Alex R.
Job Checkin

Dear Mike,
Thank you for choosing Fire Pros, Inc. as your fire protection service provider. We propose an additional trip back to this location to fix the deficiencies found during our latest inspection/service call of your fire alarm system. Our technician found a number of audio/visual devices (horn/strobes) not working at all. They traced the problem back to a bad "signal" card inside the main control panel. This devices needs to be replaced to have the output voltage to fire the horn/strobes.
The specific parts needed and the investment schedule is listed below.
FIRE PROS, INC. is fully insured and licensed. We are able to provide fast efficient 24-hours a day service. Our customer service philosophy is to provide the assurance that your building and those you employ and serve are protected by properly maintained and code compliant fire protection equipment.
We appreciate your kind consideration of our proposal and welcome the opportunity to submit future proposals for any other fi

Matthew B.
Job Checkin

Fire Sprinkler System: The Air Compressor for the Pre-Action system is seized up and will no longer operate - replace
Fire Sprinkler System: (3) Outdated System Pressure Gauges on the Pre-Action system located in mechanical room across from gym by pool reception office - replace