Triple-Rated (USE-2 or RHH or RHW-2) URD cables can be used as Type USE-2 direct-buried underground service entrance cable*, but is also listed as RHH and RHW-2, making it suitable for applications in raceways for general purpose lighting and power circuits covered under the National Electrical Code®

Recognized by ASTM in Standards B 800, B 801, B 836, and B901.

Specification

Conductor

Insulation
Thickness (mils)

Nominal
O.D. (mils)

Approx. Weight per
1000' (lbs)

Allowable Ampacities

Size (AWG or kcmil)

Number of
Strands

60℃

75℃

90℃

6

7

60

283

44

40

50

50

4

7

60

333

64

55

65

75

2

6

60

388

93

75

90

100

1

18

80

459

124

85

100

115

1/0

18

80

496

149

100

120

135

2/0

18

80

536

180

115

135

150

3/0

18

80

583

218

130

155

175

4/0

18

80

635

266

150

180

205

250

22

95

710

322

170

205

230

300

35

95

760

377

190

230

255

350

35

95

806

431

210

250

280

400

35

95

849

484

225

270

305

500

35

95

926

590

260

310

350

600

58

110

1033

718

285

340

385

700

58

110

1100

829

310

375

420

750

58

110

1128

876

320

385

435

900

58

110

1222

1039

355

425

480

1000

58

110

1280

1138

375

445

500

Corresponding parameter set not found, please add it in property template of background