Puron is Carrier’s unique refrigerant designed to help protect the environment. Puron is an HFC refrigerant which does not contain chlorine that can harm the ozone layer. The most important advantage of Puron refrigerant is that it has not been banned in future air conditioning systems as the traditional refrigerant R-22 has been. Puron refrigerant is in service in millions of systems proving highly reliable, environmentally sound performance.Easy InstallationFactory-assembled package is a compact, fully self-contained, combination gas heating/electric cooling unit that is prewired, pre-piped, and pre-charged for minimum installation expense. These units are available in a variety of standard and optional heating/ cooling size combinations with voltage options to meet residential and light commercial requirements. Units are lightweight and install easily on a rooftop or at ground level. The high tech composite base eliminates rust problems associated with ground level applications.Innovative Unit Base DesignOn the inside a high-tech composite material will not rust and incorporates a sloped drain pan which improves drainage and helps inhibit mold, algae and bacterial growth. On the outside metal baserails provide added stability as well as easier handling and rigging.Convertible duct configurationUnit is designed for use in either downflow or horizontal applications. Each unit is converted from horizontal to downflow and includes two horizontal duct covers. Downflow operation is provided in the field to allow vertical ductwork connections. The basepan seals on the bottom openings to ensure a positive seal in the vertical airflow mode.Efficient operation High-efficiency design offers SEER(Seasonal Energy Efficiency Ratios) of 14.0, 11.5 EER, and AFUE (Annual Fuel Utilization Efficiency) ratings up to 81.0%.Energy-saving, direct spark ignition saves gas by operating only when the room thermostat calls for heating. Standard units are furnished with natural gas controls. A low-cost field installed kit for propane conversion is available for all units.Low NOx units are designed for California installations. These models meet the California maximum oxides of nitrogen (NOx) emissions requirement of 40 nanograms/joule or less as shipped from the factory and MUST be installed in California Air Quality Management Districts and wherever a Low NOx rule exists.Durable, dependable componentsMonoport inshot burners produce precise air-to-gas mixture,which provides for clean and efficient combustion. The large monoport on the inshot (or injection type) burners seldom, if ever, requires cleaning. All gas furnace components are accessible in one compartment.Turbo-tubular™heat exchangers are constructed of aluminized steel for corrosion resistance and optimum heat transfer for improved efficiency. The tubular design permits hot gases to make multiple passes across the path of the supply air. In addition, dimples located on the heat exchanger walls force the hot gases to stay in close contact with the walls, improving heat transfer.ECM Motor is standard on all models.Direct-drive PSC (Permanent Split Capacitor) condenser-fan motors are designed to help reduce energy consumption and provide for cooing operation down to 40°F (4.4°C) outdoor temperature. Motormaster® II low ambient kit is available as a field-installed accessory.Thermostat controlsTime Guard® II anti-short cycle protection circuitry. If a non-corporate thermostat without anti-short cycle protection is used the Time Guard II field-installed anti-short cycle kit is recommended.Refrigerant system is designed to provide dependability. Liquid filter driers are used to promote clean, unrestricted operation. Each unit leaves the factory with a full refrigerant charge. Refrigerant service connections make checking operating pressures easier.High Pressure Switch provides added reliability for the compressor.Indoor and Outdoor coils are computer-designed for optimum heat transfer and efficiency. The indoor coil is fabricated from copper tube and aluminum fins and is located inside the unit for protection against damage. The outdoor coil is internally mounted on the top tier of the unit.Low sound ratings ensure a quiet indoor and outdoor environment with sound ratings as low as 73dBA.Easy to service cabinets provide easy 3-panel accessibility to serviceable components during maintenance and installation. The basepan with integrated drain pan provides easy ground level installation with mounting pad. A nesting feature ensures a positive basepan to roof curb seal when the unit is roof mounted. A convenient 3/4-in. (19.05 mm) wide perimeter flange makes frame mounting on a rooftop easy.Standard horizontal metal duct covers with insulation come with the unit and cover the horizontal duct openings. These can be left in place if the units are converted to downflow.Integrated Gas Control (IGC) board provides safe and efficient control of heating and simplifies trouble-shooting through its built-in diagnostic function.Cabinets are constructed of heavyduty, phosphated, zinc-coated prepainted steel capable of withstanding 500 hours in salt spray. Interior surfaces of the evaporator/heat exchanger compartment are insulated with cleanable semi-rigid insulation board, which keeps the conditioned air from being affected by the outdoor ambient temperature and provides improved indoor air quality. (Conforms to American Society of Heating, Refrigeration and Air Conditioning Engineers 62.2.) The sloped drain pan minimizes standing water in the drain. An external drain is provided.

Documentation

Specifications

Weight

349 Pound (lb.)

Width

32.625 Inches (in)

Height

51.75 Inches (in)

Country of Origin

MEX

UPC or Barcode

1P48VL-C360903-TP

Hazardous Material

No

EPA Cert Required

No

Length

48.1875 Inches (in)

AFUE

81%

Air Flow

Convertible

Blower Motor HP

3/4 HP

Blower Motor RPM

1000

Brand

Carrier

BTU Input

90000

BTU Output

73000

CFM

1150

Color

Gray

Compressor

(1) Scroll

Condenser Motor HP

1/5 HP

Condenser Motor Type

ECM

Cooling Capacity

34800

Cycle/Hertz

60

Drive Type

Direct

EER

12

Equipment Type

Gas Electric

Heating Capacity

73000

Ignition Type

Direct Spark

ISO Code

MX

Maximum Fuse Size

40

Minimum Circuit Amps

27.4

Motor Type

ECM

Number of Fan Blades

1

Phase

Single

Product Family

48VL-C

Refrigerant

R-410a

SEER

14

Sound Level (dBA)

74

Stage

Single

Tier

Comfort

Tonnage

3

UL Listed

Yes

UL Recognized

Yes

Voltage

208-230 VAC

Equipment Part List

Loading...

Customer Service

We care what an HVAC distributor helps you do. Over 1600 people in 150+ locations are working to support you.