Benefits

Integrated flow control valve at the hose end equips you with a direct and better control to fight fire

Our higher than normal industry standard burst pressure for the cylinder and hose safeguards you when fire fighting

A long life and low maintenance costs are assured as our extinguishers are manufactured from 2 mm thick steel, shot blasted, and polyester coated. A non rusting safety pin is also included.

Technical data

Fire rating

34A/233B/C

Capacity

6 Kg

Discharge Range

4 Mtr

Burst disc pressure

26 Bar

Working Pressure

13 Bar

Weight Empty

5 Kg

Weight Full

11 Kg

Height

500 mm

Diameter

180 mm

Operating temp range

-30 C to + 60 C

Incompatibility

The mono-ammonia phosphate-based ABC powder is strictly incompatible with the BC powder, a derivative of sodium bicarbonate.

Never use one of these powders to refill a device which has contained the other product

Spare Charges Regulations

Spare charges shall be provided for 100% of the first ten extinguishers and 50% of the remaining fire extinguishers capable of being recharged on board. Not more than sixty total spare charges are required. Instructions for recharging shall be carried on board

Approval documents

Directions for use

Easy To Use

Operation
Once the safety pin has been removed, the device is pressurized by pressing on the striking handle. The flow rate is controlled by the final control valve. The fact that it is so simple to use means that risks of incorrect use are greatly reduced.

Pressurization during use
Striking the internal cartridge releases the propellant (CO2), pressurizes the body and thus causes the powder to be discharged. The cartridge is interchangeable and its level can be checked accurately by weighing, so the extinguisher can be refilled on site, without having to send it back to the factory. Both preventive and corrective maintenance can therefore be carried out in optimum conditions.

Instruction for Use

Pull out the safety pin

Strike by pressing the handle

Control the flow rate by squeezing the final
control valve direct the spray at base of fire