Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

We did look at the crank journal, with the idea of installing connecting rod cap and cutting off the connecting arm and sealing the oil port. Running the compressor on 5 cylinders. The lead tech said...

oil pressure is low and will not load the compressor. i have a minnimal amount of time to have this compressor off line. We are rebuilding the pump replacing the regulator and the main bearing. this...

there are 2 refrigerant circuits that each contain 2 15 ton compressors. the short cycling is occuring between 30 and 45 tons of cooling or the second and third stages. because of that i am having a...

tech. incoming gas pressure is at 5" w.c. 24 vac at the controller. literature for the furnace or the board does not give any indication what input would cause this failure. the board will give you a...