Daikin air conditioners lead the industry
with their energy savings and wide model range. This series offers you a
flat panel design with high performances and great energy efficiency. These
indoor units are extremely quiet in operation, the outdoor unit silent
operation function brings you comfort by automatically lowering the
operation sound of the outdoor unit with 3dB(A). If night set mode is
automatically selected by pressing the ‘off’ timer button. This function
prevents any sudden change in room temperature by gently raising/lowering
the temperature before the air conditioner stops, so you can sleep more
comfortably.

Product Key Feature's

Energy efficient units: up to class A energy labels

Can be installed in both new and existing buildings

Vertical auto swing moves the discharge flaps up and down for efficient
air and temperature distribution throughout the room

5 different discharge angles can be programmed via the remote control

Both horizontal flaps and front panel can easily be removed and washed

Maintenance operations can be performed from the front of the unit

The Sky Air® inverter is developed for use in light commercial
applications, provides a more comfortable environment and offers great savings
in energy consumption to shop, restaurant and office owners

The use of inverter type outdoor units results in an air conditioning
system with a high energy efficiency and very low sound level

An inverter driven compressor allows the capacity to be adjusted precisely
to match variations in room and outside temperatures

During start up, the room can be cooled down or heated very quickly; once
the temperature in the room has reached its set point, the low power operation
starts to save energy.

Daikin outdoor units are neat, sturdy and can easily be mounted on a roof
or terrace or simply placed against an outside wall

Outdoor units are fitted with either a swing or scroll compressor,
renowned for low noise and high energy efficiency

A special acryl precoated fin for anti-corrosion treatment on the heat
exchanger ensures greater resistance against severe weather conditions

Outdoor units for pair, twin, triple, double twin application

Product Technical Data

Product

FAQ100BVV1B / RZQ100B9W1B

Cooling capacity

Nom.

kW

10.00 (3)

Heating capacity

Nom.

kW

11.20 (4)

Power input

Cooling

Nom.

kW

2.780

Heating

Nom.

kW

3.390

SEER

3.42

EER

3.60

COP

3.30

Energy label

Cooling

A

Heating

C

Annual energy
consumption

kWh

1,390

Piping connections

Liquid

OD

mm

9.52

Gas

OD

mm

15.9

Drain

OD

mm

26

Notes

Energy label:
scale from A (most efficient) to G (less efficient)

Annual energy
consumption: based on average use of 500 running hours per year at full load
(nominal conditions)