Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Trane YCD300 gas pack heat exchanger

I will change the heat exchanger in a Trane YCD300 gas pack.Please post any experiences or suggestions you have about this.I would really like to know if you employed a crane service for the removal and replacement of the heat exchanger.Thank you

Use existing back support under HE, use new bolt that comes with new unit. Most come with inducer and gas valve if ordered. 1 guy for 4 hours, 1 guy for 8 hours.No crane needed to remove and replace, may be needed to get new unit on roof .