➔ Wired LIT-Touch control panel in glossy black or pearl white for wall mounting installation.
➔ Wall mounted LIT-Touch remote control and receiver with air temperature probe and operation LED.
For on board installation
➔❖ LIT-Touch electronic control for 2-pipe systems, with 2 pipes with electrical resistance or 4 pipes, complete with a minimum water temperature probe, ON/OFF valve control and integrated master/slave function up to a total of 15 units.
➔❖ Additional board with 2 digital outputs that can be configured.
➔❖ On board air temperature probe.
➔❖ RS485 serial board for serial communication with other devices (Modbus RTU protocol).

Key: ❖ Factory fitted
➔ Supplied separately
* Previous name

YARDY-DUCT2 CXP

❶

Total cooling capacity [EN1397]

kW

kW

kW

kW

kW

kW

❷

Heating capacity (45°C) [EN1397]

kW

kW

kW

kW

kW

kW

❸

Heating capacity (50°C)

kW

kW

kW

kW

kW

kW

❹

Heating capacity (70°C) [EN1397]

kW

kW

kW

kW

kW

kW

❺

Heating capacity of additional coil (65°C) [EN1397]

kW

kW

kW

kW

kW

kW

❹

Heating capacity of additional coil (70°C) [EN1397]

kW

kW

kW

kW

kW

kW

Available static Air flow rate / Pressure

m³/h

m³/h

m³/h

m³/h

m³/h

m³/h

❻

Delivery sound power

dB(A)

dB(A)

dB(A)

dB(A)

dB(A)

dB(A)

❼

Delivery sound pressure

dB(A)

dB(A)

dB(A)

dB(A)

dB(A)

dB(A)

Absorbed power

W

W

W

W

W

W

Electrical supply

V-ph-Hz

DIMENSIONS AND WEIGHTS

L - Width

mm

H - Height

mm

P - Depth

mm

Weight

kg

40

48

50

60

74

80

88

1,9

E

2,22

E

2,59

E

3,47

E

4,43

E

4,83

E

5,69

E

1,76

E

2,06

E

2,39

3,33

4,26

4,61

5,53

1,5

1,69

2,25

E

3,18

E

4

E

4,38

E

5,42

E

1,35

E

1,57

E

1,94

3,01

3,78

4,17

5,2

1,24

1,44

1,7

E

2,65

E

3,41

E

3,91

E

4,94

E

1,07

1,25

1,3

2,42

3,14

3,86

4,8

2,1

E

2,15

E

3

E

4,11

E

4,18

E

5,77

E

6,12

E

1,9

E

1,97

E

2,77

3,92

3,98

5,62

5,8

1,53

1,59

2,6

E

3,69

E

3,75

E

5,51

E

5,74

E

1,4

E

1,46

E

2,16

3,49

3,54

5,3

5,45

1,27

1,33

1,85

E

3,21

E

3,26

E

4,78

E

5,1

E

1,11

1,16

1,55

2,94

2,98

4,61

5,06

2,44

2,53

3,44

4,74

4,98

6,68

7,16

2,21

2,32

3,21

4,52

4,75

6,51

6,84

1,8

1,89

2,99

4,29

4,5

6,37

6,76

1,65

1,73

2,52

4,05

4,25

6,13

6,44

1,5

1,58

2,14

3,7

3,89

5,53

6,04

1,3

1,37

1,79

3,39

3,56

5,35

5,99

4,18

4,3

5,98

8,21

8,5

11,48

12,21

3,78

3,94

5,54

7,84

8,1

11,2

11,63

3,07

3,2

5,22

7,44

7,67

10,98

11,52

2,82

2,93

4,35

7,04

7,24

10,56

10,98

2,56

2,67

3,74

6,48

6,65

9,52

10,32

2,22

2,31

3,11

5,95

6,08

9,2

10,26

1,97

E

1,87

E

3,18

E

3,78

E

3,6

E

4,64

E

4,42

E

1,84

E

1,75

E

2,99

3,75

3,58

4,45

4,24

1,7

1,61

2,83

E

3,62

E

3,42

E

4,36

E

4,14

E

1,5

E

1,43

E

2,5

3,52

3,36

4,25

4,05

1,41

1,34

2,23

E

3,42

E

3,22

E

4,16

E

3,95

E

1,27

1,21

1,89

3,32

3,15

4,04

3,85

2,29

2,18

3,67

4,27

4,07

5,24

4,99

2,14

2,04

3,42

4,24

4,04

5,03

4,79

1,97

1,87

3,27

4,09

3,9

4,93

4,69

1,75

1,66

2,87

3,99

3,8

4,81

4,58

1,63

1,55

2,58

3,88

3,7

4,7

4,47

1,47

1,4

2,18

3,8

3,61

4,57

4,35

275 / 56

E

275 / 56

E

450 / 69

E

620 / 66

E

620 / 66

E

912 / 62

E

862 / 62

E

250 / 50

E

250 / 50

E

411 / 58

587 / 59

587 / 59

858 / 54

828 / 54

198 / 33

198 / 33

382 / 50

E

539 / 50

E

539 / 50

E

820 / 50

E

800 / 50

E

180 / 19

E

180 / 28

E

315 / 36

504 / 44

504 / 44

772 / 45

759 / 45

163 / 16

163 / 24

270 / 26

E

445 / 34

E

445 / 34

E

715 / 39

E

708 / 39

E

140 / 9

140 / 18

210 / 19

402 / 28

402 / 28

685 / 35

680 / 35

50

E

50

E

48

E

56

E

56

E

57

E

57

E

48

E

48

E

46

55

55

55

55

43

43

45

E

54

E

54

E

54

E

54

E

42

E

42

E

42

51

52

53

53

38

38

40

E

50

E

50

E

51

E

51

E

37

37

38

48

46

50

50

41

41

39

47

47

48

48

39

39

37

46

46

46

46

34

34

36

45

45

45

45

33

33

33

42

43

44

44

29

29

31

41

41

42

42

28

28

29

39

37

41

41

68

E

71

E

94

E

128

E

135

E

154

E

171

E

60

E

63

E

78

120

126

134

134

41

43

71

E

91

E

95

E

127

E

127

E

36

E

38

E

60

88

93

109

109

32

34

49

E

84

E

89

E

105

E

105

E

27

28

39

77

80

91

91

230-1-50

230-1-50

230-1-50

230-1-50

230-1-50

230-1-50

230-1-50

40

48

50

60

74

80

88

950

950

1250

1250

1250

1250

1250

545

545

545

545

545

545

545

212

212

212

212

212

212

212

25,5

27

34,5

34,5

35,5

36,5

37,5

Data at the following conditions:

❶

Air: 27°C D.B.; 19°C W.B. - Water: 7/12°C.

❷

Air: 20°C - Water: 45/40°C.

❸

Air: 20°C - Water: 50°C, flow rate as in cooling.

❹

Air: 20°C - Water: 70/60°C.

❺

Air: 20°C - Water: 65/55°C.

❻

According to EN16583

❼

For room volume equal to 100 m³ and reverberation time = 0.5 sec.

E

Eurovent certified performance.

YARDY-DUCT2 48 - 74 - 88 with oversized 4-row coil.

For the selection with Air’Suite filter please refer to UP-TO-DATE selection software.