53VML (30MV) Ball Float Vent Valves

The OPW 53VML Ball Float Vent Valves protrude into underground storage tanks from OPW 233 Series Extractor Fittings at the Stage I vapor return riser pipe or tank vent line. During a product delivery, as the tank level rises, a counterweight stainless steel ball seats on the valve body and restricts flow of vapors back to the transport truck. As the vapors become compressed in the tank (ullage), product flow into the tank is severely restricted. The 53VML Series Ball Float meets the U.S. EPA 90% requirement for product flow restriction into underground storage tanks. The 53VML-0060 and 53VML-0065 are designed as “back-up” overfill protection for overfill prevention valves, and to minimize product mixing with underground manifold vent lines.

The OPW 89 Extractor Wrench is designed to install or remove OPW 53VML and 30MV Ball Float Vent Valves or OPW 233VP and 233VMP Test Plugs in OPW 233, 233V, and 233VM Extractor Fittings. The 89 is also designed to work with the cage assemblies on the 233E Suction Tube Extractor Fitting and 88E Extractable Angle Check Valve in suction system applications. The 89 wrench consists of a 4 foot section of pipe welded to a “T” handle with either 11/2" or 2" hook section. Both the 11/2" and 2" hook sections mate current OPW ball floats and extractable cages; the 11/2" model is designed for some discontinued OPW products.

Dimensions

Ordering Specifications - 30MV-KIT

Convert your 53VML into the 30MV Ball Float

The 30MV Series ball float has the same function as the 53VML, but allows for higher storage capacity in larger volume tanks. The 30MV meets the U.S. EPA 30-minute warning requirement for product flow restriction in the underground storage tank. Using the Tank Ullage calculation (located below), convert your 53VML to the desired length by adding the 30MV-KIT.

Product #

Description

30MV-KIT

O-Ring 1/16" Brass orifice insert

Specifying the Proper Length 53VML & 30MV Series Ball Float

Step 1:

Determine Dimension “X”: Consult the tank chart (provided by the tank manufacturer) to determine the distance that corresponds to 10% of the total tank capacity for 53VML or 308 gallons for 30MV.

Step 2:

Determine Dimension “Y": Measure the dimension from the inside top of the tank to the top of the 4" threaded tank "bung" fitting.

Step 3:

Add measurements “X" and "Y". Then subtract 1/4" and round up to the nearest length ball float.

Tank Ullage Calculator

30 minutes x 5GPM = 150 gallons

Ullage compression rate* is 27% after the ball seats

150 gallons ÷ .73 (1– ullage compression rate) = 205.48 gallons

205.48 x 1.5 (OPW recommended safety factor) = 308.22 gallons

Approximately 308 gallons required ullage

*Ullage compression rate will vary with head pressure.

Notes & Warnings

Notes & Warnings

WARNING: OPW Overfill Warning Systems should only be used on submerged pumping systems, not suction pump systems. For special applications, contact OPW Fueling Components. OPW Overfill Warning Systems should only be used on gravity drop systems. DO NOT use where Pump-Off Unloading or coax fills are used.

IMPORTANT: Installing the incorrect length OPW 53VML or 30MV Ball Float Vent Valve for your specific application may result in delivery flow restriction at levels exceeding requirements established by the U.S. EPA. Always consult the appropriate tank charts and determine the specifics of your tank installation to determine the appropriate length OPW 53VML or 30MV. The illustration and instructions are intended to serve as a guide in this determination.