Johnson Controls M9206 Series Electric Spring Return Actuators

Electric Spring Return Actuators

M9206 Series

The M9206 Series direct-mount, spring return electric actuators operate on 24 VAC or VDC power and are available for use with on/off, floating, or proportional controllers. These bidirectional actuators do not require a damper linkage, and are easily installed on a damper with a round shaft up to 1/2 in. (12.7 mm) in diameter or a square shaft up to 3/8 in. (10 mm). They may also be mounted to ball valves using an M9000-51x Valve Linkage Kit.

The M9206 models deliver 53 lb·in (6 N·m) of torque. The angle of rotation is mechanically adjustable. Integral line voltage auxiliary switches are available to indicate end-stop position or to perform switching functions within the selected rotation range. Position feedback is provided on proportional models through a proportional DC voltage signal.

Direction is selectable with the mounting position of the actuator: CCW face of the actuator away from the damper for CCW spring return; CW face of the actuator away from the damper for CW spring return