Get the latest news, updates and offers
from This Old House to your inbox

Well I have done everything I know to do I have a very high electric bill its 833.00 just electric alone the bill states I have used over 7000 kw this month . This has been a problem for a couple of years and I have replaced everything that uses electric I have just had a new heating and air unit installed last year with a heat pump. Its a goodman unit with 3 20,000 watt heats in the air handler from what the guy told me I should not have a bill over 180.00 a month ,,,,,,,,,,,I have checked everything I know to check and have had 3 electricians out and we cant find anything. any one have any Idea's ?

I find it hard to believe that 3 electricians can't find something wrong . Are they REAL ELECTRICIANS or handyman types ?
What part of the country do you live in ? How big of a house ?
What type of water heater(s) do you have ? How many people in the house ? If the new Heat/Air unit is malfunctioning , an electrician should be able to see that .
Have you contacted the power company to have your meter tested ?

Hi , Yes they are stricly electricians. I have a 50 gallon hot water heater , Me and My wife and a 3 year old live here in southern Ohio. One thing the all say is the heat does pull alot of electric... Here is what I have if I turn off the heat I get 5.3 amps on the left leg coming in to the house and 2.1 on the right leg . I turn the heat back on with just the heat pump running I get 20.1 amps on the left leg and 19.8 on the right leg. If I turn the temp up the heats kick on and the left leg goes to 78.1 amps and the right leg goes to 68.4 amps ?? This is what I just got from using a meter like the others did does this sound high ? Also its a 200 amp service coming in and the hot water heater is 240 v and the house is 1500 sf no basement 1 level 3 bedrooms 2 bath

You said that your high usage problem predates the new Heat/Air install ?

The reason I replaced the old unit was because I was getting a high bill and was told the new unit would fix it ?? Our bill in the summer runs around 240.00 . Our house has blown in insullation in the attic and walls so we have plenty there and I found a air return that was leaking and fixed it before winter hoping that fixed it but it didnt help I have checked all the ducts to make sure they work and are not open ??? Our unit turnes on about 1 to 2 times a hour if that so it dont seem to run all the time ?? I am lost and broke .

Yea I work from Home but the room I am in only has a light and a computer on and I turn off the light if its sunny outside. The thermostat is on about 70 all day long and durring the day the house warms up to about 72,,,,,,,,, Black roof and Brick I guess it helps in the winter to warm things up a bit so it keeps the unit off durring the most part of the day ?????