Matching - To minimize RF signal loss from the
"mismatch" between the different coaxial cable
and transmission line impedance.

DISCUSSION

This Application Note describes the use of Signalcrafters
Tech, Inc. products in tuning single frequency, dual frequency
and wide band Line Tuning Units.

Our customers tell us that significant time savings (on the
order of ½ to ¾), can be realized by employing Signalcrafters
Tech, Inc. Models 60, 70 and 90A. Some additional benefits: Only
one person is required at the tuner, No AC power is required. No
communications with the control room is required but is
recommended.

II.PROCEDUREIMPORTANT - CLOSE THE GROUNDING SWITCH
WHEN LIFTING OR REPLACING TUNER COMPONENT LEADS OR TEST LEADS.
OPEN TO MEASURE OR ADJUST.

PART A. SINGLE FREQUENCY LINE TUNERS

Verify that the coax is connected to the PLC equipment
normally at all locations. Verify that all transmitters
are turned off.

Turn on the Model 90A and set
the controls as follows:
A. Turn "LEVEL" fully CCW
B. Set "HI-LOW" switch to "HI"
C. "MEMORY" switch to "1"
D. " F KHZ" to "0.100"
E. "ON-OFF" switch to "ON"
F. Press the "VFO" keypad. This causes the
decimal point in the LCD Display to blink indicating the
"VFO" is unlocked and frequency entry is
possible.
G. Adjust the large tuning knob to produce the desired
frequency in the LCD Display, and of course, at the
output.
H. Press the "VFO" keypad. This causes the
decimal point in the LCD Display to stop flashing and
locks the VFO.
I. Press the "STO" keypad. This stores this
frequency into memory register 1 (per step 2C above)

At the line tuner, remove the PLC transmitter input coax.
Connect the Model 90 "RF OUT" port to the Model 70 "RF IN" port
using a coax cable. Connect the Model 70 "RF
OUT" port to the line tuner transmitter input using
the proper transition.

Verify that the grounding switch on the tuner is open.

Set the Model 70 "RANGE" control to "5
WATTS" and turn the instrument "ON".

Adjust the output of the Model 90A until the Model 70
"RF POWER WATTS" meter reads 2 watts.

Adjust the series inductor on the line tuner for the
lowest reading (dip) on the Model 70 "% REFLECTED
POWER" meter. Make note of the impedance matching
transformer tap setting and the minimum reflected power
level.

Turn off the Model 90A and charge matching transformer tap
setting one tap, one direction or the other. Turn the
Model 90A back on the note % reflected power level.
Continue this process trying to improve the % reflected
power level.

Touch up the series inductor again for the lowest reading
on the Model 70 "% REFLECTED POWER" meter.

Note: The purpose of steps 7-9 is to try several impedance
matching transformer tap settings. These taps are generally
between 250 and 375 ohms. However, they can range from 100 to 800
ohm. Normal reflected power after tuning is less than 1% and up
to 5% is probably acceptable. Reflected power percentages above
5% may be indicative of possible problems and will not be dealt
with here.

PART B. DUAL FREQUENCY LINE TUNERS

NOTE: Steps 10-17 deal with tuning the two parallel L/C units
whose purpose is to keep each transmitter signal from going
directly into its neighboring receiver.

Load a second frequency into MEMORY register 2
on the Model 90A by repeating the steps found in par 2
above. NOTE: To recall the frequency residing in memory
register 1, turn the MEMORY control to register 1 and
press the "RCL" (recall) keypad. The generator
is returned to frequency #1 which is display in the LCD
Display.

Isolate the Freq. 1 Parallel L/C unit. Connect a Model 60 across the L/C unit.
Connect the Model 90 "RF OUTPUT" to the
"SIG IN" port on the Model 60. Set the Model 90A
output frequency to F1.

Adjust the "OUTPUT LEVEL" of the Model 90A to
obtain a reading of 10Vrms on the panel meter.

Adjust the frequency 1 L/C unit for a maximum reading on
the Model 60.
Note: If some lines have a Blocking or Phase Comparison
carrier on one side of the line tuner and a Transfer Trip
(FSK) carrier on the other side of the line tuner, the
L/C unit for the transfer trip (FSK) carrier should be
tuned to the receive center frequency and the series
inductor should be tuned to the transmit center
frequency. If this is the case you will have to add a 3rd
frequency to the Model 90A memory.

Make the frequency 1 side normal. Repeat steps 11-14 for
F2 side of the tuner.

Rotate the Model 90A MEMORY control to register 2 and
press the "RCL" keypad.

Set the "RANGE" selector on the Model 70 to 5
watts and turn the instrument ON.

Adjust the "OUTPUT LEVEL" control on the Model
90A to obtain a reading of 2 watts on the Model 70
"RF POWER WATTS" meter.

Adjust the frequency 2 inductor for the lowest reading
(dip) on the Model 70 "% REFLECTED POWER"
meter. Make note of the impedance matching transformer
tap setting and the minimum reflected power level.

Turn off Model 90A. Change the frequency 2 impedance
matching transformer tap setting one tap at a time, one
direction or the other, trying to improve the minimum %
reflected power level. Remember, turn off the Model 90A
when changing impedance matching transformer taps and
turn it back on to check the results of the adjustment.

Turn on the Model 90A and touch up the series inductor
again to produce the lowest % reflected power reading on
the Model 70.

To tune the frequency 1 side of this Line Tuner repeat
steps 15-21. Remember to recall frequency 1 from the
Model 90A memory.

Turn off the Model 90A and Model 70. Remove all test
leads. Make the line tuner normal. Inform the opposite
station that you are ready for them to tune.

NOTE: After the opposite station tunes, if they have made
large changes, it may be advisable to recheck the tuning at this
station.

PART C. WIDE BAND LINE TUNERSNOTE: Part C assumes phase to ground coupling and
that the line tuner does not include hybrid.

REFER TO FIGURE 3.

CLOSE THE GROUNDING SWITCH WHEN LIFTING OR
REPLACING COMPONENT LEADS OR TEST LEADS. OPEN TO MEASURE
OR ADJUST.

Lift the LINE in and output leads from Parallel L/C (3L)
unit at E1 & E2.

Connect the Model 60 across the Parallel L/C unit at E1
& E2.

Connect the Model 90A "RF OUT" to the Model 60
"SIG IN" port.

Set the Model 90A output to the GMF @ 10Vrms.

GMF=

Tune the coil in the Parallel L/C unit for
maximum |Z| on the model 60. Refer to the Model 60
Operation Manual to determine any artifactual capacitance
if concerned.

Remove the test leads.

Tune the Series inductor (2R) and the impedance Matching
Transformer (4L) using STEPS 2-9 from PART A above.

Reconnect the Parallel L/C circuit and observe on the
Model 70 what effect this addition has had. It should be
negligible. If necessary touch up the Series Inductor to
improve the Model 70 indication.

Remove all test connections, firmly reattach all leads,
tighten the set screws on the coil knob.