These are cables with low dielectric losses used in energy networks with sudden load changes. Laid in residential or industrial areas, underground or in ducts. If the cable gets water inside due to mechanical damage, swellable tapes prevent the movement of the water inside the cable.

Specification

Electrical Properties

Dimensions & Weights

DC Conductor Resistance@ 20°C

Operation
Capacitance
(approx)

Current Carrying Capacity

Nominal
Cross
Section

Overall
Dia
(approx)

Net
Weight
(approx)

m

ohm/km

in Ground
@ 20°C

in Duct
@ 20°C

in Air
@ 30°C

in Air
@ 30°C

mm²

mm

kg/km

－

－

－

－

－

－

－

－

－

－

－

－

－

－

－

－

－

－

0.0470

0.15

668

634

863

779

1 x 400

94.0

10300

0.0366

0.16

759

719

998

895

1 x 500

98.0

11500

0.0283

0.18

864

842

1159

1031

1 x 630

102.0

13000

0.0221

0.19

970

944

1326

1167

1 x 800

106.0

15000

0.0176

0.21

1131

1100

1583

1390

1 x 1000

112.0

17500

0.0151

0.22

1221

1185

1733

1512

1 x 1200

116.0

19500

0.0113

0.24

1397

1354

2040

1750

1 x 1600

124.0

23700

0.0090

0.25

1543

1489

2309

1950

1 x 2000

130.0

27800

Corresponding parameter set not found, please add it in property template of background