Project Payback

ROI: 3.3 years

Savings

Energy: 84%

Electricity: 69,433 kWh pa

Project Overview

enLighten Australia was awarded the supply and install contract for the LED lighting upgrade of the building’s two fire stairs in mid 2012. The existing
emergency lighting in the fire stairs was twin (18W and a mixture of 32W & 36W) fluorescent tube lighting with magnetic ballast which was operating
24 hours per day with no controls.

The lighting upgrade is yet another exciting and highly successful initiative which ensures a high level of sustainability and further reduces the environmental impact of this building.

Keryn Ward
General Manager NAB House, AMP Capital

Gallery

The Solution

The retrofit resulted in the replacement of the existing 184 fluorescent fittings (368 tubes) within the fire stairs with 184 emergency Chamaeleon lights
producing the same light output levels. A combination of 10 chip ceiling and wall mounted emergency Chamaeleon fittings were used.

Fire stair meter data supplied by the building management indicated an average 81% reduction in lighting electricity usage across sub-metered lighting circuit covering fire stairs 1 and 2. The pre-installation consumption figure for May 2012 of 4,587kWh
reduced to 910kWh following the installation of the new lights.

Between 2008 & 2011, an upgrade program was undertaken including central plant upgrades, new on-floor air distribution system, new building management
control system and architectural upgrades whilst maintaining full occupancy. The building achieved a 5 Stars NABERS Energy rating in 2011 and again
achieved a 5 star rating in July 2012.

enLighten Australia was awarded the supply and install contract for the LED lighting upgrade of the building’s two fire stairs in mid 2012. The existing
emergency lighting in the fire stairs was twin (18w and a mixture of 32w & 36w) fluorescent tube lighting with magnetic ballast which was operating
24 hours per day with no controls.

Products used

Figure 1: Fire stair lighting meter report, 255 George St, Sydney

The retrofit resulted in the replacement of the existing 184 fluorescent fittings (368 tubes) within the fire stairs with 184 emergency Chamaeleon lights
producing the same light output levels. A combination of 10 chip ceiling & wall mounted emergency Chamaeleon fittings were used.

The innovative design feature of the emergency version of the Chamaeleon is the external accessible battery compartment for simple battery replacement
without needing to isolate the power supply.

Electricity savings results

Fire stair meter data supplied by the building management indicated an average 81% reduction in lighting electricity usage across sub-metered lighting circuit covering fire stairs 1&2. The pre-installation consumption figure for May 2012 of 4587 kWh
reduced to 910kWh following the installation of the new lights.

Project ROI

Calculation of the LED retrofit project ROI of 3.3 years is inclusive of electricity and maintenance savings. Maintenance savings are calculated using
conservative estimates for maintenance access, lamp and control component replacement costs, disposal costs and emergency battery costs.