460 IQ 250/260

BACnet/IP for Eaton IQ 250/260 Power Meters

Get Your IQ 250/260 Meter Data on BACnet/IP The 460MMBS-Eaton-IQ250-260 moves power and energy data between one or more IQ 250/260 Meters and BACnet/IP Clients like Johnson Controls Metasys. With Energy costs rising and increased concern about energy and power quality, more and more building managers need access to the real time energy and power data collected by Eaton IQ Meters. Managers want to access that data over BACnet/IP, the networking standard for commercial building automation. The 460MMBS-Eaton-IQ250-260 is perfect for this task. In fact, it’s been designed solely to move data from IQ Meters to BACnet-based Building Automation systems.

With the 460MMBS-Eaton-IQ250-260 you have a device that can be quickly deployed and easily configured to integrate IQ 250/260 Meters into Your BACnet Building Automation System.

No Nasty Configuration Headaches The 460MMBS-Eaton-IQ250-260 comes pre-programmed ready to be integrated. A user editable profile automatically maps many of the important IQ Modbus registers to BACnet Analog points. You simply select the Modbus address for each IQ Meter. If your application requires additional IQ Registers you can simply edit and reload the profile to access other IQ data points. In Most Apps There’s No Need To Look At The IQ Register List!

Some BACnet Clients, like Metasys require more than just data values. To meet this need the IQ profile includes tag names, unit designations and scaling factors for each IQ register. These tag strings and automatic scaling factors are easily customized for your application by editing the IQ profile.

Move Your Data Bi-directionally You can both receive energy data from your IQ 250/260 Power Meter and send new control parameters to the Meter from your BACnet/IP Client.

Configure Your Data Transfer from a Web Page No special software is required. The unit is completely configurable using your Browser.

Hardware

Electrical / Environmental

Enclosure / Hardware

Size
4.2” x 3.25” x 1”Weight
5 oz.Enclosure Type
Anodized AluminumMounting
Din Rail or Panel MountLEDs
Ethernet Link/Data LED, Ethernet Speed LED, Power LED, & 2 general purpose LEDS on sideGateway Security
You can configure up to 9 different users access to diagnostic and configuration screens.Alarming
Set =, >, ==, !=, and Change-of-State rules on any data moving through the gateway. If alarm rule is triggered an email notification can be sent.Translation Table
Allows for data manipulation during protocol translation. Scaling and other data format changes can occur in the gateway.Status and Counters
Protocol specific status, counters and error messages are accessible within the gateways diagnostics page. They can also be delivered to a connected device.Diagnostic Logging Page
Allows users to see and log start up sequences, protocol specific messages & error messages.

Features

Gateway Security

You can configure up to 9 different users access to diagnostic and configuration screens.

Alarming

Set <, <=, >=, >, ==, !=, and Change-of-State rules on any data moving through the gateway. If alarm rule is triggered an email notification can be sent.

Translation Table

Allows for data manipulation during protocol translation. Scaling and other data format changes can occur in the gateway.

Status and Counters

Protocol specific status, counters and error messages are accessible within the gateways diagnostics page. They can also be delivered to a connected device.

Product Selector

Testimonial

We provide different PLC platforms depending on customer requirements and I have found the 460MSA and 435NBX gateways from RTA to be user-friendly and have cut down our project configuration time considerably. The web interface saves time in not having to lug a laptop out to the field to make changes and the user manuals are straight forward and informative.