Features

Designed for wine cellars up to 2000 cubic feet and rated for internal or external (see notes below) applications, CellarPro's Mini-Split 8000S 3/4 Ton Nominal refrigeration system allows the noise from the condensing unit to be removed from living areas, and eliminates the need for large holes in your cellar wall. This is achieved by separating the evaporator unit from the condensing unit.

Only a few small openings for the line-set and drain line are required to connect the evaporator and condensing units. Inside the cellar, the evaporator unit is designed to mount on the wall near the top of the wine cellar. Outside the cellar, the condensing unit is attached to the evaporator unit by a line-set (sold separately) that can run up to 100 equivalent feet (and up to 30 vertical feet).

Our advanced evaporator unit uses a variable-speed centrifugal fan with three settings, including a "high" setting for maximum performance and a "low" setting for super-quiet operation. The evaporator should be mounted close to the ceiling inside the cellar.

Our high-performance condensing unit is designed to handle environments ranging from 0°F to 110°F. The condensing unit requires 12 inches of unobstructed space in front of the coils, and requires approx. 600-700 CFM of ventilation when installed in a confined space.

CellarPro Split wine cellar refrigeration systems offer a choice of wiring: 1. the Condensing unit can be electronically controlled by and wired to the Evaporator (single power source on the Evaporator side), or 2. the Condensing unit can be controlled by a Solenoid valve (dual power source, one each to the Evaporator and Condensing units.) The first choice (with electronic wiring) will allow the Condensing unit to be used in temperatures down to -20°F.

Important Notes: External installations require our outdoor hood (sold separately). For exposure to environments below 40°F, our compressor heatermodification is required. Access to the left and right side of the evaporator unit is required for installation. All split systems must be installed and charged on site by a qualified HVAC professional. Line-set equivalent feet must be calculated in accordance with ASHRAE guidelines; refer to our Line Sizing Chart for more information.

Capacity: Wine Cellars up to 2000 cubic feet with proper insulation and a moisture barrier.

Capacity: Up to 2000 cubic feet in properly insulated and sealed wine cellars.

Up to 2000 Cu. Ft. Capacity (3/4 Ton Nominal)

Engineered to operate in interior and external environments (0°F to 110°F)

Line-sets can run up to 100 equivalent feet (and up to 30 vertical feet)

Adjustable Low Ambient Fan Cycling Control

Auto Reset High Pressure Switch

Compatible with a Dedicated 15-Amp Circuit

Optional Bottle Probe

Optional Outdoor Cover

ETL Tested and Certified (UL Standards) (PENDING)

Introduction: When ducting the FRONT of CellarPro VS and Split cooling units, varying amounts of condensation can occur depending on the ambient conditions where the cooling unit will be located. The charts above are designed to provide guidance in selecting the appropriate front duct kit depending on 1. Your desired cellar temperature, 2. The ambient temperature where the cooling unit will be located, and 3. the ambient relative humidity where the cooling unit will be located.

Discussion: Condensation generally occurs on the cold surfaces of the face and around the front of the cooling unit when the temperature of the metal falls below the ambient dew point (a function of temperature and humidity). The greater the difference between the dew point and the metal temperature (ie the higher the dew point and the lower the metal temperature), the more condensation will occur.
For this reason, CellarPro has developed two front duct kits for its VS and Split systems: a duct kit for LOW humidity conditions, and a duct kit for HIGH humidity conditions. The HIGH humidity duct kit has extra insulation around the front and face of the cooling unit, and always should be used together with our remote control display kit. In some cases (shown above in red), the humidity conditions are too high even for our HIGH humidity duct kit. In this case, the cooling unit should be moved to a conditioned space and the rear should be ducted if necessary.

You might also like:

Design

Free Design Services

Do you have a room or a unused area in your home that you would want to see transformed into a wine cellar, wine storage area, or wine room?

It's actually easier than you think! Just go to our Design Request form and fill out the essential details. All you need to do is share your room dimensions with us as well as other valuable information pertaining to your wine storage needs. We will send you with a wine storage plan layout based off those, totally free of charge.

We can generate a custom-designed wine cellar for you with either our modular wine rack kits or our custom products. Our design can be done by budget, bottle capacity, or any other criteria.

Shipping

All Wooden Wine Rack Kit Series are in stock!

The multitude of orders we receive as well as the time you place your order greatly affects processing time. Please allow up to 1 1/2 weeks for your order to ship, although most smaller orders will ship out sooner than that. We do appreciate some customers have a tight deadline to receive their order so we do offer a free upgrade to our quick ship program. Factors such as material availability, stain, quantity, and items selected we can ship your order in as little as 1 day from date of receipt for no additional charge!

To take advantage of the quick ship program please select the quick ship option during checkout for your order and then please explain the timeline you are under for the order in the special instructions field on the checkout page. We will review your order during normal business hours and contact you to review your needs. In certain locations your delivery date may require expedited shipping charges even if we ship your order out with the quick ship program, which might be an additional charge you would need to authorize. All of the options will be reviewed with you when we contact you. Keep in mind that if for any reason the quick ship order does not push through after we have reviewed your needs, you are entitled to cancel your order and get a full refund.

Take note that there are additional S&H charges for shipments outside the contiguous United States and APO addresses. Also, there may be additional duties and taxes on international shipments.

Shipping Methods

We use an assortment of shipping methods to ensure that your racking and other purchases arrive to you when you need it, and free from damage. We are actually working with a number of shipping companies and utilize the most suitable ones depending on your order size and where we are shipping your order to. The list is not exclusive, but here are some of the more frequently utilized carriers: Fed Ex, UPS, Roadway Express, Overnite Transportation, Dawes Transportation, ABF, Team Worldwide, & Yellow. You will receive an email confirmation from us once your order has shipped from our facility advising you of the carrier and the tracking information, so you can plan for your delivery accordingly.

The following is for reference of larger orders or custom wine cellars:

Maximum Protection of Your Order

We ensure proper security of custom wine cellar orders by putting them in corrugated containers with corner protectors and then stacked and shrink wrapped onto skids. These skids have plywood aprons around the perimeter as shown to ensure minimal damage from fork lifts while being moved around shipping terminals and on/off the trucks. The vast majority of custom cellars ship via a common shipping carrier.

Basic Delivery

This shipping option is done via a 53' foot semi-trailer that will arrive at your residence. The driver opens the back of the truck and steps aside for the assigned party on your end to do the unloading. If the basic service does not fit your needs we also have a host of additional services listed below that you can choose from for an additional cost.

Customer pickup

This method is quite self-explanatory and we get in touch with the client the moment the order is completed. The client will then contact their design consultant with the date they will be arriving for pick up. Pick up date and times are Monday - Thursday 8:00 AM - 12:30 PM and 2:00 PM - 5:00 PM. Keep in mind that the afternoon pickup may be at the same time as large carriers are being loaded and which may at times result in delays in the loading of your product. In addition, we also need to be notified if the product will be loaded on a skid.

Third party shipping

Means the customer has their own shipping company and is going to arrange for delivery of the product to their final destination at their expense. Wine Cellar Innovations will need a completely filled out Bill of Lading at least 24 hours prior to the scheduled pick up date of the product. The product is generally loaded onto skids and the client is charged with a skid fee by us for each skid required to package your order. We then notify the client when their order is complete and ready for pick up. Pick up date and times are Monday-Thursday 8:00 AM - 12:30 PM and 2:00 PM - 5:00 PM.

Inside Delivery and lift gate service

In this method, the carrier removes the product off of their truck and delivers it into your garage or the first room that is past the threshold of your residence or place of business. Note that a lift gate service is required to unload the product from the truck due to its length and weight.

Gated community

There are only a limited number of specialty carriers who are willing to make deliveries to these communities, so the client needs to indicate it if they are residing in one. This is due to the extra work involved in clearing a time for delivery and getting the clearance with security.

Small truck

Is required if a 53' long semi trailer will not be able to make a delivery to park in front of your home or in your driveway at the time of delivery.

Two man delivery service

Will be checked by Wine Cellar Innovations if we are shipping product this in excess of 70 pounds per box or if you have requested delivery of your product inside your home to a location other than the first room pass the threshold of your residence or place of business.

Turn Key Quote

Deliveries made to the following residences require a Turn Key Quote:

Condo

High rise

Any residential area where trucking companies must use asn elevator

If the customer wants delivery past the threshold inside the residence.

If the drop off location is not directly off of the driveway or if the driveway is inaccessible.