Excellent Air Distribution

The conditioned air can be distributed evenly to every corner of the room through ducting. This helps to create a pleasant environment and maintain comfort. Furthermore, multiple area can be conditioned simultaneously by using just the one indoor unit.

Auto Random Restart with Last-State-Memory

In the event of a sudden power failure during operation, unit restarts automatically in 64 different recovery timing patterns (within 180 seconds to 244 seconds) and the unit will operate based on the previous setting (operating mode, temperature setting and fan speed). This ensures that air conditioner in the same building resume randomly instead of all units resuming at the same time, preventing power surge after a blackout

Double Protection Drainage System

The primary drain pan is designed with high thermal insulation material and moulded in gradient for better condensate water drainage. The extra secondary drain pan "built in" to the standard unit offers extra protection against possible water leaking problems

Flexibility in System Design

The unit offers fan motor that can operate up to 4 speeds, thus provide choices of external static pressure for designing ducting system. In addition, a range of FD(Y)B-CXV1 model with optional specification of low external static pressure is also provide. Please refer to technical specification.

Self Diagnosis Features

The microprocessor provides the possibility to detect and to diagnose any faults thats occurs in the system. Faults are displayed as error code in the wired controller. This will ease the troubleshooting process.