The ON/OFF timer allows you to set the time of day you would like the air conditioner to switch on or off. This simple timer is perfect if you want to program the air conditioner to switch on at a particular time in the morning. Alternatively, if the unit is already running you can set the time it will switch off at.

R32 refrigerant

R32 is a refrigerant with just one-third the global warming potential of R410A, meaning less risk of harm to the environment. R32 enables increased energy efficiency, and is said to be the next generation in refrigerants.

Quiet operation

A “Quiet Mode” setting has been added to the fan speed settings, ensuring super quiet operation below 19 dB for model sizes 35 and under. Perfect for the bedroom; it’s so quiet you’ll check to see if it’s on.

i-save Mode

the “i-save” Mode is a simplified setting function that recalls the preferred (preset) temperature at the press of a button on the remote controller. The function ensures the most suitable air conditioning settings are used contribute to reduced power consumption.

Wide airflow

The larger 71/80 models feature a “Wide-vane” mode where you can easily adjust the direction of airflow to reach any corner of the room.

Long airflow

The high-power motor combines with the “Long” mode to push air out further, helping to provide a more even air conditioned experience in the room. (models 71/80)

Blue fin condenser

Anti-corrosion treatment has been applied to the heat exchanger of the outdoor unit. This coating slows the corrosion process of the aluminium fins; this is caused by salt in the air especially in coastal areas. (Corrosion of the heat exchanger will affect efficiency and performance.)

Potentially demand response capable

Based on connection of a demand response enabling device (DRED) via DRED interface DRC-101A, Demand Response Mode is activated in response to signals sent from the electric power company at times when it is necessary to reduce peak demand. (2.5 kW – 7.8 kW)

Specifications (All models)

Model Name

MSZ-GL25VGD

MSZ-GL35VGD

MSZ-GL42VGD

Indoor Unit

MSZ-GL25VGD

MSZ-GL35VGD

MSZ-GL42VGD

Outdoor Unit

MUZ-GL25VGD

MUZ-GL35VGD

MUZ-GL42VGD

Cooling

Capacity (Rated Conditions)

kW

2.5

3.5

4.2

Capacity (Min – Max)

kW

1.1 – 3.6

1.1 – 4.1

0.9 – 4.8

Air Flow (Quiet/SHi*)

l/s

67-200

67-200

77-205

AEER/EER (Rated Conditions)

5.07/5.10

4.10/4.12

3.61/3.62

Star Rating

5.5

3.5

2.5

Running Current (Rated)

2.6

4.0

5.3

Sound Pressure Levels

Indoor at 1.5m (Quiet/Low/Med/Hi/SH*)

dBA

19-24-3-38-44

19-24-31-38-44

26-29-35-40-46

Outdoor at 1m

dBA

46

50

52

Sound Power Level – Outdoor

dBA

59

62

64

Heating

Capacity (Rated Conditions)

kW

3.2

3.7

5.4

Capacity (Min – Max)

kW

1.3 – 5.0

1.6 – 5.1

1.4 – 6.0

Air Flow (Quiet/SHi*)

l/s

62-182

62-200

67-205

ACOP/COP (Rated Conditions)

4.82/4.85

4.55/4.57

3.69/3.70

Star Rating

5.0

4.5

3.0

Running Current (Rated)

3.5

3.8

6.6

Sound Pressure Levels

Indoor at 1.5m (Quiet/Low/Med/Hi/SH*)

dBA

19-25-31-38-42

19-25-31-38-45

26-29-35-40-46

Outdoor at 1m

dBA

49

50

52

Sound Power Level – Outdoor

dBA

59

62

64

Indoor – Dimensions (HxWxD)

mm

290 x 799 x 232

290 x 799 x 232

290 x 799 x 232

Weight – Indoor

kg

10

10

10

Outdoor – Dimensions (HxWxD)

mm

550 x 800 x 285

550x800x285

550x800x285

Weight – Outdoor

kg

33

33

34

Electrical Supply

230 volt/Single Phase / 50 Hertz – Outdoor Power Supply

Breaker Size

A

10

10

10

Piping – max length

m

20

20

20

max height

m

12

12

12

Guaranteed Operating Range

ºC

-10 ~ 46

-10 ~ 46

-10 ~ 46

-15~ 24

-15~ 24

-15~ 24

Accessories

Remote Control

SG15D (Part No. E12 R80 426)

Model Name

MSZ-GL50VGD

MSZ-GL60VGD

MSZ-GL71VGD

MSZ-GL80VGD

Indoor Unit

MSZ-GL50VGD

MSZ-GL60VGD

MSZ-GL71VGD

MSZ-GL80VGD

Outdoor Unit

MUZ-GL50VGD

MUZ-GL60VGD

MUZ-GL71VGD

MUZ-GL80VGD

Cooling

Capacity (Rated Conditions)

kW

4.8

6.0

7.1

7.8

Capacity (Min – Max)

kW

1.5 – 6.2

1.5 – 7.2

2.4 – 8.7

2.4 – 9.2

Air Flow (Quiet/SHi*)

l/s

113-282

107-268

153-290

153-290

AEER/EER (Rated Conditions)

4.09/4.10

3.77/3.77

3.53/3.53

3.30/3.31

Star Rating

4.0

3.0

2.5

2.0

Running Current (Rated)

5.2

7.1

8.8

10.8

Sound Pressure Levels

Indoor at 1.5m (Quiet/Low/Med/Hi/SH*)

dBA

28-33-39-44-49

29-37-41-45-49

30-37-41-45-49

30-37-41-45-53

Outdoor at 1m

dBA

54

55

55

55

Sound Power Level – Outdoor

dBA

69

69

69

69

Heating

Capacity (Rated Conditions)

kW

5.8

6.8

8.1

9.0

Capacity (Min – Max)

kW

1.6 – 8.0

2.0 – 9.3

2.2 – 9.9

2.2 – 11.1

Air Flow (Quiet/SHi*)

l/s

113-282

107-290

170-297

170-297

ACOP/COP (Rated Conditions)

4.22/4.23

4.06/4.07

3.80/3.84

3.50/3.53

Star Rating

3.5

3.5

3.0

2.5

Running Current (Rated)

6.1

7.4

9.5

11.2

Sound Pressure Levels

Indoor at 1.5m (Quiet/Low/Med/Hi/SH*)

dBA

28-33-38-43-48

29-37-41-45-51

30-37-41-45-49

30-37-41-45-49

Outdoor at 1m

dBA

56

55

55

55

Sound Power Level – Outdoor

dBA

69

69

69

69

Indoor – Dimensions (HxWxD)

mm

305 x 923 x 250

305 x 923 x 250

305 x 1100 x 238

305 x 1100 x 238

Weight – Indoor

kg

12.5

13

15.5

15.5

Outdoor – Dimensions (HxWxD)

mm

880 x 840 x 330

880 x 840 x 330

880 x 840 x 330

880 x 840 x 330

Weight – Outdoor

kg

53

53

55

55

Electrical Supply

230 volt/Single Phase / 50 Hertz – Outdoor Power Supply

Breaker Size

A

16

16

20

20

Piping – max length

m

30

30

30

30

max height

m

15

15

15

15

Guaranteed Operating Range

ºC

-10 ~ 46

-10 ~ 46

-10 ~ 46

-10 ~ 46

-15~ 24

-15 ~ 24

-15 ~ 24

-15 ~ 24

Accessories

Remote Control

SG15D (Part No. E12 R80 426)

SG15E (Part No. E12 R86 426)

*SH = Super High

Reviews

There are no reviews yet.

Only logged in customers who have purchased this product may leave a review.