The vertical cable manager is interfering with cage nut holes and the ability to mount equipment into the NetShelter cabinet, what's wrong?

Cause:
The cable manager interferes with the mounting holes on the rails.

Resolution:
There is one of two possible installation errors:

1) After attaching the cable manager to the rail the cable manager must slide towards the side of the cabinet. This will draw it away from the equipment mounting rail. The cable manager has a slotted hole so it can slide to the side.
AR7588, see Installation Step 6: http://download.schneider-electric.com/files?p_Reference=APC_MLAN-8ZRM62_R1_EN&p_EnDocType=Instruction%20sheet&p_File_Id=1837895927&p_File_Name=MLAN-8ZRM62_R1_EN.pdf
AR7580A: see Installation Step 6: http://download.schneider-electric.com/files?p_Reference=APC_JKUR-948NBR_EN&p_EnDocType=Instruction%20sheet&p_File_Id=7849749629&p_File_Name=JKUR-948NBR_R1_EN.pdf
AR7585: See Installation Step 6: http://download.schneider-electric.com/files?p_Reference=APC_JKUR-948NBR_EN&p_EnDocType=Instruction%20sheet&p_File_Id=7849749629&p_File_Name=JKUR-948NBR_R1_EN.pdf

2) When installing the cable managers in the rear of a cabinet the accessory mounting rails must first be moved. If not, the finger-style cable manager will interfere with the equipment mounting rails.