Motors: Heavy duty, PSC, direct drive high efficiency and designed for use with SCR controllers. Motors permanently lubricated for long lif and have thermal over load protection. Motor has double insulation protection for quieter operation. Quick disconnects supplied to accommodate easy installation and service of motor

SCR Speed Controller: Supplied on all units compatible with the motor with a low end adjustment for air volume control and savings in power consumption.

UPC
686334

Unit
Width

Model
Number

Motor
HP

Standard
Unit

671200

36"

CF-36

1/2

671217

48"

CF-48

1/2

671224

60"

CF-60

1/2

Heavy
Duty
Unit

671231

36"

CFHD36

3/4

671248

48"

CFHD48

3/4

671255

60"

CFHD60

3/4

Ordering Style Number Summary for Air Curtains

Style
Number

Size

Models
Required

Ft./Min
Hi-Lo

CFM @
Nozzle

Volts

RPM
Hi-Lo

Amps
Hi-Lo

Watts
Hi-Lo

Shipping
Wt. lbs.

1/2 HP Models - up to 10 ft. high doorways

----

36"

CF36

3288 / 455

2672 / 333

115

1659 / 620

3.9 / 3.4

472 / 154

74

----

48"

CF48

4168 / 786

4515 / 766

115

1605 / 583

4.4 / 3.6

519 / 189

82

----

60"

CF60

4168 / 764

6544 / 931

115

1636 / 562

4.4 / 3.8

509 / 199

90

CF72

72"

2 ea. CF36

3288 / 455

5344 / 666

115

1659 / 620

7.8 / 6.8

944 / 308

148

CF96

96"

2 ea. CF48

4168 / 786

9030 / 1532

115

1606 / 583

8.8 / 7.2

1038 / 378

164

CF108

108"

3 ea. CF36

3288 / 455

8016 / 999

115

1659 / 620

11.7 / 10.2

1416 / 462

222

CF120

120"

1 ea. CF48
2 ea. CF36

4168 / 786
2672 / 333

9859 / 1432

115

1606 / 583
1659 / 620

12.2 / 10.4

1982 / 497

230

3/4 HP Models - up to 12 ft. high doorways

----

36"

CFHD36

3288 / 1120

2672 / 819

115

1689 / 603

4.4 / 4.3

603 / 192

77

----

48"

CFHD48

4256 / 929

4611 / 906

115

1662 / 500

5.9 / 4.8

586 / 168

85

----

60"

CFHD60

4256 / 924

5763 / 1126

115

1652 / 509

5.2 / 4.4

708 / 172

93

CFHD72

72"

2 ea. CFHD36

3288 / 1120

5344 / 1638

115

1689 / 603

8.8 / 8.6

1206 / 384

154

CFHD96

96"

2 ea. CFHD48

4256 / 929

9222 / 1812

115

1662 / 500

11.8 / 9.6

1172 / 336

170

CFHD108

108"

3 ea. CFHD36

3288 / 1120

8016 / 2457

115

1689 / 603

13.2 / 12.9

1809 / 576

231

CFHD120

120"

1 ea. CFHD48
2 ea. CFHD36

4256 / 929
3288 / 1120

9955 / 2544

115

1662 / 500
1689 / 603

14.7 / 13.4

2981 / 552

239

Heater Modules for TPI Air Curtains

All heating sections are constructed with totally enclosed, fin tubular elements. With heating section installed, unit becomes a 24 V control unit and can utilize low voltage thermostat for control of heating.

Note: For 72" through 120" units, order multiple heater modules corresponding to the actual air curtain models used.

Heater Specifications

AMPS

208/1

208/3

240/1

240/3

277/1

480/3

14.4

8.3

12.5

9.0

10.8

3.6

24.0

13.8

20.8

12.0

18.0

6.0

36.0

20.8

21.2

18.0

27.0

9.0

NA

27.7

41.6

24.0

36.1

12.0

NA

33.3

NA

28.8

43.3

14.4

NA

41.6

NA

36.0

NA

18.0

Heater Number

CFHTR

CFHTR

CFHTR

Heater Width

36"

48"

60"

Electrical Specifications

Heating
Section

Volts

Phase

Heater
Amps

Minimum
Circuit
Amps

Maximum
Fuse
Amps

75ºC
Wire
AWG

3 KW

208

3

8.3

10.4

15

14

240

7.2

9.0

15

14

480

3.6

4.5

15

14

277

1

10.8

13.5

15

14

208

14.4

18.0

20

12

240

12.5

15.6

20

12

5 KW

208

3

13.8

17.25

20

12

240

12.0

15.0

20

12

480

6.0

7.5

15

14

277

1

18.0

22.5

25

10

208

24.0

30.0

35

8

240

20.8

26.6

30

10

7.5 KW

208

3

20.8

26.0

30

10

240

18.0

22.5

25

10

480

9.0

11.3

15

14

277

1

27.0

33.8

40

8

208

36.0

45.0

50

6

240

31.2

39.0

45

8

10 KW

208

3

27.7

34.4

40

8

240

24.0

30.1

35

8

480

1

12.0

15.0

20

12

277

36.1

45.1

50

6

240

41.6

52.0

60

6

12 KW

208

3

33.3

41.6

45

8

240

28.8

36.0

40

8

480

1

14.4

18.0

20

12

277

43.3

54.1

60

6

15 KW

208

3

41.6

52.0

60

6

240

36.0

36.0

55

6

480

18.0

18.0

30

10

Attic Fans

Gable Exhause Fan

Whole House Fan

Dome Ventilator

120 V motor / 1 phase

Safety fire link protected

Automatic adjustable thermostat

Partially asssembled (mounting tabs must be assembled)

15" diameter x 6" depth

4 mounting tabs on 16" centers

Two speed motors

Shutters automatically open when fan is turned on and close tightly when fan is turned off