May 12 15:22:14 GMT: %C6KPWR-SW2_SPSTBY-4-PSOUTPUTDROP: Power supply 1 output has dropped
May 12 15:22:14 GMT: %C6KPWR-SW2_SPSTBY-4-INPUTCHANGE: Power supply 1 input has changed. Power capacity adjusted to 2671.20W
May 12 15:22:14 GMT: %C6KPWR-SW2_SPSTBY-4-PSREDUNDANTMISMATCH: power supplies rated outputs do not match.
May 12 15:22:14 GMT: %C6KPWR-SW2_SPSTBY-4-PSOUTPUTDROP: Power supply 2 output has dropped
May 12 15:22:14 GMT: %C6KPWR-SW2_SPSTBY-4-INPUTCHANGE: Power supply 2 input has changed. Power capacity adjusted to 2671.20W
May 12 15:22:14 GMT: %C6KPWR-SW1_SP-4-PSOUTPUTDROP: Power supply 1 output has dropped
May 12 15:22:14 GMT: %C6KPWR-SW1_SP-4-INPUTCHANGE: Power supply 1 input has changed. Power capacity adjusted to 2671.20W
May 12 15:22:14 GMT: %C6KPWR-SW1_SP-4-PSREDUNDANTMISMATCH: power supplies rated outputs do not match.
May 12 15:22:14 GMT: %C6KPWR-SW1_SP-4-INPUTCHANGE: Power supply 2 input has changed. Power capacity adjusted to 2671.20W

May 12 15:23:47 GMT: %C6KPWR-SW1_SP-4-INPUTCHANGE: Power supply 1 input has changed. Power capacity adjusted to 5771.64W
May 12 15:23:47 GMT: %C6KPWR-SW1_SP-4-PSREDUNDANTMISMATCH: power supplies rated outputs do not match.
May 12 15:23:47 GMT: %C6KPWR-SW1_SP-4-INPUTCHANGE: Power supply 2 input has changed. Power capacity adjusted to 5771.64W
May 12 15:23:48 GMT: %C6KPWR-SW2_SPSTBY-4-INPUTCHANGE: Power supply 1 input has changed. Power capacity adjusted to 5771.64W
May 12 15:23:48 GMT: %C6KPWR-SW2_SPSTBY-4-PSREDUNDANTMISMATCH: power supplies rated outputs do not match.
May 12 15:23:48 GMT: %C6KPWR-SW2_SPSTBY-4-INPUTCHANGE: Power supply 2 input has changed. Power capacity adjusted to 5771.64W

OVH Comment - Wednesday, 12th of may, 2010, 16:55

45 racks were in default.

The origin comes from the inverter, UPS2. The producing teams
intervened. We will raise the events at the level of the
UPS to check the origin of the problem. It is
possible that this is linked to a human manipulation's error.
To confirm what was at the basis of the problem.

Comment by OVH - Friday, 14 May 2010, 11:35AM

A human error is at the origin of this problem. The uninterruptible power supply
has been cut off voluntarily... We are trying to know what happened to this
person in charge... It is not the fingers which need to be cut...