Controller interface: Operating mode default setting for a single fume cupboard controller, readout of individual operating values such as volume flow rates for single controllers, or individual alarms

Can be used with fume cupboard, supply air, extract air or differential pressure controller EASYLAB TCU3 and with adapter module TAM

For use in laboratories, clean rooms in the pharmaceutical and semiconductor industries, operation theatres, intensive care units, and offices with very demanding control requirements

Factory mounted or for retrofitting into the EASYLAB base component casing

Special characteristics

LonWorks free topology network with an arbitrary number of branches (star, line, and arbitrary combinations)

Communication only using standard network variables (SNVT)

Data interface for an EASYLAB controller or for an EASYLAB room with different functional profiles

The LonWorks interface supports the EASYLAB room operating mode concept. It is possible to set operating mode defaults in order to control different volume flow rates for daytime and night-time operation; it is also possible to increase or reduce the air change rate by a certain amount (volume flow rate setpoint change), e.g. to influence the room temperature.

Using the LonWorks interface, an individual alarm management system can be set up by consolidating configurable EASYLAB alarms. The interface also enables the transfer of actual operating values such as volume flow rates and damper blade position for a controller or for all controllers in a room.

Expansion module to supplement an EASYLAB base component (controller TCU3 or adapter module TAM) with a LonWorks interface to link rooms or individual volume flow controllers to the central BMS.

The expansion module includes a LonWorks transceiver FTT-10A (free topology, twisted pair), a service pin push button for LonWorks integration, and indicator lights for 'sending data' and 'receiving data'.

Special characteristics

LonWorks free topology network with an arbitrary number of branches (star, line, and arbitrary combinations)

Communication only using standard network variables (SNVT)

Data interface for an EASYLAB controller or for an EASYLAB room with different functional profiles

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +54 (11) 4233 5676

Your message is send and will be processed shortly.Our department for Service-Requests will contact you asap.For general question regarding products or services you can also call:Tel.: +54 (11) 4233 5676