Packaging & Delivery

Packaging Details:

One piece hybrid pv inverter is packed by one carton box

Delivery Detail:

Within 3 days

Prostar MixSolar is a hybrid inverter which combines solar system, AC utility, and battery power source to supply continuous power. It is suitable for the remote areas where the cost of utility is too high or emergency usage when utility is not stable.

MixSolar is a flexible and intelligent hybrid inverter which utilizes solar power, AC utility, and battery power source to supply continuous power. It’s a simple and smart solar power storage system for home users to either store energy into battery and wait for night time usage or use for self-consumption first depending on demands. Priority for power source can be programmed and set up through smart software. During night time or power failure, it will automatically extract power from battery. In this way, it will reduce the dependence on the utility.

Product Description

Inverter Datasheet

Model

MixSolar MIS5KW

PHASE

Single Phase in, Single Phase out

Max. PV INPUT POWER

10000W

Rated Output Power

5000W

Maximum Charging Power

4800W

Dimension, D x W x H (mm)

204 x 460x 600

Net weight (kgs)

29

GRID-TIE OPERATION

PV INPUT (DC)

Nominal DC Voltage/Max. DC Voltage

720 VDC/900 VDC

Start-up Voltage/Initial Feeding Voltage

225 VDC/250 VDC

MPP Voltage Range

250 VDC~850 VDC

Number of MPP Trackers

2/2x10A

Maximum Input Current

GRID OUTPUT (AC)

Nominal Output Voltage

208/220/230/240 VAC

Output Voltage Range

184 -265 VAC*

Nominal Output Current

21A

Power Factor

>0.99

EFFICIENCY

Maximum Conversion Efficiency (DC/AC)

96%

European Efficiency@Vnominal

95%

OFF-GRID OPERATION

AC INPUT

AC start-up Voltage/

120-140 VAC/180 VAC

Auto Restart Voltage

Acceptable Input Voltage Range

170-280 VAC

Max. AC Input Current

40A

PV INPUT (DC)

Max. DC Voltage

900 VDC

MPP Voltage Range

250 VDC~850 VDC

Number of MPP Trackers/Max. Input Current

2/2x10A

BATTERY Mode Output (AC)

Nominal Output Voltage

202/208/220/230/240 VAC

Output Waveform

Pure Sinewave

Efficiency (DC to AC)

93%

HYBRID OPERATION

PV INPUT (DC)

Nominal DC Voltage/Max. DC Voltage

720 VDC/900 VDC

Start-up Voltage/Initial Feeding Voltage

225 VDC/ 250 VDC

MPP Voltage Range

250 VDC~ 850 VDC

Number of MPP Trackers/Max. Input Current

2/2x10A

GRID OUTOUT (AC)

Nominal Output Voltage

202/208/220/230/240 VAC

Output Voltage Range

184-264.5 VAC*

Nominal Output Current

21A

AC INPUT

AC Start-up Voltage/Auto Restart Voltage

120-140 VAC/180 VAC

Acceptable Input Voltage Range

170-280 VAC

Max. AC Input Current

30A

BATTERY MODE OUTPUT (AC)

Nominal Output Voltage

202/208/220/230/240 VAC

Efficiency (DC to AC)

93%

BATTERY& CHARGER

Nominal DC Voltage

48 VDC

Max. Charging Current

Default 60A, 5A-100A (Adjustable)

INTERFACE

Communication Port

RS-232/USB

Intelligent Slot

Optional SNMP, Modbus and AS-400 cards available

ENVIRONMENT

Humidity

0~90% RH (Non-condensing)

Operating Temperature

0 to 40 °C

Altitude

0-1000 m**

*These figures may vary depending on different AC voltage and country requirements.