What is in this article?:

Find the Answer

Ron LaRosa, president of R&L Maintenance, Inc., in Oak Park, Ill., made reference to these three Code sections when citing violations for this installation.

“110.11 — Equipment cannot be installed in an environment that will have a deteriorating effect.

“110.27 — It appears this disconnect does not have a door interlock, which would prevent you from opening it with the switch in the closed position, and coming into contact with live parts.

“300.6 — Electrical equipment and materials must be protected against corrosion.”

Charles L. Rogers Sr., SSA Regional Engineering / Smith Group, Social Security Administration — Region 4, Atlanta, offered these comments. “No lockout means; I question the 3-phase circuit to single-phase equipment; the conductors are routed through restricted space; electrical continuity is in jeopardy because of rust; phase conductors may not be properly identified; and equipment is failing because of corrosion.”

Tony Helms of the BCF Group, El Cajon, Calif., added these comments. “Bad connections at terminations. The un-switched white conductor is unused. Equipment grounding is questionable because of rusted out dirty switch enclosure, and it is corroded too!”

EC&M White Papers

Labor costs often represent one of the biggest expenses in an companies budget. You can reduce those costs and get more work done by using the techniques outlined in this eBook to improve driver efficiency and productivity....More

Designing a grounding system for industrial facilities can raise many questions along the way. The two main questions determining the final decision have generally always pertained to service continuity and single phase loads....More

Download these Frequently Asked Questions, sponsored by Westex to learn more about FR Clothing. These FAQs discuss the benefits of arc rated clothing and how NFPA 70E applies.
Download now to learn more....More

The electrical industry spends hours participating in training in order to understand the revisions found in the 2014 NEC that will enhance electrical safety for our community. Electrical code revisions also serve as a significant catalyst that enables investment,...More

Are you protected in the event of short circuit fault? Stainless steel cable ties provide a durable method of bundling, identifying and fastening cable in severe and harsh conditions.
Productivity. Reliability. Safety. We’ve Got You Covered....More

Productivity. Reliability. Safety. We’ve Got You Covered.
The connectors and crimping process make the Panduit solution unique. Offering the speed and safety of a compression connection, while exceeding the stringent requirements of IEEE Std 837-2002. Install in ANY weather. No burn permits needed....More

Arlington's TVBU810 delivers the ultimate in versatility for installing wall-mounted TVs in new or retrofit projects. You can install it horizontally or vertically to ensure proper positioning of low voltage connections behind the TV....More