*We currently CANNOT ship this product to Canada or any destination outside of the United States

Share

+Share This Product

Product Description

Specs

Reviews

Recommended Accessories

How-To Articles

Manuals

Product Description

+−

Features

Features

Modine's HEX5-75 hazardous environment unit heater is designed for rugged industrial applications in unforgiving, dirty environments. From pulp and paper mills and agricultural plants to oil refineries and coal mines, the HEX5-75 has the durability needed to withstand the most punishing of conditions. This unit heater comes equipped with the necessary features to prevent fires and explosions from flammable gases, vapors, or powdered metals that may exist around the heater.

Temperature Change ResistantThe unit heater uses an ethylene glycol and water solution as a heat transfer medium, providing freeze protection down to a level of -49 degrees Fahrenheit. An included pressure relief valve protects against overpressure damage.

Teflon-Lined Heating Element TankA liquid filled tank on the lower part of the HEX5-75 protects the electric heating elements from outside hazards. This tank is lined with Teflon, simultaneously protecting the heating elements and keeping them away from the sides of the tank.

High Current WiringThe wiring on the HEX5-75 consists of high current, industrial grade wiring attached to tin plated copper bus bars, giving the unit heater the ability to handle high current with ease.

NEMA Type 7 and 9 Wiring HousingThe rugged NEMA type control box houses a large aluminum data plate, control transformer, and convenient terminals for the wiring of accessories to the unit heater.

Fuel Type To create heat, some form of fuel is required. Fuel Type specifies what the product uses as an input to create heat.

Electric

Orientation Orientation describes the direction that air will flow through a piece of equipment. (e.g. air will flow horizontally through a "Horizontal" unit heater.) Most equipment will only function properly if installed in the proper orientation.

Horizontal

Mount Type

Suspended

Performance

Heating Capacity

25600 BTU

Maximum Input Capacity The Maximum Input Capacity describes how quickly the appliance will use fuel when delivering it's maximum capacity. The units may change depending on the fuel being used.

25600 BTU

Heating Capacity (kW)

7.5 kW

Maximum Air Flow

850 CFM

Air Throw

30 Feet

Electrical Data

Voltage

240 Volts

Phase

1

Frequency

60 Hz

Dimensions

Product Height

18 1/2 Inches

Product Width

24 5/8 Inches

Product Depth

24 5/8 Inches

Shipping Weight

151 Pounds

Certifications

Country of Origin

United States

UL Listed

Yes

Warranty Information

Parts Warranty A warranty is a safeguard from defects in manufacturing and can vary in length and terms. To see the manufacturer's warranty statement, click on the Manuals tab. Learn More

2 Years

Features

Features

Modine's HEX5-75 hazardous environment unit heater is designed for rugged industrial applications in unforgiving, dirty environments. From pulp and paper mills and agricultural plants to oil refineries and coal mines, the HEX5-75 has the durability needed to withstand the most punishing of conditions. This unit heater comes equipped with the necessary features to prevent fires and explosions from flammable gases, vapors, or powdered metals that may exist around the heater.

Temperature Change ResistantThe unit heater uses an ethylene glycol and water solution as a heat transfer medium, providing freeze protection down to a level of -49 degrees Fahrenheit. An included pressure relief valve protects against overpressure damage.

Teflon-Lined Heating Element TankA liquid filled tank on the lower part of the HEX5-75 protects the electric heating elements from outside hazards. This tank is lined with Teflon, simultaneously protecting the heating elements and keeping them away from the sides of the tank.

High Current WiringThe wiring on the HEX5-75 consists of high current, industrial grade wiring attached to tin plated copper bus bars, giving the unit heater the ability to handle high current with ease.

NEMA Type 7 and 9 Wiring HousingThe rugged NEMA type control box houses a large aluminum data plate, control transformer, and convenient terminals for the wiring of accessories to the unit heater.

Fuel Type To create heat, some form of fuel is required. Fuel Type specifies what the product uses as an input to create heat.

Electric

Orientation Orientation describes the direction that air will flow through a piece of equipment. (e.g. air will flow horizontally through a "Horizontal" unit heater.) Most equipment will only function properly if installed in the proper orientation.

Horizontal

Mount Type

Suspended

Performance

Heating Capacity

25600 BTU

Maximum Input Capacity The Maximum Input Capacity describes how quickly the appliance will use fuel when delivering it's maximum capacity. The units may change depending on the fuel being used.

25600 BTU

Heating Capacity (kW)

7.5 kW

Maximum Air Flow

850 CFM

Air Throw

30 Feet

Electrical Data

Voltage

240 Volts

Phase

1

Frequency

60 Hz

Dimensions

Product Height

18 1/2 Inches

Product Width

24 5/8 Inches

Product Depth

24 5/8 Inches

Shipping Weight

151 Pounds

Certifications

Country of Origin

United States

UL Listed

Yes

Warranty Information

Parts Warranty A warranty is a safeguard from defects in manufacturing and can vary in length and terms. To see the manufacturer's warranty statement, click on the Manuals tab. Learn More

2 Years

Product Specs

+−

Specifications

General Information

Type

Explosion Resistant

Product Line

HEX5

Fuel Type To create heat, some form of fuel is required. Fuel Type specifies what the product uses as an input to create heat.

Electric

Orientation Orientation describes the direction that air will flow through a piece of equipment. (e.g. air will flow horizontally through a "Horizontal" unit heater.) Most equipment will only function properly if installed in the proper orientation.

Horizontal

Mount Type

Suspended

Performance

Heating Capacity

25600 BTU

Maximum Input Capacity The Maximum Input Capacity describes how quickly the appliance will use fuel when delivering it's maximum capacity. The units may change depending on the fuel being used.

25600 BTU

Heating Capacity (kW)

7.5 kW

Maximum Air Flow

850 CFM

Air Throw

30 Feet

Electrical Data

Voltage

240 Volts

Phase

1

Frequency

60 Hz

Dimensions

Product Height

18 1/2 Inches

Product Width

24 5/8 Inches

Product Depth

24 5/8 Inches

Shipping Weight

151 Pounds

Certifications

Country of Origin

United States

UL Listed

Yes

Warranty Information

Parts Warranty A warranty is a safeguard from defects in manufacturing and can vary in length and terms. To see the manufacturer's warranty statement, click on the Manuals tab. Learn More

2 Years

Reviews

+−

Be the First to Write a Review

Do you own this product?Please share your insights with fellow shoppers.