Gas Fireplace, Gas Logs Service Everett, Washington

C.M. Heating offers full repair and maintenance services for hearth products in Everett, WA. If you have a dv gas fireplace, fireplace insert, gas stove, or gas logs, our service technicians have the experience to keep your system operating safely and at peak efficiency.

C.M. Heating stocks the parts and has the experience necessary to keep your gas fired fireplace or stove running properly.

CM Heating Perform diagnostic on a fireplace. Customer stated blower motor is not working. Motor is out of commission need to replace.
Install new remote/receiver.Everett, WA02-18-2019

CM Heating Performed diagnostic on a fireplace. Key valve was shut off to unit. After opening the valve and re igniting system, all system operation is normal.Everett, WA02-25-2019

CM Heating performed a diagnostic on gas fireplace unit and found the unit was installed in a propane gas configuration and needs a conversion kit from LP to NG.Everett, WA02-19-2019

CM Heating performed a fireplace and furnace diagnostic and maintenance. We found the Fireplace in good working condition. Cleaned and tested all components.
Found no issues with furnace. Tested for 15 minutes. Replaced batteries, cleared inducer port.Everett, WA02-13-2019

CM Heating performed a fireplace maintenance and found fireplace in good working order. Found a loose switch terminal on gas valve. Replaced terminal. Cleaned fireplace, adjusted logs to allow proper gas flow. Unit in good working condition.Everett, WA02-04-2019

CM Heating went out for a fireplace diagnostic but Found unit working. However found the units pilot assembly with heavy wear and pilot hood warped, recommend replacement. Replaced pilot assembly.Everett, WA01-30-2019

CM Heating went out to performed a fireplace diagnostic and found unit was on and running when I arrived, found dirty pilot assembly, cleaned pilot assembly and found body starting to crack, and glass latch bolts sheared off, no fix for either, unit needs replacement, got unit working, but replacement is needed VERY SOON. Carbon monoxide hazard will be happening in the very near future. JLvEverett, WA02-08-2019

CM Heating Checked over fireplace for loose parts or source of noise. Nothing was found. System is safe to use.
Changed batteries in remote receiver and test the unit, all operations normal at this time.Everett, WA02-11-2019

CM Heating performed a fireplace diagnostic and found Fireplace may be triggering high temp limit. To solve this, recommend fan in order to disperse heat away from fireplace. Otherwise fireplace working well, found no issues other than customer concern of fireplace pilot intermittently going out.
Furnace in good working conditionEverett, WA04-05-2019