PARCO

Possible configurations

References

Select your desired model variant

PARCO 300 10'

PARCO 360 12’

PARCO 420 14’

PARCO illuminates with gracefully iconic styling and state of the art LED technology. The luminaire is integrated into the curvilinear aluminum pole creating a gentle ellipse in pedestrian scale heights. The fully shielded luminaire utilizes two LED light engines and emits zero uplight. It is suitable for LEED zones 1 through 4 and is Dark Sky compliant. The rectangular profile pole is crafted with subtle design features such as concealed anchor bolts and absence of visible welds. It is available in three mounting heights. All hardware is stainless steel.

Specification

PARCO 300 10'

HOUSING Luminaire is fabricated from aluminum to form a sealed enclosure which houses the LED light engine and driver. Luminaire housing is mounted semi-regressed into the rectangular profile pole and is accessed with a single captive thumb screw mechanism for tool-less entry. Horizontal flat lens is clear tempered glass. Housing is fitted with stainless steel weather-tight strain relief bushing for the power cable exiting the rear of the luminaire inside the pole. All hardware is stainless steel.

OPTICSOptical assembly consists of two individual CoB LED modules with optical quality silicone lenses to produce a Type III distribution with zero uplight. Light engines are available in a choice of 3000K or 4000K color temperatures with CRI of 80. All models are suitable for use in LEED lighting zones 1 through 4 and are Dark Sky compliant.

BUG RATING: B1-U0-G1 for all variants

ELECTRICALLuminaire uses one driver per LED module for a total of two onboard power supplies. The universal electronic LED drivers are integral to the luminaire and accommodate an input voltage range from 120v to 277v at 50/60Hz. Power factor rating is 95%. Drivers include dimming control from an input signal of 0-10V DC (provided by others) when specified with the dimming option. LED driver provides 500mA drive current to the LEDs for a total power consumption of 32 watts.

DELIVERED LUMEN OUTPUT3000K: 2337 lumens4000K: 2486 lumens

NOTE : Due to rapid and continuous advances in LED technology, LED luminaire data is subject to change without notice and at the discretion of HessAmerica. Consult factory to confirm current technical data.

POLECurvilinear pole with 7.5" x 3.5" nominal cross section is formed from seamless 6061 aluminum extrusion and heat treated to produce a T5 temper. Nominal wall thickness is 3/16". Pole mounting base with internal flange is fabricated from aluminum and shows no visible welds. Access door with triangular locking mechanism at rear of base provides entry for securing pole to the internal anchor bolts and connection to power. Nominal pole height is 10'. See PARCO 360 for 12' pole or PARCO 420 for 14' pole.