Replacement solenoid value for newer Bryant Carrier Humidifiers. Valve includes a new inline strainer (pre-inserted in inlet side of valve), and a compression nut & washer for the inlet side only.

Solenoid Valve Replacement Instructions

For power units unplug electrical cord. For bypass units turn off power to furnace. Also turn the humidistat off.

Shut off water supply at the saddle valve

Disconnect inlet and outlet water compression nuts. Double wrench. Note, some water may drip on floor. Remove the orifice (which controls the water flow) from the plastic or copper tube and make sure there is no obstruction. If blocked clean or replace.

Remove the wire nuts from the water solenoid valve wire connections. Set aside.

Remove screws that secure valve to unit.

Attach new valve with screws. Do not over-torque screws into plastic housing.

Replacement solenoid value for newer Bryant Carrier Humidifiers. Valve includes a new inline strainer (pre-inserted in inlet side of valve), and a compression nut & washer for the inlet side only.

Solenoid Valve Replacement Instructions

For power units unplug electrical cord. For bypass units turn off power to furnace. Also turn the humidistat off.

Shut off water supply at the saddle valve

Disconnect inlet and outlet water compression nuts. Double wrench. Note, some water may drip on floor. Remove the orifice (which controls the water flow) from the plastic or copper tube and make sure there is no obstruction. If blocked clean or replace.

Remove the wire nuts from the water solenoid valve wire connections. Set aside.

Remove screws that secure valve to unit.

Attach new valve with screws. Do not over-torque screws into plastic housing.