The Goodman® GPG15 Packaged Gas / Electric unit uses the environmentally friendly refrigerant R-410A and provides high-efficiency performance at lower operating costs. This package unit is housed in a heavy-gauge, zinc-coated steel cabinet with a weather-resistant, powder-paint finish and allows for a ground-level or rooftop mount, horizontal or downflow application.

This package unit gas/electric unit can be easily installed in manufactured or modular homes which use smaller (high static pressure) duct work. The package unit can also be easily converted to accommodate a plenum for normal or low-static applications. The Goodman package units are self-contained so the only connections needed for installation are the supply and return ducts, the line and low voltage wiring and drain connection. The units are ETL listed and ARI certified.

Configuration

Configuration is the direction the conditioned air will pass through the unit.

Upflow units will have the air come in from the bottom and blow out the top.

Horizontal units will have the air go through the unit left to right, or right to left.

Downflow units will have the air come in from the top of the unit, and blow out the bottom.

Unsure of what configuration your home needs? Call us at 800-865-5931.
Monday through Friday, 8:30am to 5:00pm CST

Configuration

Downflow
/
Horizontal

Cooling Capacity

Not sure what size you need? Feel free to use our easy sizing calculator.

Cooling Capacity

23200
BTU

Cooling Capacity

Not sure what size you need? Feel free to watch an informational video and use our easy sizing calculator.

Cooling Capacity

2
Tons

Maximum Input BTU

The maximum amount of heat that the unit can produce. The amount delivered into the space will be the input minus the efficiency loss also know as the output. For example a 100000 btu furnace at 80% efficiency will give you 80000 out btus of heat. The same size furnace at 95% will give you 95000 btus of heat.

Maximum Input BTU

69000
BTU

Maximum Heating Output BTU

The amount of heat, rated in British Thermal Units (BTUs), that the unit can deliver into the space. Not sure how many BTUs you need? Try our easy Equipment Sizing Estimator.

Maximum Heating Output BTU

55000
BTU

SEER

Seasonal Energy Efficiency Ratio (SEER) is a measure of cooling over an entire season. It is determined by comparing the amount of cooling produced in BTUs in relation to the amount of electricity used. A higher SEER means a system is more energy efficient and would provide comfort at a lower utility cost than a lower SEER system.

SEER

15
SEER

Energy Efficiency Ratio

The measure of air conditioner efficiency at its maximum load

Energy Efficiency Ratio

12.0
EER

Minimum Output BTU

The amount of heat delivered into the space on the lower stage of heat. This number is the minimum heat input minus the efficiency loss.

Minimum Output BTU

41500
BTU

Nominal CFM

The amount of air that can be moved by the fan, measured in cubic feet per minute (cfm).

Nominal CFM

800

Refrigerant

Inside air conditioning systems are liquid/gas refrigerant. There are two types of this refrigerant available for use, R-22 (more commonly known as Freon), and a newer alternative R-410A.

An air conditioning system does not consume refrigerant, but reuses it. As long as there are no leaks in the refrigerant circuit, there is no need to ever add more refrigerant to an air conditioning system.

Although R-22 is an effective refrigerant, if it is released into the atmosphere it can contribute to the depletion of the Earth’s ozone layer. The EPA has mandated the phasing out the use of R-22. It is being replaced by R-410A.

As of 2010, manufacturers are required to make all new air conditioners with R-410A. However, R-22 is still available for sale in existing pre-2010-manufactured equipment, and for use in servicing existing R-22 equipment. By 2020, R-22 will no longer be manufactured, but will still be recycled and available for sale.

Refrigerant

R-410A

Efficiency (% AFUE)

The percentage of energy converted into output by the unit. The remaining percentage is lost during the conversion process. The higher the efficiency, the lower the operational cost.

Efficiency (% AFUE)

80
%

Maximum Overcurrent Protection (Breaker)

The maximum capacity breaker in the building's circuit panel that can be used on the dedicated electrical line supplying the equipment.

Maximum Overcurrent Protection (Breaker)

30
Amps

Fuel Type

LP Capable (Kit Required)
/
Natural Gas

ENERGY STAR® Qualified

Products earn the ENERGY STAR label by meeting the energy efficiency requirements set forth in ENERGY STAR specifications. The EPA establishes these specifications based on the following set of principles:

Qualified products must deliver the features and performance demanded by consumers, in addition to increased energy efficiency.

If the qualified product costs more than a conventional, less-efficient counterpart, purchasers will recover their investment in increased energy efficiency through utility bill savings, within a reasonable period of time.

Learning Center

In 2002 Alpine Home Air Products became the first company to sell heating, air conditioning and indoor air-quality products online. We have proudly served hundreds of thousands of customers, helping them save time and money by buying their products direct.