PRO-10 Cable Tray systems are innovative in their design based on pre-fabricated junctions/intersections and the ability to provide powder coated finishes while maintaining ground. Cutting and bending of sections is eliminated. PRO-10 trays are UL classified as to its suitability as an equipment grounding conductor only.
They are easy to install; requiring only one tool and very few accessories.
No connecting hardware required. All support hardware available to match finish. Powder coating is standard finish.

Please Select Your Color:

ChromeYellowWhiteBlackOrangeBlueRed

PRO-10TM is available in wire diameter choices CM20 (0.187) - to accommodate various cable tray load capacities. No cutting or bending is required on any of these styles.

The PRO-10TM CM20 cable tray, with a grid pattern of 2" x 4", is the standard that provides a solution for most cabling applications.CM20 is cUL-classified®, powder coated and available in widths of 6", 8", 12", 18", 24"or 36 "; lengths of 1', 2', 5', 8' or 10' and depths of 2", 4", or 6".;.

Installation

PRO-10TM should be installed from the originatinghead-end i.e., the electrical or telecommunications closet. Once the pathway has been established, it is important the layout of the pre-fabricated junctions be installed first. This allows for field measurements to be taken before installing the cable tray. If the straight sections are installed first, it will cause unnecessary field adjustments. Each section has loops at each end. When the sections are connected, the loop on the bottom aligns under the galvanized masked area of the adjoining section. The loop on the side slides into the outside loop guide. Once the trays are aligned, install the 5/16" carriage bolt (included) through the loops with the threaded end to the outside of the tray. Install and tighten the flanged nuts with a 1/2" socket. This reduces the chances of damage when pulling the cables. It is not recommended that the cable tray be cut as it will interfere with the grounding characteristics and UL classification®.PRO-10'sTM wire grid cabletray systems require only one tool and very few accessory items for installation. Pre-fabricated junctions/intersections reduce 50% or more labor hours by eliminating cutting and fabrication in the field. With center hung, trapeze, wall or floor mount accessories, PRO-10TM is prepared to handle the toughest installations.

Tray Size (D" x W" x L')

Fill Area

Max # cables 50% Fill Ratio

**Approx. Max. Cable Weight lbs./ft

Tested Load Capacity 5ft

***lbs./ft. 10ft.

2 x 6 x 10

13.2

130

4.29

46

14

2 x 8 x 10

17.6

174

5.742

29

16

2 x 12 x 10

26.4

260

8.58

34

19

2 x 18 x 10

39.6

394

13.002

43

22

2 x 24 x 10

52.8

527

17.391

52

23

2 x 36 x 10

79.2

788

*

*

*

4 x 6 x 10

25.2

253

8.349

68

122

4 x 8 x 10

33.6

331

10.923

95

35

4 x 12 x 10

50.4

496

16.368

120

50

4 x 18 x 10

75.6

751

24.783

124

52

4 x 24 x 10

100.8

998

32.934

128

55

4 x 36 x 10

151.2

1502

*

*

*

6 x 6 x 10

37.2

370

12.21

110

48

6 x 8 x 10

49.6

493

16.269

108

47

6 x 12 x 10

74.4

739

24.387

124

52

6 x 8 x 10

111.6

1106

36.498

128

55

6 x 24 x 10

148.8

1444

47.652

154

59

6 x 36 x 10

223.2

2212

*

*

*

* Contact Technical Support for 36" data.

For more information, or to continue shopping, please visit this products main webpage.