Language translation and privacy

The language translation function used by this website is machine automated therefore, should translation alter the intended meaning of the original wording as it was in the English language, then that original wording and meaning shall prevail.

We take your privacy seriously and we are committed to keeping your information safe. Your personal data will be used to process your query in accordance with our privacy policy. We may also share your information with our third party service providers to carry out surveys or works on our behalf. For more information on how we collect and process your data, please see our privacy notice.

Your browser does not support JavaScript or has it disabled. To enable full functionality of this site it is necessary to enable JavaScript.

Generation Availability Map

Please click on any of the links below to be taken to the relevant map

Please note that network constraints may be caused by a number of issues including; thermal limits on a cable, upstream restrictions, fault level or voltage rise constraints. Our innovation team are looking at different ways to overcome these challenges to view our current projects please click here.

Please note: the Constrained term at distribution level in our Central Southern England Generation Availability Map is assessed based on the addition of at least 5MVA synchronous generator. If you intend to apply for generator capacities below 5 MVA, you may consider the constrained areas as well as unconstrained.