EVOQUA DEIONIZER

This Product

EVOQUA DEIONIZER

Latest Technology, Highest Quality, Environmentally Friendly

The high quality 1.4404 stainless steel deionizers can be operated at pressures of up to 10 bar.
They are significantly more resistant to mechanical stress than conventional glass fiber reinforced plastic cartridges.
Evoqua has optimized the water flow to ensure that the resin bed can be used to its full capacity.

Product Description

EVOQUA DEIONIZER – Water Technologies

The compact design with high-quality components and intelligent control places great emphasis on cost-effectiveness. The plant systems are characterized by a consistent pure water quality. Conductivities of <0.1 µS/cm in single-phase and <0.07 µS/cm in dual-phase systems are achieved. The TOC content is < 30 ppb.

Germ reduction is achieved by means of the special arrangement of the separate bed process and a related pH-value shift into the acidic range, preventing the growth of bacteria in work spaces. No system operates more efficiently and economically, since the EDI-cell has a loss rate of only 10%. Low operating costs and a minimal maintenance outlay are features of this system.

These systems can be individually equipped with additional options such as different tank sizes and pressure boosting systems. They represent the core element in central water treatment plants in buildings and are used with the options necessary for a ring main operation. All systems have a RS 232 interface. Degassing systems to reduce the CO2 content in feed water are available – they ensure that the system remains within feed water specifications and protect the EDI-cell.

Feed for ultrapure water systems

General laboratory work

Laboratory washing machines

Water for autoclaves and environmental chambers

Buffer preparation

Polishing of RO water

Field of Use

Microbiology

Electronics

Optics

Semiconductor

Pharmaceutical

Chemistry

Clinical

Power plants

Glass industry

Plating industry

Food service

Deionizer with Quick-Couplins (SK)

​Type SG…SK

​

2000 SK​

2800 SK​

4500 SK

6200 SK​

7000 SK

11000 SK​

​15000 SK

​Capacity*

​In Liter

​2000

​2800

​4500

​6200

​7000

​11000

​15000

​Performance Max.

​l/h

​450

​800

​1000

​1000

2000

2500

3000

​Pressure Max.

​Bar

​10

​10

​10

​10

​10

​10

​10

​Dimensions

​

​

​

​

​

​

​

​

​Diameter

​mm

​230

​230

​230

​230

​360

​360

​360

​Container Height

​mm

​410

​570

​785

​1025

​660

​980

​1111

​Container Height Incl. Meter

​mm

​515

​675

​886

​1125

​780

​980

​1230

​Shipping Weight

​kg

18

24

34

48

​52

68

​92

​Material Number

​

​W3T199735

​W3T199172

​W3T199736

​W3T198029

​W3T199173

​W3T199027

​W3T199789

Deionizer with Thread Connectors (3/4″ / 1 1/4″)

​Type SG…

​

​2000 3/4″

​2800 3/4″

​4500 3/4″

​6200 3/4″

​7000 1 1/4″

​11000 1 1/4″

​15000 1 1/4″

​Capacity*

​In liter

2000​

​2800

​4500

​6200

​7000

​11000

​15000

​Performance Max.

​l/h

​450

​800

​1000

​1000

2000

2500

​3000

​Pressure Max.

​Bar

​10

​10

​10

​10

​10

​10

​10

​Dimensions

​

​

​

​

​

​

​

​

​Diameter

​mm

​230

​230

​230

​230

​360

​360

​360

​Container Height

​mm

​410

​570

​785

​1025

​660

​980

​1111

​Container Height Incl. Meter

​mm

​530

​690

​900

​1140

​710

​910

​1160

​Shipping Weight

​Kg

​18

​24

​34

​48

​53

​69

​93

Material Number

​

​W3T199409

​W3T98640

​W3T198639

​W3T198638

​W3T199061

​W3T197829

​W3T198437

Reviews

There are no reviews yet.

Only logged in customers who have purchased this product may leave a review.

Our Vision

To enhance lives and positively transform society through the relentless pursuit for excellence in the field of Life Analytical Sciences

Our Mission

To be recognised as the leading reliable provider in the region for state-of-the-art technology solutions to leading industries that satisfy the stated expectations and address the unstated requirements
of customers