QUFSD - Remediation Plan for Water Testing Locations Where Results for Lead were above 15 ppb Threshold Levels

2

High School Bldg Sample #

Sample Location

Results

Short Term Remediation Plan

Long Term Remediation Plan

Target Date for Completion

Actual Date Completed

3

HS-021

Shop Room 148

20.0

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Post permannt signs and address as necessary in Legacy Project since this area will be renovated. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

4

HS-031

Faculty Bath by Main Office

16.2

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Post permannt signs and address as necessary in Legacy Project since this area will be renovated. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

Post permannt signs and replce fixture. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; Replace faucet by the end of December and retest results.

6

HS-066

Boys Locker Coach Sink

230

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Post permannt signs and address as necessary in Legacy Project since this area will be renovated. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

7

HS-068

Girls Locker Sink 1

20.3

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Post permannt signs and address as necessary in Legacy Project since this area will be renovated. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

8

HS-075

Students by 256

24.8

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage - Address in Legacy Project. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

9

HS-083

Exterior Hose Bib: West Side

419

Install temporary signage, Use for non-potable water useage only - replace - Access requires special tool to turn on water

Install permanent signage - Address in Legacy Project. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

10

HS-084

Exterior Hose Bib: East Side

1,900

Install temporary signage, Use for non-potable water useage only - replace - Access requires special tool to turn on water

Install permanent signage - Address in Legacy Project. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

11

HS-085

Exterior Hose Bib: North Side

75.9

Install temporary signage, Use for non-potable water useage only - replace - Access requires special tool to turn on water

Install permanent signage - Address in Legacy Project. Re-test results identified lead levels less than threshold. This indicates that the fixture is the cause of the problem.

Post permanent signs by end of December 2016; remove or replace fixture during Capital Project

12

13

Concession Bldg Sample #

Sample Location

Results

Short Term Remediation Plan

Long Term Remediation Plan

Target Date for Completion

Actual Date Completed

14

CS-21

Exterior Hose Bib: NW Corner

79.5

Use for non-potable water useage only - install permanent signage

Install permanent signage; use only as non-potable water source.

By end of December 2016

15

16

17

Elementary School Bldg Sample #

Sample Location

Results

Short Term Remediation Plan

Long Term Remediation Plan

Target Date for Completion

Actual Date Completed

18

ES-033

Kitchen - West Hand Washing Sink

45

Use for non-potable water

Install permanent signage; re-test and base remediation efforts on the results of re-testing.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

19

20

21

Middle School Bldg Sample #

Sample Location

Results

Short Term Remediation Plan

Long Term Remediation Plan

Target Date for Completion

Actual Date Completed

22

MS-006

1st Floor West Wing Boys Room Right Sink

25

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage; re-test and base remediation efforts on the results of re-testing.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

23

MS-026

Girl's Coach's Office Bathroom Sink

310

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage; re-test and base remediation efforts on the results of re-testing.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

24

MS-046

Tech Wing Hall Girls Bathroom

17

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage; re-test and base remediation efforts on the results of re-testing.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

25

MS-004

Room 121 Front Desk

23

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage - this is a Lab faucet/sink and these are not to be used for potable water.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

26

MS-013

Room 216 Front Desk Sink

28

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage - this is a Lab faucet/sink and these are not to be used for potable water.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

27

MS-032

Room 123 Front Desk Sink

30

Install temporary signage, Use Sink/Faucet for handwashing ONLY

Install permanent signage - this is a Lab faucet/sink and these are not to be used for potable water.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.

28

MS-050

Basement Tech Break Room

26

Install temporary signage, Use Sink/Faucet for handwashing ONLY; sink is used for dringing water source - provide bottled water for drinking purposes.

Install permanent signage; re-test and base remediation efforts on the results of re-testing.

Post permanent signs until faucet is replaced - post signs by end of December 2016. Update plan as follow-up testing dictates.