Hermetically Sealed Transformer

Leveraging on our wide expertise and skills, we are renowned as one of the most profound manufacturers & suppliers of Transformer Hermetically Sealed Type. Streets, commercial sector and countryside lighting are some of the areas where these transformers are used. We manufacture these sealed type transformers using optimum quality of raw materials procured from reliable vendors in the market. Transformer Hermetically Sealed Type is appreciated for its features such as high operational fluency, unmatched performance and corrosion resistant surface.

Further Details: 10KV Class S9 Series Distribution Transformer

Summarization S9 Series Three Phase Oil Immersed Distribution Transformer has hermetically sealed type and conservator type. This Series (range from 6,3KVA to 2500KVA) are suitable for 10KV class, 50Hz and 60Hz distribution system.

Technical Data For 10KV Class S9 Series Distribution Transformers

Type

Rated KVA

Voltage Combination

Vector Group

Loss (KW)

No-Load Current (%)

Imp. Vol (%)

Dimension (mm) (LxWxH)

Weight (KG)

HV (KV)

Tapping Range %

LV (KV)

No-Load Loss

Full-Load Loss

Oil Weight

Total Weight

S9-6.3

6.3

6

6.3

6.6

10

10.5

11

13.2

Ã‚±2x2.5%

or

Ã‚±3x2.5%

or

Ã‚±5%

0.4

or

0.415

or

others

Y,yn0

or

D,yn11

0.036

0.210

4.0

4.0

910x450x985

52

168

S9-10

10

0.045

0.270

3.3

4.0

960x450x1010

62

210

S9-15

15

0.060

0.360

2.2

4.0

1030x450x1050

78

220

S9-20

20

0.084

0.521

2.2

4.0

1105x760x1185

80

240

S9-25

25

0.085

0.557

2.1

4.0

1110x650x750

85

250

S9-30

30

0.13

0.60

2.1

4.0

1130x700x1120

90

290

S9-50

50

0.17

0.87

2.0

4.0

950x520x1040

110

500

S9-100

100

0.29

1.50

1.6

4.0

1110x630x1090

165

670

S9-200

200

0.48

2.60

1.3

4.0

1240x700x1190

178

890

S9-250

250

0.56

3.05

1.2

4.0

1300x720x1250

191

1000

S9-315

315

0.67

3.65

1.1

4.0

1340x750x1270

216

1165

S9-400

400

0.80

4.30

1.0

4.0

1360x800x1350

270

1400

S9-500

500

0.96

5.10

1.0

4.0

1420x800x1410

300

1600

S9-630

630

1.20

6.20

0.9

4.5

1560x840x1460

345

1925

S9-800

800

1.40

7.50

0.8

4.5

1670x940x1540

415

2300

S9-1000

1000

1.70

10.3

0.7

4.5

1840x1050x1630

500

2750

S9-1250

1250

1.95

12.0

0.6

4.5

1850x1050x1720

580

3350

S9-1600

1600

2.40

14.5

0.6

4.5

1970x1180x1820

740

4150

S9-2000

2000

3

16.5

0.5

4.5

2100x1280x1920

1390

6200

S9-2500

2500

3.75

19

0.5

4.5

2210x1390x2150

2560

8200

The above parameter is only for reference as typical data, customer-made is subject to customers' request