Fixed issues with Mate3 connectivity to Optics that would cause connections to drop, large data spikes to appear, data stream and ModBus communication to go down periodically, DHCP enable/disable to not work correctly, and inverters getting deselected in Optics

Fixed issues with the internal Web page not loading, and conformed internal Web page version number to the firmware release version number for consistency

Fixed issue that caused a large number of on-site change events to post

Fixed issue that caused a firmware update error to appear in Event History

Fixed issue that caused saved settings of Upper Voltage Limit value of 256 and 258 to produce 0 and 2 respectively when restored

Fixed issue that could cause Setup Page Hold and Delay Settings to be off by a factor of ten

Fixed issue that could cause the AC Input LED to not light when AC input power is present

Fixed issue that could cause the GMT timestamp to be improperly set on certain startup conditions

Fixed issue that could cause very large numbers to appear in AC Input Current

Fixed issue that could cause distortion of characters in the LCD

Fixed issue that could cause a mismatch of settings for AC Amps between the status screen soft key and the Inverter AC Input and Current Limits settings

Fixed issue that could cause settings to revert to pre-load of a GIP file when Mate3 is power-cycled

Fixed issue that could cause settings changed locally on charge controllers (or while the charge controller was not connected to Optics) to not properly update Optics

Fixed issue that could cause AC Input Limits to display at 4x the actual setting for up to three minutes before the display updates to show the correct value

Fixed issue in the Profile Wizard that caused the scroll value to roll over from 60 to 0 without allowing the user to scroll back to 60, so the user would have to scroll from 0 up to 60 to effectively scroll back one

Fixed an issue that caused incorrect values to appear for input and output current and power for an FNDC

New Features:

Added support for SA-compliant inverters

Added support for the new OutBack FlexMAX 100 charge controller

Enhancements:

Updated internal Web page links to point to the new OutBack Power Web site resources

Improved replay functionality

Added support for data streams for FXR inverters

Improved some event history messages in Optics

Disabled Update key if no SD card is present or the SD card does not have a firmware image file. This prevents the inverter from shutting down in preparation for an update when no update is available in the SD card

Improved FXR support to discern between Grid (AC1) input and GEN (AC2) for reporting to Optics

Improved resolution of AC current settings and value display for FXR/Radian to two decimal places

Other Changes:

Removed "PF Priority" from the Multi-Function Parameter screen as it is no longer supported

Known Issues:

Unreliable data replay functionality.

Replay stores data on an SD card if the Mate3 becomes disconnected from Optics. On reconnection, the Mate3 uploads the data to Optics. We have improved the replay functionality, but some users may see a gap in the backfilled data, graphs, and event history on Optics. If you see this situation, please notify OutBack customer support

Issues causing the MATE to freeze after the lock button is pressed, freeze on the splash screen, or enter a reboot loop when the splash screen is reached are caused by corruption or failure of the NAND flash. These systems must be sent to OutBack for service

Known Issues: Unreliable data replay functionality which is responsible backfills data after a disconnect event has occurred. If the data fails to backfill, then there will be gaps of data missing in the graphing and event history sections of the application.

Additional Information: Fixed FTP client directory detection issue, DC only systems will now report a constant system voltage based upon the float voltage selection on charge controllers, improved detection of devices when devices are moved to different ports on HUB, improved reliability reporting of events to OPTICS, additional check added to ensure SD-Card is present before attempting to open files on SD card.