High capacity supply air outlet with adjustable directional blades for jet or diffused air patterns and vertical directional control

Recommended for HVAC installations which require long or short throw patterns and trajectory control

Ideally suited for accurate directional control of conditioned air within large spaces such as malls, exhibit halls, sports arenas, industrial and manufacturing facilities, atrium areas, and large office building entrances

Supplies straight 0° jet air patterns for extremely long throw requirements and diffused air patterns up to 30° spread for installations which require shorter throws and greater air diffusion patterns

Vertical direction is adjustable from 0° to ±30°

Product Features

The “IJ” is constructed from heavy aluminum extrusions for maximum strength, corrosion resistance, and dimensional stability. The drum is securely attached to the outer frame by mechanical fasteners and held in position by friction.

Comprised of cylindrical drum pivoted within a 1 1/4" outer frame gasketed on all four sides to minimize smudging

Rotatable drum has a seal on all sides to minimize air leakage

Deflection louvers or blades of the drum are individually adjustable, rear pivoted, and provide spread control at various angles from 0° to 30°

Available in four nominal heights of 6", 10", 12", and 15". Widths range from 9" to 70".

The optional opposed blade damper is gear operated & adjusted from the face by a slotted screwdriver. The use of the OBD does not limit directional control in the vertical plane nor spread adjustability. Opposed blade damper is available in standard galvanneal steel or optional aluminum.

Pole operated lever for vertical adjustment from the floor (pole not included).