1000 V - for power circuit - conforming to IEC 60158-11000 V - for power circuit - conforming to IEC 60947-41500 V - for power circuit - conforming to VDE 0110 group C

mounting mode

Fixed

mounting support

Notched mounting railsBar support bracket

connections - terminals

Power circuit : bars 4 - busbar cross section: 100 x 5 mm

tightening torque

Power circuit : 35 N.m - on bars

[Ue] rated operational voltage

<= 1000 V AC 50/60 Hz for power circuit

[Ith] conventional free air thermal current

2750 A at <= 40 °C for power circuit

Irms rated making capacity

18000 A at 1000 V AC for power circuit conforming to IEC 60158-118000 A at 1000 V AC for power circuit conforming to IEC 60947-4

rated breaking capacity

11000 A at 660...690 V for power circuit conforming to IEC 60158-111000 A at 660...690 V for power circuit conforming to IEC 60947-415000 A at 500 V for power circuit conforming to IEC 60158-115000 A at 500 V for power circuit conforming to IEC 60947-418000 A at 440 V for power circuit conforming to IEC 60158-118000 A at 440 V for power circuit conforming to IEC 60947-46000 A at 1000 V for power circuit conforming to IEC 60158-16000 A at 1000 V for power circuit conforming to IEC 60947-4

associated fuse rating

2000 A aM at <= 440 V for power circuit2400 A gI at <= 440 V for power circuit