Safety-related equipment

May the "safe" signal from a Pilz evaluation device be directed to a PLC (LOGO) in order to enable operations there or must there be another contact after the PLC?

As the PLC (LOGO) is a controller without safety-related properties - it can also be said that the standard PLC is "not a well-tried component" - it may not be connected downstream of the safety relay (e.g. PNOZ). In this type of circuit, the safe signal loses its reliability after the PLC.

Please enable JavaScript in your browser to use all features of this website.

To provide you with user-defined settings, the reminder list and the administration of the shopping basket on our web site, information on your visit is stored in cookies. By using this web site, you agree that we set cookies. Further information on cookies is available in our data protection statement.

Please activate the cookies of your browser to be able to use all the features of this web site. Further information on cookies is available in our data protection statement