The compact mount 120V, 15A AC powered SurgeX Surge Eliminator & Power Conditioner incorporates SurgeX Advanced Series Mode power conditioning and surge protection. The surge protection is rated A-1-1 for endurance. Several mounting options and receptacle configurations are available. The SurgeX ICE Inrush Current Elimination circuitry is incorporated into this Space Saver power distributor. ICE eliminates problems associated with inrush currents from large loads such as amplifiers. With SurgeX ICE it is not necessary to take inrush currents into account when designing the AC power for a system, and special time-delay circuit breakers are not required. You only need to ensure that the steady-state currents of all products plugged into the device are within the 15A rating.

The CM1115RT18 incorporates contact closure and applied DC voltage remote control capabilities. Two or more devices can be connected together to provide control and power conditioning for larger systems. It can also control other SurgeX products with the auxiliary relay contacts and/or its 12VDC output.

A plug-in Phoenix terminal block on the rear panel accommodates the remote control connections and also the low-voltage outputs. There are 3 inputs which control power state; one 12VDC output; and one auxiliary relay providing normally-open contacts. The inputs can be controlled by an applied DC voltage from 5 to 30V, or by a contact closure. The inputs and 12VDC output are designed to withstand incorrect connections including polarity reversal and short circuits.

Note: Do not install this device if there is not at least 30' (10 m) or more between the electrical outlet and the electrical service panel.

Advanced Series Mode surge elimination

Impedance Tolerant EMI/RFI filtering

ICE Inrush Current Elimination

CouVs Catastrophic Over/Under-Voltage Shutdown

Accepts both DC voltage and contact closure control inputs

Two or more units can be cascaded together for larger systems

Auxiliary relay output can be used to control other SurgeX products

12VDC output can be used to control other SurgeX products or drive LEDs

Auxiliary relay or 12VDC output can be used to provide confirmation feedback

Flexible form factor - Has a standalone brick form factor, with options for built-in receptacles, or an 18-outlet power strip