HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Just found one with a crack in the header,and a crack in the inducer bracket that hold the inducer motor will put pic on.

That is pretty common with tranes design and first thing I check. But my photos where a result of hairline cracks in the secondary plastic collector box. Only way to see it was to pull it, not sure if u could see the detail needed with a snake camera but I would like to try.

Sent from my BlackBerry using Tapatalk please excuse typographical errors

Yes I have noticed them with pin holes ,heat exchangers aren't mad like they used to be and the manufacture doesn't carry the 20 yrs like they use to ..Regards

I am not sure everyone here would agree with me but why not spend a couple extra dollars and make that cover out of stainless or anything other then plastic and I wonder if they would not be having this issue anyone else fell this way?

Sent from my BlackBerry using Tapatalk please excuse typographical errors

had one today that was leaking water on the right hand side above the blower motor in blower compartment.(tux080c942c3) i think its the inducer. alot of sloshing on startup.unit plumb and level. upflow.drains and traps clear. please advise if im wrong. rescheduled pulling inducer and gasket replacement. all ca readings were good. 0ppm in home