Application Products:

6000 Series Low Frequency Online UPS has been designed as combined advanced IGBT technology with hi-frequency wider-modulated technology (PWM), which make customer could obtain hi-quality power output and optimized efficiency under each operation load. And the advanced modular design to reduce the average time to repair (MTTR), and the best maintenance.It also with the most advanced phase-balanced technology, and it features best stability, even if loss-phase, it could still operate at normal condition, so it’s suitable for any worse power supply.Double conversion, pure sine wave output line design could supply the low-distortion pure sine wave power, so it can provide the best power protection to the users’ equipment And with the isolated output transformer, which ensure that the entire the isolation of the load and public electric.

6KVA Online UPSis three phases in & Singlephases out ups.Due to its prominent industrial and electronic design, the UPS not only could work safe in the harsh environment, but also could provide maximum protection office automation, network, security applications and industrial applications.

Main Features

1. Intelligent control of multiple CPU

Groups of new microprocessor (CPU) co-ordination,which can precisely control the parameters of UPS and its full control,providing sufficient computing power, to ensure UPS always in top working condition.

2. Humanized display interface

LCD dot matrix display,which visually indicated the UPS’s operating parameters.LED displays the working status of UPS,and the LCD + LED combinations could make you get the UPS running status clearly and quickly.

3. High-intelligence network control

Through the communication interface,with the monitoring software,which can directly monitor UPS on the computer,simplified power management;optional adapter remote monitor (SNMP card),with a variety of operating system and application software,as well as TCP / IP , SNMP,HTTP and other protocol support,which meets the users′requirements to monitor UPS via network, this is more suitable for decentralized users to centralized manage,thereby achieving the real global Management.

4. Not principal and subordinate type, but adaptive parallel technology

It has strong ability in parallel and does not need to set the quantity of parallel, it can be arbitrary online parallel expansion or N + 1 redundancy in parallel. Parallel UPS will share the same group batteries.

5. Intelligent battery management

Adopts a three-stage charging method, which is good for recovery for the deep discharge of the battery.Independent current sharing and parallel charger, which can increase he capacity according to request.It can guarantee the charging request for the long backup UPS system.With the battery reverse connect protection, short circuit protection and over temperature protection, and other functions.

SU6K（Single in and Single out）

Model

SU6K

Capacity (VA/W)

6K/4.8K

Input Voltage

Single phase with two lines+ground wire ,220V±25%

Battery Voltage

192V

Built-in Battery

NO

Noise

≤55dB(Distance 1m)

Size (W×D×Hmm)

264×530×592

Weight(Kg)

53

Input

Frequency

50Hz/60Hz±10%

Power factor

≥0.95

Output

Voltage

220V±0.5%

Frequency Stableness

50Hz/60Hz±0.05%(DC Supply)

Transient response

Output at 0~50%~100% =5%, response=10ms

Harmonic distortion

Linear Load<3%, Non-linear Load<5%

Overload capacity

110%≥300 Min,125%≥10 Min,150%≥1 Min

Wave Form

Sine Wave

Efficiency

UPS Efficiency

≥91%

Battery

Battery Type

Lead-acid sealed, maintenance-free

Charging Time

After it is fully charged, it can be filled to 90% of the total capacity after it is charged for 8 hours

Warning Sound

Battery Discharge

Alarm every 4 seconds when power supply by battery and without main power.