47
Information required for pricing To determine foam type and nozzle spacing Type of product involved, provide MSDS if available Hydrocarbon or Polar Solvants To determine foam type and nozzle spacing Type of product involved, provide MSDS if available Hydrocarbon or Polar Solvants To establish the nozzle layout Drawing or sketch of the area(s) to be protected Plan view showing dimensions and ceiling height Elevation view required for 3D hazard such as transformer Dimensions and location of obstructions that may affect discharge pattern Beams Columns Ducts Equipment To establish the nozzle layout Drawing or sketch of the area(s) to be protected Plan view showing dimensions and ceiling height Elevation view required for 3D hazard such as transformer Dimensions and location of obstructions that may affect discharge pattern Beams Columns Ducts Equipment

48
Information required for pricing To determine the system size Identify the fire scenario How many zones could be actuated simultaneously Will multiple areas be protected by a single system Single zone system or multiple zone system Could be a multiple zone system design for the largest zone Advantages to use a common foam tank and cylinder bank What is the minimum discharge time ? 5 minutes for specific hazard applications such as transformers 10 minutes for ceiling nozzle applications 20 minutes recommended for aircraft hangars To determine the system size Identify the fire scenario How many zones could be actuated simultaneously Will multiple areas be protected by a single system Single zone system or multiple zone system Could be a multiple zone system design for the largest zone Advantages to use a common foam tank and cylinder bank What is the minimum discharge time ? 5 minutes for specific hazard applications such as transformers 10 minutes for ceiling nozzle applications 20 minutes recommended for aircraft hangars

49
To complete evaluation Determine if minimum water supply is available Based of minimum flow and pressure established during design Determine if available water supply is sufficient May require fire pump if pressure is not sufficient May require stand alone water tank if flow is not sufficient Fireflex can offer a pressure vessel type tank up to 2000 US-gallons Determine if minimum water supply is available Based of minimum flow and pressure established during design Determine if available water supply is sufficient May require fire pump if pressure is not sufficient May require stand alone water tank if flow is not sufficient Fireflex can offer a pressure vessel type tank up to 2000 US-gallons

50
To complete evaluation Determine actuation means What type of fire detection is require ? There are no specific requirements for the ICAF System Heat, rate of rise or compensated, Protectowire, UV-IR, beam could be used to actuate the system Does the hazard area require explosion-proof or weather proof wiring and devices ? Are there any devices that need to be shut down prior to discharge ? Determine actuation means What type of fire detection is require ? There are no specific requirements for the ICAF System Heat, rate of rise or compensated, Protectowire, UV-IR, beam could be used to actuate the system Does the hazard area require explosion-proof or weather proof wiring and devices ? Are there any devices that need to be shut down prior to discharge ?

51
To complete evaluation Identify possible location of system and maintenance area Identify preferred piping route Identify any obstructions to the piping route Record dimensions of possible mechanical room Will a discharge test be done ? Identify possible location of system and maintenance area Identify preferred piping route Identify any obstructions to the piping route Record dimensions of possible mechanical room Will a discharge test be done ?