Product category:

Available in (kW):

Salient Features

3D Airflow

Circulates a cloud of cool air right to the corner of even large spaces

Coanda airflow

Coanda airflow operation gives you the best air-conditioning experience. The powerful air draft does not fall on your head directly, but it is steered upward letting air circulate into the corners of the room creating a comfortable ambience.

Econo mode

This function enables efficient operation by limiting the maximum power consumption. It is useful when using the air-conditioner and other electrical devices simultaneously on a shared electrical circuit.

Indoor unit quiet operation

This feature ensures low noise level resulting in sound sleep. It optimises the speed of the airflow according to low noise level to give you uninterrupted comfort.

Power chill operation

When the rooms needs to be cooled quickly in extreme heat, power chill ensures that the room temperature drops fast for immediate comfort.

Specification

Model name

Indoor unit

FTKF35TV16U

FTKF50TV16U

FTKF60TV16U

Outdoor unit

RKF35TV16U

RKF50TV16U

RKF60TV16U

Power supply

1 50Hz 230V

1 50Hz 230V

1 50Hz 230V

(220-240V)

(220-240V)

(220-240V)

Power supply intake

Outdoor unit

Outdoor unit

Outdoor unit

Cooling capacity Rated Full/Half (min.~max.)

kW

3.62/1.81 (1.17~4.0)

5.28/2.64 (1.0~6.0)

6.0/3.0 (1.0~7.0)

Cooling capacity Rated Full/Half (min.~max.)

Btu/h

12350/6175(4000~13600)

18016/9008(3412~20472)

20500/10240(3400~23900)

Power consumption Rated Full/Half (min.~max.)

W

822/281 (220-1300)

1290/450 (200-1700)

1665/545 (210-2250)

Annual Power consumption

kWh

483

767

957

ISEER / Star Rating

Wh/Wh

5.80 / 5*

5.33 / 5*

4.85 / 5*

Voltage Range

V

160-265

130-265

130-265

Operating current

Cooling

A

3.8

5.8

7.4

Indoor unit

Panel colour

White

White

White

Dimensions HxWxD

mm

298 x 885 x 229

298 x 885 x 229

298 x 885 x 229

(Package dimensions)

mm

(375 x 980 x 325)

(375 x 980 x 325)

(375 x 980 x 325)

Weight (Gross)

kg

11 (16)

11 (16)

11 (16)

Airflow rate *1 X(Y)

m3/min.

13 (11.9)

16.6(13.7

16.3(14.8)

Feet3/min (CFM)

459 (420)

586(484)

576(523)

Operation sound H/M/ML/L/SL

Cooling

dBA

40/38/35/33/31

47/45/43/37/32

47/43/39/34/30

Outdoor unit

Dimensions (H x W x D)

mm

550 x 765 x 285

595 x 845 x 300

595 x 845 x 300

(Package dimensions)

mm

(642 x 932 x 380)

(680 x 1035 x 410)

(680 x 1035 x 410)

Weight (Gross)

kg

32(38)

39(47)

39(47)

Operation sound (H)

Cooling

dBA

51

54/51

56

Breaker size

A

15

20

20

Piping length

Charge-less

m

10

10

10

Max. length

m

20

30

30

Max. height

m

15

20

20

Piping connection

Gas/Liquid

mm

9.5/ 6.4

12.7 / 6.4

12.7 / 6.4

Operation limit

Cooling

oCDB

19.4~52

19.4~52

19.4~52

Measurement conditions:

Sound levels are based on temperature conditions 1. above with 5m piping length. These are anechoic conversion values. These values are normally somewhat higher during actual operation as a result of ambient conditions.

Cooling and heating capacities above are rounded off to first decimal. 1TR (Ton of Refrigeration) = ~3.517 kilowatt.