PKV

Description

Page Content

PKV is a square PKA type diffuser with integrated motor for supply air of variable air volume (VAV). The integrated motorized damper ensures a constant throw so the Coanda effect always is maintained. The damper setting can be controlled by a room regulator, BMS or other 2-10 V control signal.

Can vary the volume flow between 0-100 %

Min. flow preset from factory *)

Max. flow to be set in MBB box based on k-value

Settings can be changed with ZTH-GEN or Belimo PC-tool

VAV zone pressure must be controlled

The diffuser must be installed together with a MBB-S type plenum box

For exhaust PKA can be used

*) Min. setting and k-value are made from a pre-defined, available constant pressure in the air duct immediately before the diffuser. The diffuser is typically used at a constant pressure of 30-50 Pa.