New devices must be added to the Control Panel and the Radio Hub, ensuring the Loop number and addresses programmed at the Radio Hub correspond to that programmed at the Control Panel. Once completed the new devices must be assigned. (See Q8).

Checking the devices analogue values and the interrogation of the devices signal readings is possible on the Control Panel, with the ‘Enable Control’ ON, by selecting; ‘VIEW DEVICES’ > ‘VIEW DEVICES BY LOOP’ > ‘VIEW LOOP 1 – 14 DEVICES ’ > ‘Scroll up and down to scroll through the devices on the selected loop.

To ensure the signal levels for each device and each RCC are at an acceptable level the Global Sig Stat menu should be checked. This menu will display the signal level in dB’s for each device and RCC over a 24 hour period. This is listed in Loop and Address Number order. After the system has been running for a 24 hour period the device signal levels should display 30dB or above and the RCC signal levels should displayed 20dB or above. If any devices are under the signal level requirements check the flowchart On How to Improve Device Signal Levels section for guidance. From Front Display > Advanced > Global Sig Stat