Notify me when back in stock

The RAV-SM564UT-E is Toshiba's 5.3kW In-ceiling Cassette Unit. This inverter Systm has a cooling capacity ranging from 1.5kW to 5.6kW and a heating capacity from 1.5kW to 6.3kW. Wall control unit not included in package.

(D-RAV-SM564UT-E)

Indoor

RAV-SM564UT-E

Outdoor

RAV-SM563AT-A

Refrigerant Type

R410A

Power Suppply

Volts / Phase / Hz

220-240 / 1 / 50

Cooling

Capacity - Rated

kW

5.3

Capacity - Range

kW

1.5 - 5.6

Efficiency (Rated)

EER

3.21

Power Input (min - rated - max)

kW

0.35 - 1.65 - 1.86

Operating Current (rated)

A

7.89

Heating

Capacity - Rated

kW

5.6

Capacity - Range (min - max)

kW

1.5 - 6.3

Efficiency (rated)

COP

3.89

Power Input (min - rated - max)

kW

0.35 - 1.44 - 2.08

Operating Current (rated)

A

6.89

Indoor Unit

Dimensions (HxWxD)

mm

256 x 840 x 840

Net Weight

kg

20

Airflow Volume (H/L)

L/s

291.7 / 216.7

Fan Motor Output

W

14

Sound pressure (H/M/L) - 1m

dBA

32 / 29 / 28

Sound Power (H/M/L)

dBA

47 / 44 / 43

Outdoor Unit

Dimensions (HxWxD)

mm

550 x 780 x 290

Net Weight

kg

44

Compressor Type

DC Twin Rotary

Fan Motor Output

W

43

Cooling Operating Noise (Sound Pressure) (H) - 1m

dBA (@spl)

46

Cooling Operating Noise (Sound Power) (H)

dBA (@swl)

63

Heating Operating Noise (Sound Pressure) (H) -1m

dBA (@spl)

48

Heating Operating Noise (Sound Power) (H)

dBA (@swl)

65

Cooling Usable Temperature Range

°CDB

-15 to 43

Heating Usable Temperature Range

°CWB

-15 to 15

Pipe Size

Liquid Line Ø

mm

6.4

Gas Line Ø

mm

12.7

Coupler Style

Flaring

Drain (Inside Diameter) Ø

mm

VP25

Maximum ength

m

50

Chargeless Length

m

20

Maximum Height Difference

m

30

SKU

D-RAV-SM564UT-E

Brand

Toshiba

Shipping Weight

64.0000kg

Shipping Cubic

0.305044m3

Be The First To Review This Product!

Help other Lawson Air users shop smarter by writing reviews for products you have purchased.