Forward osmosis for the treatment of reverse osmosis concentrate from water reclamation: process performance and fouling control

While high quality water reuse based on dual membrane filtration (membrane filtration or ultrafiltration, followed by reverse osmosis) is expected to be progressively applied, treatment and sustainable management of the produced reverse osmosis concentrate (ROC) are still important issues. Forward osmosis (FO) is a promising technology for maximising water recovery and further dewatering ROC so that zero liquid discharge is produced. Elevated concentrations of organic and inorganic compounds may act as potential foulants of the concentrate desalting system, in that they consist of, for example, FO and a subsequent crystallizer. The present study investigated conditions under which the FO system can serve as concentration phase with the focus on its fouling propensity using model foulants and real ROC. Bulk organics from ROC consisted mainly of humic acids (HA) and building blocks since wastewater-derived biopolymers were retained by membrane filtration or ultrafiltration. Organic fouling of the FO system by ROC-derived bulk organics was low. HA was only adsorbed moderately at about 7% of the initial concentration, causing a minor flux decline of about 2–4%. However, scaling was a major impediment to this process if not properly controlled, for instance by pH adjustment or softening.

Related articles

Membrane filtration is an effective way to remove pollutants and microorganisms from water and wastewater. However, membrane fouling lowers efficiency over time when considering rejection values and water flux. Fouling is typically biological or particulate; fouling rate is a function of the membrane pore size relative to the size of the foulants and also the interactions between the membrane and the foulants. Membrane surface charges and affinity for water directly affect membrane biofouling intensity. Applying...

Intermittent backwashing and relaxation are mandatory in the membrane bioreactor (MBR) for its effective operation. The objective of the current study was to evaluate the effects of run-relaxation and run-backwash cycle time on fouling rates. Furthermore, comparison of the effects of backwashing and relaxation on the fouling behavior of membrane in high rate submerged MBR. The study was carried out on a laboratory scale MBR at high flux (30 L/m2·h), treating sewage. The MBR was operated at three relaxation...

This study focuses on the use of fluidized glass beads as turbulence promoters in a laboratory-scale anaerobic membrane bioreactor treating municipal wastewater at 20 °C. The addition of fluidized glass beads into an external tubular ceramic membrane enabled the operation at low crossflow velocities of 0.053–0.073 m/s (mean fluxes between 5.5 and 9.7 L/(m2·h)) with runtimes >300 h. Glass beads with a diameter of 1.5 mm were more effective than smaller ones with a diameter of 0.8–1.2 mm. Increasing the bed...

Microbial fuel cells (MFC) and membrane bioreactors (MBR) are promising technologies for wastewater treatment. However, both of them have some drawbacks and application limitations. A cost-effective hybrid system (EMBR) integrating MFC with MBR was evaluated in terms of treatment performance and membrane fouling. In this paper, two electric field directions with a membrane module in the middle were applied to explore the mechanism of membrane fouling mitigation in EMBRs. In both configurations of EMBRs, microbial...

Reverse osmosis (RO) and nanofiltration (NF) are membrane filtration technologies that are designed to remove solute ions and molecules from a pretreated liquid stream. Well-designed RO/NF units are compact and demand relatively little maintenance, making them an attractive alternative to conventional treatment trains.
Even despite the merits of today’s efficient RO/NF technologies, it pays to understand common pitfalls associated with them. If your facility currently uses RO/NF or is considering purchasing...

Customer comments

No comments were found for Forward osmosis for the treatment of reverse osmosis concentrate from water reclamation: process performance and fouling control. Be the first to comment!

Add your comment

Great! comment successfully added!

Contact

Your message:

Your email

Your first name

Your last name

I would like to receive periodic email updates and special offers from select suppliers.