£108.99 (£130.79 inc VAT)

Indoor PIR Movement Sensor, 360 degree[5753L] - Stock: 10

The C-Bus 360 Degree Indoor PIR Movement Sensor is a C-Bus input unit used to detect movement by sensing the natural thermal radiation emitted from any moving body. When movement is detected, the unit issues commands over the C-Bus network to control C-Bus output devices. The sensor is suitable for controlling lighting in homes, apartments, offices, corridors, conference rooms etc.

The sensor incorporates the C-Bus 'Learn Mode' feature. Learn mode allows the units to be
programmed without the need for a PC to be connected to the system. Alternatively, the units can be programmed via a PC using the installation software.

The C-Bus 360 Degree Indoor PIR Movement Sensor has a 360° field of view and minimum detection coverage of 5 metres when mounted 2.4 metres above the floor, noting that the coverage is slightly elliptical.

The unit is small and unobtrusive and is designed to be flush mounted. It is ideally suited for mounting to the ceiling or to suspend from ceiling tiles. The visible lens is approximately the size of a low voltage dichroic halogen lamp.

The sensor is capable of controlling up to four C-Bus 'Group Addresses', with each being controlled for a different period if required.

An added feature is that each sensor includes an ambient light level sensor (Sunset Switch) feature,
which automatically turns lights 'on' when the ambient light level falls below the threshold level (at sunset), and then turns the lights 'off' again at sunrise. Alternatively, the lights can be programmed to
automatically turn 'off' at a set time after sunset. A light emitting diode (LED) on the sensor head can
be programmed to turn on when movement is detected. This enables easy positioning and
commissioning of the sensor.

The unit initiates a regular status report, which compares the status of all input and output units within the same C-Bus 'Application Address'. If a state disagreement exists between the output units and the input units, the C-Bus Indoor PIR Movement Sensor will change its internal state to suit the output.

Flush mount design ideal for mounting to the ceiling or ceiling tiles

Ideally suited for mounting in the centre of cellular offices

Discrete appearance ™ only 65mm diameter face is visible.

Low profile ™ only 8mm protrusion from the ceiling.

50mm circular cut-out hole

240V AC connection is not required

C-Bus Learn Enabled

360° detection pattern

Minimum 5m detection coverage when mounted 2.4m above the floor

Capable of controlling up to four C-Bus 'Group Addresses'

An LED on the sensor can be programmed to turn on when movement is detected

Light sensitivity is set via an adjustment screw located on the sensor unit

Dual element detectors minimise false triggering

Refer to 5751L Installation Instruction for location and mounting details

Designed to meet Australian and European standards for EMC Compliance and Safety