Fire Department requirements are derived from information specified in the California Fire Code and California City Municipal code. All items are subject to Fire Department approval. Additional items may apply.

o Occupancy Classification– A1 A2 A3 A4 A5 B E F H I M R S U

o Change of use or occupancy– Based on fire official approval, change shall conform to fire code and building code for specified group.

o Permit(s)– Permits required as defined by fire official shall be obtained and appropriate fees paid prior to issuance.

o Key Box– 3200 Series or approved Knox Box shall be obtained by property owner or occupant and maintained. When applicable, the Knox Box shall be mounted where the bottom of the box is 5’ from the ground and located adjacent to the main entry door.

o NFPA 704 Diamond– When required, 704 Placards shall be placed at entrances to places were hazardous materials are dispensed, stored or used.

o Water Supply– A minimum fire flow of 1,500 gallons per minute is required for commercial structures. Fire flow requirements may be reduced by fire official if approved automatic sprinkler system is installed.

o Fire Hydrant(s)– Hydrants shall be located at pre-determined locations as identified by the fire official. Maximum distance to hydrant shall not exceed 250’.

o Fire Protection Extinguishers- Fire Extinguisher(s) with a minimum rating of 2A 10B:C shall be provided per each 3000 square foot area designated as ordinary combustible. Maximum travel dispatch to the extinguisher shall not exceed 75’. Extinguisher shall be at least 4” and no more than 5’ from floor. Extinguisher shall be located with preference near main exit.