Sequence Of Operation For Sump Pumps

Sump Pump sets will be monitored by the BMS to provide the following information for smooth operation and monitoring of the pump operation.

Each pump will have its Run & Trip status monitored together with the position of its controlling switch.

Advertisement:

A general fault will be connected to the BMS from the panel together with Hi and Critical Hi Level alarms.

A graphical representation of the plant will be produced with all set points, alarms and time schedules displayed with simple mouse clicks.

Access to the graphic will be through a system of site plans, plantrooms and systems.

All values are to be historically recorded at controller level so that locally any laptop or Portable operator’s terminal may retrieve the data as well as the network BMS Supervisor.

Laboratory Waste Sump

Laboratory waste sump shall have on its compartments an actual reading of the water level. Water approaching high level and actual high level alarms will be displayed to control panel (refer to drainage system drawing) and to be connected to BMS thru volt free contact from control panel.

All values are to be historically recorded at controller level so that locally any laptop or Portable operator’s terminal may retrieve the data as well as the network BMS Supervisor.