Typical arrangment of a generating set
consists in an engine directly coupled
to alternator.
The genset is mounted on steel sheet baseframe

Generating sets are normally equipped
with manual or automatic mains failure
control panel

Applications:

Telecommunications
& Media

Airports

Banks

Supermarket & Hypermarket

Oil & Gas

Cogeneration

Data center

Shipyard

Public Work

Pahrmaceutical Field

Hospital

Industry

Compagnia Tecnica Motori SpA
can offer a wide range of standard and special
generating sets, from 9 KVA, relaying on the most
important international partners'cooperation

Prime
power PRP

Prime power is the maximum
power available during a variable power
sequence, which may be run for an unlimited
numer of hours per year, between stated
maintenance intervals and under the stated
ambient conditions; the maintenance being
carried out as prescribed by the manufacturers.

The permissible average power output (Ppp)
during a 24 h period shall not exceed dome
percentage of the prime power to be stated
by the RIC engine manufacturer (usually
this percentage is equal to 70/80%)

The limited-time running power is the maximum
power which a generating set is capable
of delivering for up to 500 h per year of
which a maximum of 300 h is continuous running,
between stated maintenance intervals and
under the stated ambient conditions.