Temperature Control Unit : Water

... Model: VT-4500-LXG-300

Water temperature control units circulate temperature stabilized water through the process for process temperature control.

A pump circulates water through the process. A heater and a cooling valve work together to control the water temperature.

This temperature control unit requires a plant water supply source.

Temperature control units are portable, built on casters to easily move the unit between processes.

Specifications

VT-4500-LXG-300 (1)

Heater (2)

kW : 24

Process Pump

HP : 5

GPM : 90

PSI : 34

Full Load Amperage (3)

230/3/60 : 70.4

460/3/60 : 35.2

575/3/60 : 29.4

Connection Sizes

To Process : 2"

From Process : 2"

Water Supply : 1/2"

Drain : 1/2"

Dimensions

Height : 44"

Width : 16"

Depth : 24"

Weight (5)

Shipping : 295 lbs

Specification Notes:

1. Since product innovation and improvement is our constant goal, all features and specifications are subject to change without notice or liability. Selection of certain optional features may change listed specifications.

2. Derate heater output by 25% for 208/3/60 operation.

3. Full load amps are higher than run load amps and must be used for sizing disconnects and supply wiring. Not for construction. Consult factory for power requirements of unit as configured and on selected options.

4. Consult factory for 50HZ operation.

5. Unit weight crated for shipment.

Features

Process Pump

5 HP process pump

Stainless steel shaft

Horizontal motor extends bearing and seal life

ODP (open drip proof) motor

Pump seal flush line

Custom designed impeller and casing

High grade mechanical contactor with over current, phase loss and short circuit protection

Cooling Vavle

PVT™ Solenoid Valve

Pulsed by the microprocessor controller

Heater

24 kW

Stainless steel sheath

Built-In flange for bolt-in mounting

Mechanical contactor

Control Instrument

Controls temperature from30°F to 300°F

LXG-300 Series

Cabinetry & Frame

Stainless steel panels

Hinged electrical cabinet door

Lift-off mechanical cover

Portable, on castors

System Limits

Water supply pressure switch

Process pump motor overload protection

Process pressure relief valve

High temperature limit protection

Control circuit fuse

Electrical

DIN rail mounted electrical components

UL approved components

Nema 1 electrical construction

Pressure Gauges

To process

From process

Heating & Cooling Cylinders

Twin cylinders - separate heating and suction tanks

Made from cast iron by custom molds

Reinforced bosses for process and ancillary connections

NPT process connections

Each cylinder is flanged mounted to the pump casing

Warranties

Lifetime on the pump seal

4 Years on the control instrument

2 Years on the cooling valve

2 Years on the mechanical system

Options

Process Pump

3/4 HP @ 35 GPMChanges Model to VT-4500--LXG-300

1 HP @ 45 GPMChanges Model to VT-4100--LXG-300

1-1/2 HP @ 65 GPMChanges Model to VT-4150--LXG-300

2 HP @ 75 GPMChanges Model to VT-4200--LXG-300

3 HP @ 80 GPMChanges Model to VT-4300--LXG-300

7-1/2 HP @ 100 GPMChanges Model to VT-4750--LXG-300

Heater

10 kWChanges Model to VT-2500--LXG-300

16 kWChanges Model to VT-3500--LXG-300

34 kWChanges Model to VT-5500--LXG-300

Control Instrument

LXT-300Changes Model to VT-4500-LXT-300

Alarms

High dB Audible Alarm

Visual / audible beacon

Electrical

Power Disconnect Switch

Solid State Heater Contactor

Unit

Total Non-Ferrous Unit

Mold Purge

Dual Zone dolly with water manifold and/or single electrical connection

Stacking Stand with water manifold and/or single electrical connection

Cabinetry & Frame

Rear Panel Cover

Control Instrument

LXG-300

Simple menu driven controller

LCD display

Home screen includes continuous setpoint and to process temperature

% Heating or Cooling indication on home screen

Standard shut down pump seal cooling feature

User configurable automatic start-up venting

Out-of-spec alarm including standard audible signal

Selectable SPI or Modbus RTU communication

Optional Modbus TCP communication

For process fluid temperature up to 300°F

Selectable °F or °C temperature display

Support Documents

Literature

3 pages Color 515 KB

Includes Specifications

Manual

84 pages Color 8.1 MB

Updated onNovember 1, 2018

Veteran Series Temperature Control Unit with LXT-300 Series Control Instrument

Temptek, Inc. 525 East Stop 18 Road, Greenwood, IN 46142 Phone: 317-887-6352 Fax: 317-881-1277
Product innovation and improvement is our constant goal. All features and specifications are subject to change without notice or liability. Products are
assembled in the United States of America. Site Map

2018 TEMPTEK, INC

Close

This site uses cookies to offer you a better browsing experience. Learn more about how Temptek, Inc. uses cookies by contacting the site administrator at
admin@temptek.com. By closing this banner, scrolling this page, clicking a link or continuing to browse otherwise, you agree to the use of cookies.
Please refer to the Privacy Policy for more information.