Naser Machinery brings you quality and precise water cooled chiller not only as one of the best manufacturers but also one of the leading suppliers in China. With decades experience in exporting our quality products, we enjoy good reputation. You can easily wholesale our water cooled chiller made in China with our factory.

Model

Techinical Paramaters of Water Cooled chiller

Type

NWS-3WC

NWS-4WC

NWS-5WC

NWS-6WC

NWS-8WC

NWS-10WC

NWS-12WC

NWS-15WC

NWS-20WC

NWS-25WC

NWS-30WC

NWS-40WC

NWS-50WC

Rated Cooling capacity

50HZ

Btu/h

43870

53941

65105

85248

107882

130210

170495

195315

266292

303846

399438

152100

645246

KW

12.85

15.8

19.1

24.97

31.6

38.1

49.9

57.2

78

89

117

150

189

Kcal/h

11051

13588

16400.2

21474.2

27176

32800.4

42948.4

49200.6

67080

76540

100620

129000

162540

USRT

3.65

4.49

5.42

7.1

8.98

10.84

14.2

16.27

22.18

25.31

33.27

42.65

53.74

Power input

380V/3P/50HZ(optional)

Compressor

Compressor power

HP

3

4

5

6

8

10

12

15

20

25

30

40

50

Type

Hermostatic expansion valve

Flow regulator

capaillary /thermostatic expensinon valve

Condenser

Style

Hub pipe type

Water flow

M3/H

2.65

3.26

3.94

5.15

6.52

7.87

10.31

11.81

16.1

18.37

24.14

30.95

39

Diamater of nipple

DN

25

25

25

25

40

40

40

50

50

65

65

80

80

Refrigreant

R22 or R134A

Evaporator

Style

*Water tank type/Hub pipe type/SS plaste heat exchanger

Capacity

L

50

55

55

55

118

148

148

178

278

310

365

528

540

Standard freezing water flow

M3/H

2.21

2.72

3.28

4.29

5.43

6.56

8.59

9.84

13.41

15.3

20.12

25.79

32.5

Diameter of standard nipple

DN

25

25

25

25

40

40

40

50

50

65

65

80

80

Built-in pump

HP

0.5

0.5

1

1

1

1

1

2

2

3

3

5

5

Machine weight

KG

120

125

150

185

315

335

355

650

750

1050

1360

1390

1420

Measure

Length

MM

890

890

890

890

1200

1200

1200

1650

1650

1650

1800

2050

2050

Width

MM

500

500

500

500

700

700

700

710

710

710

710

980

980

Height

MM

840

840

840

840

1200

1200

1200

1650

1650

1650

1720

1800

1800

"*" means optional or customizable. Capacity based on voltage 380V/50Hz/3Ph.