ASF Leak Detector Type "VAKUMATIK III F R325" - VACUUM PRINCIPLE

Article No.: 4121 0030 (Basic Unit)

Applications

The leak detector can be used on double-walled tanks according to DIN EN 12285-1 (DIN 6608 Part 2), DIN EN 12285-2 (DIN 6616 Form A), DIN 6618 part 2/4, DIN 6619 Part 2, DIN 6623 Part 2 and DIN 6624 Part 2.

DIN 6608 Part 2 containers that were previously monitored by liquid leakage can be monitored with this vacuum leak detector after extracting a specified volume.

The leak detector can also be used to monitor single-walled tanks with a leak protection lining, if it is approved for the values noted below.

For monitoring of water-polluting liquids and flammable liquids with a flash point > 55°C.

The storage medium may only have the density allowed for the container type.

The leak detector must be mounted outside the hazardous area (ex-zone)!

Product images

Operating Conditions

The media list in the technical description must be observed.

The leak protection lining in single-walled tanks must have a general building approval (certificate earlier).