12 V Optical Smoke Detector (Art. no. RM1000)

The 12 V optical smoke detector reacts to visible smoke particles. If too much smoke enters its measuring chamber, an alarm is triggered. In the measuring chamber, an integrated infrared light source generates a light pulse every 8 seconds. Smoke particles from a fire change the light signal received by the light diode. A relay trips and the alarm center reports a fire alarm. The 12 V optical smoke detector is mounted on the ceiling in the center of the room. The minimum distance to the side wall should be 30cm. We recommend a separate smoke detector for each entrance area, staircase, living-room, and bedroom. By changing a jumper, you can configure the optical smoke detector as NO or as NC detector. It is therefore suitable for every wired alarm system. The smoke detector is supplied externally with 12V operating voltage and is EN54 certified.

Art. no.:

RM1000

Dimensions:

(HxD) 46x100 mm

Connections:

Screw terminal NO or NC, 1A at 30V DC

Width:

100 mm

Type of detection:

Optical

Housing material:

ABS

Height:

46 mm

Power consumption:

0,368 W

Max. operating temperature:

50 °C

Max. humidity:

95 %

Installation location:

Ceiling

Net weight:

0,152 kg

Sensor type:

Photodiode

DC voltage supply:

12 V

Status display:

Power consumption:

35 mA

Certifications:

EN 54-7

Scope of delivery:

1x 12 V Optical Smoke Detector

1x User manual

General Downloads:

Additional Information:

Surprised in their sleep: 95% of all fire victims don’t die from fire, but from poisonous combustion gases. Smoke alarm devices can change that: in the USA the number of victims fell by more than 40% after the use of smoke detectors was made mandatory. Safety without compromises: with reliable, VdS-certified home smoke alarm devices from ABUS. ... Other interesting products from the category Smoke alarm devices