WiNG-THRM

Monitor Temperature In Ductwork, Wells, Pipes, and Refrigerators

The WiNG thermistor input sensor accepts one thermistor input. The WiNG-THRM allows you to place a temperature sensor in an environment that may be unfriendly to a wireless transmission – in ductwork, in wells, in pipes, or in refrigerators and freezers – while the transmitter portion of the sensor remains outside that environment, sending the temperature reading back to the WiNG-MGR.

Small Footprint, Big Battery Life

WiNG sensors are compact and unobtrusive, yet provide an industry leading battery life – sensor batteries will last up to 12 years at room temperatures. WiNG sensors maintain this extended battery life while communicating readings to the WiNG-MGR web interface every 10-20 seconds; we knew it was important to our customers that we didn’t sacrifice data responsiveness in order to extend our battery life.

Unprecedented Transmission Range

The WiNG system has an unprecedented transmission range between sensors and manager: up to 100 feet through multiple walls, up to 270 feet through one wall, and up to 600 feet indoor, direct line of sight. While this range is more than ample for most situations, sometimes applications require signals to be pushed through more complex physical or noisy RF
environments. The WiNG-RXT range extender can be implemented in these situations to add up to 1,000 feet direct line of sight transmission distance to the application.

Key Features

Proprietary wireless design

Accepts one 10K-2 thermistor input (12-bit A/D conversion)

Available in 868MHz and 900MHz configurations

A transmission range between manager and sensors that is second to none:

Up to 100 feet (30.5m) through multiple walls

Up to 270 feet (82.3m) through one wall

Up to 600 feet (183m) direct line of sight

Add up to 1,000 feet (305m) direct line of sight with a WiNG-RXT range extender

Unparalleled sensor battery life:

Up to 5 years across full operating range: -13°F to 185°F (-25°C to 85°C)

Up 8 years at temperatures up to 122°F (50°C)

Up to 12 year battery life at room temperature

Support 250 sensors on a single manager, up to 400 sensors with range extenders