Power switch S2-R

Power switch S2-R - Wireless with integrated power consumption metering

This universal switching actuator allows you to switch any two electrical consumers/end devices (motors as well)
with a constant power draw of up to 500VA each. Topnotch and absolutely wear-free semiconductor switches (TRIACs)
guarantee a very long life span and silent switching. Perfectly suited for double light fixtures and double switches.

Integrated power consumption metering: This ubisys component from our smart home program allows you to register
the actual power requirements of the attached end devices. It will show you exactly how much any of the end devices
in your home consumed at any given time.

This component has two connections for end devices (output, load) and two connections for operating elements
(switch or push-button). Push-buttons can also be set up to regulate a group of lamps or even activate scenarios.

Invisible: The power switch S2-R is to be installed in the control box of the sub-distribution on a DIN rail.
The standardized design allows the replacement of an existing rail mount device (e.g. a relais) by the
smart power switch S2-R. A flush-mount version for the installation behind a light switch or a wall or ceiling outlet
is also available.

The wireless components used in the smart home system by ubisys are based on the international standards
IEEE 802.15.4 and ZigBee. This guarantees long term availability of all components thus protecting your investment.

Due to the resilient and innovative radio controlled technology there are no special skills needed when installed.
This solution not only makes it ideal for new buildings but also for redevelopments and renovations.
Additional components can be added and perfectly integrated into your smart home by and by.
This leaves the decision when and how extensively you want to expand your system entirely up to you.

And with the Over-the-Air (OTA) firmware upgrade this component — as well as all other smart home components —
will always stay up to date. This makes you well prepared for the future „Smart Grid”.

Technical specifications

Features

2 end devices switch

2 operating elements (push-button)

Consumption metering

Output (end device)

1: 230V~, 50Hz, 500VA

2: 230V~, 50Hz, 500VA

TRIAC

Standards

IEEE 802.15.4

ZigBee 3.0 Certified Product

Dimensions

Length:

90mm

Width:

18mm

Height:

60,5mm

Colour
Black

Material
Plastic

Weight
50g

Installation & box contents

Installation
Rail mount. Installation on a DIN rail in the sub-distribution.