Transcription

1 September 2 2 A Binary 5D Product family: Product type: Manufacturer: Output Binary output, -fold Siemens Name: Load switch UP 5 Order no.: 5WG 5-2AB Functional description Using the application program 2 A Binary 5D, it is possible to define and delays, staircase lighting function (time switch), status response of the relay, behaviour on bus voltage failure and recovery, behaviour as a normally closed/normally open and logic operations. The switch actuator is an intelligent relay with bus capability. It has a switchable output and enables the switching of luminaires and other loads. Functions of the relay Switch Binary bus (EIS ) are converted into switching states (relay opened/relay closed) via the Switch object. The application changes the value of the Switch object during operation. It is not possible to read out the status of the relay via the Switch object. It should always be possible to read back the status via the Status object. The switching characteristic of the normal switching function can be modified by activation of functions with a higher priority (see Higher-order functions ). mode (normally closed / normally open ) It is possible to set the operation mode of the relay via the parameter mode on the General inputs parameter page. The relay can either be used as a normally closed or a normally open. The relay in the switch actuator UP 5 has a normally open. This can be operated logically (via software) as a normally closed. The relay position is thereby inverted. After bus voltage recovery, the relay is closed when the function of normally closed is selected. A status telegram is produced, provided that no other closing operation (e.g. due to a higher-order function, security function or behaviour on bus voltage recovery) switches the output to the open position. The fixed relay positions (open, closed) within the other functions are controlled directly. This behaviour is identical to that of the normally closed and normally open functions. The fixed relay position for the normally closed function is not inverted. Note: When the relay mode switches between normally closed and normally open, parameter settings and linked group addresses are reset to the basic settings. For this reason, the relay mode should be defined first. Time functions / delay The switching is carried out with a time delay. It is possible to set and delays separately. Delays between approx. 2.6 seconds to 52 hours can be assigned. The delay period is calculated by multiplying a base value with a factor. and delays can be set accordingly for switching operations. The set periods can be defined via parameters as not retriggerable or retriggerable. If a time delay is active and set to retriggerable, the delay period is restarted on receipt of a new telegram ( Switch object). If not retriggerable is selected, the relay closes immediately once the time has elapsed. If the output of the actuator is forced into a new switch position by a higher-order function (positive drive, blocking function, logic operation) during a delay period, the relay switches into this position immediately. The delay period is deleted i.e. when the higher-order switch function is deactivated, the time period that has already started does not continue. delay / time switch mode If the normally open function is selected, the device switches off automatically again after a period defined between 2.6 seconds and 52 hours, after it has been switched on via the Switch object. The delay period is calculated by multiplying a base value with a factor. If a telegram is received before the device is switched off, the interval is restarted (retriggerable). If the time switch mode is selected, an delay can also be activated (see timing diagram for delay). It can be set whether the receipt of a telegram switches the device off prematurely or whether the telegram is ignored and the staircase lighting timer continues (with/without manual function). If the output of the actuator is forced into a new switch position by a higher-order function (positive drive, blocking function, logic operation, security function) during a delay period, the relay switches into this position immediately. The delay period is deleted i.e. when the higher-order switch function is removed, the time period that has already started does not continue. If the closed relay position is triggered in the normally open mode once the higher-order function has finished, the staircase lighting timer starts. In the normally open mode, the staircase lighting function is activated with the setting opened. Siemens AG 5D, 2 pages Technical manual Electrical Installation Technology Siemens AG 2 Update: P.O. Box 9 53, D-939 Regensburg /

2 September 2 2 A Binary 5D Oscillator (blinking) The relay opens and closes automatically with the astable oscillator. The duration of the and periods can be set separately. The periods are calculated by multiplying a base value with a factor. The oscillator can be switched on and off via the bus with the help of a higher-order function (see Higher-order functions ). Note Attention should be paid to any heat development at the relay s due to rapid switching of the loads. This function does not exist in the normally closed relay mode. The Switch object is not available when the oscillator is switched on. Control is carried out by the higher-order function. Inverted time switch mode / delay: ce it has been opened (normally open ) with a telegram via the Switch object, the relay closes automatically again after a period defined between 2.6 seconds and 52 hours, after it has been switched on via the Switch object. The period is calculated by multiplying a base value with a factor. If a further telegram is received before the relay closes, the timer period is restarted (retriggerable). If a telegram is received while the staircase timer is running, it can be set whether the relay should only close once the remainder of the period has elapsed (without manual function) or immediately (manual function). This behaviour is exactly the opposite to that of a staircase lighting timer. If the inverted time switch mode is selected, it is also possible to activate an delay (see timing diagram for delay). If the output of the actuator is forced into a new switch position by a higher-order function (positive drive, blocking function, logic operation) during a delay period, the relay switches into this position immediately. The delay period is deleted i.e. when the higher-order switch function is removed, the time period that has already started does not continue. The staircase timer starts once the higher-order function has finished, if the closed relay position is triggered in the normally closed mode. In the normally open mode, the staircase lighting function is activated with the setting opened. Status message The switching state of the output as regards logic operations and time delays can be sent via a separate communication object to a display element (e.g. status LED). This means that after each switching operation, the status of the relay is available as a telegram on the bus. The value of the Status object always reflects the current relay state. The value is if the relay is closed and when the relay is open, regardless of the normally closed/normally open function. bus voltage recovery, a status telegram is sent via the Status object after 7 seconds if the relay is closed. A telegram is not generated however if the is open. Higher-order functions Logic operations (AND/OR logic function), positive drive and a blocking function can be selected via the Function parameter. It is only possible to select either one or none of these three functions. The higher-order function has the highest priority after behaviour on bus voltage failure and takes precedence over the other switchable functions in the switching characteristic of the actuator. Logic operations: With this functionality, the Switch object can be logically linked with the Logic operation object. Either an AND or OR function can be set. It is defined via a parameter whether the logic function should be activated immediately or on receipt of the first telegram to the Logic operation object. The logic function has the next highest priority after behaviour on bus voltage failure. The actuator will therefore always be set according to the logic result of the higher-order function and not according to the status of the functions with a lower priority. For example, if the OR function is set to active at once (the Logic operation object is immediately set to after initialisation), the actuator remains switched on after a reset until a telegram has been received at the Logic operation object. If behaviour on bus voltage recovery has been assigned, it is only carried out once the logic operation has finished. AND function If the Logic operation object is set to, switching operations can be carried out as usual via the address of the Switch object. Any specified delay intervals and time switch periods are observed. If the relay is opened via the Logic operation object, it has an immediate effect (object with a high priority). Any delays are no longer carried out. If the Logic operation object is then reset to by a telegram, the device is switched immediately even if there is an active delay. The behaviour of an activated staircase lighting timer can be taken from the table Behaviour on bus voltage recovery. Technical manual 5D, 2 pages Siemens AG Update: Siemens AG 2 Electrical Installation Technology P.O. Box 9 53, D-939 Regensburg /2

3 September 2 2 A Binary 5D The characteristic of the logic function can deviate from the normal AND function via the parameter state after a transition from to of the logic operation object. In the default setting preferring to logic operation, the AND function is carried out as required. The relay state can also be set to a fixed switch position (open/closed) when the value of the Logic operation object changes from to. This is a deviation from the AND function. Example: A closing lock-out can be implemented with an AND function. This means that it is not possible to switch the device on via the Switch object while the value of the Logic operation object is set at. If the value of the Switch object is set to, the device is automatically switched on (closed) when the value of the Logic operation object changes from to. If the automatic closing of the relay is not required however, the switch can be opened by selecting opens in the parameter state after a transition of to of the logic operation object. The logic operation does not become active until the Logic operation object of the switch actuator has received a telegram for the first time. For example, when a closing lock-out is implemented by an AND function after a reset, it is possible to carry out switching operations via the Switch object. The logic operation (closing lock-out) is only activated on receipt of the first telegram at the Logic operation object. The parameter setting Logic function active at once causes the Logic operation object to be set to. After a reset, the actuator will not switch the output to the normally open mode and these settings until a telegram has been received at the Logic operation object. OR function It is possible to carry out switching operations as usual via the address of the Switch object provided that the Logic operation object is set to. Any assigned delay periods are observed. Closing the relay via a telegram to the Logic operation object has an immediate effect (object with a high priority). A time delay is no longer carried out. If the value of the Logic operation object is then reset to the value, the actuator likewise switches to the required state without a delay. The behaviour of an activated staircase lighting timer can be taken from the table Behaviour on bus voltage recovery. The characteristic of the logic function can deviate from the normal OR function via the parameter state after a transition from to of the logic operation object. In the default setting preferring to logic operation, the OR function is carried out as required. The relay state can also be set to a fixed switch position (open/closed) when the value of the Logic operation object changes from to. Example: An opening lock-out or a central function (e.g. light for cleaning the building) can be implemented with an OR function. If the value of the Switch object is also locally set to, the relay remains closed when the lockout has been removed (change of the value of the Logic operation object from to ). This characteristic can be changed with the setting opens in the parameter state after a transition of to of the logic operation object and by switching off the output. The relay can only be closed via the Switch object if a telegram has been received via the Logic operation object. This logic operation also has no time delay. Note: The parameter setting Logic function active at once causes the Logic operation object to be set to the value. After a reset, the actuator will immediately switch the output to the normally open mode and these settings. The OR function is only reset by a telegram to the Logic operation object. Positive drive This signifies the conversion of 2 bit into highpriority switching states (relay open / relay closed). The positive drive function is activated if the 2 bit Positive drive object receives a telegram whose first bit (bit ) indicates the value. In this case, the switch actuator switches to the mode that has been defined by the second bit (bit 2) of the telegram. When operated as a normally open, a causes the relay to close while the relay is opened when operated as a normally closed. When operated as a normally open, a causes the relay to open while the relay is closed when operated as a normally closed. Using a parameter, it is possible to set the behaviour of the respective channel when the positive drive is removed (first bit (bit ) is set to ). The actuator can be switched on or off or follow the current state of the switching object. The positive drive function is carried out without a time delay. The behaviour of an activated staircase lighting timer can be taken from the table Behaviour on bus voltage recovery. Siemens AG 5D, 2 pages Technical manual Electrical Installation Technology Siemens AG 2 Update: P.O. Box 9 53, D-939 Regensburg /3

4 September 2 2 A Binary 5D Blocking function With the aid of the Blocking object, the switch actuator can be switched off functionally when the blocking function is assigned. When the blocking function is activated, are no longer converted via the Switch object into switching commands for the relay. The blocking function can be triggered by an or telegram ( active or active). With the parameter Default position, it is possible to define whether the blocking function is only activated once a blocking telegram has been received via the Blocking object or immediately after a reset. With the parameter state after blocking (no change / opens / closes), the output is switched to a defined position after blocking. Telegrams to the Switch object are received and stored. ce the blocking function is deactivated, this switching characteristic can be assigned to the relay with the setting preferring to switch object or a fixed state can be selected ( opens/ closes). Blocking function with switching delay / staircase lighting timer When the blocking function is activated, it always switches without a delay in the required direction. When it is deactivated, the actuator likewise switches immediately to the required state. The behaviour of an activated staircase lighting timer can be taken from the table Behaviour on bus voltage recovery. Behaviour on bus voltage recovery bus voltage recovery, the relay can assume the assigned state. In the setting as before bus voltage failure, the stored status object value is restored (see Behaviour on bus voltage failure ). If a time switch mode has been assigned, it is started depending on the following table. Function Parameter setting on voltage recovery Switch opens open / delay opens open Time switch mode (normally open ) opens open Time switch mode (normally closed ) Inverted time switch mode (normally open ) Inverted time switch mode (normally closed ) opens opens opens start time switch mode start time switch mode open Switch closes closed / delay closes closed Time switch mode (normally open ) Time switch mode (normally closed ) Inverted time switch mode (normally open ) Inverted time switch mode (normally closed ) Switch / delay Time switch mode closes closes closes closes as before bus voltage failure as before bus voltage failure as before bus voltage failure start time switch mode closed closed start time switch mode as before reset stored relay state as before reset stored relay state (without delay) The relay state that was stored before the reset behaves as in the parameter setting ( opens/ closes) Note: states that have been retrieved by functions with a higher priority (higher-order function and security function) have priority over the behaviour on bus voltage recovery. They have however the same function as described in the table. Technical manual 5D, 2 pages Siemens AG Update: Siemens AG 2 Electrical Installation Technology P.O. Box 9 53, D-939 Regensburg /4

5 September 2 2 A Binary 5D Security function The security function monitors the communication between a sensor and the switch actuator. When the security function is enabled, are expected from the sensor (e.g. binary input BE) at cyclical intervals within the set monitoring time. The monitoring time is calculated by multiplying a base value with a factor. If the device does not receive any from the sensor within this period, the actuator switches to the set safety position ( opened, closed or last safety object value). The sensor must be able to send cyclically with a cyclic interval that is shorter than the monitoring time. In addition to the cyclical monitoring function, the safety position can be activated by defined telegram values. If the security function is interrupted by a higher-order function (logic operation, blocking function, positive drive), the monitoring time is not deleted but continues for the remainder of the period once the higher-order function has been deactivated. If the actuator receives a telegram at the Safety object while a higher-order function is active, it does not evaluate the telegram until the higher-order function has been removed. Note: After a reset, the security function is immediately activated and the actuator switches into the safety position. Before the first switching operation can be carried out via the Switch object, the monitoring time must be started (telegram to the Safety object). If however a higherorder function is selected with the setting active at once, the security function can be deactivated until reach the Safety object via the bus and the security function is operating normally. Assigning parameters to the relays Switch Communication objects Obj Function Object name Type Flags / Status Bit CRT The current switching state of the channel is stored in this object. The object value is dependent on the switching to the Switch object and on the status of the Logic operation and Positive drive objects. No are sent when there is a change in the object value. The switching state can be read out via the ETS or via a visualisation unit. / Switch Bit CW The switching output of the relay is addressed via this object. The application changes the value of the Switch object during operation. Reading out the Switch object via the bus does not reproduce the relay state. The status should always be read back via the Status object. Positive drive object Logic operation object Blocking object Resetting times and redefinition of switching object Higher-order function Bus voltage failure object Switch and time logic Bus voltage recovery Security function Safety object Redefinition of switching object Status object Maximum number of group addresses: 22 Maximum number of associations: 22 Siemens AG 5D, 2 pages Technical manual Electrical Installation Technology Siemens AG 2 Update: P.O. Box 9 53, D-939 Regensburg /5

6 September 2 2 A Binary 5D Function None Logic operations Positive drive Blocking function In the case of the higher-order functions, it is possible to select logic operations, positive drive, blocking function or no function. The higher-order function has the highest priority after the behaviour on bus voltage failure and takes precedence over the other switchable functions in the switching characteristic of the actuator. mode normally open normally closed The operating mode of the relay can be set here. The relay can be used either as a normally open or a normally closed. Status message The current switching state of the channel is stored in this object. The object value is dependent on the switching to the Switch object and on the status of the Logic operation and Positive drive objects. No are sent when there is a change in the object value. The switching state can be read out via the ETS or via a visualisation unit. Behaviour on bus voltage failure opens closes no action The behaviour of the relay on bus voltage failure is set here. no action : failure of the bus voltage, the relay maintains its current switching state. closes : bus voltage failure, the relay is closed with the parameter setting mode: normally open and opened with the setting mode: normally closed. opens : bus voltage failure, the relay is opened with the parameter setting mode: normally open and closed with the setting mode: normally closed. Behaviour on bus voltage recovery opens closes as before bus voltage failure The behaviour of the relay on bus voltage recovery can be set here. The settings only refer to the Switch object. as before bus voltage failure : The behaviour on bus voltage recovery is influenced by the parameters Logic operation and Default position. If no logic operations are active, the relay maintains its current switching state. closes : The parameter Behaviour on bus voltage recovery influences the behaviour on recovery of the voltage. If no logic operation is active, the relay is closed in the parameter setting mode: normally open and opened in the setting mode: normally closed. opens : The parameters Logic operation and Default position influence the behaviour on recovery of the voltage. If no logic operation is active, the relay is opened with the parameter setting mode: normally open and closed with the setting mode: normally closed. Limit number of 3 per 7 sec. 6 per 7 sec. per 7 sec. 27 per 7 sec. The number of that are sent can be set in this parameter. Security function Communication objects Obj Function Object name Type Flags 3 / Safety Bit CW The security function monitors the communication between the sensor and switch actuator. The security function can be switched on and off via the parameter. Technical manual 5D, 2 pages Siemens AG Update: Siemens AG 2 Electrical Installation Technology P.O. Box 9 53, D-939 Regensburg /6

7 September 2 2 A Binary 5D Factor for monitoring time (5 27) The monitoring time is set in these parameters. The time is calculated from the selected base multiplied by the factor that is entered here. Note: An attempt should always be made to set the required time with the smallest possible base as the base that is selected here also simultaneously specifies the maximum timing error. 72 Security function The security function can be switched on and off via this parameter. Start security position by telegr. or missing cyclical telegr. or missing cyclical missing cyclical or The security function monitors the communication between a sensor and the switch actuator. It is possible to select here how the safety position is triggered: The options are: telegr. or missing cyclical telegr. or missing cyclical missing cyclical or It can be set via this parameter when the safety position is triggered. Safety position closed opened preferring to last security object value If the device does not receive any from the sensor within the set monitoring time, the actuator switches to the set safety position. It is possible to choose between opened, closed and preferring to last security object value. Base for monitoring time. seconds 2. seconds 4.2 seconds 8.4 seconds 7 seconds 34 seconds. minutes 2.2 minutes 4.5 minutes 9 minutes 8 minutes 35 minutes.2 hours Time functions Time functions none / delay Time switch mode Oscillator (blinking) Inverted time switch mode Via this parameter, it is possible to select the s / delay, Time switch mode, Oscillator (blinking), Inverted time switch mode and no. If none is selected, the parameters for setting the delay periods are no longer displayed. delay The delay can be switched on and off via this parameter. If the function is disabled, the parameters for setting the delay periods are no longer displayed. Siemens AG 5D, 2 pages Technical manual Electrical Installation Technology Siemens AG 2 Update: P.O. Box 9 53, D-939 Regensburg /7

8 September 2 2 A Binary 5D Base for delay 52 milliseconds. seconds 2. seconds 4.2 seconds 8.4 seconds 7 seconds 34 seconds. minutes 2.2 minutes 4.5 minutes 9 minutes 8 minutes 35 minutes.2 hours Factor for delay (5-27) The period for the delay is set here. The time is calculated from the selected base multiplied by the factor that is entered here. Note: An attempt should always be made to set the required time with the smallest possible base as the base that is selected here also simultaneously specifies the maximum timing error. delay is retriggerable not retriggerable If a telegram is received before switching off, the period is restarted (retriggerable). If a telegram is received before switching off, the period is not restarted (not retriggerable). In this parameter, the delay can be set to retriggerable or not retriggerable. delay The delay can be switched on and off via this parameter. If the function is disabled, the parameters for setting the delay periods are no longer displayed. Base for delay 52 milliseconds. seconds 2. seconds 4.2 seconds 8.4 seconds 7 seconds 34 seconds. minutes 2.2 minutes 4.5 minutes 9 minutes 8 minutes 35 minutes.2 hours Factor for delay (5-27) The period for the delay is set here. The time is calculated from the selected base multiplied by the factor that is entered here. Note: An attempt should always be made to set the required time with the smallest possible base as the base that is selected here also simultaneously specifies the maximum timing error. delay retriggerable not retriggerable If a telegram is received before switching off, the period is restarted (retriggerable). If a telegram is received before switching off, the period is not restarted (not retriggerable). In this parameter, the delay can be set to retriggerable or not retriggerable. Obj Function Object name Type Flags / Status Bit CRT The current switching state of the channel is stored in this object. The object value is dependent on the switching to the Switch object and on the status of the Logic operation and Positive drive objects. No are sent when there is a change in the object value. The switching state can be read out via the ETS or via a visualisation unit. / Switch Bit KS The switching output of the relay is addressed via this object. The application changes the value of the Switch object during operation. Reading out the Switch object via the bus does not reproduce the relay state. The status should always be read back via the Status object. 2 / Blocking/Logic Bit KS operation This object enables the Switch object can be logically linked with the Logical operation object. Technical manual 5D, 2 pages Siemens AG Update: Siemens AG 2 Electrical Installation Technology P.O. Box 9 53, D-939 Regensburg /8

9 September 2 2 A Binary 5D Function None Logic operations Positive drive Blocking function In the case of the higher-order functions, it is possible to select logic operations, positive drive, blocking function or no function. The higher-order function has the highest priority after the behaviour on bus voltage failure and takes precedence over the other switchable functions of the actuator. Status message The current switching state of the channel is stored in this object. The object value is dependent on the switching to the Switch object and on the status of the Logic operation and Positive drive objects. No are sent when there is a change in the object value. The switching state can be read out via the ETS or via a visualisation unit. Behaviour on bus voltage failure opens closes no action The behaviour of the relay on bus voltage failure is set here. no action : failure of the bus voltage, the relay maintains its current switching state. closes : bus voltage failure, the relay is closed with the parameter setting mode: normally open and opened with the setting mode: normally closed. opens : bus voltage failure, the relay is opened with the parameter setting mode: normally open and closed with the setting mode: normally closed. Behaviour on bus voltage recovery opens closes as before bus voltage failure The behaviour of the relay on bus voltage recovery can be set here. The settings only refer to the Switch object. as before bus voltage failure : The behaviour on bus voltage recovery is influenced by the parameters Logic operation and Default position. If no logic operations are active, the relay maintains its current switching state. closes : The parameter Behaviour on bus voltage recovery influences the behaviour on recovery of the voltage. If no logic operation is active, the relay is closed in the parameter setting mode: normally open and opened in the setting mode: normally closed. opens : The parameters Logic operation and Default position influence the behaviour on recovery of the voltage. If no logic operation is active, the relay is opened with the parameter setting mode: normally open and closed with the setting mode: normally closed. Timing diagrams: Examples for the relay. Switch (normally open ) 2. Switch (normally closed ) Siemens AG 5D, 2 pages Technical manual Electrical Installation Technology Siemens AG 2 Update: P.O. Box 9 53, D-939 Regensburg /9

, GH Q631 0075 R0111 The 8-fold switch actuator is a DIN rail mounted device for insertion in the distribution board. It is connected to the EIB via a bus terminal. In the event of bus voltage failure,

/monitoring 1307/1.0 (6325xx) General In the following the device will be referred to as the movement detector. The movement block will only switch off when there is no more movement in front of the device

, GH Q631 0076 R0111 2CDC 071 240 F0003 The Shutter Actuator Standard is used to control a maximum of four independent 230 VAC drives for positioning shutters, blinds, awnings and other hangings as well

, GH Q631 0030 R0111 SK 0010 B 98 The application unit is a DIN rail mounted device for insertion in the distribution board. The connection to the EIB is established via a bus connecting terminal at the

Universal Interface, -fold, FM, GH Q631 0031 R0111 SK 0060 B 98 The device has four channels which can be assigned parameters as inputs or outputs by selecting the application with the ETS2 program. Conventional

In the Master function, the remote control entries will be acknowledged as follows: acknowledged 3 x with the red LED In the Slave function, each detection is acknowledged 2 x with the green LED. 6 TEST

NortechCommander Software Operating Manual MAN-00004 R6 If the equipment described herein bears the symbol, the said equipment complies with the applicable European Union Directive and Standards mentioned

1 V2 software 1.1 Update from V1 to V2 Additional files must be installed when updating from software version 1 to version 2. In version 2.xx, the volume settings are stored in the model memory. The volume

Version 1.11.0 NOVA Autolab control tutorial 1 The Autolab control command The Autolab control command is one of the most important commands in the NOVA software. Through this command, all of the hardware

HART Communication Manual The information and technical data disclosed in this document may be used and disseminated only for the purposes and to the extent specifically authorized in writing by General

Product and functional description The KNX / DALI gateway N 141/02 is a 4 MU wide, DINrail mounted KNX device with one DALI interface to which up to 64 DALI actuators (e.g. DALI ballasts) can be connected

Case study: how to use the event counters in NOVA? 1 Event counter support NOVA Technical Note 22 Event counters in NOVA Most of the measurement commands, like CV staircase or Record signals (> 1 ms) provide

CHAPTER 11: Flip Flops In this chapter, you will be building the part of the circuit that controls the command sequencing. The required circuit must operate the counter and the memory chip. When the teach

Multi Event Timer for Beer Brewing (version.) This timer is designed based on commonly used beer-brewing recipe. It can help brewers track duration of the whole boiling process and remind brewers to add

I.S. 1 remote I/O system Redundant coupling via PROFIBUS DP 1. Functions An I. S. 1 fieldstation can be equipped with a primary and a redundant central unit (), whereby each has its own independent PROFIBUS

LiteKeeper 4 & 8 Programming Guide and User Manual Table of Contents Safety Instructions... 3 Chapter 1: Introduction... 4 p1 How It Works... 4 What are relays?... 4 What are inputs?... 4 How do I program

AD350-SE Multi-Function Auto Dialer Installation Install the AD350 SE Multi Function Auto Dialer as shown in the below diagram. The AD350 SE is only work on standard analog phones. Do not install the dialer

ZME_05459 Wall Blind Control Set for Busch-Jaeger DURO 2000 Firmware Version : 1.8 Quick Start A This device is a Z-Wave Actuator. Triple click one of the buttons on the device will include the device.

Programmable Interval Timer 85/5 9. ecessity and Introduction The 85/5 solves one of most common problem in any microcomputer system, the generation of accurate time delays under software control. Instead

Mode Enable Sensor Options Variable Air Volume - VAV The temperature of this sensor will determine if the unit is in heating, cooling or vent mode during occupied operation. The following options are available:

PART 1 - GENERAL SECTION 13XXX CONTROL DESCRIPTION (DICP Models 02-412NC, 412, 622, 826, 1030) 1.01 SUMMARY This section describes the operation and control of a drip irrigation system. The major components

Automatic Telephone Dialer TD-101(W) The TD-101 is an automatic dialing device which can transmit prerecorded information via the telephone line. The dialer can send two different 10 second voice messages

Laser Merge Module Document # SU-256521-09 Rev A The information presented in this document is proprietary to Spectral Applied Research Inc. and cannot be used for any purpose other than that for which

2.0 System Description The wireless alarm system consists of two or more alarm units within a specified range of one another. Each alarm unit employs a radio transceiver, allowing it to communicate with

Unica for KNX system 6 P117504 Greater flexibility and comfort, better energy efficiency with KNX More and more electronic appliances are needed for modern comfortable homes that contain everything from