A96447 Introduction Congratulations! As the owner of Bryant’s Zone Perfect Plus zoning system, you have made a commitment to improving your indoor comfort. Zone Perfect Plus allows your heating and cooling system to follow your schedule and provide greater comfort in areas which are difficult to heat or cool. Here’s how it works: Your Bryant dealer has divided your home or business into zones which are controlled separately. Instead of setting one temperature for the entire house or business, yo

Built into these units are features most desired by consumers today. SEER ratings of up to 16.0 SEER and 9.1 HSPF can be reached when combined with specific Bryant equipment. All models are listed with UL, c-UL, ARI, CEC, and CSA-EEV. The 698B meets the Energy Star® guidelines for energy efficiency. FEATURES COIL PROTECTION—The DuraGuard coil protector, made of a 12 gage coated steel wire grid with vertical 3/8 in. spacing, is designed to help protect the coil from inclement weather, vandalism,

This is done in Advance Setup Step #5, by selecting 1. The room temperature may be viewed by holding in the On/Off button for 2 seconds. Releasing the On/Off button will return the display to the previous screen. OUTDOOR SENSOR An outdoor temperature sensor may be connected to this thermostat. Totaline offers wired or wireless models. Compatible models include: P474-0401RF/REC & P474-0400. Consult the remote sensor instruction sheet for wiring connections. Page 15 About Advanced Features & Opera

DISCONNECT POWER TO THE HEATER - AIR CONDITIONER BEFORE REMOVING THE OLD THERMOSTAT AND INSTALLING WARNING THE NEW THERMOSTAT. CAUTION The 2 Alkaline “AA” batteries must be replaced at least every 12 months to assure proper operation. The thermostat will display the Low Battery code (fig. 1) on the display of the thermostat when it is time to replace the batteries. FIG. 1 When is displayed the batteries must be replaced immediately. The manufacturer cannot be liable for improper operation of the

When disabled, AUTO icon does not appear when successive presses of MODE button are used to move between OFF, HEAT, and EHEAT (in heat pump systems). Factory default is ON (AUTO mode enabled). TO SELECT: 1. Enter configuration mode (if not already there). 2. Use up and down buttons to display Option 15. The SET icon should be off. 3. Press MODE button once. The SET icon will come on. The display now shows Option 15 setting. 4. Use up and down buttons to move between available Option 15 choices o

TO ADJUST: 1. Enter configuration mode (if not already there). 2. Use up and down buttons to display Option 01. The SET icon should be off. 3. Press MODE button once. The SET icon will come on. The display now shows Option 01 setting. 4. Use up and down buttons to move between the available Option 01 values of 1 to 9. Factory default is 3. 5. Press MODE button again to return to Option 01. The SET icon will now be off. 6. Use up and down buttons to select another Option, or press FAN button to e