The P-5210 Pressure Transmitter is designed to measure a pressure, convert the measurement into a proportional 3 to 15 PSIG (21 to 105 kPa) output signal, and transmit the signal through air pressure piping to a pneumatic receiver controller or indicator. Pneumatic feedback and a ball type control port are incorporated to provide an exact proportional relationship between the measured pressure and the transmitted signal. The P-5210 is a low volume output device used with an

external .007 in. restrictor. The supply/output signal connection is at the top of the unit, and the measured pressure connection is at the bottom. All models are

furnished with a hypodermic needle test point on the air connection to facilitate checking the transmitter output pressure.