Technical Information:

Manufactured from 1.2mm galvanized steel, curtain head box rated at same temperature as curtain.

Removable cover plates are incorporated to allow access to the curtain rollers.

Standard head box sizes are 150mm x 150mm for single rollers (maximum width 5.5m) and 250mm x 150mm for multiple rollers (over 5.5m wide). Larger headboxes may be required where the curtain drop is in excess of 3m.

A motor control circuit (MCC) is housed in a steel enclosure and mounted onto the motor end of the head box.

U.S. Smoke & Fire is the nationally and internationally recognized supplier of Smoke and Fire Curtains that are UL, Listed, UL Labeled and UL Certified. File R26410 is ble. Our products are on display in leading institutions across the globe. Learn more about our technology and make U.S. Smoke & Fire the basis for your next design.