L 2/10 230 ff 1+1

L 2/10 230 ff 1+1 is a ready to install assembly of a voltage limiting and a voltage switching SPD providing two modes of protection, typically installed in Sub Distribution Boards (SDBs) for single-phase 230 V TT-systems where connection type CT2 (1+1) is required according to HD 60364-5-534, with the following features and benefits:

• Impulse test classification: Test class II / Type 2 (according to IEC/EN 61643-11);• Backup protection is not required with an upstream MCB ≤ 125 A or up to an Isccr ≤ 4 kA rms;• NFC No Follow Current® technology, there are no follow currents drawn from the power supply system after operation;• Three colour Status Indicator with progressive indication of remaining performance.