Thermostatic regulating valve for circulation pipes according to DVGW work sheets W551 and W553.

Thermal control: Recommended control range 55°C to 60°C (max. control range 40°C to 65°C). Temperature setting can be protected against unauthorised tampering.

Automatic thermal disinfection. The volume of flow is increased about 6K above the set temperature and is reduced – irrespective of the set temperature – to the residual volume of flow when reaching approx. 73°C. The valve thus guarantees an optimum support of thermal disinfection in the succeeding system. Drain valve for hose connection. Temperature monitoring by attaching a thermometer or temperature sensor. Presetting and isolation of the max. volume of flow irrespective of the set control temperature. All parts coming into contact with potable water are made of non-brass materials.

Dimensions of article

Length

Width

Height

Weight

188 mm

141 mm

80 mm

1 kg

Packing units

Type

Qty.

Length

Width

Height

Weight

Carton

1

205 mm

177 mm

111 mm

1,13 kg

Cage pallet

180

1200 mm

800 mm

1100 mm

288,58 kg

We are sorry...

but the CAD viewer which is normally displayed here is not compatible with your browser. We are currently working on a solution supporting all standard browsers. We should like to ask you to use Internet explorer until a new CAD viewer will be available.