Question details

CORRECTION Page 4-39 The connection numbering for the AI625 module is wrong. CH12U is connected with pin 34, not 35 as shown in figure 4-25 CH12I is connected with pin 35, not 36 as shown in figure 4-25

Page 4-73 The connection numbering for the DO630 module is wrong. The first output channel is connected with pin 3 and 4, not 2 and 3, as shown in figure 4-52 All following connections are then shifted by one, so that the 16th channel is connected with pin 47 and 48, not 46 and 47