Hello, Your privacy is important to us. On May 24, 2018, we published an updated Privacy Statement. Please read these updated terms. We use cookies to create the most secure and effective website possible. By using this site, you consent to the use of cookies. Full details in our Privacy Statement.

FAQ #101803

The Ethernet Smart-RIO devices PCD3.T665 and PCD3.T666 can execute a user program.

It's also possible to make small webeditor projects on this devices.

But it is not possible to use the Alarming feature (Alarming Macro and the associated FBoxes) because the firmware of the Smart-RIO don't support this feature.

In case that Alarming FBoxes are placed in a Fupla-File of a Ethernet Smart-RIO device PCD3.T665 or PCD3.T666, then there will be no error message shown on PG5 during the build of the project. But after the download of the project to the Smart Automation Manager there will be an invalid configuration on the Smart-RIO and the Status-LED on the PCD3.T665/T666 will blink Red/Green and the program on the Smart-RIO will not be executed.

Categories

The requested software / document is no longer marketed by Saia-Burgess Controls AG and without technical support. It is an older software version which can be operated only on certain now no longer commercially available products.