A. Provide cameras complete with Vandal-Resistant surface mount housings, mounting hardware and brackets as necessary. Provide, at minimum, housings having accessible maintenance facilities. Provide power and signal cable harnesses and connectors as suitable to allow for the ease of removal or replacement of a camera. The housings are subject to approval by the Engineer and S.O.

B. Video cables shall have no more than one splice between camera and controller bay/video amplifier. Use coaxial copper or glass fibred cable throughout. Do not exceed the CCTV equipment manufacturer’s recommendations for any cable run.

C. Provide only CCD color cameras having, at minimum, the following attributes:

Signal System - PAL : 625 Lines

Scanning System - 2:1 Interlace

Total Pixels No. - 470K

S/N Ratio - More Than 48dB (AGC Off)

Resolution - Horizontal : 480 TV Lines

Video Output Level - 1.0Vp-p (75ohm. Composite)

Lens - Fixed Lens (f = 2.4 - 6mm)

Sync. System - Internal

Sensitivity - 0.O1 Lax

Electronic Shutter - 1/50-1/10.000sec

BLC - Auto

White Balance - Auto

AGC - Auto

Supplied Voltage- DC9V-15V (Recommendation : DC 12V+/-0.5V)

Power Consumption - Less Than 150mA

Weight - Approx. 450q

Dome Size – 100mm

Connector - Video (Yellow), Power (Red), GND (Black)

D. For copper cabling runs over 100m in length use either RG-59 cabling with line equalization and/or signal bolstering or RG-6 cabling. Signal runs over 150m in length and main inter controller switcher runs shall be in glass fibred cabling only.

E. Provide all cameras with auto-iris and bloom-reducing lens facilities giving low distortion imaging. 1/3 inch format cameras may be supplied providing that the indicated and required fields of view and light level performances are attained.

F. Final details of locations and mountings shall be approved by the Engineer.

Kod:

<div style="overflow:auto;width:100%;height:200px;padding:0px">

- TEKS ANDA -

&lt/div>

♦ Scrollbar Dengan Border:

1. CCTV CAMERAS AND HOUSINGS

A. Provide cameras complete with Vandal-Resistant surface mount housings, mounting hardware and brackets as necessary. Provide, at minimum, housings having accessible maintenance facilities. Provide power and signal cable harnesses and connectors as suitable to allow for the ease of removal or replacement of a camera. The housings are subject to approval by the Engineer and S.O.

B. Video cables shall have no more than one splice between camera and controller bay/video amplifier. Use coaxial copper or glass fibred cable throughout. Do not exceed the CCTV equipment manufacturer’s recommendations for any cable run.

C. Provide only CCD color cameras having, at minimum, the following attributes:

Signal System - PAL : 625 Lines

Scanning System - 2:1 Interlace

Total Pixels No. - 470K

S/N Ratio - More Than 48dB (AGC Off)

Resolution - Horizontal : 480 TV Lines

Video Output Level - 1.0Vp-p (75ohm. Composite)

Lens - Fixed Lens (f = 2.4 - 6mm)

Sync. System - Internal

Sensitivity - 0.O1 Lax

Electronic Shutter - 1/50-1/10.000sec

BLC - Auto

White Balance - Auto

AGC - Auto

Supplied Voltage- DC9V-15V (Recommendation : DC 12V+/-0.5V)

Power Consumption - Less Than 150mA

Weight - Approx. 450q

Dome Size – 100mm

Connector - Video (Yellow), Power (Red), GND (Black)

D. For copper cabling runs over 100m in length use either RG-59 cabling with line equalization and/or signal bolstering or RG-6 cabling. Signal runs over 150m in length and main inter controller switcher runs shall be in glass fibred cabling only.

E. Provide all cameras with auto-iris and bloom-reducing lens facilities giving low distortion imaging. 1/3 inch format cameras may be supplied providing that the indicated and required fields of view and light level performances are attained.

F. Final details of locations and mountings shall be approved by the Engineer.

A. Provide cameras complete with Vandal-Resistant surface mount housings, mounting hardware and brackets as necessary. Provide, at minimum, housings having accessible maintenance facilities. Provide power and signal cable harnesses and connectors as suitable to allow for the ease of removal or replacement of a camera. The housings are subject to approval by the Engineer and S.O.

B. Video cables shall have no more than one splice between camera and controller bay/video amplifier. Use coaxial copper or glass fibred cable throughout. Do not exceed the CCTV equipment manufacturer’s recommendations for any cable run.

C. Provide only CCD color cameras having, at minimum, the following attributes:

Signal System - PAL : 625 Lines

Scanning System - 2:1 Interlace

Total Pixels No. - 470K

S/N Ratio - More Than 48dB (AGC Off)

Resolution - Horizontal : 480 TV Lines

Video Output Level - 1.0Vp-p (75ohm. Composite)

Lens - Fixed Lens (f = 2.4 - 6mm)

Sync. System - Internal

Sensitivity - 0.O1 Lax

Electronic Shutter - 1/50-1/10.000sec

BLC - Auto

White Balance - Auto

AGC - Auto

Supplied Voltage- DC9V-15V (Recommendation : DC 12V+/-0.5V)

Power Consumption - Less Than 150mA

Weight - Approx. 450q

Dome Size – 100mm

Connector - Video (Yellow), Power (Red), GND (Black)

D. For copper cabling runs over 100m in length use either RG-59 cabling with line equalization and/or signal bolstering or RG-6 cabling. Signal runs over 150m in length and main inter controller switcher runs shall be in glass fibred cabling only.

E. Provide all cameras with auto-iris and bloom-reducing lens facilities giving low distortion imaging. 1/3 inch format cameras may be supplied providing that the indicated and required fields of view and light level performances are attained.

F. Final details of locations and mountings shall be approved by the Engineer.

A. Provide cameras complete with Vandal-Resistant surface mount housings, mounting hardware and brackets as necessary. Provide, at minimum, housings having accessible maintenance facilities. Provide power and signal cable harnesses and connectors as suitable to allow for the ease of removal or replacement of a camera. The housings are subject to approval by the Engineer and S.O.

B. Video cables shall have no more than one splice between camera and controller bay/video amplifier. Use coaxial copper or glass fibred cable throughout. Do not exceed the CCTV equipment manufacturer’s recommendations for any cable run.

C. Provide only CCD color cameras having, at minimum, the following attributes:

Signal System - PAL : 625 Lines

Scanning System - 2:1 Interlace

Total Pixels No. - 470K

S/N Ratio - More Than 48dB (AGC Off)

Resolution - Horizontal : 480 TV Lines

Video Output Level - 1.0Vp-p (75ohm. Composite)

Lens - Fixed Lens (f = 2.4 - 6mm)

Sync. System - Internal

Sensitivity - 0.O1 Lax

Electronic Shutter - 1/50-1/10.000sec

BLC - Auto

White Balance - Auto

AGC - Auto

Supplied Voltage- DC9V-15V (Recommendation : DC 12V+/-0.5V)

Power Consumption - Less Than 150mA

Weight - Approx. 450q

Dome Size – 100mm

Connector - Video (Yellow), Power (Red), GND (Black)

D. For copper cabling runs over 100m in length use either RG-59 cabling with line equalization and/or signal bolstering or RG-6 cabling. Signal runs over 150m in length and main inter controller switcher runs shall be in glass fibred cabling only.

E. Provide all cameras with auto-iris and bloom-reducing lens facilities giving low distortion imaging. 1/3 inch format cameras may be supplied providing that the indicated and required fields of view and light level performances are attained.

F. Final details of locations and mountings shall be approved by the Engineer.