Telescopic Hot Stick

Our HV brake pull-rods are widely used for power equipments, lines and other power facilities of 10kv, 35kv, 63-110kv, 220kv and other voltage class. Telescopic hot stick classification: 1. Extendible: Telescopic hot stick is designed in 3 sections and 6m length, which is light in weight, small...

Our HV brake pull-rods are widely used for power equipments, lines and other power facilities of 10kv, 35kv, 63-110kv, 220kv and other voltage class.

Telescopic hot stick classification:

1. Extendible: Telescopic hot stick is designed in 3 sections and 6m length, which is light in weight, small in volume, portable and easy for use, and can be extended to any length in the used space, thus having effective overcome the shortcoming of screw type rod that is inconvenient for use due to fixed length.

2. The brake pull-rod is classified by voltage class as below:

10 KV、35KV、110KV、220KV。

Features:

High Voltage Telescopic Hot Stick is designed in 3 or 4 sections and 6m length, which is light in weight, small in volume, portable and easy for use, and can be extended to any length in the used space, thus having effective overcome the shortcoming of screw type rod that is inconvenient for use due to fixed length.

Model

Rated operating voltage（kv）

Effective insulation length（mm）

1min power-frequency withstand voltage test

Allowable load（N·m）

Minimum failure load（N·m）

Total length（mm）

Number of sections

LK­—1

10kv below

≥700

100kv

≮110

＞330

2000

2

LK­—2

35kv

≥900

150kv

≮110

＞330

3000

3

LK­—3

63~110kv

≥1300

250kv

≮110

＞330

4000

4

LK­—4

220kv

≥2100

450kv

≮110

＞330

4500

3

The series of hot stick are composed of an end metal head, an insulating rod, a middle joint head and a tail end sealing member. The whole set of operating rods are equipped with different specifications of moisture-proof and rain-proof packaging bags, and are accompanied by the product certificate.