Insulated conductors are cabled with a bare ground wire, interstices are filled with suitable non-hygroscopic fillers, as required
A binder tape of synthetic material assembles the core in an essentially round configuration

Spec Ground

Bare compact stranded AA-8000 series aluminum alloy (ACM)

Armor

Aluminum interlocked armor

Power lighting, control and signal circuits and as branch circuits and power feeders in industrial, commercial, institutional and residential installations up to 600 volts

Fished or embedded in plaster and concrete except in damp or wet locations

Concealed or exposed applications

Cable trays and other raceways

Under raised floors of information technology rooms

Environmental air-handling spaces per NEC Article 300.22 (C)

Places of Assembly per NEC Article 518.4 and theaters per NEC Article 520.5

Suitable for use in hazardous locations: Class I and II, Division 2 as well as Class III, Division 1 and 2

UL 1569

Meets UL 44, XHHW-2 600 V conductors

Cable Tray Rated

NEC Article 330 (can be messenger supported)

RoHS Compliant

Questions & Answers

Ask a Question

Name Required Field

Email Required Field

Question Required Field

Part Number Table

Part #

Gauge

Conductors

Insulation Thickness

Nominal OD over Armor

Material Weight (Lbs./M')

MCA10603

6

3

.045

.776

210

MCA10403

4

3

.045

.876

285

MCA10203

2

3

.045

1.008

396

MCA10103

1

3

.055

1.124

503

MCA11/003

1/0

3

.055

1.198

586

MCA12/003

2/0

3

.055

1.285

687

MCA13/003

3/0

3

.055

1.388

814

MCA14/003

4/0

3

.055

1.499

992

MCA125003

250

3

.065

1.781

1172

MCA135003

350

3

.065

1.859

1521

MCA140003

400

3

.065

1.951

1709

MCA150003

500

3

.065

2.248

2249

MCA175003

750

3

.080

2.68

3213

Note: The data shown are approximate and subject to standard industry and manufacturer tolerances