mark g.

Derek D.

Jim C.

Jim C.

Michael S.

Near Centre St, Quincy, MA02169

286 days ago

mark g.

Near Falls Blvd, Quincy, MA02169

375 days ago

mark g.

Near Falls Blvd, Quincy, MA02169

400 days ago

Nicholas L.

Kitchen Hood Suppression System - NON COMPLIANT
Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiencies were found on order 13492845
- ITEMS TO BE CORRECTED BY CLIENT - MOVING OF APPLIANCES BACK UNDER NOZZLE COVERAGE
improper coverage to the griddle, chargrill, and range. Base refrigeration unit needs to be moved to the left and then realign appliances to there nozzles. Range will also need to be moved to the left. Only half the range is under the protected hood. Chargrill is caulk to the refrigerator unit and will need to be unsealed so adjustments can be made to the chargrill allowing it to sit under the nozzles properly.
- Tri State Fire Protection to: replace and adjust the salamander nozzle for proper listings/compliance
Repair of these deficiencies is essential to overall life safety. Please see attached compliance quote. If you have any questions, feel free to call me.