Pressure-switch

Ambient temperature : 0 to 160°F (-18 to 71°C) with Buna-N construction; 0 to 180°F (-18 to 82°C) withlimits :Viton® construction; set point shifts less than 1% of range for a 50°F (28°C) ambient temperature change. Unit will operate down to -40°F (-40°C) but with reduced repeatability

Set point repeatability : Models 10-12: ± 1% of full scale range; Models 13-16: ± 1.5% of full scale range

Switch output : One SPDT

Electrical rating :Rated to 5 A resistive and 5 A inductive (75% power factor), at 125 VAC & 250 VAC, 1/4 HP; 5 A resistive and 3 A inductive at 30 VDC; 0.5 A resistive and 0.25 A inductive at 125 VDC; gold flashing over silver contact for loads down to 5 mA at 6 VDC, 2 mA at 12 VDC and 1 mA at 24 VDC