Option 3.4.3. Control Limits for (Specific) Values

You can use your own criteria to set control limits
using the Values option in the Limits tab of the Properties dialog
box. Also, you can use the Force Auto Recalc feature to override
limit values set in the dialog box.

Enter the values for the R or S chart's range or
standard deviation as follows:

R/S UCL—Upper control
limit.

R/S CL—Center line.

R/S LCL—Lower control
limit.

If you want to use the current control limits
elsewhere in your project, or download them to a device, indicate
the floating-point array Point of six (6) elements in the
Setpoint ID field. The
Point contains six elements for all values to be set in the
following order: XBar LCL, XBar CL, XBar UCL, R/S LCL, R/S CL, R/S
UCL. Do one of the following:

Click to browse for an existing Point
in the Select a Point dialog box, or