S37 - The Phoenix - Tubular Motor 2 Hour Fire Rated Roller Shutter

Our Series 37 Phoenix 2 Hour Fire Rated Electrically Operated roller shutters are a compact and robust product ideally suited to protect schools, commercial and industrial premises with openings up to 4000mm x 2500mm high. In addition to providing ease of operation, the 2” flat lath allows for a more compact box, which is aesthetically pleasing especially on kitchen serveries.

The door is designed for opening applications where there is need for protection from fire and a physical security deterrent. The roller shutter can be used for daily operation via push button or key switch. In the event of a fire, the door can be triggered by the fire alarm linked to a UPS FDI, which drives the door down under power.

Each roller shutter is made to measure and CE marked, ensuring each product complies with European directives and gives you peace of mind.

Each design has been thoroughly tested and inspected by Exova Warrington Fire Research to BS 476 Part 22 enabling us to issue Declaration Of Performance.

All our Roller Shutters are manufactured in house at our facility in Leigh and are subject to continuous product development, ensuring the products we offer are of the highest quality whilst maintaining ease of installation.

Each roller shutter can be manufactured to suit your specific requirements, with a dedicated team on hand to give advice and technical support, we can back up an already high quality product with first class service and support.

TECHNICAL SPECIFICATION

Operation – Keyswitch / Rockerswitch

Typical Application
Kitchen Servery / Reception Counter

MAXIMUM SIZE
3000mm WIDE x 3000mm HIGH

CURTAIN
2” flat lath galvanised to BS729:1971, 20swg (0.9mm) thick. Alternate laths are fitted with high quality pressed steel endlocks, which are double pop riveted to prevent lateral movement. The curtain is attached to the shutter barrel using high tensile hexagon head set screws. A high strength inverted “T” section bottom rail is added to the base of the curtain for rigidity and fire integrity.

FLAGS
Endplates are constructed from flat 6mm thick mild steel plate (BS 1449) bolted to the endplate using high tensile hexagon head bolts. The motor drive endplate is fitted with a motor mounting plate using hexagon head high tensile set screws, the non-motor end is fitted with a lost bobbin arrangement. Fixing angles are formed using hot rolled angle section, 75mm x 50mm x 6mm, attached to the fixing angles are the galvanised (BS 729:1971) shutter guides, the guide section is typically 2 1/2” in depth x 1” inside dimension, the guide thickness is 3mm. The flags are coated in a black primer paint finish.

PHOENIX FIRE SHUTTERS ARE LINKED INTO THE FIRE ALARM SYSTEM AS STANDARD, OTHERWISE A LOCAL SMOKE DETECTOR WILL BE REQUIRED (BY OTHERS) TO ACTIVATE THE SHUTTER. THE FIRE SIGNAL REQUIRED IS A NORMALLY OPEN VOLT FREE SIGNAL.

A PHOENIX FIRE SHUTTER MUST HAVE A “MAINTAINED SUPPLY”, A BATTERY BACK UP SYSTEM CAN BE PROVIDED AT AN EXTRA COST.

ACTIVATED UPON RECEIPT OF SIGNAL FROM FIRE ALARM / SMOKE DETECTOR. A TIME DELAY CAN BE PROGRAMMED IN TO THE F.D.I. PANEL, WHEREBY THE SIGNAL WILL BE HELD FROM THE SHUTTER UNTIL THE PROGRAMMED TIME HAS ELAPSED. DURING THE TIME DELAY THE F.D.I. PANEL WILL FLASH “FIRE DOOR CLOSING”, SIMULTANEOULSY AN AUDIBLE ALARM WILL SOUND. ONCE THE TIME HAS ELAPSED, THE DOOR WILL DRIVE DOWN UNDER POWER UNTIL IT HITS THE BOTTOM LIMIT.