MP series modular UPS is regarded as the leading digital power supply. It concentrates the most advanced technological achievements in power electronic industry and automatic control field with 10 patents, greatly improving the power supply reliability, availability and maintainability of the key equipments.

MP series provides all kinds of specification power module as well as the cabinet system, the user may carry on the flexible disposition according to the load demand. The single cabinet may realize the 200kVA capacity, after parallel, may realize the 400kVA capacity disposition.

N+X redundancy modularization design

Each power module in the system is designed for hot plug online, which is convenient for customers’ installing, maintenance as well as promotion dilatancy demands. Each power module is the self-contained guidance, non-simple point breakdown risk. The single power module will quit automatically when it fails and not affect other modules working as well as system's normal power supply. Intelligence battery management plan

Each power module built-in independent 3200W digitization high efficiency battery charger, so 200kVA modular UPS system may provide 32kW charge ability. The chargers are DSP digital control to ensure the remarkable battery management performance. Compare with partial factories methods-hanging directly battery with the direct-current bus bar, MP series modulation UPS uses the independent battery discharge converter to reduced the single unit battery quantity greatly, besides realize the remarkable charging and discharging management and control as well as lengthen battery's service life

Strong load capacity

MP series modulation UPS has the remarkable load adaptation performance, providing strong load capacity to all kinds of linearity and misalignment load. Each power module and the cabinet system can provide the load ability compares favorably with any tower system, thus has guaranteed this serial products in various professions application scope.

Intelligence protect plan

MP series modulation UPS power module and system use the hardware and the software dual protection design proposals. Regarding any voltage, current, thermal properties, and short circuit possibly appear abnormal for the power module and system, it can protect promptly and effectively, thus guarantee system's security and reliability.

♦ The system cabinet interior integration electrical power distribution system installment facilitates extremely, and saves the user investment

♦ Remarkable generator match performance.

♦ It can start by battery DC (cold start), convenient for operation.

♦All circuit wafers use the water-stain-dust-proof craft.

System Options

♦ SNMP network card

♦ Lightning-protection module

♦ Battery temperature compensator

♦ SMS alarm apparatus

♦ Dust screen

High reliable design

MP series modulation UPS uses the integration to seal the IGBT module, not the separate component (as shown in fig.). Compared with the separate IGBT components, the integration seals IGBT module has the bigger electric current bearing capacity and a smaller power loss, regarding enhances the power module efficiency and reliability has the huge advantage. Using separate component to carry on the power module design needs to parallel many IGBT components, simultaneously needs to process the postproduction diode's design and the craft problems, and has brought the enormous risk for system's reliability as well as production process's uniformity. The integrated sealed IGBT module has the enormous electric current make-and-break ability, and satisfies the power module demand without parallel, besides integrates the postproduction diode to reduce the risks of design craft and production process. Using the integrated sealed IGBT module, MP serial products while realizes the high efficiency and low power loss, has guaranteed the power module as well as system's high reliability.