After-Sales Service Provided: Engineers Available to Service Machinery Overseas

Specification: 50T

Cooling Method: Counter Flow

Material: Metal

Air Contact Way: Closed

Noise Level: Low

Certification: ISO, CE

Warranty: One Year

Trademark: Rongtai

Origin: Weifang, Shandong

Product Description

Fully closed water cooling system

1. Principle of closed water cooling system: Water circulates in the coil of closed cooling tower, and fluid heat will be absorbed by the coil pipe wall, through the fan at the top, the heat will be taken outside. When the water temperature is higher than set temperature, the spray system will start automatically. The spray water become steam in the hot and humid tube, and is then taken away by the air flow; the remaining water stay in water tank for recycling use. The fluid flow in the coil has little consumption, which is just 1-2% of unit flow.

2. Product parameters:FBN-50T

Items

FBN-50T

Cooling amount

228000 kcal/h

Cooling water amount

40m3/h

Working water pressure

0.25-0.35Mpa

Inlet/outlet caliber

DN100

Fan power

2.2KW*2

Spray pump power

2.2KW Q=40M3

Water cooling tower main components:

Shell type(two options)

1.High quality aluminum zinc board,thickness 2mm.

2. High quality stainless steel board, thickness 2mm

Cooling unit

1. High quality copper tube 2. High quality stainless steel tube

Spray pump

Rongtai brand

Air-inlet grille

PVC

Circulating water pump

Nanfang pump or Weifang pump

Auxiliary cistern

350 stainless steel

Spray water tube

PVC

Cistern connecting tube

PPR

Valve

Stainless steel

3. Product detail pictures:

4. Closed cooling system characteristics: 1). Fully closed loop cooling, there is no debris into the cooling pipe system, pipe blockage phenomenon will not occur. 2). Soft water circulation cooling, no scale formation during high temperature, does not cause cooling pipe system scale. 3). Little place occupation, do not need to dig a pool, convenient for place change, save water, reduce energy consumption. 4). Adopts evaporation heat absorption cooling method, high cooling efficiency. 5). The closed circulating water consumption is little, which is in line with the requirement of environmentprotection and energy saving requirement.6). Automatic digital temperature control, automatic level control, energy saving, convenient operation and simple.