Рumps ПЭ type

ТУ У 29.1-33412036-002:2007

Pumps of centrifugal horizontal single-effect cell type with onesided wheels location can be assigned for transferring and piping of feed water pH valued 7-9,2; temperature not more 438K (165C°) and not to be contained of solid particles. Pumps can be used for water feeding of stationary steam boilers with total steam pressure 3,9; 5,2; 6,2 MPa (40, 53, 63 kgs/sm²).

Technical characteristics

Pump type

Pumping agent, t °С

Nominal supply, m³/h

Nominal pressure, m

Speed of rotation, per min

Engine power, kW

ПЭ 65-28

В, до +165

65

290

2940

110

ПЭ 65-32

В, до +165

65

320

2960

110

ПЭ 65-40

В, до +165

65

440

2960

132

ПЭ 65-53

В, до +165

65

580

2965

200

ПЭ 100-32

В, до +105

100

330

2960

160

ПЭ 100-53

В, до +165

100

580

2980

315

Pumps СЭ type

ТУ У 29.1-33412036-005:2007

Pumps of centrifugal single-effect (CЭ 800-100-11, CЭ 1250-140-11 as double-effect) spiral type with double-sided working wheels entry can be assigned for transferring and piping of water which has temperature up to 180C°; contains the solid particles sized not more 0,2 mm while its concentration not more 5 mg/l.

Pumps can be used for water transferring in boilers.

Technical characteristics

Pump type

Pumping agent, t °С

Nominal supply, m³/h

Nominal pressure, m

Speed of rotation, per min

Engine power, kW

СЭ 500-70-16

В, до +180

500

70

3000

160

СЭ 800-55-11

В, до +180

800

55

1500

200

СЭ 1250-70-11

В, до +180

1250

70

1500

315

Рumps КсВ type

ТУ У 29.1-33412036-003:2007

Pumps of centrifugal vertical double-effect type can be assigned for transferring and piping of condensed fluid and other liquids which have similar viscosity and chemical activity features as condensed fluid has; minimum temperature of pumping liquid is 10°С; maximum temperature is 125°С, 160°С depending on pump type and size. Pumps can be used for condensed fluid transferring in thermal power stations operating with organic fuel.

Technical characteristics

Pump type

Pumping agent, t °С

Nominal supply, m³/h

Nominal pressure, m

Speed of rotation, per min

Engine power, kW

КсВ 125-55

К, до +125

125

55

2950

30

КсВ 125-55а

К, до +125

125

45

2950

30

КсВ 125-55б

К, до +125

125

40

2950

30

КсВ 125-140

К, до +125

125

140

2950

75

КсВ 125-140а

К, до +125

125

125

2950

75

КсВ 125-140б

К, до +125

125

125

2950

55

КсВ 320-160-2

К, до +140

320

320

1480

250

Рumps Кс type

ТУ У 29.1-33412036-004:2007

Pumps of centrifugal horizontal single-effect cell type with onesided wheels location can be assigned for transferring and piping of condensed fluid in steam and water system of thermal power stations as well as other liquids which have similar viscosity and chemical activity features as condensed fluid has; temperature not more than 125°C and 160°C.