4 Page Method of Operation 1.1 General When using the digital locking system in an object that is secured by alarm, one condition that is to be met is that when the alarm system has been activated, an accidental entry of the area is not possible. This can be realized by using our shunt lock components. These consist of an activation unit and a deactivation unit. 1. The activation unit is for switching the alarm system. In the locking plan, the authorizations for turning the system on and are granted by mouse click. 2. The deactivation unit sees to it that a door of the securing area cannot be accidentally opened with an authorized transponder when the alarm system has been activated; it thereby avoids false alarms. It is equipped with an LED that signals the status activated-deactivated. 1.2 Turning the Alarm System On The one authorized to do the switching activates his or her transponder near the activation unit. This sends a signal to all available deactivation units. If the doors are equipped with lock contacts, the deactivation units verify that the doors are correctly locked. Only when this is the case are the digital locking cylinders or Smart Relays deactivated so that an entry into the securing area is no longer possible. The deactivation unit s LED is extinguished. The activation unit activates the alarm system via a floating contact after the successful deactivation of the locking cylinders or Smart Relays. 1.3 Turning the Alarm System Off The one authorized to do the switching again activates his or her transponder within the transmitting range of the activation unit. The deactivation units signalize this to the digital locking cylinders or to the digital Smart Relays. The doors can now be accessed again with all authorized transponders. The deactivation unit s LED lights again. 1.4 Activation Transponder In case of an emergency, you can use the locking plan software to program a transponder that removes the deactivation of the locking cylinder so that the doors can be opened with an authorized transponder. The alarm system remains activated, however, and the alarm is triggered.

5 Page Special Model If a log is to be kept of who switched the alarm system and when, an activation unit with access logging (PLUS Version) is required. 2.1 Activation Unit PLUS This is the same model as for the standard version, but with access logging and time zone control. Access logging The activation unit stores the last 128 accesses with date, time of day and the transponder s user name. The data can be read out using the Config-Device, PalmCD or over the network. Time zone control You can program activation units in such a way that authorized transponders can switch the alarm system only at specific times. 2.2 Overview of the Models Activation unit Activates and deactivates the alarm system Switches the deactivation unit (optional) Activation unit PLUS Activates and deactivates the alarm system Switches the deactivation unit (optional) Access logging Time zone control

6 Page Assembly Instructions 3.1 General The installation is always done in the protected area, for example, in the inner area behind the door, behind brickwork, etc. However, there are materials, such as stainless steel or aluminium, for example that can considerably reduce the range. In the same way, magnetic interference sources that are in the area around the activation unit or the deactivation unit can very sharply reduce the range. When making the connection, please pay attention to the technical data for the activation unit and the relay. Falling short of or exceeding these values can lead to interference with the function or to the destruction of components. The polarity is not pertinent when connecting the supply voltage. The components (deactivation unit and activation unit) can be surface-mounted on the wall with two 4mm x 30mm countersunk head screws and two S5 plastic plugs. Carefully remove the electronics from the spring-loaded latch in the bottom of the housing. You can also install the components in a flush socket device that is at least 70 mm deep. Please do not use flush socket devices made of metal. If the housing cannot be integrated into the flushmounted box, you must insulate the activation units and deactivation units carefully (e.g. with shrink sleeve). Program the shunt lock components and accompanying lockings before the installation. Keep the following points in mind during the programming: Program the activation unit, deactivation unit and cylinder/ Smart Relay in the same locking plan. Select type Control unit for the shunt lock components. During programming, supply only one component with power at a time and do not connect the cables to one another. After programming, read out the components and verify that they report correctly. Refer to Chapter 1 Shunt lock in the software operating instructions for more information.

7 Page Locking Cylinder/ Smart Relay Install the digital locking (Smart Relay or locking cylinder) that should be deactivated by the shunt lock function. 3.3 Deactivation Unit (DA) Before permanently installing the components, check the radio transmission to the digital locking. To do this, connect the deactivation unit to the supply voltage (9-volt compound battery) and position the unit within radio range of the digital locking. Deactivation unit Digital Locking Cylinder Deactivation unit Digital Smart Relay 20 cm to 40 cm (8 to 16 inches) 50 cm to 1 m (20 to 40 inches) The ranges depend on the structural circumstances and so will vary. Connect the red line with the blue one. The cylinder or Smart Relay is deactivated (signal tone for cylinder) and the LED on the deactivation unit goes out. When you remove the connection, the cylinder or Smart Relay is activated. The LED lights again. Repeat the tests several times until the radio link works perfectly. Then install the deactivation unit. You can increase the range between the cylinder and deactivation unit by using FH version locking cylinders. Install the other deactivation units, if any, and conduct a series of test on all deactivation units. 3.4 Activation Unit (AU) Before installing, apply voltage to the activation unit and test whether its relay switches. Install the components in the door area, making sure that the distance to the digital locking is at least 1 m (40 inches). If the distance is less, turn the activation unit by 90 degrees so that the AU antennas are aligned horizontally. If it is required, you can move the activation unit LED to the outside area so that you can tell whether the alarm system is turned on or off even from outside. You must allow a distance of at least 3 m (approximately 10 feet) from other deactivation units if you are installing activation units that are not directly connected to a deactivation unit but that are in the same locking plan. Connect the white, blue, red and green cables of the activation unit and the deactivation unit(s) to one another (see connecting plan on page B7). Do not connect the yellow lines with one another. It is absolutely important that you do not connect the blue line with one of the white lines, because otherwise the electronics will be damaged. If the lines are not long enough, feel free to lengthen them. Recommended cable type: J-Y(ST)Y 6-pole Ø 0.6mm.

8 Page 8 Apply supply voltage to terminals 1 and 2 on the activation unit. The polarity of the supply voltage does not matter. Check whether there is a minimum voltage of 9 volts on the deactivation units (voltage drop from the cable). Perform a function test by operating the activation unit with an authorized activation unit. The light emitting diodes on the activation unit and the deactivation unit(s) go out and the cylinder(s) or Smart Relay(s) must be deactivated. When you activate the components, the LEDs light again. Test the shunt lock function several times. 3.5 Lock Contact Evaluation (optional) If you want the alarm system to wait until all doors in the security area have been locked, i.e., the bolts of the locks have been driven out, before activating, then you must connect the yellow cable of the deactivation unit to the lock contact. Connect the other connection of the lock contact to the blue cable. The lock contact has to be a floating break contact. If the lock contact is missing, it is not possible to check if all doors are locked, i.e., the alarm system could also be activated if a door has accidentally been left open. In this case the yellow cable is not connected. Test the shunt lock function again. 3.6 Activation Suppression (optional) If you want to use activation suppression, wire it between the yellow and blue lines. This suppresses the activation process under certain conditions, such as when a window is open. Test the shunt lock function again. 3.7 Connection to the burglar Alarm System Remove the supply voltage from the shunt lock components and connect contacts 3 and 4 or 3 and 5 to the alarm system. You can then reconnect the supply voltage to clamped connections 1 and 2 on the activation unit. We recommend that you always connect the shunt lock components to a separate power supply. This effectively eliminates interfering signals and spikes. Do not connect the clamped connections on the deactivation unit. Now check the shunt lock function.

9 Page Terminal connecting plan (Example) Example: Meaning of the colour-coding: White Supply voltage Blue Signal reference point Green Deactivation ack Red Deactivation request Yellow Activation suppression with AU (optional) Lock contact evaluation with DA(optional) AU Alternatively: opening or locking contact Alarm system white white white white red red green green blue blue yellow Optional: Activation suppression yellow Optional: lock contact evaluation If the bolt is driven out, the lock contact opens, if not, it stays closed. DA Do not use connecting terminals Do not connect the yellow cable if the lock contact is missing. This also applies to the activation suppression for the activation unit. You are not permitted to connect the blue cable with a white one because otherwise the electronics can be destroyed.

10 Page Connection Possibilities 5.1 Standard Shunt lock function a) For alarm systems with one securing area, you can have any number of deactivation units (DA) controlled. Example: If a deactivation unit (DA) fails to acknowledge because, for example, a door is still open, the activation unit receives a signal from the deactivation unit. This is sufficient to keep the alarm system from turning on. See page B8 for the terminal connecting plan. a) XXXX b) For alarm systems with several securing areas: an activation unit is required for each securing area. You can connect any number of deactivation units to each activation unit. Example: See page B8 for the terminal connecting plan.

11 Page Activation of the Alarm System from Several Locations If you want to activate and deactivate the alarm system from different locations, use additional Digital Smart Relays. Switch their switch contacts 3 and 5 to parallel and connect them to a transponder with completed cable. Install this special transponder in the immediate vicinity of the activation unit. The Smart Relays are to be set to pulse control (default setting). Example: Transponder with completed cable See page B8 for the terminal connecting plan. Smart Relay connection: Batterie Netzteil Power { + / ~ - / ~ SREL.BAT Battery SREL.BAT { Relais R NC COM NO

12 Page Special Versions of the Shunt lock function 3066 A Operation of the Activation Unit without Deactivation Unit If only the alarm system is to be activated and deactivated using a transponder instead of with a key, only one Smart Relay is required. In this case, however, the true purpose of the shunt lock function is abandoned. If the additional function of activation suppression is wished, an activation unit must be used. Connection assignments: Connect contacts 3 and 4 or 3 and 5 to the alarm system. Connect the supply voltage to the clamped connections 1 and 2 of the Smart Relay or activation unit (separate power pack). If you want to use activation suppression, wire it between the yellow and blue lines. This suppresses the activation process under certain conditions, such as when a window is open. B Do not connect the other lines of the activation unit. Operation of the Deactivation Unit without Activation Unit If the alarm system is to continue being operated with a conventional key, the activation unit is not required. Connection assignments: Connect the supply voltage (separate power supply) to the two white lines or to clamped connections 1 and 2. Connect the red and blue lines over a relay point on the alarm system (floating make contact). If there is a lock switch contact, wire it between the yellow and blue lines. As long the red and blue cables are connected to one another, for example, by a relay point on the alarm system, all locking cylinders that have a deactivation unit are deactivated, which means that it is not possible to accidentally use one of these doors when the alarm system is activated. Do not connect the green cable.

EQUIPMENT SPECIFICATIONS IC-1600 Intelligent Controller The IC-1600 Intelligent Controller is a fully intelligent panel that has a complete database on board. It operates in conjunction with the Access

Model 201 Wiegand Touchpad Reader Installation Guide P/N 460353001C 15AUG11 2011 UTC Fire & Security. All rights reserved. This document may not be copied in whole or in part or otherwise reproduced without

Cable Plug acc. to DIN EN 175301-803, Form A Complete program Contact form 18 mm Also available with LED indicator Optional 4-pin version for pressure switch or impulse valves respectively Versions with

Wireless Home Security Alarm System AM 500 12 MONTH GUARANTEE Installation & Operating Instructions INTRODUCTION The AM500 is a simple self-contained alarm system. It protects the home by sounding a siren

Automatic Telephone Dialer TD-101(W) The TD-101 is an automatic dialing device which can transmit prerecorded information via the telephone line. The dialer can send two different 10 second voice messages

Liquid Level Sensor Installation on pipes. Sensing by means electrostatic capacity and is not influenced by the color of the pipe or liquid. Available in 8 to mm dia. and to mm dia. models to enable sensing

Model Number Single head system Features Parameterization interface for the application-specific adjustment of the sensor setting via the service program ULTRA 000 programmable switch outputs Hysteresis

1. INTRODUCTION FSLIMRF is a fully wireless, battery-powered infrared beam barrier for the protection of doors and windows with alarm radio transmission. The barrier is made up of two aluminium sections

5A2 3 Slot Payphone Controller The 3 Slot Payphone -- Part of American History Building a Coin Relay Controller Version S1BX Instruction Manual and Safety Precautions It is very important that for your

Business/Home GSM Alarm System Installation and User Manual Brief Introduction: GSM 900/1800/1900 bands, can be used in most parts of the world Full duplex communication with the host Monitor the scene

GSM Smart Switch USER GUIDE GSM Smart Switch allows switching almost any appliance ON and OFF remotely via mobile network. It is designed to receive start/stop commands from specially coded messages or

Product and functional description The KNX / DALI gateway N 141/02 is a 4 MU wide, DINrail mounted KNX device with one DALI interface to which up to 64 DALI actuators (e.g. DALI ballasts) can be connected

IRB-325 Infrared Photocell UL325 Compliant Non-monitored Operating Instructions This product is an accessory or part of a system. Always read and follow the manufacturer s instructions for the equipment

TEMPERATURE SENSOR This sensor measures temperature in degrees Celsius or Fahrenheit. It works with all SensorHawk base units (SensorHawk-2, SensorHawk-8 and SensorHawk8/20) as well as the SecurityHawk-8

RCDC1 Radio Controlled Device Controller- 1 Channel When the Mode Switch is in Position 1, Moving the joystick forward turns on the relay. When the joystick returns to center, the relay goes off (momentary

ATTENTION: This wiring information is being provided free of charge and on an as is basis, without any representation or warranty. It is your responsibility to verify any circuit before interfacing with

GSM AUTO DIALER Remote Monitoring & Control using your mobile phone www.gsm-activate.co.uk Product Information Our GSM Auto-Dialer is a versatile unit which can be attached to many of your electronic devices

WIRELESS MAGNETIC CONTACT The magnetic contact wireless MAG HCS is a sensor able to detect opening or closing doors or windows and transmits via radio a alarm signal. It is composed of two distinct elements:

User Manual These low profile standalone proximity readers are able to read EM4002 type card / fobs and have capacity up to 4000 users. All electronics are self contained within the reader, therefore no

CR-2020 SERIES CASH DRAWER USER S MANUAL Rev. A0 FCC Notes: This equipment generates, uses, and can radiate radio frequency energy and, if not installed and used in accordance with the instructions manual,

HM-W536 Install Guide 9/13/2013 IMPORTANT SAFETY INSTRUCTIONS Warning - When using electrical devices, basic safety precautions should be followed to reduce the risk of fire, electrical shock or injury.

MANUAL Connection Unit Conditions: Transactions, deliveries et cetera will be according to the general terms of delivery as deposited at the Chamber of Commerce at Meppel, The Netherlands. Registration

Proximity Switches RS (Reed Switch) General Pneumatic systems can often be combined with electric control circuits. The position of the piston in the cylinder can then be sensed by means of a proximity

PAC1 Door Access Controller Series 2 IMPORTANT DIFFERENCES FROM SERIES 1 1. A PACDL data logger revision 4.0 or higher attached to the DLOG terminal is able to program all features (i.e. times, relay type,

Generator Meter Model: VAAFH Installation/Operation Manual I) Introduction The VAAFH is an ideal monitor system for 240/120 generators and grid power sources and provides monitor of load balancing on the

TruPower-Portable-500W Solar Starter kit This Solar starter kit is an easy to use solar power supply system that is the complete solution for all your solar power needs. It is a solar generator that converts

Used in conjunction with an EntraGuard Telephone Entry System, the -48 provides No Phone Line communication and door or gate control through existing building telephone lines without the need to purchase

Understanding Emergency Power Off (EPO) White Paper #22 Executive Summary Emergency Power Off (EPO) is the capability to power down a piece of electronic equipment or an entire installation from a single

Compact size and high performance for the most challenging detection applications Compact dimensions (14x42x25 mm) Background suppression for transparent and shiny objects High speed contrast sensor up

GLOLAB Universal Telephone Hold 1 UNIVERSAL HOLD CIRCUIT If you have touch tone telephone service, you can now put a call on hold from any phone in the house, even from cordless phones and phones without