View PDF - Conference Proceedings

7tiE AMERICAN SOCIETY OF MECHANICAL ENGINEERS
345 E. 47th St., New York, N.Y. 10017
97-GT-5
The Society shall not be responsible for statements or opinions advancedin papers or driCussion at meetings of the Society or of its Divisions or
Sections, or printed in its publications. Discussion is printed only lithe paper is published in an ASME Journal. Authorization to photocopy
material for Internal or personal use under circumstance not falling within the fair use:provisions of the Copyright Act is granted by ASME to
libraries and Other users registered with the Copyright Clearance Center (CCC) Transactional Reporting Service provided that the base tee of $0.30
per page is paid directly to the CCC, 27 Congress Street Salem MA 01970.. Requests for special permission or bulk reproduction should be addressed
to the ASME Technical Flashing Department
Copyright 0 1997 by ASME
All Rights Reserved
. Printed in U.S.A
BIOMASS GASIFICATION FOR GAS TURBINE BASED POWER GENERATION
111111111111RIII111111111
Mark A. Paisley and Donald Anson
Battelle
505 King Avenue
Columbus, Ohio 43201
ABSTRACT
The Biomass Power Program of the US Department of Energy
(DOE) has as a major goal the development of cost-competitive
technologies for the production of power from renewable
biomass crops. The gasification of biomass provides the
potential to meet his goal by efficiently and economically
producing a renewable source of a clean gaseous fuel suitable
for use in high efficiency gas turbines. This paper discusses
the development and first commercial demonstration of the
Battelle high-throughput gasification process for power
generation systems. Projected process economics are
presented along with a description of current experimental
operations coupling a gas turbine power generation system to
the research scale gasifier and the process scaleup activities in
Burlington, Vermont.
INTRODUCTION
The history of biomass fueled power systems is as old as the
steam engine. In the early days, and for decades afterwards:
wood was a common fuel, and was used in fairly simple
combustion systems with little preparation other than size
reduction and some air drying. As steam technology developed
and competition from other fuels increased, the characteristics
of wood and other biomass fuels became better understood,
and these characteristics increasingly came to control the
design of the power system.
BIOMASS FUEL CHARACTERISTICS
Biomass fuels are characterized by high and variable moisture
Content, low ash content, low density, and fibrous structure.
In comparison with other fuels they are regarded as of low
quality despite low ash content and very low sulfur content. A
major concern in using biomass in more thermodynamically
percentage of alkali in the ash. The significance of alkalis is
their propensity to form, in combination with other elements,
mixed sulfates and other salts having low fusion points and high
corrosive potentials. Table 1 gives some examples of biomass
fuel ash composition. It should be noted that the compositions
can vary greatly from those listed because in many cases there
is contamination by adventitious material picked up during
handling. Also alkali levels, notably potassium, may be much
higher than reported because of losses during analysis (1 ). The
numbers quoted are an amalgam from various sources and have
been rounded to total nearly 100 percent in each case. They
indicate that grasslike materials have high silica contents and
generally high alkali, whereas woods tend to have high calcium
content and less alkali. It is significant that poplar, which is
potentially suitable for fuel wood plantations, has a high
potassium content compared to pine and maple.
Table 1. Examples of Biomass Ash Compositions
SPOCM
•
Ash.
%
Ash Composition. %
AJ,03
Co0
AO,
MgO
N.,0
K,0
SiO,
Bagasse
2-3
15
4.6
14.4
3.3
0.8
4.1
46.6
Cam Cob
2-3
-
0.8
0.1
8
0.0
40
60
Cern
Stalk
6-10
0
14
1.4
18
20
0.1
40
Wheat
Straw
1015
1.7
10
1.9
2.6
1.2
26
48
POplat
2-3
1
47
0.5
4.4
0.2
20
2.6
Pi.
2-3
4.6
49
3.6
0.6
0.4
2.0
32.6
Map
3-6
4
68
2
20
advanced thigh temperatures equipment is the relatively high
Presented at the International Gas Turbine is Aeroengine Congress & Exhibition
Orlando, Florida — June 2–June 5, 1997
This paper has been accepted for publication in the Transactions of the ASME
Discussion of it will be accepted at ASME Headquarters until September 30, 1997
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms
10
Many older wood burning steam power plants use steam
temperatures below 400C (750F) and sometimes below 300C
(570F) so ash behavior is a minor concern as long as sulfur
bearing secondary fuels (oil or coal) are not used. When back
pressure turbines are used to provide process steam as well as
power, good overall energy utilization is possible, typically 70
percent or more, but the electrical output is only 10-15 percent.
With condensing turbines (no process steam supply) the
electrical efficiency may be 15-20 percent. In more modern
plants, especially those of larger size (over 50 MW capacity)
steam temperatures up to 480C (90019 have been used and
electrical efficiencies around 25 percent can be reached, but
with increasing concern about the formation of glassy ash
deposits and superheater corrosion.
The latest generation of electric power plant utilizes gas
turbines combined with steam turbines to utilize the exhaust
heat. With support from the DOE's Advanced Turbine Systems
program, thermal efficiencies of 60 percent are being targeted
(2) while 58 percent has been attained (3) in large utility scale
systems. In the small sizes (5 to 20 MW) combined cycle
efficiencies are over 40 percent (4). These efficiency levels are
unattainable by the direct use of biomass fuels because of the
high sensitivity of gas turbines to erosion by solid particles,
deposit formation by dust, and corrosion by molten ash or salts.
Attempts have been made to operate modified gas turbines by
direct combustion of wood (5), but even with turbine inlet
temperatures (TIT) as low as 750C (1380F) serious problems
Figure 1. Effect of TIT on Performance
1.2
1
01
it
0.5
; 0.4
0.2
0
610
Tao
171
TIT, C
082
1003
1204
have been experienced with the fuel ash (5). A TIT of 750C
represents a large departure from normal modern gas turbine
practice in which a TIT of 980-1200C is more usual. Figure 1
illustrates how gas turbine performance falls off with lower TIT.
Biomass conversion to a clean essentially ash-free form, usually
by gasification and purification, is necessary to obtain high
efficiency.
BIOMASS DERIVED FUEL GASES
As well as the ash behavior, the chemical composition and
the heating value of the fuel gas affect its suitability as a
turbine fuel. Chemical composition, especially hydrogen
content, affects flame speed, which can cause problems in the
distribution of heat release in the combustor and eventually
flash back and overheating. The presence of nitrogen
compounds makes it difficult to attain low NO, emission levels
(6). To some extent it is possible to modify the combustion
system to suit specific fuels, but this increases turbine cost.
Problems in the utilization of solid fuels and their derivatives
have recently been discussed by DeCorso et al. (7) who found
that, although many processes have been proposed for
producing "clean" fuels from coal and biomass, acceptable
levels of fuel impurities have not yet been adequately defined,
particularly in the context of advanced gas turbines using high '
strength materials with undemonstrated corrosion resistance.
While the problems may be somewhat less severe in more
modestly rated industrial gas turbines, it is nevertheless true
that properties of fuels derived from biomass are vital to the
successful operation of gas turbine-based biomass fueled
plants. Specifically, the following are desirable, and in some
cases essential, characteristics:
The fuel gas must have very low ash content
(equivalent to less than 1 ppm at the turbine inlet).
The ash must not contain significant amounts of alkali
(alkali concentration below 10 4 at the turbine inlet).
The burning characteristics (Flame speed, heating
value) of the fuel should not be too different from
those used in standard gas turbines designed for
natural gas or petroleum liquid fuels.
The heating value of the fuel should be high enough to
permit attainment of the design turbine inlet
temperature.
Combined nitrogen in the fuel should be low to avoid
formation of fuel derived NO,.
Relatively clean fuel gas can be derived from biomass either
by gasification (through a partial oxidation process) or by
pyrolysis. Pyrolysis involves thermal decomposition of the
biomass into volatile and solid fractions, without oxidation. The
volatile fraction in this case is of higher heating value than
gases obtained by partial oxidation, but only a part of the input
combustible (the volatile fraction) is transformed to the gaseous
(or vapor) form. All of the combustible material can be gasified
by oxidation. The volatile produced in pyrolysis can also be in
the form of condensible tars which require further treatment.
These difficulties have been largely overcome by a rapid
pyrolysis process developed by Battelle, with support from
DOE. This process depends on very rapid heating of the raw
biomass, to minimize tar formation, and on the efficient use of
the solid residue (or char) as a heat source for the pyrolysis
process. Compared with air-blown partial oxidation processes,
this process produces a gas of much higher heating value, and
it does not require the oxygen separation usually necessary for
production of medium Btu gas. This gas has been
demonstrated to be interchangeable with natural gas as a gas
turbine fuel, firing a small (200 KW) Solar gas turbine with only
minor modifications to the fuel feed system (8). Fuel
changeover is achieved simply by operation of a solenoid valve
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms
combustion reactor that burns the residual char to provide heat
for gasification. Heat transfer between reactors is
accomplished by circulating sand between the gasifier and the
combustor.
The Battelle/FERCO Process, unlike conventional gasification
processes, takes advantage of the inherently high reactivity of
biomass feedstocks. The reactivity of biomass is such that
throughputs in excess of 14,600 kg/hr-m2(3000 lb/hr-ft2) can be
achieved. In other gasification systems throughput is generally
limited to less than 1,000 kg/hr-m2 (200 lb/hr-ft2).
The basic uniqueness of the process compared to other
biomass gasification processes is that it was designed to
exploit the unique properties of biomass while the other
processes were either developed for coal gasification or were
heavily influenced by coal gasification technology.
Technology Status
The process has been under development .since the late
1970s and has been extensively tested with woody biomass,
herbaceous crops (switch grass), and a highly prepared ROE.
Recent testing in Battelle's 10 ton per day Process Research
Unit (PRU), has coupled a small scale gas turbine power
generation system to the PRU gasifier. This testing has
demonstrated the feasibility of biomass gasification for power
generation, and has identified areas that require further
investigation to improve the projected performance of a
commercial scale gasification power generation system.
A Commercial Scale Demonstration Plant
Based on the successful operation in the PRU, a decision was
made to scale up the process to a commercial scale. A scale
of 200 tons per day (dry) was chosen for the scale up plant to
provide both scale up data and an economically viable
gasification power generation system after the initial
performance data was collected.
The commercial scale demonstration of the Battelle
Gasification process is underway at the McNeil Generating
station in Burlington, Vermont. In the first phase of the project.
a 200 ton per day gasifier based on the Battelle technology will
be constructed and operated at the McNeil site. The product
gas produced during initial operation will be used in the existing
McNeil power boilers. In the second phase, a gas combustion
turbine will be installed to accept the product gas from the
gasifier and form an integral part of a combined cycle system.
The construction of the gasification plant is under way and
is expected to be completed in the early part of 1997.
THE DN34 GAS CONDITIONING SYSTEM
Battelle has developed a low cost, disposable cracking
catalyst (DN34) that can be used to condition the product gas
prior to its use in a power generation system. DN34 is a
proprietary catalyst described in US Patent 5,494,653.
which switches the fuel supply.
Gas Cleanup
While there are a number of routes by which biomass can
produce an acceptable combustion turbine fuel gas, the critical
stage in the process is treatment of the gas to remove
impurities. Established methods, used for many years in the
gas making industry, use wet scrubbing methods; these can
remove solid particles, soluble gdses, soluble salts, and
condensible liquids, to produce high levels of fuel purity. Their
disadvantages relate to disposal of contaminated water, and the
associated heat losses. Alternative methods, currently under
development (9), involve cooling the gas to below 600C
(1100F) to allow condensation of volatile salts, followed by
filtration to remove solids and chemical sorption of alkali and
sulfur over regenerable reactants. With biomass feedstock
sulfur sorption is generally not an issue. Hot gas clean up
methods are becoming more effective, but there remain some
problems with filter reliability and pressure drop over long
operating periods. Filters do not remove condensible vapors,
which contribute to the heating value of the product gas but
can affect adversely fuel control systems if they condense and
also lead to soot formation. Feeding hot fuel gas to the turbine
can avert condensation in the fuel system, but presents some
obvious problems in fuel system design. Nitrogen compounds
are not removed in hot gas treatments. Overall, wet gas
treatments present fewer problems to the turbine, but carry an
efficiency penalty.
In the case of the Battelle gasifier described below, the
relatively high heating value of the gas minimizes the sensible
heat loss in the scrubbing operation. Also, the condensible
fraction of the gas is very low (on the order of 0.5%), and the
condensates are predominantly of low boiling point and
immiscible in water. Thus, water treatment is simplified and
toxic effluents eliminated. Condensibles can be fed to the
process combustor.
In a further development of the Battelle process a novel hotgas conditioning catalyst (0N34) has been developed that
converts these condensible products to noncondensible forms.
This catalyst permits the use of a dry gas cleanup without the
problems associated with a high fuel gas temperature in high
pressure gasifiers or, as in the case of the Battelle atmospheric
pressure process, will result in the elimination of the gas
scrubbing operation and replace it with a simple water cooler
prior to gas compression. The resulting gas can be used in
virtually any gas turbine with minimal or no modification to the
engine.
THE BATTELLE BIOMASS GASIFICATION PROCESS
The Battelle biomass gasification process, licensed in North
America by Future Energy Resources Corporation (FERCO) in
Atlanta, GA, produces a medium-Btu product gas without the
need for an oxygen plant. The process schematic in Figure 2
shows the two reactors and their integration into the overall
gasification process. This process uses two physically separate
reactors: (1) a gasification reactor in which the biomass is
converted into a medium Btu gas and residual char and (2) a
Results of Testing with DN34
Tar concentrations measured in the product gas from the
Battelle gasifier are typically 16 g/m 3. These tars are highly
aromatic in character and are relatively insoluble in water. As
discussed above, these tars can be removed by conventional
water based scrubbing, however such scrubbing
3
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms
The Battelle High Throughput
Gasification Process
Wet
Feed
I
Medium BTU
Product Gas
Daily
Storage
Steam
Figure 2. Schematic of The Battelle/FERCO Gasification Process
Figure 3 it can be deduced that the pyrolyzer/gas turbine
system could supply electrical power form the gas turbine at
about 23 percent efficiency (before auxiliaries) and could also
deliver over 60 percent of the input fuel energy as process heat.
The overall utilization of thermal energy in this case is around
80 percent, which compares well with cogeneration systems
based on natural gas. The power to heat ratio, which is over
0.35, is also very good, although lower than could be obtained
with natural gas, at around 0.5. Where an industrial site has
traditionally used biomass waste to produce steam only, usually
at less than 80 percent efficiency, a change to cogeneration,
with imports of electrical energy, could be very profitable.
When considering biomass as fuel for power generation on a
larger scale, say upwards of 25 MW, schemes rather more
sophisticated than that shown in Figure 3 are appropriate.
Consonni and Larson (1976), for example, examined a number
of gasification/combined cycle operations based on the use of
aeroderivative gas turbines. They assumed a gas turbine inlet
temperature (TIT) of 1232C (2250F), and a pressure ratio of
19.4:1 with a steam turbine operating between inlet conditions
of 60 atm (900 psi), 450C (842F), and exhaust temperature of
95F (0.82 psi). Using the Battelle/FERCO gasifier concept a net
efficiency of 42.5 percent based on LHV of the fuel was
predicted. It is interesting that direct air blown gasification
yielded gases that had insufficient heating value to permit
achievement of the same turbine inlet temperature. For these
cases the TIT was reduced to 1000C (2012F), resulting in
slightly lower net power output than with the Battelle/FERCO
system. Efficiencies were 45.2 percent for a pressurized
gasifier, and 41.9 percent for a near atmospheric pressure
gasifier.
methods can leave significant amounts (up to 30% of the
incoming tar) of tar behind in the product gas. By providing hot
gas conditioning of the product gas using DN34, significant
improvement in the quality of the product gas can be realized.
By combining DN34 with a water based cooler, no measurable
condensibles or particulates remain in the gas.
INTEGRATED BIOMASS BASED POWER SUPPLY
To achieve the best overall efficiency, the Battelle
gasification system must be carefully integrated into a
combined cycle power generator. This permits effective
recovery of heat from the pyrolyzer and its associated heat
source, and of course it also utilizes the exhaust heat from the
gas turbine.
Figure 3 shows in schematic form how this integration can be
achieved. The gas turbine uses a turbine inlet temperature of
1090C (2000F) and a pressure ratio of 10:1. The plant
conditions assumed in this case are consistent with current
practice for relatively small industrial scale power plants with
electrical outputs in the range 5 to 15 MW. The plant has not
been optimized and some further improvement in output would
certainly be possible. The gross thermal efficiency is 36
percent, and the overall electrical efficiency allowing for gearing
and electrical losses is 34.5 percent. After deducting power for
auxiliaries, the net output would be about 32 percent. This is
a substantial improvement over a wood-fired steam plant
operating at the same steam conditions, which would provide
less than half the power at 15 percent efficiency, before
deducting auxiliary power.
Industrial power plants frequently operate in a cogeneration
mode, supplying both process heat and electrical power. From
4
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms
1:11
AIR
BRIJ
•
Figure 3. Biomass Gasification Combined Cycle Schematic
COED
EP, 1%
YAI
•
• EXII 110C
II%
FIGURE 3 LEGEND:
COMP
GT
COMB
ST
COND
FP
EXH
IC
GC
HX
FD
HRU
BIOMASS FEED
113% MOISTURE
Condenser
Feed Pump
Exhaust
Intercooler
Scrubber
Gas Compressor
Heat Exchanger
Forced Draft Fan
Heat Recovery Unit
NOTE: % figures refer to heat energy relative to LHV of the fuel fed
to the gasifier
Temperatures in degrees C.
II%
LEV 30%
Compressor
Gas Turbine
Combustor
Steam Turbine
COMBUSTOR
2
4250
PROJECTED ECONOMICS OF A COGENERATION SYSTEM
The production of product gas in the indirectly heated gasifier
More advanced versions of the Battelle gasifier/combined
cycle system probably would not use a pressurized gasifier
because it would be necessary to pressurize both the pyrolyzer
vessel and the FBC unit. Pressurization would not greatly
reduce the size of the pyrolyzer, and it would become
necessary to recover energy from the FBC exhaust stream
through a pressure recovery turbine. These complications
would hardly, if at all, be offset by the savings in gas
compression costs, which use less than 9 percent of the input
energy because of the relatively high heating value of the gas.
Meanwhile, the net efficiency of 42.5 percent quoted earlier
represents a target that can be obtained using available
technologies with virtually no modification to current turbine
designs.
In all of the systems outlined above, the moisture content of
the biomass feed is important. With partial combustion
systems it affects the product gas quality; hydrogen content
increases with fuel moisture, changing the heating value, mean
molecular weight, and flame speed, as well as affecting the
overall gasification efficiency. With the Battelle system the gas
quality is virtually unaffected by fuel moisture, but the FBC
must supply additional heat to evaporate the moisture, and this
heat is a major component of the scrubber loss. Thus it is
important to ensure that the biomass feed is as dry as possible,
preferably in the 10-20 percent range. The exhaust gas
streams must be utilized to supplement air drying if these
values are to be attained.
coupled with the relatively high efficiency of gas turbine power
production provides the potential for a cogeneration system that
can be readily applied to existing industrial sites. A conceptual
process design was developed and based on the following
criteria: 1) electrical production of approximately 50 MW; 2)
basing the design on an industrial gas turbine system; 3) using
a dual pressure steam cycle; 4) using steam generator exhaust
gas for chip drying. (11)
For this evaluation, a GE MS 6001 (B) was chosen as the gaS
turbine. The decision to use this turbine system was based on
the desire to have a currently available turbine system rather
than optimizing the turbine pressure ratio. The MS 6001
turbine has a pressure ratio of 11.8 and a thermal efficiency
(LHV) of 31.4 percent.
Projected Economics
An economic analysis was done for installation of this
system into an existing industrial site. Based on such an
installation capital costs were built up from FOB equipment
costs and factored battery limit installation costs to develop the
total physical plant costs. Total installed equipment costs on
a dollars per installed kilowatt basis, including a conditioning
catalyst system, were estimated to be $1037/kw, less than
projections for a new central power station.
Operating costs for system are shown in Table 2 along with
the cost of power. For the cash flow analysis used in
5
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms
developing the estimate for the cost of power, a capital charge
rate of 20 percent was used, which is equivalent to a 20
percent ROI. Which results in a power selling price of
50.047/kWh.
(3)
Dodman K. (Ed.). Gas Turbine Development Emphasizes
Improved Efficiency. Power Engineering International,
March/April 1996.
(4)
DeMoss, T.B. (Ed.). "They're Here (almost): The 60%
Efficient Combined Cycle.' Power Engineering, July
1996.
(5)
Ragland, K.W., Misra, M.K., Aerts, D.J., and Palmer,
C.A. "Ash Deposition in a Wood Fired Gas Turbine,'
ASME, Journal for Gas Turbines and Power, July 1995,
Vol. 117, p 509.
(6)
Tang, A.S. and Purvis, M.R.I. 'NO ), Emissions and
Thermal Efficiencies of Small Biomass Fueled
Combustion Plant with Reference to Process Industries
in a Developing County," International Journal of Energy
Research Vol. 20, p 41-55, 1996.
(7)
DeCorso, M., Newby, R., Anson, D., Wenglarz, R., and
Wright, I. Coal/Biomass Fuels and the Gas Turbine:
Utilization of Solid Fuels and Their Derivatives, ASME
Paper 96-AT-76.
(8)
Paisley, M.A. and Overend, R.P. Biomass Gasification
for Power Generation, EPRI 13th Conference on
Gasification Power Plants, October 1994.
(9)
Judkins, R.R., Stinton,.D.P., and DeVan, J.H. A Review
of the Efficiency of Silicon Carbide Hot Gas Filters in
Coal Gasification and Pressurized Fluidized Bed
Combustion Environments, Trans ASME, J. Eng. For Gas
Turbines and Power, Vol. 118, p 500, July 1996.
(10)
'Biomassand Larson,
E.D.
Consonni,
S.
Gasifier/Aeroderivative Gas Turbine Combined Cycles.
Part B. Performance Calculations and Economic
Assessment," ASME, Journal of Engineering for Gas
Turbines and Power, Vol. 118, p 517, July 1996.
(11)
Paisley, M.A., and Farris, G. "Commercialization and
Development of a Biomass Gasification Power System,
EPRI Conference on New Power Generation Technology,
October, 1995.
Table 2. Operating Cost Estimate -818 TPD Combined Cycle
Plant
Operating Costs:
Load Factor = 0.9 (Base-Loaded Plant)
Fuel - Whole Tree Chips - Delivered Cost of $16/ton wet
Capital Charge Rate = 0.200
Operation and Maintenance - Personnel = 12 @ $15/hr
Supplies Per Year for Operation and Maintenance
- GT/SP Plant - 1 % of Capital Cost;
Gasification Plant - 5 % of Capital Cost
Power Delivered/Year = 441.5 x lOs kWh
Cost Component
Cost
S/Yr
Cents/kWh
Fuel
11.6 x 106
7.17 x 1CP
2.63
1.62
Oper. & Maintenance
Personnel
0.56 x 1CP
0.13
Purchased Supplies
1.18x 105
0.27
20.51 x 1CP
4.65
Capital
Total
CONCLUSIONS
The gasification/gas turbine power system provides both
provide power costs and system efficiencies that surpass a
biomass direct combustion system, typically having a process
efficiency in the range of 17 percent with corresponding power
costs. The system has a low risk associated with it since the
primary power system components, gas compression, and gas
turbine have all been demonstrated commercially with similar
fuels. The gasifier, combustor and scrubbers have not been
commercially demonstrated, but based on the current testing at
Battelle, data will be available to result in a manageable risk for
these components as well. The integration of the systems is
simplified due to the relatively high heating value of the Battelle
product gas minimizing the modifications necessary to use the
medium Btu gas in a gas turbine.
REFERENCES
(1)
Zicherrnan, J.B. and Thomas, R.J. 1972. "Analysis of
Loblolly Pine Ash Materials'. Paper 3574 Journal Series
of North Carolina State University, Ag. Experimental
Station.
(2)
Webb, H.A., Parsons, Et, and Borjuror, R.A. 1993.
Advanced Turbine Systems Program and Coal
Applications, ASME, Paper 93-GT-356.
6
Downloaded From: http://proceedings.asmedigitalcollection.asme.org/ on 12/29/2014 Terms of Use: http://asme.org/terms