The HVAC system consists of a water source heat pump system utilizing horizontal ceiling hung heat pumps, a nominal 2000 GPM hydronic piping loop, nominal 750 ton closed circuit evaporative coolers, plate and frame heat exchangers to allow year round use, a nominal 34,000 CFM make-up air unit with an air-to-air heat exchanger recovering energy from the general exhaust system. The boiler system consists of two gas-fired, modulating boilers.

The electrical system consists of a 13,200 volts primary feeder serving primary metal enclosed switchgear which in turn feeds two independent pad mounted transformers each rated at 1500 amperes at 480/277V/3Ø/4W. Either primary feeder and/or transformer can be shut-down without discontinuing building operations. The transformer secondaries feed double-ended switchgear with an internal tie-breaker which also provides redundant back-up ability. A 600 KW diesel generator provides back-up power for life safety systems, elevators, 125 KVA UPS System and critical tenant loads.

The building is fully equipped with a raised floor structure to allow access for modular electric power, data and voice communications cabling.