CUON21002SS Outdoor cooling unit 2100W

This outdoor vertical cooling unit, CUON, with a IP 55 protection degree, is available in many different sizes for different cooling requirements. This means that the right cooling solution can be chosen easily. Smart energy management reduces energy consumption with up to 23% compared to traditional solutions. The cooling unit is easy to install and is also available in stainless steel for harsh environments.

CE Declaration of ConformityEACcULus_UL Listed

Feature: IP 55 TYPE 4, 4X

Characteristics

Height

999 mm

Width

409 mm

Depth

286 mm

Cooling capacity L35L35 (W)

2100 - 2200

Cooling capacity L35L50 (W)

1750 - 1850

Power consumption L35L50 (W)

1120 - 1240

Power supply (V/ph/Hz)

230 / 1 / 50 - 60

Starting current (A)

34

Pre-fuse (A)

15

Max. running current (A)

6.3

Side cabinet fan flow (m³/h)

580

Noise level (dB)

69

Weight (kg)

53.33

Item no.:CUON21002SSEAN no.:8713574212145

Technical data

Features

Downloads

Certificates

Technical data

Description:

High performance cooling unit for vertical installation. CUON is the air conditioning solution for critical environments which the air conditioner is installed outdoors. The unit is external mounted in order to maximize space inside the enclosure. Common to all models is the self cleaning condenser coil which eliminates the necessity for an air filter, avoiding ordinary maintenance. The thermostat is inside the unit and it is adjustable between 25 °C and 45 °C with the Electronic Key-Pad (CUK01) which is available as an accessory. The factory setting is 35 °C. The cooling unit can also be supplied with a mechanically adjustable thermostat upon request. Ozone friendly refrigerant R134a.

Type of connection:

Terminal included.

Material:

Galvanized steel powder coated. The items ending in "SS" are made of stainless steel AISI 304. Stainless steel AISI 316 is available on request.

Temperature limits inside:

+25 °C to +45 °C.

Temperature limits outside:

-40 °C to +55 °C.

Protection:

IP 55 | TYPE 4, 4X.

Finish:

RAL 7035 for the galvanized steel versions.

Features

Feature:

Outdoor vertical cooling unit with smart energy management, available in a wide range of sizes for different cooling capacities, with a IP 54 protection degree.

Advantage:

Customers can choose the cooling unit that meets their requirements the most, removing any extra costs due to oversizing. Smart energy management reduces the cooling units energy consumption by up to 23%.

Benefit:

The efficient cooling unit allows customers to optimise the enclosure's design ensuring that the correct cooling unit is chosen and it hasn't been over specified. The smart energy management and ease of installation will reduce both operational and installation costs. Stainless steel outdoor cooling units are available for harsh environments.

Comment:

To minimise how much energy the cooling unit consumes, it is recommended to install the door switch, DSW01. Once installed, the door switch will turn the cooling unit off, once the door is opened.