Main menu

You are here

P-ION Sedona Programmable Controller

General

P-ION series products are universal programmable controllers that can be used to manage a variety of building systems including heating, ventilation, air-conditioning (HVAC) systems. Basic and advanced control strategies can be programmed by Sedona Framework™ for optimized performance.

Universal Inputs

All universal inputs can be configured as analog or voltage free digital inputs.

All inputs are protected against short circuits to ground and against direct connection up to 50 VAC.

Flex Points

All flex I/O points can be configured as analog output, digital input or pulse input.

Analog outputs are used to control 0(2)-10V valve and damper actuators, humidifiers, frequency drives, etc. Convertor relay boards can be used to drive on/off loads.

All outputs are protected against short circuits to ground and against direct connection up to 50 VAC.

Optional Relay Board Extension

Two relay modules (RK-4) can be connected by ribbon cable to provide a total of 8 additional relay outputs at 10A. Further RK4 relay modules can be driven by flex-outputs to convert analog outputs to relay outputs.

Developed by Tridium, the Sedona Framework™ is the industry's first, open source development framework that provides a complete software platform for developing, deploying, integrating, and managing pervasive device applications. It brings the power of programmable control and the Internet down to edge devices. The Sedona Framework distributes decision making control and manageability to any device and brings intelligence and connectivity to the network edge and back.