Single Drench Shower ValveTM-600-LF

DURA-trol® solid bimetal thermostat directly linked to valve porting to control the intake of hot and cold water and compensate for supply temperature and pressure fluctuations. DURA-trol is highly responsive and cannot be damaged by extremes in temperature. Thermostatic Mixing Valve can be set to the correct temperature for the application. Locking type temperature regulator to prevent accidental movement set for 85ºF (29ºC), Recommended Hot Inlet Temperature 140°F. Mixing valve will close down on failure of cold water supply, Mixing Valve with special internal cold water bypass capable of 20 GPM (76 l/min) @ 30 PSI (2.1 Bar) upon failure of hot water supply. Adjustable high temperature limit stop set for 90ºF (32ºC), Full 3/4” top or bottom inlets and 1” top outlet, Integral wall support, Dial thermometer (range 0 to 140ºF, -10 to 60ºC), Rough bronze finish. Union angle checkstops on inlets

To determine the amount of Hot Water needed to maintain a steady outlet temperature for 15 minutes, click Hot Water Requirements.

This guide is not meant to be used as a means to size the hot water heaters but rather to illustrate consumption.

This product is certified to meet Low Lead requirements of wetted surface area containing less than 0.25% lead by weight