Hi I am trying to communicate with this Lenze drive I have kicking around.
My PLC is a Productivity 1000.

This drive has a built in Modbus module with a RJ-45 connector. This is not the plug-in Modbus module. I can not seem to get a hold of the pin-out for this RJ-45 connector. Lenze tech support says this drive was custom made for Captive Aire and they don't know the pin-out. Has anyone had any success communicating with this drive before? If so could you provide me with the pin-out of the RJ-45 connection. I have the manual and it says it is for Modbus RS-485 Daisy chaining.
Attached is the picture of the Modbus comms

Is it likely that Modbus RTU over RS-485 is the only signal on the RJ-45? Probably. If that's the case, then it is a known fact that swapping the driver lines will not damage the driver lines. Comm won't work if the lines are swapped, but there's no damage. So you can break out those lines and give it a try.

You might be able to confirm the signal GND by testing for continuity to the frame ground. It might or might not be the same point.

If those pins 4 and 5 do not modulate when Modbus is polling, then use a voltmeter to check for which pins modulate/oscillate when Modbus is polling. It is very likely too be 2 wire half duplex and only 2 wires out of the 8.