LBS series: Striker mechanism is employed in which the striker opens the switches automatically when the fuse blows.
LB series: Wide variation is available by combining each unit’s functions and the combination is easy to rearrange.

FUJI air load break switch type LBS is provided with current limiting power fuses and type LB is not so fitted. Both types are compact and incorporate arc-extinguishing devices of FUJI’s own design. The arc is drawn into a long narrow chamber with close clearances in which the gases are rapidly cooled and dispersed. Contact points therefore wear very slowly, so giving switches a long service life. FUJI air load break switches are recommended for use with power capacitors and transformers.

The RB 104 and 105 relays are designed for printed circuit board use. These relays are extremely thin (5mm) and so, can be densely mounted on PC boards. As a result, PC board size and cost can be greatly reduced. Employing of bifurcated contacts ensure high contact reliability, allowing the RB104, 105 relays to be used in low-level circuits. Coil voltages are available in ranges from 4.5V to 24V DC.

Ideal for control circuits of all types of control panels, or protection of your equipment.

The CP31 and CP32 have a similar functions to a molded case circuit breaker and they can be used for normal switching ON and OFFoperations while breaking bothoverload and short-circuit currents.
They are available in two time – current versions — an instantaneous and a time-delay version.
A suitable type should be selected to match the thermal and permissible current requirements.
These are recommended for sequential control circuits, motor control circuits, solenoid-operated valves, heaters and solid – state applications.

A perfect choice for the protection of your electrical equipment, or control circuit for control panels of all kind.
A global model, Super slim body with full of functions.

FUJI’s compact and high-performance CP-F series circuit protectors incorporate FUJI’s advanced technology.
Their thin sizes make them ideal for use as AC/DC line switches in office andindustrial equipment.

The fuse can be used independently or incorporated with switches that are not provided with a tripping device, from back-up fuses to current limiting fuses which can interrupt all current ranges.

FUJI current limiting power fuses are available in general purpose and back-up versions. Type SCF and HF ··· E general purpose fuses will interrupt all excessive current ranging from the minimum melting current to the rated interrupting current. They will accurately interrupt a 200 – 300% overcurrent of the rated current. The fuse can be used independently or incorporated with air load break switches not provided with trip mechanisms. Very economical to install. The back-up fuses are rated at 12kV or higher and used with switches provided with trip mechanisms incorporated with CT or OCR.

Reliable disconnecting switches that have been chosen by customers for a long time. Small, light, and easy-to-operate. It is easy to mount them on cubicles.

FUJI high voltage disconnecting switches comprise the V and RF types.
The small size and lightness of the V type disconnecting switches make them highly suitable for cubicle use.
They make use of FUJI’s specially designed coil spring, a line-contact and ball contact (RF type) system which gives them a high efficient operation without overheating.
V type disconnecting switches are not provided with latches but their design will not permit them to be opened by magnetic force. Switches provided with latches can also be supplied upon request.

In the earth leakage relay the breaking mechanism is omitted from the ELCB, and the ZCT and earth leakage tripping device are integrated into a common body.
These relays are available in both instantaneous and time-delay versions.
Generally these relays are used in conjunction with MCCB’s, ACB’s and motor starters.