AirBooster Pro & AirModulator

Airflow management for Data Centers

STULZ airflow system solutions are employed directly in front of the server rack, under the raised floor. They utilize the same air conduction system from the air-conditioners to the racks and are controlled exactly in line with cooling requirements. Fast, simple and reliable.

Solutions for airflow units

For medium-sized and large Data centers

Suitable for high-density racks up to 15 kW

IT sector

Easy installation, Operational in minimal time

Poorly controlled airflows will fail to cool the servers sufficiently or damage their internal fans through over supply

A Tailored, controlled "need-based" airflow for the right air supply in the right volumes

AirModulator – For efficient cold-aisle cooling

Guaranteed intelligent, energy-efficient air volume control.The Air Modulator has louvered dampers that are fitted under the floor panel and can be precisely positioned via a servo motor. This provides smart, efficient air control from your raised floor, using variable apertures to release only the amount of air actually required by the racks.

AirModulator

Suitable for use with cold-aisle containment

For installation in Data Centers with uniform pressure distribution under the raised floor

Two sensors for temperature readings

The unit delivers only the actual airflow required

The fins are precisely positioned to target locations that require increased cooling. This concentrated airflow goes to work on the targeted areas, reducing overall hot spot problems by also ensuring an adequate supply of cold air is still supplied to other areas.

AirBooster Pro

Suitable for Data Centers with raised floor

No enclosure required

Airflow of up to 2,500 m³/h

For installation in areas with insufficient air supply

Conveys the required airflow efficiently from the raised floor to the server racks