PRODUCT MODELS & ACCESSORIES

The floor grille shall have horizontal fixed vanes without deflection, and an 18 mm wide flat or 25 mm rounded frame, with an anodised standard finishing.

The floor grille can be used for both supply or exhaust air. The bevel angles of the outer frame shall be welded so that the joints are almost invisible. The floor grille shall be mechanically strong in order to bear external loads

The floor grill shall be detachable in order to provide access to the duct.

Special dimensions

In addition to standard sizes, other sizes can be specially ordered. The maximum size is 1500x300 mm (LxH).It is possible to have a continuous grille of modular design when the installation length is greater than 1500 mm. The maximum total length is 20 m.

ADJUSTMENT

Airflow adjustment damper OD

SERVICING

The grille can be removed for cleaning. Remove from the floor, by gently pulling the grille from the outer frame. Use a screwdriver, if necessary.Clean the components with a damp cloth. They must not be immersed in water.Push the grille back into place, so that the springs lock.

SUGGESTED SPECIFICATIONS

The floor grille shall have horizontal fixed vanes without deflection, and an 18 mm wide flat or 25 mm rounded frame, with an anodised standard finishing.

The floor grille can be used for both supply or exhaust air.The bevel angles of the outer frame shall be welded so that the joints are almost invisible.The floor grille shall be mechanically strong in order to bear external loads

The floor grill shall be detachable in order to provide access to the duct.