Straight pattern model with secured, infinitely adjustable fine presetting controllable at any time. Optical display of the pesetting depending on the position of the handwheel. Valve body, bonnet and other parts coming into contact with the fluid made of brass resistant to dezincification (DZR) or stainless steel. Maintenance-free stem seal due to double O-ring. All functioning components in one plane.

Suitable for the connection of thermostats (e.g. “Uni XH”), actuators (e.g. electromotive actuators “Uni EIB/LON”) and a differential pressure regulator bonnet (connection thread M 30 x 1.5) without draining the system (conversion of DN 15, DN 20 and DN 25 with the help of the “Demo-Bloc”).

Insulation for temperatures up to 110 °C supplied with each valve (as packaging). A separate insulation for temperatures up to 120 °C is available as accessory. When equipped with additional polystyrol shells, also suitable for cooling systems.

Both ports male thread with colra nut.Installation is possible in either the supply or the return pipe.

Dimensions of article

Length

Width

Height

Weight

198 mm

110 mm

150 mm

1,93 kg

Packing units

Type

Qty.

Length

Width

Height

Weight

Carton

1

200 mm

120 mm

160 mm

2,06 kg

Carton

5

370 mm

255 mm

395 mm

10,85 kg

We are sorry...

but the CAD viewer which is normally displayed here is not compatible with your browser. We are currently working on a solution supporting all standard browsers. We should like to ask you to use Internet explorer until a new CAD viewer will be available.