MultifunctionPower
and Energy Meter/TransducerAdvanced
Features Include:

•
Multifunction Electrical Measurement

•
V-Switch™ Technology–
Upgrade in Field
without Removing Installed Meter

•
Designed for Replacement to Existing
Analog
Meters or New Metering Applications

• % of Load Bar for Analog Meter
Perception

•
Optional 100 BaseT Ethernet

•
Optional KYZ Pulse and IrDA Port

•
Optional RS485 Modbus & DNP 3.0
Protocols

•
Ultra Compact, Easy to Install

•
Sleek Industrial Design and Bright Red,
3 Line .56” LED display

Unparalleled Technology

• Front Mounted IrDA Port for
PC Remote Read

• 0.2% Class Revenue Certifiable
Energy and Demand Metering

• Meets ANSI C12.20 (0.2%) and
IEC 62053-22 (0.2%) Accuracy Classes

• Revenue Grade

• 400+ Samples per Cycle Rate
Measurement

• 57.6K Baud RS485

• Fits Both ANSI and DIN Cut-outs

•
Power Quality Measurements (%THD and
Alarm Limits)

• Available in a Transducer Only
Version

Applications

Utility Energy Billing

Substations Panels

Power Generation

Sub-Metering

Commercial Metering

Industrial Metering

Campus Metering

Analog Meter Replacement

Original Equipment Power Metering

Electro
Industries/GaugeTech introduces industry leading metering
technology. Designed to address the most demanding applications,
the Shark® 100 surpasses others providing advanced
performance metering in a low cost, compact, panel meter
design. Based on an all new platform, this meter significantly
outperforms other devices many times its price. This
unit is perfect for new metering applications and for
a simple replacement to existing analog meters.

The
Shark® 100 is equipped with EIG’s exclusive
V-Switch™ Technology. V-Switch™, virtual
switch technology allows users, OEMs or Power
Utilities to minimize different levels of meters
and reduce stocking to one type of hardware. In
this manner, the meter can be expanded to meet
the specific application even after installation.
Using V-Switches, you can purchase what you require
now and field upgrade functionality as needed,
which allows you to optimize your investment.
Advanced versions of the Shark® 100 (V3 and
V4) also include DNP 3.0 communication protocol.

Accuracy
percentage of Voltage L-N, Voltage L-L, and Current
is 0.1%. For Watts, Wh, VARs, VARh, VA, Vah, and PF
the accuracy is 0.2%. Accuracy for Frequency is 0.01
Hz, %THD is 1%, and for % load bar 1-120% readings.

The
Shark® 100 is a traceable revenue meter, that contains
a utility grade test pulse allowing power providers
to verify and confirm that the meter is performing to
its rated accuracy.

Easy
to Use and Install

The Shark® 100 was engineered to be as easy to use
and install as possible. From user interface to mechanical
construction, many hours were spent to make the Shark
straightforward and intuitive so an installer with minimal
meter experience and training can succeed with the product.
Shark is programmed using a PC Computer or through
a simple keypad interface. By using the PC, a technician
or electrician can see a visual phasor diagram of the
vectors insuring that CT and Voltage polarities are correct.
All inputs are color coordinated and have clear simple
to understand labeling to avoid cross wiring mistakes.

Optical IrDA port which allows unit to be set up and programmed using remote laptop PC without communication cable - just point at the meter with an IrDA-equipped PC and configure it.

Superior
Voltage and Current Inputs

Ruggedly designed for harsh electrical applications
on both high and low voltage power systems.

Voltage inputs allow measurement to 416 Volts Line
to Neutral and 721 Volts Line to Line, which ensures
proper meter safety when wiring directly to high voltage
systems.

Current inputs use a dual input method: CT Pass Through
and Current “Gills”

CT Pass Through – Preferable to utility users
when sharing relay class CTs because the CT passes
directly through the meter without any physical termination
on the meter, which ensures the meter cannot be a
point of failure on the CT circuit.

Current “Gills” – This method provides
additional ultra rugged termination pass-through bars,
allowing the CT leads to be terminated on the meter.

Utility
Peak Demand Metering

The Shark® 100 meter provides user configured fixed
window or rolling window demand. This allows you to set
up the particular utility demand profile. A Fixed window
demand is the demand used over a user configured demand
period (usually 5, 15 or 30 minutes). A rolling window
demand is a fixed window demand that moves for a user
specified sub-interval period. An example is a 15 minute
demand using 3 sub-interval provides a new demand reading
every 5 minutes based on the last 15 minutes. Readings
for kW, kVAR, kVA and PF are calculated using utility
demand features. All other parameters offer max and min
capability over the user selectable averaging period.
Voltage provides an instantaneous max and min reading
displaying the highest surge and lowest sag seen by the
meter.

Physical
Configuration

The unit mounts directly in an ANSI C39.1 (4”
Round form) and an IEC 92 mm DIN square form. This
is perfect for new installations and for existing
panels. In new installations, simply use existing
DIN or ANSI punches. For existing panels, pull out
old analog meters and place this meter in its place.
The meter uses standard voltage and current inputs
so that CT and PT wiring does not need to be replaced.