Local Reviews for Kensington, MD

Great Service

Blackbelt - Kensington, MD171 days ago

Thank you for your 5 start rating of Daniel! We appreciate your time and look forward to working with you in the future! Have a Supreme day!

Overall Experience
5 / 5

Quality

Price

Convenience

101 days ago

Christopher A.

I replaced the outdoor fan motor and also replaced the defrost board and coil and ambient temperature sensors. Unit operating normal.
I called the office because the invoice did not transfer to the dispatch. I had customer sign just to acknowledge that the repair work was completed. Customer says the office has the card on file for billing.

Near Metropolitan Ave, Kensington,
MD20895

122 days ago

Christopher A.

I called Carrier tech support to help me confirm the exact cause of the unit freezing up. The defrost board is corrupt and it needs to be replaced along with the coil temperature sensor. There is no way to verify for sure the operation of the outdoor fan motor because it gets its voltage from the defrost board. I did verify that it had line voltage.
The part is covered under warranty but the labor is not as the 2 year full warranty expired in early January.
I spoke with the customer and Mr. Koehler will call the office if they decide to have the repair done.
Also I let Donna know that the customer is expecting a call from the office for payment as I could not collect over the phone and previously this is how the customers paid for any invoices.

Christopher A.

I replaced the filter in the basement unit and the filter in the return air grill for the attic unit. I operated the units on 100% v.s. heat pump heating and measured very good temperature rise. I forced the defrost cycle on both outdoor units and it cycled normal. I also ran units on aux heat to make sure it was working properly. I checked the electrical wiring and electrical systems, all are within specification. Units are working very well.
Customer called the office and asked about billing. Customer was told that the office would send an email to collect payment. I will let Donna know.

Near Metropolitan Ave, Kensington,
MD20895

172 days ago

Daniel M.

Replaced heat exchanger and inducer motor . Started system and checked operations . Supply air at 118 degrees and return air 74 degrees

Daniel M.

Replaced heat exchanger and inducer motor . Started system and checked operations . Supply air at 118 degrees and return air 74 degrees

Near Metropolitan Ave, Kensington,
MD20895

176 days ago

Daniel M.

Started all four Reznors heaters . Used two bottles of nitrogen to clean them out before starting them . Then I had to lite each pilot and test units . All four are working . Changed filters on furnaces in ceiling for front lobby area . Both at from 1994 and are working . Did a heat exchanger inspection and did not see a crack . Costumer has heat in training area and lobby are .

Daniel M.

Found both RTU unit with cracks/ breaches in the heat exchangers . Wrote up a quote sheet and put them into job documents. All the gas valves were shut off to Reznor heating and none were turned on . We need to come back and check all 4 reznor heaters. Need to schedule a time when they donâ€™t have classes I signed off for RJ because he was in the middle of instructing a class