Immersion Temperature Transmitter, Nylon Fitting

Part Number: BA/

Immersion Temperature Sensors with T1K Transmitter are available in 2”, 4” and 8” or custom probe lengths. The sensor is potted inside a 1/4” stainless steel probe with a thermally conductive compound. Immersion Units come with a 2×4” steel J-Box or the new BAPI-Box Crossover enclosure with green power LED.

Special Document

BAPI has available and verified the following temperature ranges for the T1K Temperature Transmitter. Ranges are sorted by span, low temperature first. Fahrenheit ranges are on the left and Celsius ranges on the right. Any …

Overview
In some applications with non-BAPI products, there are thermal transfer concerns due to a large gap between the interior wall of the thermowell and the outside of the immersion temperature sensor probe that is inserted …

BAPI's certification form matches the requirements of the National Institute of Standards and Technology data reporting standard.
The column labeled "Reference" is the actual test condition as measured by the Calibration Standards referenced in the inventory …

The IEC (International Electrotechnical Commision) is an international committee that developes and publishes its recommendations for standardising international wiring devices and products. Ingress Protection (IP) is the grades of protection against external solids contacting the …

The National Electrical Manufacturers Association (NEMA) Standards Publication No. 250 defines 13 different enclosure “types” for non-hazardous locations. These NEMA types define the applications and the environmental conditions that enclosures are designed to protect against …

Building Automation Products, Inc. (BAPI), a leading manufacturer of HVAC/R control system sensors and peripherals, is committed to environmentally responsible manufacturing practices. BAPI has been working since early 2005 to remove environmentally harmful materials from …

Shown below is an NIST Traceable Certificate of Calibration for a recent T1K Temperature Transmitter order.
Each transmitter is calibrated for its range using precision resistors. A Class A RTD is given a unique serial number …

All of BAPI’s indoor sensor bodies and transmitter enclosures are made from UL94, V-0 rated plastics.
UL94 serves as a preliminary indication of a plastic’s acceptability for use as part of a device or appliance with …

Thermowells are hidden in pipes and are rarely seen. How dimensions are established for the wells and the immersion probes that fit into them are not readily apparent. This application note exposes how the dimensions …

Current Loop History
Many of us still remember the days of pneumatic control; some of us still use pneumatic control systems. Ratio controllers, PID controllers, temperature sensors and actuators are powered by compressed air. Three to …

NIST (National Institute of Standards and Technology) Traceability can be defined as an unbroken record of documentation (“documentation traceability”) for the measurement device authenticity and an unbroken chain of measurements (with documentation with associated uncertainties) …

This document describes five of the most basic 4 to 20 mA current loop configurations:
1. A two-wire transmitter with external power and an external resistor
2. A two-wire transmitter with controller power and a 4 to …