2.0 DESCRIPTION - The house shall be completely assembled, ready to install, and capable of housing any equipment as shown on the drawings. The Bevco House shall be model 7523-F and shall be supplied with all components factory mounted and wired.

3.0 DESIGN - The house shall be compartmentalized with two separate sections, one section for chlorine or other equipment and the other section for electrical equipment. The house shall be of a one piece molded fiberglass reinforced polyester (FRP). The floor shall be 11 gauge steel, provided as an integral part of the house, and reinforced to support gas cylinders or other heavy objects. The floor shall be vinyl covered. The interior of the house shall be insulated with a 1" minimum layer of plastic insulation. The plastic insulation shall meet U.L. specifications for fire resistant SE -1 foam with an R-value of 7.2. The house shall have dimensions of 67-1/4" wide, 29" deep, by 81" high with pre-drilled holes for fastening to 1/2 inch bolts preset in concrete. The roof shall be pitched and provided with a drip lip. The side wall shall contain two screened vents, one for an air inlet and one for exhaust. The house shall have two independent, continuously hinged, three point latched doors. One door shall have a key lock handle. On the chlorination compartment, a gas tight window, 9"x7", shall be provided for inspection of the interior without opening the door.

4.0 COMPONENTS - The house shall have the following components factory mounted and wired in non-conductive, non-corrosive electrical conduit, boxes and fittings.