Inside this Article

The rated output of this generator is the combined wattage of both 120 V legs. At most, half of that power is available at 120 V—full power is only available at 240 V.

Look for a generator that includes electric start and a panel switch that internally reconfigures the generation coils to provide full output at either 240 or 120 V — common on higher-quality portable generators.

This Onan RS20000, 20 kW LP generator is a perfect match for four OutBack VFX3648 inverters (see next photo).

This large home system uses four OutBack charger/inverters in a 120/240 output configuration. The middle two inverters are mainly used to achieve a C/13 charge rate for 2,200 Ah of batteries at 48 V.

Some inverter/chargers, like this Magnum MS4448AE, can accept either 120 or 240 VAC output from a generator.

Inverter–generators, like this Honda EU6500is, can adjust engine rpm to meet loads while an onboard inverter keeps the output waveform on spec.

An autotransformer can convert 240 V output from a generator to 120 V needed by an inverter’s charger.

Beginner

Unless you have a good hydro or dependable wind source, or an excessively large PV system, sometimes the only way to keep your off-grid power system operating is by using an engine generator. But many residential generators are poorly matched to the job, since the selection and purchase of a generator is often an afterthought. The result is the generator becoming the weak link in the system, with inefficient, unreliable performance, rather than being an integral component of a well-functioning system. Here’s how to analyze your generator needs and choose the right unit for the job.

Function & Purpose

Generators serve three main roles in off-grid home systems:

The first is backup charging, where the generator makes up for any deficit in energy from the solar array or wind turbine, since the generator will work in any weather.

The second function is battery equalizing. All flooded batteries need to be overcharged several times each year for best service life and performance. Equalizing is the deliberate overcharge of an already-full battery—raising the battery voltage to a higher-than-normal voltage (as specified by the battery manufacturer) and keeping it there for 2 to 3 hours. A minimum charge rate of about C/20 is necessary to overcome internal resistance to achieving such a high voltage (see “C-Rating” sidebar). Most off-grid PV arrays aren’t powerful enough to accomplish this, especially during the winter, so a generator becomes an essential tool to achieve this.

The third role is to run specific loads that exceed the capacity of the inverter(s), such as 240-volt deep-well pumps, stationary shop tools, and even air conditioners.

The Basics

“You get what you pay for” might as well have been coined by a generator owner. Even in a well-designed off-grid power system, the generator is likely to be the single greatest source of maintenance and aggravation. It’s a mechanical device, rather than electrical, so it requires regular maintenance and will eventually break down—usually when it’s most needed.

Ask yourself: Is a breakdown just an annoyance or will it completely disable my home’s power system? The more serious the consequences of the inevitable breakdown, the greater the appeal of a top-quality commercial/industrial generator. Consider also that unless you are prepared to maintain and repair the machine yourself, you will need reliable local support when the eventual failure occurs. An investment in quality quickly pays off.

Generators for home use may be purchased for as little as $300 or as much as $12,000. The least-expensive units are designed for occasional homeowner use with power tools or cement mixers, for instance. “Contractor’s specials,” common at home-improvement centers, are just that—with their low initial cost, they are designed to provide temporary power until utilities are installed or to build a remote cabin. They’re designed to be worked hard and then written off as a business expense when they die.

For off-grid backup, your choice will constitute a compromise between application, cost, availability, and support. But a higher-quality unit will generally have the following features:

Electric start with two-wire remote start capability: “Two-wire” means all starting control functions (such as cranking and crank duration) are handled within the generator, rather than externally. Remote start capability means that the start and stop signals can be sent from an inverter or other controller. (See “Automatic Generator Start” sidebar.)

No or minimal standby load: Some generators, designed primarily for on-grid standby use, draw energy—even when not running—for control functions, charging the starter battery, and even for block-heating in cold climates. This may be acceptable for use with utility power, but not for off-grid systems. Look for a generator that has no parasitic draw when off, or expect to add a separate small PV module and charge controller to keep the starting battery charged.

Engine speed: In general, quality conventional generators run at lower speeds—typically 1,800 rpm versus 3,600 rpm—which directly translates into longer life. An 1,800 rpm unit will also operate more quietly, with less vibration and lower fuel usage.

Floating or unbonded neutral-to-chassis connection. Quality generators allow the neutral conductor to either connect to the generator chassis (for prime power application) or remain separate from it. Portable generators are seldom properly grounded, so manufacturers ground the neutral output conductor to the chassis. When connected into a grounded power system, however, this presents a safety hazard, as the neutral is now bonded to the ground at two places—one in the power system AC (such as in the main AC service panel) and one in the generator—and the safety ground wire becomes current-carrying. Some units also include AC ground-fault protection, which is incompatible with connection to a grounded power system. There is no simple, code-compliant solution to this. The safest noncompliant approach is to bundle an insulated, green ground conductor with the power conductors between the generator and the main ground bus, which serves to ground the chassis and minimize shock potential.

A well-earned reputation for after-sale support by the local dealer. Even the best generator will eventually need service and repair, often on-site.

A warranty of at least two years, valid in off-grid applications.

Selecting Your Fuel

Generators are fueled by gasoline, propane (or its cousin, natural gas), diesel, or biodiesel. The least expensive generators and nearly all portable units use gasoline, which offers some advantages­—mainly that gasoline is familiar and manageable by the unskilled user. However, it’s highly flammable, and fuel storage will need to be a consideration. Allowed to sit in a generator’s fuel tank, gasoline will eventually deteriorate, leading to clogged orifices and preventing the generator from starting when needed. Cold-starting also requires engaging a choke. Most auto-start generators are not gasoline-fueled for these reasons. A gasoline generator may be best suited to applications where it is only used occasionally and the gasoline is drained (or run out) after each use.

LP gas (propane) is commonly used in higher-quality stationary generators. Many off-grid homes already have an LP tank and lines for cooking and heating, so the fuel is convenient and relatively safe. Propane has an almost unlimited storage lifespan. LP generators will generally start reliably down to about 10°F. Natural gas and propane burn cleaner than gasoline and diesel, and wear on internal engine parts is reduced.

With some notable exceptions, diesel generators are typically long-lived and high-quality—and relatively expensive. However, the fuel is best suited to warmer climates, as it gels below freezing temperatures. The drawback to diesel fuel is that, compared to natural gas or propane, it’s a “dirtier” fuel, producing more pollution. Fuel storage requires extra care against spills and leaks, and may even be regulated. For the eco-tinkerer, diesel units may also be run on biodiesel or either virgin or waste vegetable oil, taking the appeal of “living on renewable energy” to a greater level. Vegetable-based fuels don’t generally need additives to prevent gelling; the fuel is heated instead.

Sizing a Generator

As a general rule, a generator should be able to supply the full charging capacity of your inverter, plus loads that typically run while charging and provide some reserve capacity. This both minimizes runtime and maximizes C-rate—the charge rate necessary for good battery care. Generators used in home systems will vary between about 2,500 watts and 20 kilowatts of continuous rated power.

Often, a generator is purchased before the power system is designed, as an early source of power for construction and water supply. The result is that the RE system designer must take the existing generator and adapt the system design to best use it—a backward approach to system design. A better plan is to consider a generator as part of the overall power system design. The preferred approach to sizing a generator starts with the battery bank.

Most PV arrays for off-grid homes will be sized to meet or exceed design loads for part of the year. This seasonal duration may cover all except the heart of winter in the sunny Southwest, or may only cover half of the year in northern climes. Battery banks are typically sized to provide two to four days of autonomy (time the batteries can supply energy without further charging), depending on the seasonal climate and other factors.

Because arrays and batteries are sized to different purposes, the array is seldom large enough to meet even the minimum C-rate needed to routinely fully charge and regularly overcharge (equalize) the battery bank. Hence the need for the generator, which can add the necessary charge current to get this done, and may be even the only contributing charging source during winter—so it should be sized to handle the job.

AC Voltages

Typical utility power is split-phase 120/240 VAC. If you look inside a home’s electrical distribution panel, you will see three non-ground wires coming in: two “hot” conductors and one “neutral” conductor. The voltage between each hot and the neutral conductor is 120 V, and the voltage between the two hot legs is 240 V. Most off-grid homes have only one hot conductor, and operate at 120 V.

An off-grid system’s generator must be matched to the voltage needs of the inverter/charger. Generators provide AC output in one of four ways:

120/240 V with full-rated power only available at 240 V. Most inexpensive, homeowner-grade generators are set up this way. The rated output is the combined wattage of both 120 V legs, and at most, half of the rated output is available at 120 V.

120/240 V with a switch that internally reconfigures the power generation coils to provide full output at 120 V when desired. This is a valuable feature and is fairly common on higher-quality portable generators.

Straight 120 V: Many of the newer “inverter-generators” (see below), and most models designed for RVs, put out power only at 120 V. Small, portable units (less than 2,000 watts, generally too small to use effectively as charging sources) are only 120 V.

Field-reconfigurable: Most top-quality generators may be reconfigured to offer either full-output 120 V or 120/240 V by changing the connections of the output wires inside the generator. This task is best handled by a generator service technician or skilled RE installer.

Most inverters manufactured since the late 1980s can only receive 120 V input from a generator. For most off-grid homes, this is not a problem, since 240 V loads are typically large bulk loads from water heaters, clothes dryers or electric ranges that are inappropriate in an off-grid home. With the exception of AC well pumps, off-grid homes are unlikely to have 240 V loads.

When a typical 120/240 V generator that is not capable of full output at 120 V is paired with a 120 V inverter, two problems occur. First, a 120/240 VAC generator is only capable of half of its rated output when connected to the input of a 120 V-only inverter. Second, the load on the generator is unbalanced, with one 120 V leg fully loaded and the other unloaded. This imbalance can lead to premature generator failure.

This means that the less-expensive generators are least able to efficiently back up the most common inverters. For example, a low-cost generator may be specified at 5,500 W maximum output. But the usable “rated” output is not “maximum” output. Similar to the way an inverter’s continuous-duty capacity is compared to its capacity to meet larger surges, “rated” output is the level of power a generator can deliver continuously. Usually, it’s about 85% of the “maximum” power, although some lower-quality generators are not even capable of their “rated” capacity. How much power is really available? First, check the rating carefully: the 5,500 W rating is likely to be around 4,700 W in continuous duty, such as battery charging through an inverter. Second, the continuous rated power is available only at 240 V, so a single 120 V inverter can only access half of this output capacity, or 2,350 W.

One solution is to use a balancing autotransformer to step down the 240 volts to 120 V before sending it to the inverter. This allows the full power and both 120 V legs to work in balance. However, a typical autotransformer for this purpose retails for more than $500, making the “low-priced” generator much more expensive.

Another solution, usually practical only in larger systems, is to use a stacked pair of inverters to both receive and produce 120/240 V power. This is a common approach with OutBack inverters. A few modern off-grid inverters, including Magnum’s AE series, Xantrex’s XW, and Apollo’s TrueSineWave are configured as 120/240 V split-phase units. These units are able to use both 120 V legs of a generator to provide balanced charging from both hot legs. The new Silent Power SP4024 inverter can use either 120 or 240 V input. No step-down transformer is needed with any of these inverters.

Another option is to select an inverter-generator, a relatively recent development. The inverter (which cannot substitute for the RE system’s inverter) is an integral part of the generator, electronically synthesizing the voltage, current, and waveform, while maintaining full-peak voltage up through their maximum load. As the 60-hertz AC waveform is not dependent on engine speed, the engine speed varies according to the load. This allows an accurate pure-sine waveform, while reducing fuel consumption and noise.

Recommendations

Generator models are rapidly evolving, with new models entering the market and old favorites being discontinued. Most of the reliable, small generators of years past were made obsolete by California’s emissions standards and changing markets. Newer models have been developed primarily for the on-grid home standby market, rather than for stand-alone use. Standby models, intended for backup power during utility outages, are marketed as low-maintenance home appliances. They will commonly require utility power to maintain controls and charge the starting battery, and even for running block and intake heaters in cold weather—all unacceptable loads in off-grid use. In addition, fierce competition in this market has encouraged an emphasis on low price over high quality. There is a clear and unmet need for simple, reliable, commercial-grade generators not designed for the residential standby market.

The safest bet is to buy a well-respected brand, or at least a generator that comes with a brand-name engine—it will be much easier to find parts and service for a well-established brand than for some no-name model. Finding a high-quality used machine with low hours and evidence of proper care may also be a possibility. Consider also an inverter–generator, as these are gaining wide acceptance, with sizes available up to 6.5 kW. Honda, Yamaha, Robin, and Cummins make high-quality inverter-generators. All run on gasoline, but some of these brands may be converted to LP gas without voiding manufacturers’ warranties.

Among conventional portable units 6 kW or less, Honda’s EM or EB, and Yamaha’s EF and YG series have been well regarded for years. Multi-Quip and Robin—made by Fuji Heavy Industries and marketed under the Subaru, Makita, and Baldor names—also have solid reputations.

In higher-quality commercial units, Kohler’s 10ERG is a well-regarded model developed for the RV market and adaptable for off-grid use. Onan makes several adaptable units, including the RV QG 6500LP, RS 12000, and RS 20000 LP, the latter two suited to larger systems. There are some nice Onan diesel inverter/generators (the HQD series) up to 18 kW.

Notable negative comments have generally been directed at the cheapest generators, with poor waveforms, inflated output claims, and lack of long-term reliability. Also, avoid knockoffs of well-known models, especially low-cost inverter-generators now on the market. Reliability is unknown, and repair parts may be unavailable.

Access

A PV system installer since 1988, Allan Sindelar founded Positive Energy Inc. of Santa Fe, New Mexico, in 1997. He is a licensed commercial journeyman electrician and a NABCEP-certified PV installer.

This article was prepared with the assistance of Roy Butler of Four Winds Renewable Energy, Arkport, NY; Tad Jennings of Power Generation Services, Albuquerque, NM; John Klesk of Cummins Power Generation, Minneapolis, MN; Terry Graybeal of Backwoods Solar, Sandpoint, ID; and Tom Bishop of Sunelco, Hamilton, MT.

Comments (13)

Hey there "redpoint_13", simply put "off-grid" refers to not being connected to the hydro or any other cables for that matter. We rely only on our solar array and generator for power. During November and part of December north of the border here, we normally have a thick fog, low clouds or snow here that limits our solar production. This year it's actually extended into January. As a result in order to keep our batteries (our solar energy storage) charged for power, we need to run our genny for an hour or so on selected days. We run a Cummins Onan 20kw propane fired generator. We acquired it with our home. It had 500 hours on it when we moved in and it has about 800 hours on it now. Works awesome, remote start switch, powers my welder, and whole house while charging batteries. Regular self maintenance, oil & filter, spark plugs, air filter and antifreeze. Had a propane regulator diaphram go but an easy replacement. You just can't say enough for good quality. Minus 28 degrees celcius and the genny started no problem when we needed it. Just on a side note, we heat with wood, nothing warms your bones better than wood heat!

Hi Brady.
Thank you for the reply.
Off-grid living and an "off-grid" generator seem to be quite different things when one reads manufacturer websites. It appears that there is a home, and then a commercial market and very different products made. Commercial ones are made with car engines that can run for years, while home gens seem to be limited to 1000 hours. During Okanogan fires there was no power for weeks in some places. What if you need to continue sprinkling to save the house?!
Since no one really wants to elaborate on the engineering side, and users are mostly making wild guesses, unclear what to buy, and what happens if say I replace oil every 50 hours. Would it then last and work fine?

What model is your Onan? Do they still make it? I am very confused by marketing, fine print and forum comments about the home-market products..
Seems though that the solution is on craigslist, ha-ha!

Hi there!
I am not very clear on the "off-grid" designation. The Onan/Cummins today does not mention the word, and Kohler says 1000 hours warranty.
So what kind of experience do people have with these, or other brands.
Caveat: my wife cannot tolerate fire inside the house because of smoke, so I need to look for more powerful options that run for a few hours if necessary for heating

Hello.
Thanks for posting! Good question, and one you will need to pose to technical support at Yamaha directly. But from what I found on their website (hopefully that is correct) it looks like you will have Rated AC Current of 45.8 amps @120V .
Best,
Justine Sanchez
Home Power Magazine

I read and love your site. I have a question. I just ordered a
Yamaha Inverter EF6300iSDE . With this generator will I be able
To get the full running watts using just the 120 side ? Like you said
In the article, some will cut you in half if you are not using the 120/240. I'm hoping I can get the full power from just the 120. It sure cost me a lot of $$$. I'm going to use this for camping and other uses and also for a temporary home back up. But if it cuts me to only
1/2 power using just the 120 side, I may be better off buying the Yamaha EF 4,500 ise. If I can get the full power out of it, it'll be more power than 1/2 the 6,300. Please help because I've already ordered and have to act quickly if I'm going to change. Thanks a lot for any info.

Thanks for the great info, however I was hoping you would be able to answer a question. My cabin (soon to be house) is currently powered by a 20kw Onan propane generator connected the main AC panel. I am installing a 4kw solar system with a Magnum-PAE 4400 inverter. Will I need to rewire the generator directly to the inverter or logically can I leave it on the main AC panel?

Hi Brady. NO! Your inverter will now power your home, so it's output should take the place of the generator. The generator will be rewired to feed into the inverter/charger.
But it is not that simple. The documentation that came with the inverter/charger will give you some of the details. But I strongly suggest that you hire an electrician experienced in off-grid systems to handle all the wiring.

Thanks Michael. For sure I will be hiring an electrician to do the final connections. As I'm sure you are well aware there is some good info on the web and some "confusing" info, that's why I posted the question here, a reliable source that I only recently found. Item number 12 on my task list "get electrician to rewire genny to inverter". Thanks again.

What about noise? Having a good generator is all very well, but the experience can be spoiled by the neighbors throwing rotten vegetables at you every morning because your $%^& generator keeps them up at night.

And if you decide to choose a super quiet generator, how do you go about purchasing one? From the manufacturers claims, all generators are "whisper quiet", and you would be more likely to be disturbed by a mouse tripping over a pillow.

Yes, noise is an unavoidable problem with any engine-generator, and none are as quiet as a whisper (or mouse). Some are better than others. But for my money, I would find the best-operating generator, not the quietest one.

About those neighbors? Most generators we talk about are for rural, off-grid systems. But if you are in town, how about offering to power their fridge for a few hours a day during any blackouts?

Can a home that has a whole house generator have a grid tied PV system added to it? I know grid tied inverters have tight tolerances on input voltage and normally wouldn't start, could this cause problems?

Great question! In a residential application the system needs to be configured so there is no possibility of the batteryless grid-tied (GT) inverter trying to synch with the engine generator. And if not configured correctly, yes there could be problems with a GT inverter trying to backfeed a generator (likely causing damage to generator) if the inveters's strict power tolerances were actually met with the inverter output exceeding the household loads. However from my understanding a solution is to connect the GT inverter output to the grid upstream of the automatic transfer switch, so that the GT inverter would have no pathway to the generator and vice versa. I.e. the main service panel would be connected to either the grid/PV system OR the generator but could not be connected to both at the same time.