Thermal Control Products, Non-Drip Couplings & Nipples

Series 677, DN14 Stainless steel

Precision-made dry-break coupling suitable for liquid cooling

Safety lock feature to prevent unintentional disconnection

One-hand-operated connector with compact dimensions

This robust stainless steel quick connect coupling series 677 is adaptable to virtually all thermal control applications. The colour-coding feature helps to separate incoming cool lines from outgoing hot lines. The non-drip design ensures zero spillage and eliminates pollution and air inclusion during connection and disconnection for long-term use. This stainless steel disconnect series with DN14 is available in three configurations: double shut-off, single shut-off and straight through. In addition, 677 can be delivered with colour-coding and/or key coding for extra safety. Optional seal material is available upon request.

The series is available in four other sizes: series 277, 477, 577 and 777. Please refer to series 667 for an all-brass version. For other sizes in brass, refer to series 267, 467, 567 and 767. If you can’t find a product that meets your requirements, don’t hesitate to contact us, and we’ll put our R&D department at your disposal.
Applications: Data server chiller cooling lines, chassis manifolds, IGBTs, power converters, power inverters, rectifiers, industrial drives, power generators, heat exchangers, medical and industrial lasers, traction control, machine tools, solar power, alternative energy.

Check with an authorized CEJN distributor for availability and prices. Other connections and sealing material on request. Some part numbers may be subject to minimum order quantities. CEJN reserves the right to make changes without further notification. Thread connections are listed according to ISO Standards. All measurements are in mm. *Available color coding: green, red, blue, yellow, white and black. Also available with mechanical key coding.

Technical data

Nominal flow diameter:

14 mm (9/16")

Water flow (double shut-off):

97.8 l/min (21.5 GPM UK)

Max. working pressure:

20 bar (290 PSI)

Min. burst pressure:

80 bar (1160 PSI)

Temperature range:

-20°C — +150°C (-4°F — +302°F)

Material coupling:

Stainless steel, AISI 316

Material nipple:

Stainless steel, AISI 316

Kv (double shut-off):

5.87

Cv (double shut-off):

6.78

Comment:

Also available in singel shut-off or straight through version.

Water flow capacity measured at 1.0 bar (14.5 PSI) pressure drop.

Available files for download

Please complete the form below in order to gain access to downloadable product files. The data you provide is for internal information purposes only and will not be published or made available outside of CEJN.