HMT 6
6 channel heating actuator for controlling of thermic
actuating drives
Description:
The housing are especially suitable for the mounting of
heating circuit distributors with triacs enabling a noisless
switching of the actuating drives.
The heating actuators (HMT 6/HMT 12 EIB/KNX) optimise
the efficiency when using room temperature controllers
together with thermic actuating drives and enable the
integration of a boiler control

HMT 12
12 channel heating actuator for controlling of thermic
actuating drives
Description:
The housing are especially suitable for the mounting of
heating circuit distributors with triacs enabling a noisless
switching of the actuating drives.
The heating actuators (HMT 6/HMT 12 EIB/KNX) optimise
the efficiency when using room temperature controllers
together with thermic actuating drives and enable the
integration of a boiler control.

Cheops drive EIB/KNX
Motor-driven actuating drive with stroke index.
The setting commands are transmitted by room
temperature sensors.
Description
The actuators have been developed for a continual valve
regulation. The drives receive their supply voltage from the
EIB/KNX. The integrated regulation with the CHEOPS
control EIB/KNX including actual temperature recording
allows an absolute independent single room control. The
temperature can be changed at any time via the hand key

The LU 131 - EIB combination sensor is sensitive to brightness and temperature. These values can be sent to the bus.
In addition, the device is equipped with the following threshold switches for controlling switching actuators, dimming actuators and window shade system actuators depending on the ambient brightness and/or temperature.
• Threshold switch for brightness
• Threshold switch for temperature
• Threshold switch for shading (combination of brightness and temperature)
Via an inhibition object (1 bit), it is also possible to deactivate one or more threshold switches temporarily.

The push button interfaces TA2, TA 4 and TA 6 are binary input modules with
2, 4 or 6 inputs for floating switch/push button contacts.
The connected switches/push buttons can be used to issue commands to actuators
to dim or switch lights on/off, to raise and lower
blinds.
Furthermore, depending on the device, up to 4 channels can be configured for LED
control.
The device can be installed in combination with conventional push buttons/switches in flush-mounted sockets. This allows all switching programs to be integrated in EIB systems.
The installation height is only 10 mm which corresponds to the height of the EIB connection block.
The following functions can be configured:
• Switch / push button input
• Dimmer control
• Control of blinds
• Value
• Command LED*
The telegram type (switching, priority, value and temperature value) and the response for rising and falling edges can be specified individually.
The response to disable telegrams or after restoration of the bus power can also be configured.

The push button interfaces TA2, TA 4 and TA 6 are binary input modules with
2, 4 or 6 inputs for floating switch/push button contacts.
The connected switches/push buttons can be used to issue commands to actuators
to dim or switch lights on/off, to raise and lower
blinds.
Furthermore, depending on the device, up to 4 channels can be configured for LED
control.
The device can be installed in combination with conventional push buttons/switches in flush-mounted sockets. This allows all switching programs to be integrated in EIB systems.
The installation height is only 10 mm which corresponds to the height of the EIB connection block.
The following functions can be configured:
• Switch / push button input
• Dimmer control
• Control of blinds
• Value
• Command LED*
The telegram type (switching, priority, value and temperature value) and the response for rising and falling edges can be specified individually.
The response to disable telegrams or after restoration of the bus power can also be configured.

The push button interfaces TA2, TA 4 and TA 6 are binary input modules with
2, 4 or 6 inputs for floating switch/push button contacts.
The connected switches/push buttons can be used to issue commands to actuators
to dim or switch lights on/off, to raise and lower
blinds.
Furthermore, depending on the device, up to 4 channels can be configured for LED
control.
The device can be installed in combination with conventional push buttons/switches in flush-mounted sockets. This allows all switching programs to be integrated in EIB systems.
The installation height is only 10 mm which corresponds to the height of the EIB connection block.
The following functions can be configured:
• Switch / push button input
• Dimmer control
• Control of blinds
• Value
• Command LED*
The telegram type (switching, priority, value and temperature value) and the response for rising and falling edges can be specified individually.
The response to disable telegrams or after restoration of the bus power can also be configured.

The RAM 713 FAN COIL room thermostat is a continuous EIB room thermostat for ventilator convectors (fan coil) in 2 and 4 pipe systems.
It measures the current room temperature (actual value) and sends a continuous control variable (0...100%) to a fan coil actuator (FCA 1 order no. 492 0 200) to achieve the desired room temperature (setpoint value).
The RAM 713 fan coil works in both heating and cooling modes.
A fan step can also be selected manually via a button.
3 binary inputs are available for connecting switches or buttons (floating) for switching, dimming or controlling blinds.
The blinds and dimmer channels can also be controlled with a single button (single-surface operation)
An external temperature sensor can alternatively be connected to input 3 (analogue).
In order to easily adapt to the setpoint values in respect of living comfort and energy saving, RAM 713 FAN COIL has four operating modes:
• Comfort
• Standby
• Night mode
• Frost protection mode
A setpoint value is assigned to each operating mode.
comfort mode is used when the room is occupied
The setpoint value is reduced slightly in standby mode. This operating mode is used when the room is not occupied but is expected to be shortly.
The setpoint value is drastically reduced in night mode as the room is not expected to be occupied for several hours.
In frost protection mode , the room is controlled to a temperature that eliminates the risk of damage to the radiators through freezing at low outdoor temperatures.
This can be desirable for 2 reasons:
- The room is not occupied for several days.
- A window has been opened and no further heating is required for the time being.
The operating modes are usually controlled by a time switch.
However, a presence detector and/or presence keys and window contacts are recommended for optimum control.

The fan coil actuator FCA 1 is a series device and suitable for connection
to a Bus EIB/KNX. The actuator FCA 1 is suitable for 2-pipe and 4-pipe
systems. It controls up to 3 fan stages as well as 2 or 3-point heating and
cooling valves. An additional relay enables the actuation of an electrical
heater or a cooler bank. The actuator FCA 1 features 2 inputs for floating
contacts, e.g. window contact and condensate monitoring (the window
contact input can be reconfigured as a temperature sensor input). The
actuator is suitable for dry rooms only.

Presence detector switches or controls a maximum of two lighting groups dependent on the presence of persons and the current brightness. A brightness level is defined for this, the second light group is then switched or controlled with a brightness difference. With brightness-dependent switching, the lighting is switched on for an adjustable length of time if movement is detected in detection area and there is insufficient light.

With constant light control, the lighting is controlled to constant accumulated brightness of artificial light and daylight if movement has been detected in the detection area

An additional channel transmits the presence information in the room to further devices such as heating, ventilation or blinds controls. The channel has a switch-on delay and a switch-off delay.

Another channel is for room monitoring, the presence of persons is shown with a high degree of certainty.

The presence detector also has another integrated scene component as well the possibility of processing scene numbers for both lighting groups.

In combination with the remote control, the presence detector is not only capable of switching and dimming its own lighting groups but also other external consumers such as lights, blinds etc.1.2 Features

?? Optional control of one or two light channels

?? Optional constant light control or brightness-dependent switching

?? Brightness-dependent switching with dimming values override

?? Reduction of switch-off delay time in the event of short presence

?? Separate channel (presence) for controlling other devices such as HVAC systems with delayed switch-on and switch-off delay

?? Separate channel for room monitoring with cyclical report object

?? Parallel connection Master-Slave for complete coverage of large areas

6-way heating actuator MIX2With 6 temperature controllers (P/PI) for heating and coolingBasic module MIX2Can be upgraded to maximum of 18 channelsFor controlling 6 thermal actuators 24 V - 240 V AC in 2 groups with 3 outputs and 450 mA each(Due to the switch-on behaviour of the actuators, we recommend not to exceed a maximum load of 3x1 actuators 24 V AC or 3x5 actuators 230 V AC)Short-circuit-proof and overcharge protectedContinuous or switching actuating value selectableValve protection function can be deactivatedWith the modes: comfort, standby, night as well as frost/heating protectionChangeover to summer mode possibleUp to two extension modules MIX or MIX2 can be connected to one basic moduleDevice and KNX bus module can be swapped independently of each otherRemovable KNX bus module enables devices to be changed without reprogrammingManual set-up and use of actuator is possible without KNX bus moduleLED switching status display for each channelManual operation on device (even without bus connection)

Heating actuator6-wayCan be installed directly on a wall or a rail in the heating circuit distributorMains plug on transformer for easy installationScrewless terminal technologyIntegrated power supply for a maximum of 13 thermal actuatorsSilent semiconductor switch (triac)For integrating boiler controlSummer mode and valve protectionContinuous or switching actuating value selectableEmergency program in case of bus and telegram failureCompulsory object for each channel

Heating actuator12-wayCan be installed directly on a wall or a rail in the heating circuit distributorMains plug on transformer for easy installationScrewless terminal technologyIntegrated power supply for a maximum of 13 thermal actuatorsSilent semiconductor switch (triac)For integrating boiler controlSummer mode and valve protectionContinuous or switching actuating value selectableEmergency program in case of bus and telegram failureCompulsory object for each channel

KNX Passive infrared presence detector for ceiling mountingSquare detection range of 360° (up to 64 m2) for safe and easy planning2 channel light C1, C2 with 1 light measurement2 presence channels C4, C5 can be set individuallyAdaptable 1 channel light measurementMixed light measurement suitable for LEDs, fluorescent lamps (FL/PL/ESL) and halogen/incandescent lampsCan be used as fully or semi-automatic, switchableSwitch or constant light control mode with stand-by functionDimmable lighting in switch mode with stand-by functionBrightness switching value or set point value can be set in lux using parameters, on the device itself or via remote controlTeaching in of the brightness switching value or the set point valueRoom correction factor setting for ­brightness measurement calibrationLight time delay can be set using parameters, on the device itself or via remote controlSwitch on delay and time delay ­for presence can be setDetection sensitivity can be setSelf-learning time delayReduced time delay in the event of a shorter stay in the room (short presence)Scenario functionsExtremely easy setting of energy saving characteristics with the new "eco plus" functionTest mode for checking function and detection rangeParallel switching of several detectors in Master/Slave or Master/Master possibleUser remote control and management-remote control (optional)Room monitoring

Common functions- Fan-Coil Actuator- For controlling fan coil (fan coils)- For 2-pipe systems and 4-pipe systems- For up to three fan speedsAdditional relay for electric heaters or cooling coil- Potential-free input for window contacts Or temperature sensor- Potential-free input Condensate monitoring- Display of the operating status via 9 LEDs- Manual operation on the device (fan stages, Switching between heating and cooling)- Adjustment of the setpoint for cooling in Dependence on the outside temperature- Potential - free switching contact for Cooling or heating coil- With emergency program

Features• Recording of wind, rain, brightness and temperature• Highly sensitive rain sensor Moreover, it is possible to seta delay time after the end of the rain, in order to avoidunnecessary raising and lowering of blinds.• Measurement variables can be directly transmitted to thebus• Wind, brightness, temperature are each transmitted as a2 byte value, rain as a 1 bit value• Optionally, wind can be transmitted in m/s or km/h• Evaluation takes place directly in the device• Supply from bus voltage and 230 V• Brightness range: 1–100,000 lux• Temperature range –20 °C ... +55 °C• 4 universal channels• 3 sun protection channels (especially for blinds andshutters applications)• Integrated bus coupler• Heater for rain sensor integrated• Automatic sun protection device for independent controlof blinds, awning, etc.The teach-in objects for the brightness thresholds areuser-friendly, since they allow the customer to establishthe thresholds later on by a simple key press. This doesnot require the weather station to be re-parameterized.• The automatic sun protection controls the blinds (shutters/awnings) independently during the day, withoutmaking any intervention necessary. When a threshold isreached, two separate telegrams can be sent, e. g.for height and slat of a blind or a value and switchtelegram.• Any parameterization of the various channels possibleAdvantages• Only one weather station in a housing that records allvariables and evaluates them.• The device is connected directly to the bus, as a result ofwhich no other cables must be laid.• Sun protection possible for up to three façades (idealcombination with LUNA 133 EIB/KNX, see page 121Mast bracket for Ø 60–80 mm

OBELISK memory card for TERMINA top2 devices for transferring programs from timer to timer or from a PC to a timer and vice versa. Operation of second program possible with the timer providing memory card is loaded.

Radio control via antenna with top2 RC devices: To ensure good reception, do not install the antenna in cellars or on distribution boxes. Connection is made via separate 2-wire, unscreened high-voltage power cable (max. 100 m), up to 10 Theben top2 RC devices can be connected. Polarity, short-circuit and interruption of the antenna circuit are each visually displayed to help with installation.

6-way heating actuator MIX2With 6 temperature controllers (P/PI) for heating and coolingExtension module MIX2For upgrading to maximum of 18 channelsFor controlling 6 thermal actuators 24 V - 240 V AC in 2 groups with 3 outputs and 450 mA each(Due to the switch-on behaviour of the actuators, we recommend not to exceed a maximum load of 3x1 actuators 24 V AC or 3x5 actuators 230 V AC)Short-circuit-proof and overcharge protectedContinuous or switching actuating value selectableValve protection function can be deactivatedWith the modes: comfort, standby, night as well as frost/heating protectionChangeover to summer mode possibleUp to two extension modules MIX or MIX2 can be connected to one basic moduleDevice and KNX bus module can be swapped independently of each otherRemovable KNX bus module enables devices to be changed without reprogrammingManual set-up and use of actuator is possible without KNX bus moduleLED switching status display for each channelManual operation on device (even without bus connection)

Actuator for radiators, heating circuit distributors or individual heating circuits Operating voltage 230 V AC For opening and closing of valves in the fields of heating, ventilation and air conditioning The actuator control is by a room thermostat with two-point output or pulse-width-modulation Inrush current max. 300 mA for max. 2 min., Operating current 8 mA "First open function" for easy installation and heating start-up Plug-in installation on valve adapter to suit the most common valve bottoms and heating circuit distributors Normally closed (Valve is closed when the operating voltage is cut) Simple snap-on mounting to a valve adapter Valve adapter not included in delivery 100% protection against damaging drives through leaking valves Function and adjustment checking Installation vertical, horizontal and up-side-down possible Up-side-down position may reduce product life through special circumstances (e.g. contaminated water) Guaranteed overvoltage protection

Futurasmus KNX Group is a highly specialized and internationally active KNX Wholesaler, being our forte the excellent technical support we provide. You can visit our online catalogue in this website and, if you are a professional, ask for a non binding offer for your KNX projects. Should you be interested in buying KNX components, you are welcome to read our General Sales Conditions and contact our technicians and commercial agents per telephone, e-mail or online help.

Since 2003 we have been a Certified Training Centre KNX++, which means that we are entitled to impart the KNX Basic Course as well as the KNX Advanced Course and KNX Tutor Course. We are manufacturer-independent and also offer other specialized and monographic KNX seminars. After teaching more than 1.500 KNX partners, our KNX Trainers have quite a large and positive expertise. Please, contact us for customized KNX training worldwide (groups of at least 8 people) at training@futurasmus-knxgroup.org

We use our own and third-party cookies, analyzing your browsing habits in out website, with the finality of ensuring the quality, security and improvement of the offered services through the same. In the case that the user does not explicitly state whether to accept the installation of cookies, but continues using our website, it will mean that he has consented expressly, informing him about the possibility to block or remove the installed cookies on his computer by configuring the appropriate settings of the browser. You can get more information on this subject reading our "Cookies Policy".