4208U

• Can be used on controls that support up to 250 zones
• Can be optionally powered from an external DC power supply to reduce the amount of current draw from the polling loop
• Uniquely identifies eight EOLR supervised zones (all zones use 10K resistors, supplied)
• Each zone is identified by a unique serial number, which is assigned via on-board DIP Switches
• Detects faults on all zones within 400ms of occurrence
• Loops A & B can be programmed for fast (10ms) response
• Provides cover tamper protection, which may be enabled or disabled via on-board DIP Switches