Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Spark Ignition safety for Gas

Hey Everyone,

A little background on me, I'm new out of tech school, still looking for an apprentice job. In the mean time I'm trying to learn all I can by visiting this site (I've applied for pro, just waiting now) and watching videos on youtube, etc...

This afternoon I was watching one video on YouTube where a guy has a furnace with a spark ignition that won't light. The spark is sparking but not lighting the gas. Eventually he takes a lighter and lights the gas. Watching this has me curious about what safety is in place for no flame on a spark ignition gas furnace? In class we dealt with a standing pilot and hot surface ignitor when we worked with gas, and they both had thermocouples to cut off gas supply if no flame was present, but we didn't learn much about spark ignition. Does a spark ignition use the same safety? If so, why was this guy able to light the furnace with a lighter after no ignition from spark? If anyone has a little time to provide me with some additional knowledge, I'd appreciate it.

I was watching one video on YouTube where a guy has a furnace with a spark ignition that won't light. The spark is sparking but not lighting the gas. Eventually he takes a lighter and lights the gas.

Does a spark ignition use the same safety? If so, why was this guy able to light the furnace with a lighter after no ignition from spark? If anyone has a little time to provide me with some additional knowledge, I'd appreciate it.

IID (intermittent ignition device) systems light a pilot, and then the main burners only after the pilot has been proven to be lit.

This is usually done through flame rectification (possibly thermal detection). Some flame rectification systems use a separate sensor and ignitor, while others use a combination ignitor/sensor, which is referred to as "local sensing".

DSI (direct spark ignition) systems light the main burners with a spark ignitor. Flame rectification is also used on DSI systems.

All systems have a short time (only a few seconds) to prove that the pilot/burners are lit. If they do not light within this short safety period, the control will shut off the system automatically.

In order to prevent nuisance lockouts, systems will try to relight a predetermined number of times.

So all the guy is doing on the video is bypassing the spark ignitor and manually lighting the flame (pilot or main burner) with a lighter. If the flame isn't proven shortly there after, the gas valve will still close.

Flame rectification is the SAFETY, regardless how the burner is lit.

Just a note - view cautiously what you see on YouTube. There is some bad info on HVAC topics being uploaded.

Great reply, rundawg. Just to add a little, the DSI also has purge times before, and between ignition attempts. This is to purge any gas from a failed ignition cycle. It also allows the combustion/draft motor to prove its operation to the ignition control board.