Features&colon; 1&period; Three phase in and out system&comma; compatible with utility of 380&sol;400&sol;415V&comma; 50&sol;60Hz2&period; Online double conversion&comma; offering load with best power quality3&period; Support all kinds of load&comma; high overload capability4&period; Fully digital control with three DSPs including IGBT rectifier&comma; inverter&comma; charger5&period; Digital circulating current control technology&comma; increasing the parallel reliability6&period; Wide input voltage window&comma; compatible with different utilities7&period; Green power technology&comma; high input power factor&comma; low current THD&comma; high efficiency8&period; Intelligent battery management&comma; extending battery lifetime9&period; Intelligent self-diagnose function&comma; all kinds of fault protection&comma; large capability of history record storage&period; 10&period; Full front maintenance&comma; saving space&period; 11&period; Redundant design of power model fans&comma; increasing the system reliability12&period; Modularized design of subsystem&comma; convenient field maintenance13&period; High MTBF&lpar;mean time before failure&rpar;&lpar;>200&comma; 000h&rpar;&comma; low MTTR&lpar;mean time to repair&rpar;&lpar;<0&period;5h&rpar;14&period; Large LCD display&comma; friendly human machine interface15&period; Configured with top and bottom cable connection16&period; Parallel up to 6 units&period; 17&period; All kinds of options include main back feed protection&comma; bypass back feed protection&comma; battery leakage protection&comma; battery start kit&comma; output isolation transformer and lighting protection kit&period;

Model

HT3310

HT3315

HT3320

HT3330

HT3340

HT3360

HT3380

HT33100

HT33120

HT33160

HT33200

Capacity

10KVA

15KVA

20KVA

30KVA

40KVA

60KVA

80KVA

100KVA

120KVA

160KVA

200KVA

Main Input

Input voltage

380V/400V/415V(line to line), 50/60Hz

Input connection

3Ph+N+PE

Power factor

>0.99

Input cuurent THD(Total Harmonic Distortion)

<3%

Input voltage window

+20%~-20%, full load

-20%~-40%, power derating between 100% to 70%

Frequency window

40-70HZ

Bypass input

Input voltage

380V/400V/415V

Input voltage window

+20%--20%, full load

-20%--40%, power derating between 100% to 70%

Frequency window

±3Hz (adjustable)

Battery

Battery voltage

±240VDC

Charger power

20%*Power

Charger voltage precision

1%

Output

Voltage precision

±0.5% (balance load),2% (unbalance load)

Output voltage transient

2%(0~100% load step)

Voltage THD(Total Harmonic Distortion)

THD<0.5%(linear load),THD<3%(nonlinear load)

Power factor

0.8

Frequency tracking range

50/60Hz±3Hz, adjustable

Frequency precision (free running)

±0.01%

Phase tolerance

120°±0.5° (balance and unalance load)

Voltage unbalance degree (100% unbalance load)

±3%

Frequency tracking speed

0.5Hz/s to 5Hz/s, adjustable

Crest factor

3:1

Overload capabiltiy

105% long time operation

110%, transfer to bypass after 1hour

125%, transfer to bypass after 10 minutes

150%, transfer to bypass after 1 minute

>150%, transfer to bypass after 200ms

Bypass overload capability

150%, long time operation

150%< load <180%, last for more than 1 minute

>1000%, last for more than 100ms

System

System efficiency

Normal mode: 95%

ECO mode: 99%

Battery mode efficiency

95%

Battery configuration

12V, 40PCS (38~42pcs acceptable)

Display

LCD+LED, Touch screen and keyboard

EMI

IEC62040-2

EMS

IEC61000-4-2(ESD)

IEC61000-4-3(RS)

IEC61000-4-4 (EFT)

IEC61000-4-5 (Surge)

Insulation resistance

>2M (500VDC)

Dielectric strengh

(input,output to PE)2820Vdc, leakage current lower than 3.5mA, no flashover in 1 minute