The Teddington KBB Fire Valve is a tried and tested brand used within domestic oil heating systems. Designed to close off the oil supply to the burner in the event of a fire, and as a precaution, will not reopen until the temperature has fallen below 30°C and the manual reset is activated. Available with a number of capillary lengths and has a built in isolation valve for easier system servicing.

Brass body c/w copper tube sensor

¼” F BSPT inlet/outlet

Flow rate: 56 L/Hr @ 1m Head

Built in isolation valve for easy servicing

Suitable for kerosene and Biodiesel up to B50

BSRIA & OFTEC approved to E101

Cut off temperature of 65°C or 90°C (depending on model)

This compact KBB valve is resistant of corrosion, consists of a noncombustible construction and its operations is entirely mechanical (no power supply needed). The sensor and capillary are connected via the valve and cannot be detached. The reset button, at the base of the valve head can be pressed to reset the valve. To shut off the valve, pull the reset button with the toggle.

Install the Teddington KBB Fire Valve in the oil supply pipe outside the building. This should be above the burner, with the sensor inside the appliance. The capillary should then be run in a near the sensor and ensure the valve is in a protected position.

Quick acting

Thermally operated

Spring loaded trip mechanism

Sealed temperature system

This safety shut off valve detects if the temperature at the sensor phial exceeds the set value, the valve will snap closed. The valve will remain in the shut off condition until the reset button has been pressed which will restore normal operating conditions.