HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

He wants the biggest and the best for everything---Just the way he is.

His theory is that a renter just wants to be cold under the worst 97 degree ambient------tired of renters complaining CAC not working cold enough in July and August. And that a renter could give a crap about proper sized systems and proper humidity control.

He just had changed out a 3.5 ton straight AC with oil furnace Rheem unit for a 5 ton Trane heat pump.

5 tons of AC/heat pump?

For a house that might be at most 1600 sq ft?

(although with a lot of heat loss through hurricane type windows all over and a large Floriduh room,--- almost solid glass area, Hurricane type windows on three sides, facing south---built in the mid 50's --that room was really never meant to be air conditioned. )---

-(Replaced a 3.5 ton unit whiched seemed to work fine, except for the Floriduh room.--which never cooled well--what would you expect?, was never designed for AC, just air flow off a lake for cooling effect was its original design)

He went for that 5 ton Trane with an seer of 18 because of the price ---left over from last year or something like that.

Now I tried to talk him out of so seriously oversizing a unit. The guy who sold that 18 seer 5 ton unit tried to talk him out of buying it.

He hasn't turned it on yet for the Florida summer---still pretty cool here.

What would you all expect to happen when he does turn that monster on?

And does an 18 seer 5 ton Trane have a good reputation? I know that the higher the seer the more likely for problems (bugs) to develop especially with a latest design. Were they just unloading 5 ton 18 seer Trane unit at a good price because there were problems?

Any input appreciated on this.

(I know that this coming summer I will get hit with all kinds of questions about the unit from my brother, if it does not perform well.---which I doubt it will)

The one nice thing about this all is that I got his old, relatively new 3 and 1/2 ton unit for free. Which will work very well in my house.

First off he was sold a bill of good suggesting he bought an 18 SEER Trane Heat Pump, there is no such beast. Especially at 5 tons. They got a 2.5 or 3 ton that can get to 17.9. The 19i on the unit is intentionally misleading. At best he's getting 15.9 SEER or 15.25 and HSPF's in the mid 8's. His sound rating is almost 79 dB. (80dB is equal to that of a Garbage disposal or freight train(at 15 meters) I'd say he bought a label.

Anyway back to your question....being potentially OK although not right. If he can move the air he might be somewhat ok since he is dealing with a 2 stage unit, just lock it out from going into second stage in cooling. Kind of an expensive single stager but hey he got one big ol unit to show off,

Hard to tell my older brother anything. Guess he will have to learn on his own.
----------------------------------------------

I also wonder about the sound level of that moose when he finally starts running it.

79 db's eh? As loud as a garbage disposal eh?------assume of course you are talking about the condensing unit. But I wonder about the sound level of the blower too.

Massive blower unit is now inside in a hallway close to 3 bedrooms. (the old furnace blower and AC evap was out in the garage----couldn't even hear it run unless you listened very hard)

The massive Trane condensing unit now sits right outside the largest bedroom. (Old 3 and 1/2 ton condensing unit sat on the other side of the garage way away from living space---never heard it run either from inside the house.)

----By the way I did mean heat gain, not heat loss, in that first post----

Over Sized Beast

Did your brother happen to mention if they added any duct work or reworked the return?

I see trouble brewing in the near future when that thing cycles off in heat mode if they didn't and a short life in cooling mode...

Just went thru the same thing here with a customer who in Dec had someone out to check heatpump 2.5 Goettl (Over/Under) diagnosis was it wasn't moving enough air because it was to small. Jack Ass installed a 4 ton system on undersized ducting. HO has complained since Dec 2004 no heat, just blowing cool air...

HO stuck with 4 ton system, added 2-10" trunk replaced all the duct work all 6" now equal 8" and so on and the 12" RA is now a 18" , more than they need. Thank goodness for dry summers here in Calfiornia, unlike Florida...

Never have had much luck telling my older brother anything at all. Although I do try.

I always told him the best way to go was to stick with the original set up---proper sized AC unit (3 and 1/2 ton) with gun fired oil furnace in the garage and condensing unit outside on the other side of the garage, where you couldn't hear it run.

And if he really wanted to be able to cool that all window Florida room to put a 15 to 18000 BTU wall unit in there to be used as necessary.

He had 2 problems with that.

1-----He hates wall units ---something about holes in walls he doesn't like (don't know why--I think they are excellent in their place)

2----He wanted the garage to be a true 2 car garage--the old original air handler and furnace in the garage made it impossible for a second car to fit in there.

He will just have to find out for himself. Spent $11,000 on that monster too.

I asked him if they had done anything to improve the ductwork. He said he thought so. For $11,000 I hope so.

It is very helpful to find out that one good way to reduce the oversize problem is to disable one of the compressors.

The sound level, at least from the massive Trane condensing unit sitting right outside a bedroom, could be corrected by relocating it back to the other side of the garage, where the old condensing unit used to be. Would mean a line set of maybe 50-60 feet. Any problems with that besides adding a little refrigerant?

I think that the sound level of the now indoor blower, right next to all the bedrooms will end up being troublesome--------but maybe a little extra sound insulation will help enough.

You all might wonder about some of this. The house was originally built in about 1950---with a gun fired oil floor furnace in the hallway---no AC at all.

(That cubby hole in the hallway where the old original gun fired oil furnace used to be is now where the new Trane air handler is.)

The original floor furnace in the hallway was modified over the years for a gun fired oil furnace in the garage, and an added Chrysler central air. All of which have worked quite well for the past 40 years or so. (Only problem was that you no longer had a useable 2 car garage.)----

--and an extra problem--the Florida room, rather large with 3 sides facing south and mostly glass area would never cool with the old 3 and 1/2 tonner)--- That room is almost impossible to cool--too much heat gain. Why I always suggested to my brother a simple wall unit of maybe 15 to 18,000 BTU's to cool that room if desired and only when needed.

(Actually it is a great room to just open the damned windows and enjoy the off-lake breeze-----that was what it was always intended to do)

Interesting advantage is that, unusual for Florida nowadays with now prevalent slab construction------there are 2 duct systems. --the original return for the old floor furnace, underneath and in the crawl space under the house.------and an added duct discharge system in the attic. Added ductwork in the attic done in the mid 60's when the original Chrysler Air Temp unit was installed.

The condensing unit has been replaced at least a couple of times and the evap replaced once with an Addison. All 3 and 1/2 ton.--up until now.

So there is an awful bunch of ductwork. Much more ductwork than you usually see in modern day homes in Florida.

And whoever did the installation just recently might actually have improved the ductwork generally. For an $11,000 total cost for this new 5 ton Trane heat pump, I would think so. Of course you never know.

I live over 100 miles away from my brother and don't get over to Orlando all that much. ------but every time I do go over there--I always get all kinds of questions about anything and everything mechanical (my brother is a complete ding a ling when it comes to mechanical stuff)

I know I am going to get hit with all kinds of questions about this "poor working" and very noisy Trane monster he decided to have installed next time I visit.

So all input appreciated.

I do like my brother, even with all his stubborness. And I try to help him out when I can.

the real shame here is next summer when it is arround 80 or 90 degrees and the people are sitting in a cold clammy damp house and still sweating amd the tech who knows what he is doing has to take the heat after he tells them its to big and there is nothing he can do about it
poor guy
so much for sizing a unit just take a guess from the curb