NIGHTFALL NF1 Series Cylinder LED Emergency Lighting Unit

Price: $267.00

Code: ESW-NF1

SKU: ESW-NF1

LED Wattage:

Mounting:

Options:

Quantity:

NIGHTFALL NF1 Series Cylinder LED Emergency Lighting Unit

Product Overview
Designed to blend with any environment, this surface down light
provides an attractive, architectural, cylinder style to your emergency
lighting needs. The high performance LEDs make this an ideal, yet
decorative, choice for any indoor installation in long corridors, hotels,
and shopping centers.

Features

50-55 foot on center spacing

Architectural, cylinder style design, surface mount downlight

10 or 15 watt Luxeon LED options

Pure white light output at 5600K

Optical LED lens coupled with a prismatic polycarbonate lens for optimal light output and protection

Mounts with standard back plate to wall or ceiling, direct to J-box. Pendant mount (P6/P12) also available

Maintenance-free NiMH battery, standard

Optional PathSafe security/night lighting (SEC) allows the fixture
to be used as an emergency lighting and as security/night lighting
fixture

Illumination
Fixtures are supplied with high powered Luxeon LEDs offering 10 watts or 15
watts of light output with a pure white color temperature of 5600K. Optical
lenses on the LED module combined with the prismatic polycarbonate
lens produce an optimized elongated pattern of light throughout the path
of egress. The high-performance LEDs have an expected life over 50,000
hours with normal use. Lamps are connected in parallel � if one lamp fails, the balance of the lamps
will continue to operate.

Electrical Input
120-277 volt, 50/60Hz.

Nickel metal hydride batteries are maintenance-free with a life
expectancy of 15 years. NiMH batteries perform optimally in temperatures
ranging from 0-40 degrees C.

Emergency
The Nightfall Cylinder will operate for a minimum of 90 minutes during a loss
of power with a 24 hour minimum recharge time for the battery. The power
supply delivers a regulated current and voltage to LED lamps to optimize
lamp life. A momentary test switch and LED charge indicator are included.

Brownout Circuit
The brownout circuit monitors the flow of AC current to the unit and triggers
the emergency lighting system once a set reduction of AC power occurs.
This dip in the voltage will cause many fixtures to extinguish causing loss of
normal lighting even though a total power failure has not occurred.

Low Voltage Disconnect
When the battery's terminal voltage falls below predetermined levels, the
low-voltage circuit disconnects the emergency lighting load. The disconnect
remains in effect until normal power is restored, preventing deep battery
discharge and improving the life of the battery. The disconnect will also
automatically reconnect the load circuit once the battery voltage returns to a
normal value after charging.

Solid-State Transfer
The unit features a solid-state switching transistor which eliminates damaged
contacts or mechanical failures associated with relays. The switching circuit
is designed to detect a loss of AC power and automatically energizes the
lamps. Upon restoration of the AC voltage, the emergency lamps will switch
off and the charger will automatically recharge the battery.

Overload and Short-Circuit Protection
The solid-state overload monitoring system in the DC circuit disconnects
the lamp load from the battery should excessive wattage demands be made
and automatically resets when the overload or short-circuit is removed. This
overload current protective characteristic eliminates the need for fuses or
circuit breakers for the DC load.

Installation
This Nightfall emergency unit mounts with a standard back plate to the wall
or ceiling for traditional installations. Optional pendant mounting or mounting
direct to J-box for exposed conduit applications such as unfinished ceilings
are also available.

Damp Location Rated (Option: DR)
Damp location rating ensures the fixture is designed to operate safely in
outdoor locations that are protected from the direct elements. Damp location
rated fixtures may be installed indoors. Products with damp location ratings
are not designed to withstand constant or significant moisture or direct
contact with water or steam.

Made in the USA
Made in the U.S.A. and is in full compliance with the American Recovery
and Reinvestment Act of 2009 (ARRA) requirements and Buy American
provisions.

The purpose of this option is to provide visual signaling in response to a
possible fault. If a failure is detected, visual status will occur immediately via
the CHARGER LED and/or the BATTERY FAULT LED. The LEDs will stay
illuminated until the fault is corrected.

The Guardian circuit also monitors the transfer circuit and performs
automatic code compliant testing. The Guardian circuit will perform a 30
second discharge and self-test every 28-30 days. A 90 minute discharge and
self-test is performed every 6 months.

Pathsafe Security Lighting/Night Light (Option: SEC)
The PathSafe option allows the fixture to be used both as an emergency
lighting fixture and security / night lighting fixture. Models with battery backup
and the PathSafe option will operate each LED at 2 watts (SEC option)
offering 50% output when in security lighting mode when connected to the
active building AC supply and wired according to the installation instructions.
The security lighting circuit is independent of emergency lighting and may
be switched manually by exterior photocell (supplied by others) or other
automatic means.