TM 5-6115-332-14P-8-614-14TO 35C2-3-424-1(4) Remote Mode Starting. The remote con-trol terminal board (fig. 2-9) is located on the right rear of the control box. It provides the connectionpoints required for starting and stopping the gener-ator set from a remote position. TS 6115-332-14/2-9Figure 2-9. Remote control terminals.(a) Position the REMOTE-LOCAL switch(fig. 2-7) in the REMOTE position.ent temperature is -25°F (-31.7°C) and below it will(b) To start the generator set from a re-be necessary to preheat the engine using a blow-mote positon, make contact between the start ter-torch (see para. 2-4). After preheating the engine,minal and the common terminal of the remote con-proceed with electrical or manual starting as out-trol terminal board (fig. 2-9). As soon as the unitlined in (2) and (3), above.starts, break contact.c. Stopping.(1) Local Mode Stopping. Refer to figure 2-10 for local mode stopping instructions.2-15(5) Cold Weather Starting. When the ambi-