Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Call your installer back and thoroughly explain the problem you are having. Go higher up the food chain if the person you're dealing with does not bring you a solution.

Offhand it sounds like a configuration/programming issue within the thermostat. Not hard to remedy if the control wiring was done correctly.

Thanks for your response..
I have placed a call to them and am waiting for a response. I am at the top of the food chain already as it's a father/son owned company.

I am just trying to get some confirmation as I am not sure they have installed many systems of this configuration. Hopefully they will do the "head smack, oh ya" thing.

I have suspected a programming/config issue all along, but I hate to drag them out when I am unable to duplicate the issue for them. I used to be in the car repair business, and know unless I can duplicate the weather dependant conditions, a visit from them will prove nothing.