This product is intended to replace mechanical contactors especially when switching is frequent. The smallest product width in the range is 2.13" (54mm) (3xDIN) and goes up to 2.84" (72 mm).

2-pole and 3-pole switching options are available. Switch ON occurs at the voltage zero cross and switch OFF occurs at the current zero cross. Apart from resistive and slightly inductive loads, the SSR is certified for motor switching with associated motor ratings. Varistors are integrated for output over-voltage protection. A green LED gives indication of control voltage presence. Fan operation is controlled for the versions which have an integrated fan.

Detection of SSR overheat, mains loss, SSR malfunction and load loss is possible with the monitored (-M) versions. An EMR alarm output is available for remote signaling. An additional feature with the monitored (-M) is the electronic auxiliary output. The monitored (-M) has additional LED's for load status and alarm status indication.

Specifications are at a surrounding temperature of 25°C unless otherwise specified.

2-pole & 3-pole AC switching solid state contactors

Product width up to 2.84" (72 mm)

Rated operational voltage: up to 600 VAC

Rated operational current: up to 75 AAC

Control voltages: 5-32 VDC, 20-275 VAC (24-190 VDC)

Up to 15,000A²s for l²t

Motor ratings up to 11 kW @ 400 VAC, 25 HP @ 600 VAC

Integrated varistor protection on output

Optional monitoring for SSR and load malfunction

EMR alarm output and auxiliary output

Controlled fan operation for versions with integrated fan

UL, cUL Listing

100 kA Short Circuit Current Rating according to UL 508

DIN or panel mount

RoHS compliant

Line & Load accepts: 10-14 AWG (20 & 25 units)

Line & Load accepts: 3-14 AWG (30, 40, 65 & 75 units)

Motor Ratings: HP (UL 508) / kW (EN/IEC 60947-4-2) @ 40°C

2PSS60A25
2PSS60D25

115 VAC
1½ HP / 1.1 kW

230 VAC3 HP / 3.0 kW

400 VAC5 HP / 5.5 kW

480 VAC7½ HP / 5.5 kW

600 VAC10 HP / 9.0 kW

2PSS60A40
2PSS60D40

115 VAC3 HP / 1.5 kW

230 VAC5 HP / 4.0 kW

400 VAC10 HP / 7.5 kW

480 VAC10 HP / 9.0 kW

600 VAC15 HP / 11 kW

2PSS60A75
2PSS60D75

115 VAC5 HP / 3.0 kW

230 VAC10 HP / 7.5 kW

400 VAC15 HP / 11 kW

480 VAC20 HP / 15 kW

600 VAC25 HP / 22 kW

3PSS60A203PSS60D20

115 VAC
1 HP / 0.75 kW

230 VAC3 HP / 2.2 kW

400 VAC5 HP / 4.0 kW

480 VAC7½ HP / 5.5 kW

600 VAC10 HP / 7.5 kW

3PSS60A253PSS60D25

115 VAC2 HP / 1.1 kW

230 VAC3 HP / 2.2 kW

400 VAC7½ HP / 4.0 kW

480 VAC10 HP / 5.5 kW

600 VAC10 HP / 7.5 kW

3PSS60A303PSS60D30

115 VAC2 HP / 1.5 kW

230 VAC5 HP / 3.0 kW

400 VAC10 HP / 5.5 kW

480 VAC10 HP / 7.5 kW

600 VAC15 HP / 11 kW

3PSS60A403PSS60D40

115 VAC2 HP / 1.5 kW

230 VAC5 HP / 4.0 kW

400 VAC10 HP / 7.5 kW

480 VAC10 HP / 9.0 kW

600 VAC15 HP / 11 kW

3PSS60A653PSS60D65

115 VAC3 HP / 3.0 kW

230 VAC10 HP / 5.5 kW

400 VAC15 HP / 11 kW

480 VAC20 HP / 15 kW

600 VAC25 HP / 20 kW

Filtering - EN/IEC 55011 Class A Compliance

2PSS60.25
220 nF / 760V / X1
Max. heater AAC 25

2PSS60.40330 nF / 760V / X1
Max. heater AAC 40

2PSS60.75470 nF / 760V / X1
Max. heater AAC 65

3PSS60.20
220 nF / 760V / X1
Max. heater AAC 25

3PSS60.25
330 nF / 760V / X1
Max. heater AAC 25

3PSS60.30470 nF / 760V / X1
Max. heater AAC 30

3PSS60.40470 nF / 760V / X1
Max. heater AAC 40

3PSS60.65470 nF / 760V / X1
Max. heater AAC 65

Fusing / Short Circuit Protection

Co-ordinationType 1 (UL508): Suitable For Use On A Circuit Capable Of Delivering Not More Than 100,000 A rms Symmetrical Amperes, 600 Volts Maximum when Protected by Class J Fuses. Use Fuses Only. Tests with Class J fuses are representative of class CC fuses