Slideshare uses cookies to improve functionality and performance, and to provide you with relevant advertising. If you continue browsing the site, you agree to the use of cookies on this website. See our User Agreement and Privacy Policy.

Slideshare uses cookies to improve functionality and performance, and to provide you with relevant advertising. If you continue browsing the site, you agree to the use of cookies on this website. See our Privacy Policy and User Agreement for details.

Guide to transformer resistance testing

1.
1 / 19
2009-02-02
Matz Ohlen
Peter Werelius
A Guide to Transformer DC Resistance
Measurements
By Bruce Hembroff, CET, Manitoba Hydro
Additions and editing by Matz Ohlen and Peter Werelius, Megger
Abstract: Measuring a transformer's DC resistance from one external terminal to another can
reveal a great deal of information about the transformer. In addition to the obvious faulted winding
(i.e., an open winding or shorted turn), more subtle problems can be detected. The DC current, in
addition to flowing through the winding, must also flow through the off-load ratio adjusting switch
(RA switch), the on-load ratio adjusting switch (load tap changer or LTC), as well as numerous
welded and mechanical connections. Hence, the integrity of all these components can be verified.
Authors note: Specific aspects of safety are addressed herein; however comprehensive procedures
are not detailed. It is assumed the operator has sufficient knowledge of electrical theory and safe
working practices to use the test instrument in a safe and responsible manner.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

3.
3 / 19
2009-02-02
Matz Ohlen
Peter Werelius
A Guide to Transformer DC Resistance
Measurements
1 Introduction
Winding resistance measurements in transformers are of fundamental importance for the following
purposes:
• Calculations of the I2R component of conductor losses.
• Calculation of winding temperature at the end of a temperature test cycle.
• As a diagnostic tool for assessing possible damage in the field.
Transformers are subject to vibration. Problems or faults occur due to poor design, assembly,
handing, poor environments, overloading or poor maintenance. Measuring the resistance of the
windings assures that the connections are correct and the resistance measurements indicate that
there are no severe mismatches or opens. Many transformers have taps built into them. These taps
allow ratio to be increased or decreased by fractions of a percent. Any of the ratio changes involve
a mechanical movement of a contact from one position to another. These tap changes should also
be checked during a winding resistance test.
Regardless of the configuration, either star or delta, the measurements are normally made phase to
phase and comparisons are made to determine if the readings are comparable. If all readings are
within one percent of each other, then they are acceptable. Keep in mind that the purpose of the test
is to check for gross differences between the windings and for opens in the connections. The tests
are not made to duplicate the readings of the manufactured device which was tested in the factory
under controlled conditions and perhaps at other temperatures.
This application note is focusing on using winding resistance measurements for diagnostic
purposes.
2 Transformer DC Resistance Measurements
2.1 At Installation
Risk of damage is significant whenever a transformer is moved. This is inherent to the typical
transformer design and modes of transportation employed. Damage can also occur during
unloading and assembly. The damage will often involve a current carrying component such as the
LTC, RA switch or a connector. Damage to such components may result in a change to the DC
resistance measured through them. Hence, it is recommended that the DC resistance be measured
on all on-load and off-load taps prior to energizing.
If the transformer is new the resistance test also serves as a verification of the manufacturers work.
Installation measurements should be filed for future reference.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

4.
4 / 19
2009-02-02
Matz Ohlen
Peter Werelius
2.2 At Routine (Scheduled) Transformer Maintenance
Routine maintenance is performed to verify operating integrity and to assure reliability. Tests are
performed to detect incipient problems. What kind of problems will the resistance test detect?
2.2.1 Ratio Adjusting Switch (ratio adjusting off-load tap changer)
Contact pressure is usually obtained through the use of springs. In time, metal fatigue will result in
lower contact pressure. Oxygen and fault gases (if they exist) will attack the contact surfaces.
Additionally, mechanical damage resulting in poor contact pressure is not uncommon. (E.g. A
misaligned switch handle linkage may result in switch damage when operated). Such problems will
affect the DC resistance measured through the RA switch and may be detected.
2.2.2 Load Tap Changer
The LTC contains the majority of the contacts and connections in the transformer. It is one of few
non-static devices in the transformer and is required to transfer load current several thousand times
a year. Hence, it demands special consideration during routine maintenance.
In addition to detecting problems associated with high resistance contacts and connectors, Megger
MTO will also detect open circuits (drop-out test). LTCs transfer load current and are designed for
make-before-break, they are NOT designed to interrupt load current. An open circuit would likely
result in catastrophic failure. On installation and after maintenance it is certainly prudent to verify
operating integrity by checking for open circuits. LTC maintenance often involves considerable
disassembly and the test will provide confidence in the reassembly.
It is recommended DC resistance measurements be made on all on-load and off- load taps to detect
problems and verify operating integrity of the RA switch and LTC.
2.3 At Unscheduled Maintenance/Troubleshooting
Unscheduled maintenance generally occurs following a system event. The objectives of
unscheduled maintenance are:
• To detect damage to the transformer.
• To determine if it is safe to re-energize.
• To determine if corrective action is necessary.
• To establish priority of corrective action.
Many transformer faults or problems will cause a change in the DC resistance measured from the
bushings (shorted turns, open turns, poor joints or contacts). Hence, the information derived from
the resistance test is very useful in analyzing faults or problems complimenting information derived
from other diagnostic tests such as Frequency Response Analysis (FRA), Dielectric Frequency
Response (DFR), 50/60 Hz tan delta/power factor, turn-ratio tests and other measurements. The
winding resistance test is particularly useful in isolating the location of a fault or problem and
assessing the severity of the damage.
2.4 At Internal Transformer Inspections
Internal inspections are expensive due primarily to the cost of oil processing. When such
opportunities do present themselves the inspection should be planned and thorough. Prior to
dumping the oil, all possible diagnostic tests including the resistance test should be performed.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

5.
5 / 19
2009-02-02
Matz Ohlen
Peter Werelius
3 Test Equipment
Prior to modern digital electronic equipment, the Kelvin Bridge was used. Batteries, switches,
galvanometers, ammeters and slidewire adjustments were used to obtain resistance measurements.
Current regulators were constructed and inserted between the battery and the bridge. Input voltage
to the regulator of 12 volts dc from an automobile storage battery provided output currents variable
in steps which matched the maximum current rating of the bridge on the ranges most used on
transformers. The current regulator increased both speed and accuracy of the bridge readings. The
approximate 11 volt availability was used to speed up the initial current buildup and tapered off to
about 5 volts just before the selected current was reached and regulation started. When the
regulation began, the current was essentially constant in spite of the inductance of the windings and
fluctuation of the battery voltage or lead resistance.
The testing times have been greatly reduced using modern microprocessor based test equipment.
Direct readings are available from digital meters with automatic indications telling when a good
measurement is available. On some testers like the Megger MTO, two measurement channels are
available allowing two resistance measurements at the same time.
4 Safety Considerations
While performing winding resistance tests hazardous voltages could appear on the terminals of the
transformer under test and/or the test equipment if appropriate safety precautions are not observed.
There are two sources to consider:
• A-C induction from surrounding energized conductors, and
• The D-C test current.
4.1 A-C Induction
When a transformer is located in an A-C switch yard in close proximity to energized conductors it
is quite probable an electrostatic charge would be induced onto a floating winding. This hazard can
be eliminated by simply tying all windings to ground. However, to perform a winding resistance
test only one terminal of any winding can be tied to ground. Grounding a second terminal will short
that winding making it impossible to measure the resistance of the winding. Two grounds on the
winding under test would probably result in measuring the resistance of the ground loop. Two
grounds on a winding which is not under test will create a closed loop inductor. Because all
windings of a transformer are magnetically coupled the DC test current will continually circulate
within the closed loop inductor (the shorted winding). The instrument display would probably not
stabilize and accurate measurements would not be possible.
It does not matter which terminal is grounded as long there is only one terminal of each winding
tied to ground. When test leads are moved to subsequent phases or windings on the transformer it is
not necessary to move the ground connections. Ensure the winding is grounded prior to connecting
the current and potential test leads, and when disconnecting leads remove the ground last.
4.2 D-C Test Current
Should the test circuit become open while DC current is flowing hazardous voltages (possibly
resulting in flash over) will occur. Care must be taken to ensure the test circuit does not
accidentally become open:
• Ensure the test leads are securely attached to the winding's terminals.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

6.
6 / 19
2009-02-02
Matz Ohlen
Peter Werelius
• Do not operate any instrument control which would open the measured circuit while DC
current is flowing. Discharge the winding first.
• Do not disconnect any test leads while DC current is flowing. Ensure the winding is
discharged first.
• When terminating the test, wait until the discharge indicator goes off before removing the
current leads. When testing larger transformers it may take 30 seconds or more to
discharge the winding. If a longer time (30 seconds plus) is required to charge a winding
when the current is initiated a corresponding longer time will be required to discharge the
winding.
4.3 Summary of Safety Precautions
• Ensure all transformer windings and the test instrument chassis are grounded prior to
connecting the test leads.
• Take appropriate precautions to ensure the test circuit is not opened while DC (test) current
is flowing.
Failure to take appropriate precautions can result in hazardous potentials which could be harmful to
both personnel and test equipment. It should be noted that transformer windings are essentially
large inductors. The higher the voltage and the larger the (MVA) capacity, the higher the induction
and hence the potential hazard.
5 Selecting the Proper Current Range
Transformer manufacturers and measurement standards typically recommend that the current
output selected should not exceed about 10% of the rated winding current. This could cause
erroneous readings due to heating of the winding (e.g. A transformer rated 1500 kVA, 1 ph: the
rated current of the 33 kV winding is 45 amps; therefore the test current should not exceed 4.5 A.
Do not select more than 4 A current output on Megger MTO.)
Always choose the highest current output possible for the expected resistance value. Typical ranges
are 1-10 % of rated winding current.
6 Measurements
Wait until the display has stabilized prior to recording resistance values. Generally, readings on a
star-configured transformer should stabilize in 10-30 seconds. However, the time required for
readings to stabilize will vary based on the rating of the transformer, the winding configuration,
output voltage of the test instrument and the current output selected. On large transformers with
high inductance windings it could take a few minutes for readings to stabilize.
For large transformers with delta configuration, magnetization and getting stable readings can take
significantly longer time, sometimes as long as 30-60 minutes (see Figure 4). If the readings don't
stabilize within the maximum measurement time, check leads, connections and instrument. It may
be necessary to reduce the test current and inject current on HV and LV windings simultaneously
(recommended!), see sections 7.3 and 11, table 1.
• Record measurements as read. Do not correct for temperature. Do not calculate individual
winding values for delta connected transformers.
• Record DC test current selected.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

7.
7 / 19
2009-02-02
Matz Ohlen
Peter Werelius
• Record unit of measure (ohms or milli-ohms).
• Review test data. Investigate and explain all discrepancies.
As a general rule, the first measurement made is repeated at the end of the test. Consistent first and
last readings give credibility to all measurements. Whenever an unexpected measurement is
obtained the test method and procedure is questioned. If the measurement can be repeated the doubt
is removed. In situations where time is of concern the repeat measurement can be omitted if all
measurements are consistent.
Always check the winding schematic on the nameplate, and trace the current path(s) through the
windings. The nameplate vector representation may be misleading. Also, check the location of
grounds on the windings and ensure the grounds do not shunt the DC test current.
When a winding has both an RA switch (ratio adjusting off-load tap changer) and an LTC (load
tapchanger) take measurements as follows:
• With the LTC on neutral measure resistance on all off-load taps.
• With the RA switch on nominal/rated tap measure resistance on all on-load taps.
6.1 RA Switch Measurements
The recommended procedure for testing RA switches is as follows:
• Prior to moving the RA switch measure the resistance on the as found tap. Note: This
measurement is particularly useful when investigating problems.
• Exercise the switch by operating it a half dozen times through full range. This will remove
surface oxidization. See "Interpretation of Measurements - Confusion Factors".
• Measure and record the resistance on all off-load taps.
• Set the RA switch to the as left tap and take one final measurement to ensure good contact.
Do not move the RA switch after this final measurement has been made.
6.2 LTC Measurements
As found measurements are performed for diagnostic purposes in both routine and non-routine
situations. As left measurements are performed to verify operating integrity following work on the
LTC. The resistance test on a transformer with an LTC is time consuming; hence the value of the
as found test in each particular situation should be evaluated. Consider maintenance history and
design. Certainly, if the proposed work involves an internal inspection (main tank) or a problem is
suspected the as found test should be performed.
Prior to taking as left measurements exercise the LTC. Operating the LTC through its full range of
taps two to six times should remove the surface oxidation.
When testing windings with LTCs, use the tap-changer setup on MEGGER MTO to ensure that the
measurement value for each tap is stored separately. The current generator is on throughout the test
sequence while changing from tap to tap. With respect to the number of consecutive tests to
perform, SW operation and data storage is recommended. However MEGGER MTO can perform
TC testing stand-alone.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

8.
8 / 19
2009-02-02
Matz Ohlen
Peter Werelius
Measure the resistance for first tap. Operate TC. Measure resistance for second tap, resistance
value and current ripple for the previous tap change is stored. Operate TCS. Measure resistance for
third tap etc.
Should the LTC open the circuit and cause current interruption, Megger MTO will automatically
stop and go into its discharge cycle indicated by the discharge LED. This gives the operator a clear
indication of a possible fault within the tap changer. Such transformers should not be put back in
service.
7 Connections
7.1 General
Prior to connecting the instrument leads to the transformer all transformer windings must be
grounded. See Safety Considerations. Make connections in the following order:
1. Ensure winding terminals are not shorted together and tie to ground (the transformer tank)
one terminal only of each transformer winding (i.e. both the winding to be tested as well as
those not being tested). Note: It does not matter which terminal is grounded (a line terminal
or neutral) as long as only one terminal on each winding is grounded. There is no need to
move the ground as the test progresses to measuring subsequent phases or windings.
2. Ensure the instrument's power switch is in the off position and connect it to the mains
supply. Note: The instruments chassis is grounded through the supply cable to the station
service. (On occasion it has not been possible to stabilize the display when the instrument's
chassis ground was not connected to the same ground point as the winding (i.e., the
transformer tank) This problem is most likely to occur when the station service ground is
not bonded to the transformer tank and is easily remedied by connecting a jumper between
the instrument chassis and the transformer tank.)
3. Connect the current and potential leads to the instrument.
4. Connect the current and potential leads to the transformer winding. The potential leads
must be connected between the current leads. Do not clip the potential leads to the current
leads. Observe polarity.
5. Upon completion of the test ensure the winding is discharged before disconnecting any test
leads. Remove the ground from the transformer winding last. Caution: Do not open the test
circuit in any way (i.e. disconnecting test leads, or operating the current selector switch)
while DC current is flowing. Hazardous voltages (probably resulting in flash-over) will
occur.
7.2 Wye Windings
Refer to Figures 1-3 and Table 1. Measuring two windings simultaneously is possible if a suitable
common test current can be selected. Take resistance measurements with the indicated connections.
Connecting the test equipment as per Figure 3 is the preferred method because it allows the
operator to measure two phases simultaneously. Compared to measuring each phase individually
there is a significant time saving particularly when measuring a winding with an LTC. Alternately,
if the instrument will not energize both windings simultaneously, measure one winding at a time.
If time is of concern the last test set up, which is a repeat of the first, may be omitted if all
measurements are consistent when comparing one phase to the next or to previous tests.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

9.
9 / 19
2009-02-02
Matz Ohlen
Peter Werelius
7.3 Delta Windings
Refer to Figures 1-2 and Table 1. If possible, always inject test current to HV and LV (and measure
two windings) simultaneously. This will magnetize the core more efficiently and shorten the time
to get stable readings. If single-injection single-channel measurement is chosen, please note that the
time for stabilization on larger transformers may be long!
Take resistance measurement with the indicated connections. Again, if time is of concern the last
test set up, which is a repeat of the first, may be omitted if all measurements are consistent when
comparing one phase to the next or to previous tests.
8 Interpretation of Measurements
Measurements are evaluated by:
• Comparing to original factory measurements
• Comparing to previous field measurements
• Comparing one phase to another
The latter will usually suffice. The industry standard (factory) permits a maximum difference of 1/2
percent from the average of the three phase windings. Field readings may vary slightly more than
this due to the many variables. If all readings are within one percent of each other, then they are
acceptable.
Variation from one phase to another or inconsistent measurements can be indicative of many
different problems:
• Shorted turns
• Open turns
• Defective ratio adjusting (RA) switch or LTC
• Poor connections (brazed or mechanical)
The winding resistance test is very useful in identifying and isolating the location of suspected
problems.
8.1 Confusion Factors
Apparent problems (i.e., inconsistent measurements or variations between phases) can also be the
result of a number of factors which are not indicative of problems at all. Failure to recognize these
factors when evaluating test data can result in confusion and possibly unwarranted concern.
8.1.1 Temperature change
The DC resistance of a conductor (hence winding) will vary as its temperature changes, for copper
windings 0.39 % per degree C. This is generally not a significant consideration when comparing
one phase to another of a power transformer. Loading of power transformers is generally balanced,
hence temperatures should be very similar. However, when comparing to factory measurements or
previous field measurements small but consistent changes should be expected. In addition to
loading, temperature variations (likewise resistance variations) can be due to:
• Cooling or warming of the transformer during test. It is not uncommon for one to two
hours to pass between taking a first and last measurement when testing a large power
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

10.
10 / 19
2009-02-02
Matz Ohlen
Peter Werelius
transformer with an LTC. A transformer which has been on load can have a significant
temperature change in the first few hours off- load.
• When measuring the DC resistance of smaller transformers care should be exercised to
ensure that the test current does not cause heating in the winding. The test current should
not exceed 10 percent of the windings rating.
When using the Megger MTO PC SW, automatic re-calculation to normalized temperature can be
done and the recalculated value is reported together with the measured value.
8.1.2 Contact oxidization
The dissolved gases in transformer oil will attack the contact surfaces of the RA switch and LTC.
The problem is more prevalent in older transformers and heavily loaded transformers. Higher
resistance measurements will be noticed on taps which are not used. (Typically a load tapchanger
installed on a subtransmission system will only operate on 25-50 per cent of its taps.) This apparent
problem can be rectified by merely exercising the switch. The design of most LTC and RA switch
contacts incorporate a wiping action which will remove the surface oxidization. Hence, operating
the switch through its full range 2 to 6 times will remove the surface oxidization.
A potential transformer installed in one phase could become part of the measured circuit and affect
the measured DC resistance of that phase.
A two winding CT installed in one phase would have a similar effect. Usually donut bushing type
CTS are used in power transformers. However, on rare occasions an in-line two winding CT may
be encountered.
8.1.3 A measuring error
There are many possibilities:
• A wrong connection or poor connection
• A defective instrument or one requiring calibration
• An operating error
• A recording error
8.1.4 Ambiguous or poorly defined test data
There is often more than one way to measure the resistance of a transformer winding (e.g., line
terminal to line terminal or line to neutral). Typically, field measurements are taken from external
bushing terminals. Shop or factory measurements are not limited to the bushing terminals.
Additionally internal winding connections can be opened (e.g. opening the corner of a delta)
making measurements possible which are not practical in the field .Details of test set ups and
connections area often omitted in test reports which can lead to confusion when comparing test
data.
8.2 How Bad is Bad?
When a higher than expected measurement is encountered what does it mean? Is failure imminent?
Can the transformer be returned to service? Is corrective action needed? To answer these questions
more information along with some analytical thinking is usually required.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

11.
11 / 19
2009-02-02
Matz Ohlen
Peter Werelius
• Firstly, have the confusion factors been eliminated?
• Secondly, what are the circumstances which initiated the resistance test? Was it routine
maintenance or did a system event (e.g. lightning or through fault) result in a forced
outage?
• Is other information available? Maintenance history? Loading? DGA? Capacitance bridge?
Excitation current? If not do the circumstances warrant performing additional tests?
• Consider the transformer schematic. What components are in the circuit being measured?
Has the location of the higher resistance been isolated? See "Isolating Problems".
• How much heat is being generated by the higher resistance? This can be calculated (I2R)
using the rated full load current. Is this sufficient heat to generate fault gases and possibly
result in catastrophic failure? This will depend on the rate at which heat is being generated
and dissipated. Consider the mass of the connector or contact involved, the size of the
conductor, and its location with respect to the flow of the cooling medium and the general
efficiency of the transformer design.
9 Isolating Problems
The resistance test is particularly useful in isolating the location of suspected problems. In addition
to isolating a problem to a particular phase or winding, more subtle conclusions can be drawn.
Consider the transformer schematic (nameplate). What components are in the test circuit? Is there
an RA switch, LTC, diverter isolating switch, link board connectors, etc.? By merely examining the
test data, problems can often be isolated to specific components. Consider:
9.1 RA Switch
In which position does the higher resistance measurement occur? Are repeat measurements (after
moving the RA switch) identical to the first measurement or do they change.
9.2 LTC
The current carrying components of the typical LTC are the step switches, reversing switch and
diverter switches. Carefully examine the test data looking for the following observations:
9.2.1 Step Switch Observation
A higher resistance measurement occurring on a particular tap position both boost and buck (e.g.,
both +1 and-1, +2 and -2, etc.)
The above observation would indicate a problem with a particular step switch. Each step switch is
in the circuit twice. Once in the boost direction and once in the buck direction.
9.2.2 Reversing Switch Observation
All boost or buck measurements on a phase are quantatively and consistently higher, than
measurements in the opposite direction or other phases.
The reversing switch has two positions, buck and boost, and operates only when the LTC travels
through neutral to positions +1 and -1. Hence a poor contact would affect all boost or buck
measurements. If the LTC is operated between +1 and -1 the resistance measured through a poor
reversing switch contact would likely change.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden

12.
12 / 19
2009-02-02
Matz Ohlen
Peter Werelius
9.2.3 Diverter Switch Observation
All odd step or all even step measurements in both the buck and boost direction are high.
There are two diverter switches. One is in the current circuit for all odd steps and the other for all
even steps.
The foregoing discussion is only typical. LTC designs vary. To draw conclusion based on
resistance measurements, the specific LTC schematic must be examined to identify the components
which are being measured on each step. This information is usually available on the transformer
nameplate.
9.3 Contacts vs Connectors or Joints
Is the higher resistance measurement consistent and stable when the RA switch or LTC is
operated? Generally inconsistent measurements are indicative of contact problems while a
consistent and stable high measurement would point to a joint or connector.
10 Limitations
The transformer resistance test has several limitations which should be recognized when
performing the test and interpreting test data:
The information obtained from winding resistance measurements on delta connected windings is
somewhat limited. Measuring from the corners of a closed delta the circuit is two windings in
series, in parallel with the third winding (see Figure 4).
The individual winding resistances can be calculated; however this is a long tedious computation
and is generally of little value. Comparison of one 'phase' to another will usually suffice for most
purposes. Additionally, since there are two parallel paths an open circuit (drop out) test does not
mean too much. However, the test is still recommended. Problems involving LTCs and RA
switches will yield measurements which are not uniform, and often unstable and inconsistent.
Hence the resistance test will detect most problems.
The resistance of the transformer's winding can limit the effectiveness of the test in detecting
problems. The lower the resistance of a winding the more sensitive the test is with respect to
detecting problems. Windings with high DC resistance will mask problems.
The detection of shorted turns is not possible in all situations. Often shorted turns at rated AC
voltage cannot be detected with the DC test. If the fault is a carbon path through the turn to turn
insulation it is a dead short at operating potentials. However, at test potential, 30 V DC, the carbon
path may be a high resistance parallel path and have no influence on the measured resistance.
Certainly if the conductors are welded together the fault should be detectable.
It is not possible on some transformer designs to check the LTC using the resistance test (e.g.,
series winding). The circuit between external terminals simply excludes the LTC. On such units the
resistance test is of no value in verifying the operating integrity of the LTC. If the LTC selector
switch is in the main tank (i.e., same tank as windings) and cannot be physically inspected it is
recommended that samples for DGA be taken as part of routine LTC maintenance.
Megger AB phone: +46 8 510 195 00
Eldarvagen 4 fax: +46 8 510 195 95
187 75 Taby website: www.megger.com
Sweden