This Is A Custom Widget

This Sliding Bar can be switched on or off in theme options, and can take any widget you throw at it or even fill it with your custom HTML Code. Its perfect for grabbing the attention of your viewers. Choose between 1, 2, 3 or 4 columns, set the background color, widget divider color, activate transparency, a top border or fully disable it on desktop and mobile.

This Is A Custom Widget

This Sliding Bar can be switched on or off in theme options, and can take any widget you throw at it or even fill it with your custom HTML Code. Its perfect for grabbing the attention of your viewers. Choose between 1, 2, 3 or 4 columns, set the background color, widget divider color, activate transparency, a top border or fully disable it on desktop and mobile.

For over 80 years Bry-Air has been a leader in dehumidifying with a silica gel desiccant. As a global company with headquarters in Sunbury OH, Bry-Air offers industrial solutions to bring any amount of air at any inlet down to any humidity level. “0 grains or lower”. Precision can be utilized by modulating the regeneration heat source, bypass dampers or the wheel itself. Pre-Cool and post cool options are available. Regeneration can be achieved by using direct or indirect gas fired heat, house steam, or electric Heat.

Units can be a simple pre-engineered “Mini-Pac” or a built to order skid encompassing all the required particulars. Our DC series allows us to provide a module without the fan to be added to a custom air handler (existing or new).

Our VFB Series (300-30,000 cfm) is built with premium features including all welded aluminium construction, vapor proof gasketing, hinged access doors, optional primary heat and filtration, and more.

The Bry-Air Eco Dry system takes advantage of variable loads and maximizing energy consumption by varying the wheel speed, regeneration output and supply air flow to reduce the input kw by as much as 45% using its unique algorithms. This system is available on the VFB and DC series.

Novelaire builds competitive high quality built to order commercial grade desiccant dehumidifiers. The desiccant wheel is very efficient and effective at removing moisture from the air. While this approach is associated with highly industrial processes (10 grains, or example 70F,10% RH)), commercial grade is more in the range of 20-40 grains (such as 70F, 40%RH). Units come in small and large sizes and can be recirculating or 100% OA with energy recovery. In some cases these units qualify for NJ energy rebates.

We also can help you in an “Industrial” process requiring greater dehumidification power (10 grains!). In this case, we would steer your project into a more traditional active desiccant with more robust regeneration. To achieve better dehumidification, we would use a gas heater (direct fired is most common, but indirect is available for class 100 spaces), steam heat, or electric heat. We can provide the package with Pre-cool and/or Post Cool as required.

Again, we can provide just the dehumidifier or an entire HVAC package for all the temperature and humidity control.

Remember, Units can be Spot Dehumidifiers or Complete Packages!

For systems where there is high humidity loads, but extreme low dew points are not needed and cost is an issue,mechanical dehumidification is likely your best choice. Many of our brands have this feature (Geo-comfort water source heat pumps, United Cool Air Indoor Packaged Units and Addison Outdoor and traditional split systems)

Use the Cooling Coil to wring the moisture out and allow the warm condenser air to reheat the air to neutral. This is known as Hot-Gas Reheat (learn more)

Addison brings dehumidification to a higher level by using a 2 step approach. A subcooling coil coming from the condenser line upstream to the cooling coil will be the first stage of reheat. The genius part of this first step is the refrigerant on its way to the evaporator is actually cooled by that subcooling coil, providing a lower dewpoint! Better performance and higher efficiency is the result. For an added step of reheat, a traditional hot gas reheat coil would be downstream of the subcooling coil.

Hot Gas Reheat can be on/off or controlled by a modulating valve. A humidistat would force the cooling on and enable the dehumidification cycle. In the case of modulating hot-gas reheat, a discharge setpoint would be enabled, and similiar to cruise control on a car which will accelerate/decelerate to maintain 55f, the unit controller will modulate the warm refrigerant to maintain a specific discharge air dry bulb.

ADVANCED COOLING TECHNOLOGIESBesides Energy recovery with a supply and exhaust stream, a Heat Pipe wraparound loop can use the sensible heat to do reheat for make-up air applications. Component can be installed in a new HVAC unit or retrofitted into existing.ACT offers capacity control with fixed flow orifices or solenoid valves!Applications:– Corridors– Schools– Chilled Beam– Locker RoomsAdditional Heat Pipe informationRECENT JOB WITH HEAT PIPE

About US

Since 2013, Engineered Air Solutions has represented and distributed quality ventilation products from a broad range of companies, targeting Commercial and Industrial applications.We consist of Sales Engineers with decades of experience