3 Safety and Application notes The SubstiTUBE condition. Advanced UO UN must not be damaged or operated in a damaged When operating with CCG, the included SubstiTUBE Start has to be inserted as well. If the conventional starter is not replaced the SubstiTUBE Advanced will start blinking. Switch off immediately, the SubstiTUBE Advanced UO UN can be damaged! Lamp suitable for 50 Hz or 60 Hz operation Lamp suitable for high frequency operation Lamp not suitable for emergency operation Not usable in luminaires with serial lamp connection i.e. more than one tube at one magnetic ballast (tandem circuitry). The SubstiTUBE Advanced UO UN emits light only with a limited angle, not like a fluorescent tube with 360 output. The temperature range of this lamp is more restricted. SubstiTUBE Advanced UO UN is compatible with ECGs of various brand manufacturers. For further information regarding the tested ECGs a compatibility list can be found on the following page. The compatibility list is based upon testing conducted by the manufacturer in a lab simulated environment, and the results can vary in certain field applications due to a number of factors. OSRAM does not take over any responsibility, warranty or liability that these results can also be achieved by using the devices under other conditions, or when using successor models of the tested devices, or different models of the same manufacturer. In case of non-observance of the instructions, safety risks like overheating of SubstiTUBE or ECG may occur in rare cases. Due to the characteristic light distribution of the SubstiTUBE Advanced UO UN, the resulting luminaire light characteristic is likely to change. It is not guaranteed that e.g. standards for lighting at working places will be complied to after replacement. A photometric check of the installation is recommended. The effective energy savings depend on the efficiency of the luminaire setup to be replaced and should be considered individually in each case. Particularly magnetic ballast losses are reduced to ohmic losses and are normally only about 1 W. The SubstiTUBE Advanced UO UN is protected according to IP20. Applications with external risk of moisture and dust can be served with an adequately protected luminaire. SubstiTUBE products differ in their diameters and geometries from fluorescent lamps. Their use in open batten luminaires with gaskets is possible if no excessive force is expended during the fixing. Obtaining the necessary IP protection in open batten luminaires with gaskets cannot be ensured. ST8AU-1.2m-UN August 2016 Page 3 of 6

4 SubstiTUBE Advanced UO UN may also be driven directly on line voltage. In order to grant a safe operation mode please refer to the installation instructions for further information. Photobiological Safety of lamps and lamp systems according to IEC Risk Group: Exempt Installation Instructions for CGG Make sure that the supply voltage is disconnected. Carefully remove the fluorescent tube and starter according to the lamp holder type. Insert SubstiTUBE Advanced UO UN and SubstiTUBE Start properly. Remark: Please use the starter which is enclosed in the packaging! Below an example for typical lamp holder types is described Turn the conventional lamp 90 degrees and take it out of the socket. Remove the conventional starter by turning it. Insert and latch the SubstiTUBE Start into starter socket. Insert SubstiTUBE Advanced UO UN into socket and locate into position by turning 90. Press safety buttons on each side of the lamp and connect SubstiTUBE to supply voltage Check light emission direction. ST8AU-1.2m-UN August 2016 Page 4 of 6

SubstiTUBE T8 Advanced UN Installation instructions for SubstiTUBE T8 ADVANCED UNIVERSAL Starter-Test: See whether the luminaire has a starter. If it does not have a starter, you need an operation on an

Philips InstantFit LED PL-C/T Lamp The Philips InstantFit LED PL-C/T lamp is a technology breakthrough out of our LED lamps portfolio. This product is compatible with programmed start ballasts and is the

Guidelines for Specification of LED Lighting Products 2010 September 2010 Introduction With LED s emerging as a new functional light source there is a need to ensure performance claims are made in a consistent

PLCC Series PLCC Series 2835 1W Datasheet Bulb General Lighting Floor Lamp Wall Light Tube Light Introduction : Ultra high luminous efficacy, combined with the flexibility in design due to its slim and

PLCC Series PLCC Series 5630B HE High CRI Datasheet Down Light Commercial Lighting General Lighting Introduction : PLCC 5630B HE Series features ultra high luminous efficacy and compact package size which

Data Sheet 1 / 5 240 Light Distribution 260 Light Distribution At 470 to 806 lumen, Toshiba s design classic is way ahead from an aesthetic and performance perspective. As a lamp with an intense beam of

PLCC Series ET-5050x-BF1W Datasheet Features : High luminous Intensity and high efficiency Based on GaN technology Wide viewing angle : 120 Excellent performance and visibility Suitable for all SMT assembly

The systematic way to get more light In most cases, the lamp developments are effectively system developments as they also involve modern electronic control gear at every stage. This is the only way to

Introduction Edison Opto advanced a variety of AC modules, such as ceiling light module and down light module. With reference to the property, these Modules have been driven by AC power, so that products