side down in electrical contact with a 0.5 mm 2 tinned copper drain wire.

Type 1 8 x diameter.

A 23 micron isolation tape is applied over the screening tape with a

Type 2 12xdiameter.

minimum 50% overlap.

Voltage rating

Temperature rating

300 volt core to earth and 500 volt core to core at maximum

During Operation:-40 ℃+70℃

temperature of 65 ℃

During Operation:-0 ℃+50℃

These cables are not for direct connection to the public mains supply

Electrical characteristics

Parameter

Note

Unit

Conductor size

0.5mm 2
(1/0.8mm)

0.5mm 2
(16/0.2mm)

0.75mm 2
(24/0.2mm)

1.0mm 2
(1/1.13mm)

1.5mm 2
(7/0.53mm)

Conductor resistance

max.

Ω/Km

36.8

39.7

26.5

18.2

12.3

Insulation resistance

max.

GΩxKm

5

5

5

5

5

Mutual capacitance at 1 kH
-One pair and two pair(Quad)cables with collective screen and all
cables with individually screened pairs
-Cables with only collective screen except one pair and two pair(Quad)