Pelton turbine is widely used in water head of 10m- 1000m that is suitable for hydropower station with high head but small water flow&period; The runner works by being heavily pushing force with jet flow that is from injection nozzle through high-pressure pipe&period; Pelton turbine is regarded as compact structure&comma; stable operation and easy handling&period;

Technical parameters&colon;

1 Turbine type Pelton Turbine

2 Applicable water head 100~1000m

3 Discharge&colon; 0&period;1m3&sol;s-3&period;6m3&sol;s

4 Max efficiency 91&percnt;

Model

Diameter of Runner &lpar;cm&rpar;

Water Head&lpar;m&rpar;

Discharge&lpar;m3&sol;s&rpar;

Output&lpar;kw&rpar;

Maximum Model Efficiency&lpar;&percnt;&rpar;

XJ02 series

32 40 50

32-175

0&period;1-0&period;72

25-957

81&period;96

XJATseries

40 50 53 55 60 63

50-240

0&period;2-1&period;325

81-2650

85

XJE series

40 42 50 55 60 63 70

50-350

0&period;071-0&period;976

29-2852

84

CJ22 series

45 55 70 80 90 110 125

63-400

0&period;048-2&period;75

25-8848

87&period;1

CJA237 series

70 80 90 100 110 125 140 160

98-600

0&period;12-3&period;2

100-16950

90

CJA475 series

70 80 90 100 110125 140 160 180

100-750

0&period;12-3&period;6

100-23500

90&period;6

1&period; Before making quotation&comma; please send us the following basic parameters&colon;

A&period; Flow------ m³&sol;s

B &period;Water head----- m

C &period;Installed capacity--- KW

D&period; Frequency---- 50HZ or 60HZ

E&period; Length and diameter of the penstock

F&period; Voltage of the generator

G&period; Voltage of the transmission line&lpar;if the setup transformer is supplied by us &rpar;&period;