Thursday, September 13, 2007

Sewage Treatment

Post by Voon Chen Li

From Wikipedia, the free encyclopedia• Learn more about using Wikipedia for research •Jump to: navigation, searchSewage treatment, or domestic wastewater treatment, is the process of removing contaminants from wastewater, both runoff and domestic. It includes physical, chemical and biological processes to remove physical, chemical and biological contaminants. Its objective is to produce a waste stream (or treated effluent) and a solid waste or sludge also suitable for discharge or reuse back into the environment. This material is often inadvertently contaminated with toxic organic and inorganic compounds.Sewage is created by residences, institutions, and commercial and industrial establishments. It can be treated close to where it is created (in septic tanks, Biofilters or aerobic treatment systems), or collected and transported via a network of pipes and pump stations to a municipal treatment plant (see sewerage and pipes and infrastructure). Sewage collection and treatment is typically subject to local, state and federal regulations and standards (regulation and controls). Industrial sources of wastewater often require specialized treatment processes (see Industrial wastewater treatment).Typically, sewage treatment involves three stages, called primary, secondary and tertiary treatment. First, the solids are separated from the wastewater stream. Then dissolved biological matter is progressively converted into a solid mass by using indigenous, water-borne bacteria. Finally, the biological solids are neutralized then disposed of or re-used, and the treated water may be disinfected chemically or physically (for example by lagoons and micro-filtration). The final effluent can be discharged into a stream, river, bay, lagoon or wetland, or it can be used for the irrigation of a golf course, green way or park. If it is sufficiently clean, it can also be used for groundwater recharge.

DescriptionRaw influent (sewage) is the liquid waste from toilets, baths, showers, kitchens, sinks etc. Household waste that is disposed of via sewers. In many areas sewage also includes some liquid waste from industry and commerce. In the United Kingdom, the waste from toilets is termed foul waste, the waste from items such as basins, baths, kitchens is termed sullage water, and the industrial and commercial waste is termed trade waste.The division of household water drains into greywater and blackwater is becoming more common in the developed world, with greywater being permitted to be used for watering plants or recycled for flushing toilets. A lot of sewage also includes some surface water from roofs or hard-standing areas. Municipal wastewater therefore includes residential, commercial, and industrial liquid waste discharges, and may include stormwater runoff. Sewage systems capable of handling stormwater are known as combined systems. Such systems are usually avoided since they complicate and thereby reduce the efficiency of sewage treatment plants owing to their seasonality. The variability in flow also leads to often larger than necessary, and subsequently more expensive, treatment facilities. In addition, heavy storms that contribute more flows than the treatment plant can handle may overwhelm the sewage treatment system, causing a spill or overflow (called a combined sewer overflow, or CSO, in the United States). It is preferable to have a separate storm drain system for stormwater in areas that are developed with sewer systems.The construction of combined sewers is a less common practice in the U.S. and Canada than in the past and is no longer accepted within building regulations in the UK and other European countries. Instead, liquid waste and stormwater are collected and conveyed in separate sewer systems, referred to as sanitary sewers and storm sewers in the U.S. and as foul sewers and surface water sewers in the UK.As rainfall runs over the surface of roofs and the ground, it may pick up various contaminants including soil particles and other sediment, heavy metals, organic compounds, animal waste, and oil and grease. Some jurisdictions require stormwater to receive some level of treatment before being discharged directly into waterways. Examples of treatment processes used for stormwater include sedimentation basins, wetlands, buried concrete vaults with various kinds of filters, and vortex separators (to remove coarse solids).The site where the raw wastewater is processed before it is discharged back to the environment is called a wastewater treatment plant (WWTP). The order and types of mechanical, chemical and biological systems that comprise the wastewater treatment plant are typically the same for most developed countries:Mechanical treatment;Influx (Influent)Removal of large objectsRemoval of sand and gritPre-precipitationBiological treatment;Oxidation bed (oxidizing bed) or aeration systemPost precipitationEffluentChemical treatment (this step is usually combined with settling and other processes to remove solids, such as filtration. The combination is referred to in the U.S. as physical-chemical treatment.).Treatment stages

Primary treatment

Primary treatment removes the materials that can be easily collected from the raw wastewater and disposed of. The typical materials that are removed during primary treatment include to fats, oils, and greases (also referred to as FOG), sand, gravels and rocks (also referred to as grit), larger settleable solids including human waste, and floating materials. This step is done entirely with machinery, hence the name mechanical treatment.Influx (influent) and removal of large objectsIn the mechanical treatment, the influx (influent) of sewage water is strained to remove all large objects that are deposited in the sewer system, such as rags, sticks, condoms, sanitary towels (sanitary napkins) or tampons, cans, fruit, etc. This is most commonly done with a manual or automated mechanically raked screen. This type of waste is removed because it can damage or clog the equipment in the sewage treatment plant.

Sand and grit removalPrimary treatment typically includes a sand or grit channel or chamber where the velocity of the incoming wastewater is carefully controlled to allow sand grit and stones to settle, while keeping the majority of the suspended organic material in the water column. This equipment is called a detritor or sand catcher. Sand grit and stones need to be removed early in the process to avoid damage to pumps and other equipment in the remaining treatment stages. Sometimes there is a sand washer (grit classifier) followed by a conveyor that transports the sand to a container for disposal. The contents from the sand catcher may be fed into the incinerator in a sludge processing plant, but in many cases, the sand and grit is sent to a landfill.Primary sedimentation tank at a rural treatment plantSedimentationMany plants have a sedimentation stage where the sewage is allowed to pass slowly through large tanks, commonly called "primary clarifiers" or "primary sedimentation tanks". The tanks are large enough that fecal solids can settle and floating material such as grease and oils can rise to the surface and be skimmed off. The main purpose of the primary stage is to produce a generally homogeneous liquid capable of being treated biologically and a sludge that can be separately treated or processed. Primary settlement tanks are usually equipped with mechanically driven scrapers that continually drive the collected sludge towards a hopper in the base of the tank from where it can be pumped to further sludge treatment stages.Secondary treatmentSecondary treatment is designed to substantially degrade the biological content of the sewage such as are derived from human waste, food waste, soaps and detergent. The majority of municipal and industrial plants treat the settled sewage liquor using aerobic biological processes. For this to be effective, the biota require both oxygen and a substrate on which to live. There are number of ways in which this is done. In all these methods, the bacteria and protozoa consume biodegradable soluble organic contaminants (e.g. sugars, fats, organic short-chain carbon molecules, etc.) and bind much of the less soluble fractions into floc. Secondary treatment systems are classified as fixed film or suspended growth. Fixed-film treatment process including trickling filters and rotating biological contactors where the biomass grows on media and the sewage passes over its surface. In suspended growth systems—such as activated sludge—the biomass is well mixed with the sewage and can be operated in a smaller space than fixed-film systems that treat the same amount of water. However, fixed-film systems are more able to cope with drastic changes in the amount of biological material and can provide higher removal rates for organic material and suspended solids than suspended growth systems.Roughing filters are intended to treat particularly strong or variable organic loads, typically industrial, to allow them to then be treated by conventional secondary treatment processes. Characteristics include typically tall, circular filters filled with open synthetic filter media to which wastewater is applied at a relatively high rate. They are designed to allow high hydraulic loading and a high flow-through of air. On larger installations, air is forced through the media using blowers. The resultant wastewater is usually within the normal range for conventional treatment processes.

Activated SludgeActivated sludge plants use a variety of mechanisms and processes to use dissolved oxygen to promote the growth of biological floc that substantially removes organic material. It also traps particulate material and can, under ideal conditions, convert ammonia to nitrite and nitrate ultimately to nitrogen gas, (see also denitrification).Fluidized bed reactorsThe carbon adsorption following biological treatment was particularly effective in reducing both the BOD and COD to low levels. A fluidized bed reactor is a combination of the most common stirred tank packed bed, continuous flow reactors. It is very important to chemical engineering because of its excellent heat and mass transfer characteristics. In a fluidized bed reactor, the substrate is passed upward through the immobilized enzyme bed at a high velocity to lift the particles. However the velocity must not be so high that the enzymes are swept away from the reactor entirely. This causes high mixing; these type of reactors are highly suitable for the exothermic reactions. It is most often applied in immobilized enzyme catalysis.Filter beds (oxidising beds)Trickling filter bed using plastic mediaIn older plants and plants receiving more variable loads, trickling filter beds are used where the settled sewage liquor is spread onto the surface of a deep bed made up of coke (carbonised coal), limestone chips or specially fabricated plastic media. Such media must have high surface areas to support the biofilms that form. The liquor is distributed through perforated rotating arms radiating from a central pivot. The distributed liquor trickles through this bed and is collected in drains at the base. These drains also provide a source of air which percolates up through the bed, keeping it aerobic. Biological films of bacteria, protozoa and fungi form on the media’s surfaces and eat or otherwise reduce the organic content. This biofilm is grazed by insect larvae and worms which help maintain an optimal thickness. Overloading of beds increases the thickness of the film leading to clogging of the filter media and ponding on the surface.Biological aerated filtersBiological Aerated (or Anoxic) Filter (BAF) or Biofilters combine filtration with biological carbon reduction, nitrification or denitrification. BAF usually includes a reactor filled with a filter media. The media is either in suspension or supported by a gravel layer at the foot of the filter. The dual purpose of this media is to support highly active biomass that is attached to it and to filter suspended solids. Carbon reduction and ammonia conversion occurs in aerobic mode and sometime achieved in a single reactor while nitrate conversion occurs in anoxic mode. BAF is operated either in upflow or downflow configuration depending on design specified by manufacturer.Secondary Sedimentation tank at a rural treatment plantMembrane biological reactorsMembrane biological reactors (MBR) combines activated sludge treatment with a membrane liquid-solid separation process. The membrane component utilizes low pressure microfiltration or ultra filtration membranes and eliminates the need for clarification and tertiary filtration. The membranes are typically immersed in the aeration tank (however, some applications utilize a separate membrane tank). One of the key benefits of a membrane bioreactor system is that it effectively overcomes the limitations associated with poor settling of sludge in conventional activated sludge (CAS) processes. The technology permits bioreactor operation with considerably higher mixed liquor suspended solids (MLSS) concentration than CAS systems, which are limited by sludge settling. The process is typically operated at MLSS in the range of 8,000–12,000 mg/L, while CAS are operated in the range of 2,000–3,000 mg/L. The elevated biomass concentration in the membrane bioreactor process allows for very effective removal of both soluble and particulate biodegradable materials at higher loading rates. Thus increased Sludge Retention Times (SRTs)—usually exceeding 15 days—ensure complete nitrification even under extreme cold weather operating conditions.The cost of building and operating a MBR is usually higher than conventional wastewater treatment, however, as the technology has become increasingly popular and has gained wider acceptance throughout the industry, the life-cycle costs have been steadily decreasing. As well, in developed urban areas where the footprint of the treatment plant is considered a limiting factor MBR facilities can be considered a desirable option.Secondary sedimentationThe final step in the secondary treatment stage is to settle out the biological floc or filter material and produce sewage water containing very low levels of organic material and suspended matter.Rotating biological contactorsRotating biological contactors (RBCs) are mechanical secondary treatment systems, which are robust and capable of withstanding surges in organic load. RBCs were first installed in Germany in 1960 and have since been developed and refined into a reliable operating unit. The rotating disks support the growth of bacteria and micro-organisms present in the sewage, which breakdown and stabilise organic pollutants. To be successful, micro-organisms need both oxygen to live and food to grow. Oxygen is obtained from the atmosphere as the disks rotate. As the micro-organisms grow, they build up on the media until they are sloughed off due to shear forces provided by the rotating discs in the sewage. Effluent from the RBC is then passed through final clarifiers where the micro-organisms in suspension settle as a sludge. The sludge is withdrawn from the clarifier for further treatment.Tertiary treatmentTertiary treatment provides a final stage to raise the effluent quality before it is discharged to the receiving environment (sea, river, lake, ground, etc.). More than one tertiary treatment process may be used at any treatment plant. If disinfection is practiced, it is always the final process. It is also called "effluent polishing".FiltrationSand filtration removes much of the residual suspended matter. Filtration over activated carbon removes residual toxins.LagooningLagooning provides settlement and further biological improvement through storage in large man-made ponds or lagoons. These lagoons are highly aerobic and colonization by native macrophytes, especially reeds, is often encouraged. Small filter feeding invertebrates such as Daphnia and species of Rotifera greatly assist in treatment by removing fine particulates.Constructed wetlandsConstructed wetlands include engineered reedbeds and a range of similar methodologies, all of which provide a high degree of aerobic biological improvement and can often be used instead of secondary treatment for small communities, also see phytoremediation. One example is a small reedbed used to clean the drainage from the elephants' enclosure at Chester Zoo in England.Waste removalWastewater may contain high levels of the nutrients nitrogen and phosphorus. Excessive release to the environment can lead to a build up of nutrients, called eutrophication, which can in turn encourage the overgrowth of weeds, algae, and cyanobacteria (blue-green algae). This may cause an algal bloom, a rapid growth in the population of algae. The algae numbers are unsustainable and eventually most of them die. The decomposition of the algae by bacteria uses up so much of oxygen in the water that most or all of the animals die, which creates more organic matter for the bacteria to decompose. In addition to causing deoxygenation, some algal species produce toxins that contaminate drinking water supplies. Different treatment processes are required to remove nitrogen and phosphorus.Nitrogen removalThe removal of nitrogen is effected through the biological oxidation of nitrogen from ammonia (nitrification) to nitrate, followed by denitrification, the reduction of nitrate to nitrogen gas. Nitrogen gas is released to the atmosphere and thus removed from the water.Nitrification itself is a two-step aerobic process, each step facilitated by a different type of bacteria. The oxidation of ammonia (NH3) to nitrite (NO2−) is most often facilitated by Nitrosomonas spp. (nitroso=ammonium). Nitrite oxidation to nitrate (NO3−), though traditionally believed to be facilitated by Nitrobacter spp. (nitro=nitrite), is now known to be facilitated in the environment almost exclusively by Nitrospira spp.Denitrification requires anoxic conditions to encourage the appropriate biological communities to form. It is facilitated by a wide diversity of bacteria. Sand filters, lagooning and reed beds can all be used to reduce nitrogen, but the activated sludge process (if designed well) can do the job the most easily. Since denitrification is the reduction of nitrate to dinitrogen gas, an electron donor is needed. This can be, depending on the wastewater, organic matter (from faeces), sulfide, or an added donor like methanol.Sometimes the conversion of toxic ammonia to nitrate alone is referred to as tertiary treatment.Phosphorus removalPhosphorus can be removed biologically in a process called enhanced biological phosphorus removal. In this process, specific bacteria, called polyphosphate accumulating organisms, are selectively enriched and accumulate large quantities of phosphorus within their cells (up to 20% of their mass). When the biomass enriched in these bacteria is separated from the treated water, these biosolids have a high fertilizer value.Phosphorus removal can also be achieved by chemical precipitation, usually with salts of iron (e.g. ferric chloride) or aluminum (e.g. alum). The resulting chemical sludge is difficult to handle and the added chemicals can be expensive. Despite this, chemical phosphorus removal requires significantly smaller equipment footprint than biological removal, is easier to operate and can be more reliable in areas that have wastewater compositions that make biological phosphorus removal difficult.DisinfectionThe purpose of disinfection in the treatment of wastewater is to substantially reduce the number of microorganisms in the water to be discharged back into the environment. The effectiveness of disinfection depends on the quality of the water being treated (e.g., cloudiness, pH, etc.), the type of disinfection being used, the disinfectant dosage (concentration and time), and other environmental variables. Cloudy water will be treated less successfully since solid matter can shield organisms, especially from ultraviolet light or if contact times are low. Generally, short contact times, low doses and high flows all militate against effective disinfection. Common methods of disinfection include ozone, chlorine, or ultraviolet light. Chloramine, which is used for drinking water, is not used in wastewater treatment because of its persistence.Chlorination remains the most common form of wastewater disinfection in North America due to its low cost and long-term history of effectiveness. One disadvantage is that chlorination of residual organic material can generate chlorinated-organic compounds that may be carcinogenic or harmful to the environment. Residual chlorine or chloramines may also be capable of chlorinating organic material in the natural aquatic environment. Further, because residual chlorine is toxic to aquatic species, the treated effluent must also be chemically dechlorinated, adding to the complexity and cost of treatment.Ultraviolet (UV) light can be used instead of chlorine, iodine, or other chemicals. Because no chemicals are used, the treated water's taste is more natural and pure as compared to other methods. UV radiation causes damage to the genetic structure of bacteria, viruses, and other pathogens, making them incapable of reproduction. The key disadvantages of UV disinfection are the need for frequent lamp maintenance and replacement and the need for a highly treated effluent to ensure that the target microorganisms are not shielded from the UV radiation (i.e., any solids present in the treated effluent may protect microorganisms from the UV light). In the United Kingdom, light is becoming the most common means of disinfection because of the concerns about the impacts of chlorine in chlorinating residual organics in the wastewater and in chlorinating organics in the receiving water. Edmonton, Alberta, Canada also uses UV light for its water treatment.OzoneO3 is generated by passing oxygen O2 through a high voltage potential resulting in a third oxygen atom becoming attached and forming O3. Ozone is very unstable and reactive and oxidizes most organic material it comes in contact with, thereby destroying many pathogenic microorganisms. Ozone is considered to be safer than chlorine because, unlike chlorine which has to be stored on site (highly poisonous in the event of an accidental release), ozone is generated onsite as needed. Ozonation also produces fewer disinfection by-products than chlorination. A disadvantage of ozone disinfection is the high cost of the ozone generation equipment and the requirements for highly skilled operators.