Temperature Control Unit : Water

... Model: VT-4750-30

A pump circulates water through the process. A heater and a cooling valve work together to control the water temperature.

This temperature control unit requires a plant water supply source.

Temperature control units are portable, built on casters to easily move the unit between processes.

Units are available with a variety of different control instruments, heater sizes, cooling valves and physical packages.

Specifications

VT-4750-300 (1)

Heater (2)

kW : 24

Process Pump

HP : 7-1/2

GPM : 100

PSI : 47

Full Load Amperage (3)

230/3/60 : 76.0

460/3/60 : 38.0

575/3/60 : 31.7

Connection Sizes

To Process : 2"

From Process : 2"

Water Supply : 1/2"

Drain : 1/2"

Dimensions

Height : 44"

Width : 16"

Depth : 24"

Weight (5)

Shipping : 310 lbs

Specification Notes:

1. Since product innovation and improvement is our constant goal, all features and specifications are subject to change without notice or liability. Selection of certain optional features may change listed specifications.

2. Derate heater output by 25% for 208/3/60 operation.

3. Full load amps are higher than run load amps and must be used for sizing disconnects and supply wiring. Not for construction. Consult factory for power requirements of unit as configured and on selected options.

4. Consult factory for 50HZ operation.

5. Unit weight crated for shipment.

Features

Process Pump

7.5 HP process pump

Stainless steel shaft

Horizontal motor extends bearing and seal life

ODP (open drip proof) motor

Pump seal flush line

Custom designed impeller and casing

High grade mechanical contactor with over current, phase loss and short circuit protection

Temptek, Inc. 525 East Stop 18 Road, Greenwood, IN 46142 Phone: 317-887-6352 Fax: 317-881-1277
Product innovation and improvement is our constant goal. All features and specifications are subject to change without notice or liability. Products are
assembled in the United States of America. Site Map

2018 TEMPTEK, INC

Close

This site uses cookies to offer you a better browsing experience. Learn more about how Temptek, Inc. uses cookies by contacting the site administrator at
admin@temptek.com. By closing this banner, scrolling this page, clicking a link or continuing to browse otherwise, you agree to the use of cookies.
Please refer to the Privacy Policy for more information.