Flow Switch | Type VHS06 by Ross Brown Sales

You can position this flow switch in multiple locations. Ross Brown Sales specialises in a modular approach in designing their flow switches, allowing variance in application.

CONTACT THIS SUPPLIER TO FIND OUT MORE

Possible areas of application

Our SIKA flow switches are used for monitoring volume flows. Depending on requirements, these are available for various nominal widths and set-point ranges. Our modular approach allows product designs and options to be matched to a wide variety of applications.

The broad temperature and pressure ranges, choice of materials and connection options ensure a very high level of versatility, which is why SIKA flow switches are used in so many areas:

Heating

Industrial cooling circuits

Water treatment

Potable water applications

Function

The flow switch comprises a paddle system to whose end a permanent magnet is attached. Above this magnet is a reed contact, located outside the flow of fluid. A second magnet creates the force necessary to reset the switch back to the no flow position.

When the flow being monitored pushes against the paddle system, the paddle swings away. This changes the position of the magnet in relation to the reed contact and thus activates the contact.

As soon as the flow is interrupted, the paddle moves back to its starting position, thus activating the reed contact once again. The force necessary to push the magnet back is provided by the two magnets repelling each other. Using magnetic force instead of the usual leaf spring means that the switch is considerably more stable in the long term and much less sensitive to pressure peaks.

Our temperature products include a large range of Bi-metallic thermometers from 80mm to 125mm diameter, digital thermometers and glass thermometers. Data loggers for pressure, temperature and humidity are also available.