Orientation Orientation describes the direction that air will flow through a piece of equipment. (e.g. air will flow horizontally through a "Horizontal" unit heater.) Most equipment will only function properly if installed in the proper orientation.

A Floor-mounted model for concealed or exposed applications, the Williams Vertical Series offers the right standard and optional equipment for your application. The Vertical Modular (LV-M) is the standard LV-S model with a flat top cabinet. A removable, single-piece front cabinet provides complete access to the unit for servicing the motor, coil, valve package, drain pan, filter and all other components. The cabinet includes top-discharge and front-return grilles.

Williams LV010W2M302R00 Floor Console Fan Coil Features:

Two or Four-pipe hydronic heating and/or cooling. Four-pipe system may be converted to a two-pipe system by capping off one set of pipes. Manual air-vents on water coils.

Coils are 1/2" OD copper tubes with aluminum fins (12 FPI) with right-hand connection and tested underwater at 350 PSI with a 300 PSI working pressure.

Drain pan is a black epoxy, powder-coat finished, insulated with 1/4" elastomeric insulation and has a bottom drain connection.