Motor Amps

I read the article on the use of variable-frequency drives on forced-draft fans at the University of Rochester (“Variable-Frequency Drive Improves Boiler Operation,” January 2011, http://bit.ly/Eisenhauer_0111).

Why do the amps on the motor not change significantly when the demand on the boiler changes with the damper-controlled airflow?

I put a monitor on a motor, and the amps did not change significantly.James B. Jones NutraSweet/GreenWood Augusta, Ga.

Co-author's response:

I do not know the type of air handler you have or where the dampers are positioned. Therefore, a rough explanation of why your amps do not drop significantly when you throttle the flow via a damper on a centrifugal air handler basically is based off of this equation:

In the case of inlet dampers, flow, pressure, and fan efficiency drop. Therefore, inlet dampers are more electrically efficient than outlet dampers. However, they don't compare to reducing the speed of the blower and taking advantage of the affinity laws:

hp = speed3

Following are links to documents providing a much more thorough explanation:

This webinar will walk you through a systematic approach to maintaining building controls systems and the benefits that are gained through this approach, both during building startup and throughout the lifecycle....More

This webinar will cover important tasks that should be performed during summer break to ensure school HVAC systems operate reliably and efficiently throughout the school year, providing good indoor-air quality and thermal and acoustical comfort for students and staff members....More