Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

My years may be off but did this year chiller have the black box guard pak controller??? I remember a SB that came out after I found a guard pak nusance tripping on compressor contactor pull in, creating an electrical inrush that tripped the guard pak. Ended up being a guard pak design flaw and had to replace all guard paks of that vintage. Same situation I got a hotel, lawn chair, 20 meters and 100 tattletales and watched this chiller for 3 days straight before I finally caught it in action. It was tripping but no safeties were telling it to the second the compressor contactor was engaged.