33 KV, 200 A Rotating Isolator

33 KV, 200 A Rotating Isolator

Product Code : 16

Product Description

Rotating Isolator

Since our establishment in 1996, we have been specialized in offering Rotating Isolator. By using quality-tested basic materials and state-of-art techniques, our ingenious professionals manufacture this isolator in conformance with set international quality standards. The offered isolator is used for the isolation of transformers and overhead lines from the distribution transmission network. Extensively used in commercial and industrial sectors, this Rotating Isolator is made available for clients at the most reasonable prices.

Features:

Easy to install

Low contact resistance

Robust construction

Easy to operate

Application The triple pole double break isolator is rotating type gang operated and designed for outdoor application. The isolator is designed to suit overhead systems used in high density urban situations or high load centers, where the load is much higher and the need of improved and steady quality power supply is much greater. Main function of this product is to isolate the Transformer, Overhead lines, System or Cables from distribution network. Construction The rotating isolator has triple pole construction and shall be suitable for Horizontal upright mounting. Each pole consist of galvanized steel base, solid core or post type insulators of reputed make, EC grade copper fix and moving contacts. G.I. coupling pipe of adequate length for rotating operation, required length of G.I. pipe for operation from ground level and operating handle is specially design for smooth operation. Adjustable pins are provided to limit over travel of moving post. Ferrous parts are hotdip galvanized and non-ferrous parts are heavily tinned to withstand weather.

Features

Low Contact resistance through the life of switch.

Sturdy design of current carrying parts.

Smooth and trouble free operation.

Operation The handle, fabricated from channel, lever and turned pipe gripper, are designed for smooth, sturdy and trouble free operation. The handle is provided with locking arrangement in both ON and OFF position. Installation

It is designed to be mounted in horizontal upright position on 2 nos. channels based on structure. Install three phases of isolator on structure parallel to each other, couple the pole with coupling pipe, link it with operating lever, align all the elements in ON position, fix the operating pipe vertically and clamp the handle in ON position. Make it ON and OFF several times.