“PRESTIGE GPM” – are radiators with side water supply
“PRESTIGE GCM” – are radiators with bottom water supply

These radiators, with their discreet, box-like casing, show off as elegant designs and will satisfy needs of both users and interior designers. They are suitable for every type of premises, residential and business alike, wherever thermal comfort and aesthetics of the rooms are equally observed.
The “Prestige” radiators feature very durable structure.

External surfaces of radiators are made of aluminium and are covered with polyester-epoxy enamels in the powder technology. This ensures durability of the radiator working even in rooms of increased humidity, e.g. in swimming pool halls, bath facilities, laundries, etc.

Additionally, the “Prestige Plus” version is offered by the Convector company, a radiator with a case reinforced with and additional board, for the rooms where the radiator may be exposed to mechanical damages (e.g. staircases).

The coil pipe of water radiators is made of copper, while elements of ribs making up the case are made of aluminium.
Only the coil pipe is in contact with the installation water in Convector radiators.

The outlet grate, with its properly shaped elements, performs the function of a drive for the heated air leaving the radiator. The structure of the outlet grate allows placing it so that the outlet air is directed to the centre of the room.

Type
GPM
GCM

Dimensions

Water capacity

Radiator weight

Normal thermal power(*)
acc.to EN-442
75/65/20°C

Length L

Height H

GPM

GCM

GPM

GCM

cm

dm3

kg

W

2/4

40

20

0,12

0,13

3,3

3,8

191

2/5,5

55

20

0,17

0,18

4,2

4,7

281

2/7

70

20

0,21

0,22

5,2

5,6

377

2/8,5

85

20

0,26

0,27

6,1

6,5

476

2/10

100

20

0,30

0,31

7,0

7,5

580

2/11,5

115

20

0,35

0,36

7,9

8,4

687

2/13

130

20

0,39

0,40

8,9

9,3

797

2/14,5

145

20

0,44

0,45

9,8

10,2

910

2/16

160

20

0,48

0,49

10,7

11,1

1025

2/17,5

175

20

0,53

0,54

11,6

12,1

1143

2/19

190

20

0,57

0,58

12,6

13,0

1263

4/4

40

40

0,25

0,29

4,9

5,4

362

4/5,5

55

40

0,34

0,38

6,3

6,8

533

4/7

70

40

0,43

0,47

7,7

8,2

714

4/8,5

85

40

0,52

0,56

9,1

9,6

903

4/10

100

40

0,61

0,65

10,5

11

1100

4/11,5

115

40

0,70

0,74

11,9

12,5

1303

4/13

130

40

0,79

0,83

13,3

13,9

1512

4/14,5

145

40

0,88

0,92

14,8

15,3

1725

4/16

160

40

0,97

1,01

16,2

16,7

1944

4/17,5

175

40

1,06

1,10

17,6

18,1

2167

4/19

190

40

1,15

1,19

19,0

19,5

2394

6/4

40

60

0,37

0,44

6,5

7,1

527

6/5,5

55

60

0,51

0,58

8,4

9,0

775

6/7

70

60

0,64

0,71

10,3

10,9

1038

6/8,5

85

60

0,78

0,85

12,2

12,8

1313

6/10

100

60

0,91

0,98

14,1

14,6

1599

6/11,5

115

60

1,05

1,12

15,9

16,5

1894

6/13

130

60

1,18

1,25

17,8

18,4

2198

6/14,5

145

60

1,31

1,39

19,7

20,3

2508

6/16

160

60

1,45

1,52

21,6

22,2

2826

6/17,5

175

60

1,53

1,65

23,5

24,1

3150

6/19

190

60

1,72

1,79

25,4

26,0

3480

8/4

40

80

0,50

0,60

8,1

8,7

687

8/5,5

55

80

0,68

0,78

10,5

11,1

1011

8/7

70

80

0,86

0,96

12,9

13,5

1354

8/8,5

85

80

1,04

1,14

15,2

15,8

1713

8/10

100

80

1,21

1,32

17,6

18,2

2085

8/11,5

115

80

1,39

1,49

20,0

20,6

2470

8/13

130

80

1,57

1,67

22,4

23,0

2860

8/14,5

145

80

1,75

1,85

24,8

25,4

3271

8/16

160

80

1,93

2,03

27,1

27,8

3686

8/17,5

175

80

2,11

2,21

29,5

30,1

4108

8/19

190

80

2,29

2,39

31,9

32,5

4539

Report from the ITGiS Radom research No. 120 and 121/2001/LA
(*) For selection of radiators for parameters other than 75/65/20°C, use the GPM and GCM radiator correction indexes.
GPM and GCM radiators are produced only to specific orders: delivery time – 21 days