For RAYCHEM JBS-100, JBM-100, E-100, and E-100-L components, select the appropriate pipe strap from the following list: Pipes 20 till 47 mm (1/2" to 1 1/4") use pipe strap PSE-047 Pipes 40 till 90 mm (1 1/4" to 3") use pipe strap PSE-090 Pipes 60 till 288 mm (2" to 10") use pipe strap PSE-280, except for the JBM-100 where PSE-540 should be used. For Pipes 60 till 540 mm (2" to 20") , use pipe strap PSE-540 for all kits. These sizes are correct for use with or without the small pipe adapter included in the kit.

Thermostats like the new RAYSTAT-EX-03 can be directly connected to the box without any additional terminals (JBS) or a reduction of the capacity for the number of heaters (JBM). The power cable coming out of these thermostats can carry phase, neutral and earth.For use with RAYSTAT-EX-02 and similar thermostats that only have one entry, additional WAGO terminals have to be installed in the boxes. You need one phase terminal (WAGO 284-691), one earth terminal (WAGO 284-607), and one end plate (WAGO 284-318) which can be ordered from your local electrical distributor or ordered as a kit from nVent Thermal Management (HWA-WAGO-TSTAT-KIT). This construction can be used for direct switching up to 25A.

No. The hazardous area approval of the thermostats allows for the connection of one cable per terminal entry only.

(1294)

RAYCHEM Certified PRO

nVent RAYCHEM Certified PRO

If you are looking into ways to develop your business and expand your commercial activities, joining the certified PRO installer programme could be your fast track to business growth.
Become a Certified PRO

Connection and Protection

Ask a question

Need help finding a product or full solution for your home, business or customer?
Send us a note or give us a call.