1 System is over water supply
To control the water supply by adjusting
the valve or change to the water pump with lower power.

2 Non-evenness of the water spreading
on the paper pad
To check the installation
is under the correct way or not. Adjust valve to control
the water supply; Change the water pump with more
power or water pipe with high caliber. Clean the pool,
pump entrance, filter and pipe etc. in time. Eliminate
the dirt inside the water recycling system.

3 leaking treatment
To check whether water is
over supply, pad is damaged, dilapidated on the edge
or leaking at the connection. Use silicon glue to
plug after water supply stops.

4 Pad cleaning
Elimination of the scale and
alga on pad's surface: Use the soft brush to remove
up and down after the pad's completely drying out.
Do not remove horizontally. (Can brush a small part
to verify if the pad stand or not). Then only switch
on the water supply system to wash the scale and alga
on pad's surface. (Do not use steam or high pressure
water)

Maintenance of the SAT

1 Daily maintenance
Turn off the exhaust fans
after 30min of the pump stopped to make sure the complete
dry of the pad. To check if all empty in the bottom
frame after system stopped to avoid the pad bottom
is dipped in the water all the time.

2 Water quality control
The pool must be sealed with
a cover. Keep the water resource clean. The ph value
should be between 6 ¨C 9 and the electric conductance
should be less than 1000 micro-ohm. Clean the pool
and water recycling system regularly to assure the
cleanness of water supply system. (usually once a
week). Maintain the good quality of the water supply.
To prevent alga and other microbe from spreading the
SAT, two measures can be adopted: put in 3-5ppm
Chlorine or Bromine for short time treatment or 1ppm
for continuous processing.

3 Rats prevention
Can install rats defense or
use rats killing spray at the bottom of the pad when
not in use