We use cookies to improve your website experience. To learn about our use of cookies and how you can manage your cookie settings, please see our Cookie Policy. By continuing to use the website, you consent to our use of cookies.

Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

Use the occupied terminals in the RTUs. When it's unoccupied the economize will close 100% unless it's economizing. It will ignore the minimum position. Even better use DCV to run the actuator. Then...

We have a NTI VM153P at our shop. The heat exchanger holds 3.9 gallons. The smaller 110 holds 3.2 gallons. It shows the capacity in the manual may also be on the heat exchanger itself. The internal ...

Maybe it was the early adopters of EVs were snobby privileged tree huggers? The stigma may have stuck around for some and its took out on Tesla because they are the largest EV manufacturer. There are...

Take a look at the backside of the heat exchanger where the exhaust connects. The earlier series had a problem with the cast corroding out. I have probably swapped out 3 or 4 ultra heat exchangers. I...