Quick Overview

Details

The NRT2- U3300 Rack 2U UPS Tower is the complete solution for IT infrastructures. It is the solution for switching, storage, servers and networking devices, VoIP communication systems, structured cabling systems, control systems and Video surveillance systems

• No configuration necessary on first startup. • Wide range of communication protocols for integration into LAN networks or Building Management Systems (BMS). • Clear LED interface with buzzers that immediately indicate the operating status of the UPS, even for less specialist users (1100‑3000 VA). • LCD display with menu available in 6 languages (5000-11000 VA).

Meets practical needs

• Online double conversion technology with sinusoidal waveform, completely filters out all disturbances from / to the mains power supply and ensures maximum protection of the utility. • Modular battery extension (EBM) to meet all back-up time requirements, even after installation. • Possibility of 1+1 parallel redundant configuration to maximise the availability of critical utilities, even in the event of a module breakdown (5000‑11000 VA).

Parallel redundant operation for business continuity

To achieve the highest level of availability and to power critical utilities, NETYS RT UPS modules above 3 kVA can be configured for 1:1 redundancy. Redundant operation (1+1) means: the system incorporates one more UPS module than is needed to protect the load ; in the event of a breakdown, it guarantees sufficient power supply capacity to the load by maintaining online protection. Parallel technology is based on the principle of load sharing, whereby both units are always kept active. In a redundant configuration, overall system availability is much higher than a conventional UPS system using similar technology. 1+1 redundant configuration does not require additional circuits and can therefore be set up at a later date, simply by using two UPS modules and a collector / manual bypass module which simplifies cabling and maintenance of the UPS installation. To further streamline the solution, it is also possible to select between operation with separate battery or shared battery, which is extremely useful in the case of applications requiring high levels of autonomy.