Fully or semi-automatic: In "Fully automatic" mode, the lighting switches on and off automatically according to presence and
light. In "Semi-automatic" mode, it must be switched on manually and it switches off automatically

Manual override: The lighting can be manually switched on or off at any time via sensors or switches

Room/corridor sensor function: In the "corridor" setting, the detector functions as a staircase timer and it cannot be switched
off manually

Master/slave parallel switching: Up to ten detectors can be connected with each other to extend the detection area. The master
switches the load. All other detectors merely provide presence information as slaves

Device can be connected as master or slave

Lighting control with light threshold value and self-learning switch-off delay

Pulse function for staircase time switch

HVAC control with switch-on and switch-off delay

Room monitoring with selective movement detection

The switching behaviour of the presence detector is controlled by presence and light

The self-learning switch-off adjusts to occupants' behaviour

The pulse function is for controlling a staircase time switch

The presence detector has a mixed light measurement and is suitable for switching the following types of lamp: Fluorescent
lamps (FL/PL), halogen and incandescent lamps as well as LEDs

Presence switch contact for HVAC control: The switching behaviour of the potential-free contact is only controlled by presence

The switch-on delay prevents instantaneous switch on. The contact only closes on completion of the switch-on delay

Master/master parallel switching: Up to ten detectors can be connected with each other to control several lighting groups.
Each master controls its lighting group according to its own brightness measurements. Presence is detected by all the detectors

The sensitivity of the presence switch output is reduced in the "monitoring" position. The contact indicates the presence
of people with a high degree of certainty

Test operation mode checks the detection area and installation

The parameters can either be set using the potentiometer or via the optional service remote control SendoPro 868-A