTY INFORMATION Model Serial No. Date Purchased Always specify model and serial numbers when communicating with the factory. We reserve the right to amend these specifications at any time without notice. The only warranty applicable is our standard written warranty. We make no other warranty, expressed or implied. VENT-FREE PROPANE/LP GAS HEATERS DESA International warrants this product to be free from defects in materials and components for four (4) years and five (5) years on stainless steel burners from the date of first purchase, provided that the product has been properly installed, operated and maintained in...