CPH CONVERTIBLEAvailable in 1/2, 3/4 and 1 HP. Includes: pump, motor and pressure switch. Order ejector, control package and pressure gauge separately.* Add “R” to end of model number to include 134349 control package with pump.

CPJS AND CPHS SHALLOW WELL PERFORMANCE WITH SHALLOW WELL EJECTORS

Model

No.

HP

Ejector* Assembly

Suction

Lift Ft.

Discharge Pressures (PSI)

Suction & Discharge

Pressure Switch Setting

Shut Off Pressure PSI

Pump Shipping Weight

20

30

40

50

60

CAPACITY - U.S. GALLONS PER

MINUTE

CPJ03SB

1/3

SW03E-1626

5

15

25

11.3

8.7

5.3

10.7

8.5

5.3

9.5

7.8

5.2

6.7

5.3

4.2

1-1/4” X 3/4”

30-50

74

69

65

49

CPJ05SB CPH05S

1/2

SW05E-1630

5

15

25

17.2

12.8

7.7

16.8

12.7

7.5

14.8

12.2

7.2

10.0

7.7

5.3

1-1/4” X 3/4”

30-50

69

64

60

50

43

CPJ07SB CPH07S

3/4

SW07E-1432

5

15

25

19.8

15.5

9.8

19.5

15.2

9.5

19.2

14.8

9.3

18.0

14.2

8.8

1-1/4” X 1”

30-50

65

60

55

58

CPJ10SB CPH10S

1

SW10E-1334

5

15

25

23.7

18.3

11.7

23.5

18.3

11.7

23.3

18.2

11.5

23.0

18.0

11.3

1-1/4” X 1”

30-50

70

65

58

62

53

CPJ15S

1-1/2

SW15E-1238

5

15

25

30.0

24.0

15.0

29.8

23.8

15.0

29.8

23.7

15.0

29.8

23.5

14.8

23.3

18.7

8.0

1-1/4” X 1”

30-50

77

72

63

72

CPJ AND CPH SHALLOW WELL CAPACITIES WITH CONVERTIBLE EJECTOR

Model

No.

HP

Ejector

Assembly

Suct. Lift Ft.

Discharge Pressure (PSI)

Suction & Discharge

Pressure

Switch

Setting

Shut Off

Pressure

PSI

Pump

Ship

Weight

20

30

40

50

60

70

80

90

CAPACITY - U.S. GALLONS PER MINUTE

CPJ05B CPH05

CPH05R†

1/2

DW40E-1730

5

15

25

14.8

11.8

7.3

14.5

11.3

7.2

13.2

11.2

7.0

10.0

8.3

6.5

6.7

5.0

3.3

1-1/4” X 3/4”

30-50

76

72

67

46

38

DW40E-1828

5

15

25

12.0

9.0

5.3

11.5

8.8

5.3

11.3

8.7

5.2

10.2

8.5

5.2

7.8

6.7

5.0

5.0

4.2

3.3

1-1/4” X 3/4”

30-50

90

85

80

CPJ07B CPH07

CPH07R†

3/4

DW40E-1630

5

15

25

16.0

12.5

8.3

15.7

12.3

8.3

15.5

12.3

8.2

15.0

12.2

8.0

10.3

7.0

4.2

1-1/4” X 1”

30-50

75

72

66

56

DW40E-1726

5

15

25

10.2

8.0

4.8

10.0

7.5

4.7

9.7

7.3

4.5

9.5

7.3

4.3

9.3

7.2

4.2

9.2

7.2

4.2

7.5

6.7

4.2

5.7

5.0

3.3

1-1/4” X 1”

30-50

120

115

110

CPJ10B CPH10

CPH10R†

1

DW40E-1634

5

15

25

20.8

16.7

11.7

20.8

16.7

11.5

20.5

16.3

11.3

20.3

16.2

11.2

15.8

13.0

9.3

1-1/4” X 1”

30-50

80

75

70

58

49

DW40E-1828

5

15

25

12.2

9.5

5.7

11.7

9.2

5.5

11.7

9.0

5.3

11.3

8.8

5.2

11.2

8.8

5.0

11.2

8.8

5.0

10.8

8.7

5.0

8.0

6.7

5.0

1-1/4’ x 1”

30-50

125

120

115

CPJ15

1-1/2

DW40E-1736

5

15

25

23.8

18.0

11.0

23.3

17.8

10.7

23.3

17.5

10.7

23.0

17.3

10.5

18.7

16.3

10.3

13.8

11.7

8.3

8.3

6.0

2.0

1-1/4” x 1”

30-50

93

88

82

66

[/custom-specifications][custom-features]

High Tensile Gray Iron Pump BodiesLarge water cavities provide fast, easy priming. Separate priming ports enable quick water fill and the fast evacuation of air. Separate 1/4” tappings are provided for the convenient mounting of pressure/vacuum gauges and the pressure switch, and for pump draining.