A contract to No. 2. Change

Szügy Község Önkormányzata | PublishedDecember 4, 2015

Winner

Riebenbauer Energy Kft.

cpvs

Within the framework of carrying out "Development of Solar System Collars" works construction contract business. Main place of performance: belonging to a municipality, Collars downtown hrsz 36 ,, 2699 Collars nature, Rákóczi road by installing a partial satisfaction of 99-101, under the heading Szügyi Madách Imre Elementary School in demand for solar power systems.. The required solar panels fully placed the school in the south roof of their exposure. - Roof angle: 15 ° - Roof exposure: 0 ° The system consists of 88 pieces of Risen Energy SYP 250S polycrystalline solar cell with a total power of 250 Wp x 88 pieces, which is 22,000 Wp. The annual expected energy yield based on the PV-SOL design software identification: 24,926 kWh / year of the current annual electricity consumption: 35,959 kWh / year of solar cells (connected in series) are connected according to the diagram below insurer in the regenerative power GROWATT 20000 UE (20 kVA) The inverter is used for connecting 6 mm2 solar cells developed solar UV-resistant cable. The inverter will be placed in electrical kapcsolóhelysigében located next to the school entrance. The system is protected against overvoltage. The main elements of this system are: - 88 pieces of Risen Energy SYP 250S polycrystalline solar panel - 1 GROWATT 20000 UE (20 kVA) Specifications Inverter Solar Power: Maximum power 250 Wp, Tolerance: - 0 + 3% Efficiency η: 15.37% , voltage V P max: 30.30, P max current of 8.26, voltage V Open: 37.30, short circuit current of 8.90 belonging to a municipality, Collars downtown hrsz 36 ,, 2699 Collars nature, Kossuth út 99 -101 installing., under the heading Szügyi partial satisfaction of district notary electricity demand solar system. The meter is located in the school office. - Roof angle: 30 ° - Roof exposure: 0 ° to 32 Risen Energy System 250S is SYP polycrystalline solar cell with a total power of 250 Wp x 32, which is 8,000 Wp. The expected annual energy yield of PV-based design program SOL data: 9352 kWh / year of the current annual electricity consumption: 9,425 kWh / year of solar cells (connected in series) connected to the regenerative power to ensure GROWATT 8000 UE (8kVA) inverter. The connection is used for 6 mm2 solar cells developed solar UV-resistant cable. The inverter is placed in electrical kapcsolóhelysigében located next to the school entrance. The system is protected against overvoltage. The main elements of this system are: - 32 Risen Energy SYP 250S polycrystalline solar panel - 1 GROWATT 8000 UE (8kVA) Inverter PV technology by: Maximum power 250 Wp, Tolerance: - 0 + 3% Efficiency η: 15.37%; voltage V P max: 30.30, P max current of 8.26, voltage V Open: 37.30, short circuit current of 8.90

Modification of a contract

Szügy Község Önkormányzata | PublishedJune 10, 2015

Winner

Riebenbauer Energy Kft.

cpvs

Within the framework of carrying out "Development of Solar System collars" construction works contract business. Main place of performance: belonging to a municipality, downtown Collars 36 u ,, 2699 Collars nature, Kossuth road by installing a partial satisfaction of 99-101, under the heading Szügyi Madách Imre Elementary School in electricity demand solar system.. The required solar panels fully placed the school in the south roof of their exposure. - Roof angle: 15 ° - Roof exposure: 0 ° The system consists of 88 pieces of Risen Energy SYP 250S (or equivalent) of polycrystalline solar cell with a total power of 250 Wp x 88 pieces, which is 22,000 Wp. The annual expected energy yield based on the PV-SOL design software identification: 24,926 kWh / year of the current annual electricity consumption: 35,959 kWh / year of solar cells (connected in series) connected insurer in the regenerative power REFUsol AE 3TL 20K SCI inverter according to the diagram below ( or equivalent). The connection is used for 6 mm2 solar cells developed solar UV-resistant cable. The inverter will be placed in electrical kapcsolóhelysigében located next to the school entrance. The system is protected against overvoltage. The main elements of this system are: - 88 pieces of Risen Energy SYP 250S (or equivalent) of polycrystalline solar cells - 1 REFUsol AE 3TL 20K SCI (or equivalent) specifications Inverter Solar Power: Maximum power 250 Wp, Tolerance: - 0 + 3% , η Efficiency: 15.37% voltage V P max: 30.30, P max current of 8.26, voltage V Open: 37.30, short circuit current of 8.90 belonging to a municipality, Collars downtown hrsz 36, the nature Collars 2699, Rákóczi road by installing a partial satisfaction of 99-101., under the heading Szügyi district notary electricity demand solar system. The meter is located in the school office. - Roof angle: 30 ° - Roof exposure: 0 ° The system consists of 32 pieces of Risen Energy SYP 250S (or equivalent) of polycrystalline solar cell with a total power of 250 Wp x 32, which is 8,000 Wp. The annual expected energy yield based on the PV-SOL design program details: 9352 kWh / year of the current annual electricity consumption: 9,425 kWh / year of solar cells (connected in series) connected insurer in the regenerative power REFUsol AE 3TL 8K (or equivalent) inverter. The connection is used for 6 mm2 solar cells developed solar UV-resistant cable. The inverter is placed in electrical kapcsolóhelysigében located next to the school entrance. The system is protected against overvoltage. The main elements of this system are: - 32 Risen Energy SYP 250S (or equivalent) of polycrystalline solar cells - 1 REFUsol AE 3TL 8K (or equivalent) Inverter PV technology by: Maximum power 250 Wp, Tolerance: - 0 + 3% η Efficiency: 15.37% voltage V P max: 30.30, P max current of 8.26, voltage V Open: 37.30, short circuit current of 8.90