HVAC-Talk site will be slow for the next few days. It's normal site/server maintenance. Thx -Dad

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

ICE-Con burner setup questions...

An En Mar model HTDM mua unit.

I've got this Canadian made gas fired make-up air unit with a modulating burner. The combustion fan motor is speed controlled, along with the main gas valve (2-10vdc) from a version two ICE-con board.
We replaced the heat exchanger and now the burner rumbles a bit in the middle of the modulation. Apparently version 1.7b of the software can be use to set the 6 steps in the burner operation. Each step burns hotter, air and gas are increased, the fan RPM ramps up too. Each step is tested with a combustion analyser to assure good burning. This is the procedure for fine-tuning the burner.

My question is:
The software sets up gas and RPM but the fan speed can't be dialed in with the RPM desired, only a factor number like 42.3 and so on is changed. The board then changes that to an RPM.

I started this on Friday and found the process tedious and frustrating, all trial and error.

A done deal...

A day and a half on a roof with a frozen laptop, frozen fingers, and every mistake you can make, I managed to set up 6 stages of burner operation from Min to Max and then run it past the combustion analyser for the last check. Passed. It can be done, but it's not pretty.

A day and a half on a roof with a frozen laptop, frozen fingers, and every mistake you can make, I managed to set up 6 stages of burner operation from Min to Max and then run it past the combustion analyser for the last check. Passed. It can be done, but it's not pretty.

D.

Too bad it was so cold.
Sounds like a good setup to cut your teeth on.
Havn't seen or heard of that unit.
The last dc burner setup I did was for a school, got slapped around for a bit but in the end the boiler gave in!

ice con cable and software...

I think I tried 4 or 5 nine-pin cables Mini sub D type and finally found one to work. You'll need a gender bender too.
There's some software for it with minimal help, but once you get it going, it's a breeze to set the steps of combustion and fan and gas and I had a combustion analyser in the stack to make sure my settings were valid. Trick was to get past a burner rumble at the 2/3 range.

All this sitting on a milk crate at minus 5C outside. Laptop must be plugged in for an hour and on city power to keep it from freezing up.

I'll try to dig up the software and pass it on to you. Not proprietary so don't anyone get their knickers in a knot.