Disk Check Valves

Sunday, 07 October 2012 07:18
administrator

Description:Embee DCV- Series Investment Cast Stainless Steel Disc Check Valves are designed to be sandwiched between flanges. i.e. water type. Their function is to prevent reverse flow on a wide variety of fluids for applications in process lines, hot water systems, steam and condensate systems etc.Limited Conditions:

Maximum body design P N 40.

Max. Operating Pressure 40 bar g.

Max. Operating Temperature 300 C.

Maximum Cold Hydraulic test 60 bar g.

Minimum Operating Temperature - 50 C.

Sizes and Pipe Connections:

DN 15,20,25,32,40,50,65,80,100. they can be fitted between BS 10 tables "E" and "H"; BS 4505 / DIN Pn6, 10,16,25,40; JIS 5.10,16,20 flanges with the following exceptions: DN 40,50,80 and 100 - will not fit between JIS flanges. DN 65 and 80 will not fit between BS 10 "E" flanges.