Dear visitor, welcome to SPRINKLER TALK FORUM - You Got Questions, We've Got Answers. If this is your first visit here, please read the Help. It explains how this page works. You must be registered before you can use all the page's features. Please use the registration form, to register here or read more information about the registration process. If you are already registered, please login here.

Cracks in ball valve handle section....(both)

I was talked into letting me leave my back flow outside during winter..........turned it on an I have cracks on the side of the bal valves on the side, spraying water out the side. need to replace both, an also water started pouring out the bottom release, will this stop when I replace the two handle section ball valves? Paid the last 2 years to have the back flow rebuilt! Wilkins! Please help.......trying to say an do it myself.......twinsmom930@bellsouth.net

Even with a replacement shutoff valve installed in the basement, it is always best to work from a standpoint of not trusting the shutoff valve to be 100 percent effective, and to have an open drain in a low point to allow water to drip out before it gets into the expensive parts of the outdoor plumbing.

Does the pipe exiting the house "elbow" up into the backflow, or does it have a "T" that needs to be plugged? Regardless, both styles of plumbing, like wetboots stated, should have a drain in the basement. The elbow style always has a drain, the T style rarely does. In any event, the technician either forgot to drain back into the basement, or the shut off valve is allowing water to weep past it. Or, he drained it, closed the drain, and the weeping shut off valve refilled the line.

This post has been edited 1 times, last edit by "Central Irrigation" (Apr 29th 2012, 11:28am)

The problem we find is that even with a 3/4" drain outside, it can freeze closed and still cause damage. I see it more often when the home owner installs a boiler drain in place of the plug.
We install our backflows with a T below the backflow with a 3/4" blow out fitting. Remove the plug and drain everything outside. We do blow through the backflow. Now, before anyone jumps on me for it...99% of our backflow and plumbing repairs are due to hard water build up, leaky shut off valves, or blow outs scheduled to late. I just repaired a Febco 765 that had 15 years of hard water build up on it, that only needed a cleaning and an O-ring. It's been blown through 15 times.
I've been toying with the idea of adding a basement drain to the installs, but the 1% of the 1% that need one, doesn't justify the time. A good service tech. can tell when a shut off needs replacing. And a homeowner should realize that icicles hanging from the backflow is not a good thing.

Of course, I should mention that a boiler drain at an outdoor low point needs to be an "old-school" model with a large opening, which is not a thing you can get unless you specifically look for it, and even that won't help if there is any plastic plumbing between it and the basement. Heat conduction is the thing. Houses radiate heat, and basement warmth works its way into outdoor copper plumbing.