(By-the-Foot) 1/0 Black Stranded CU THHN Wire

Sorry, but we ran into issues loading these options. Please try refreshing.

Frequently Bought Together

Product Overview

Southwire’s THHN and THWN-2 is a multi-purpose building wire used in conduit and cable trays for service, feeders and branch circuits in commercial and industrial applications. It is also used as a conductor in NM-B, UF-B, SER, SEU and MC. Southwire’s THHN is rated for 600-Volt and has a heat capacity of up to 90˚C.

Enter your desired electrical wire length in quantity box.

Can be used in wet or dry locations

Made with annealed (soft) copper, compressed

Insulation is high heat and moisture resistant polyvinyl chloride (PVC)

greetings , is this cable rated for wet locations by nec definitions?
I'm actually looking for thwn-2 cable
This is for underground conduit for main service to home

Asked by: rock

Hello,
According to the Spec sheet i have attached our THHN products are moisture resistant.. &quot;600 Volts. Copper Conductor. Thermoplastic Insulation/Nylon Sheath, Heat, Moisture, Gasoline and Oil Resistant II. All Sizes Rated Both THHN and either THWN (sizes 14, 12, and 10 AWG) or THWN-2 (sizes 8AWG and larger). Also Rated MTW and AWM (See Below). SIMpull&reg; Technology for Easier Pulling.&quot; I have attached the link below.
http://www.southwire.com/ProductCatalog/XTEInterfaceServlet?contentKey=prodcatsheet276The above advice is based upon the current edition of the National Electric Code (NEC). Free access to the latest version of the NEC is available online at www.nfpa.org/freeaccess. The NEC and local building codes regulate the types of wire and cable that can be used in specific electrical applications, as well as the manner of installation. Check your local building codes before you start any wiring and cable electrical project and be sure to obtain required permits. When your work is complete, always have it inspected for compliance with local codes to ensure that it has been safely installed.

Answered by: SouthwireCustomerService

Date published: 2017-06-17

im wiring a garage and have a 100 amp main breaker and a 125 amp fuse box i need cable to go from pole to garage

Asked by: willy

If I understand properly, you need a wire or cable capable of 100 Amps (it is protected by a 100A breaker at your main panel). You can use THHN conductors for this application but they will need to be installed in conduit, both inside and outside. For a 100 Amp circuit, you would need at least size 3 AWG CU THHN conductors. For the ampacities of CU THHN conductors, please see the catalog sheet at:
http://www.southwire.com/ProductCatalog/XTEInterfaceServlet?contentKey=prodcatsheet276
Use the 75&deg;C column for the allowable ampacity. If you really need 125 Amps, use size 1 AWG conductors.

Customer Reviews

Rated 5 out of
5 by
Anonymous from
5 Star ReviewRating provided by a verified purchaser

Date published: 2017-04-04

Rated 5 out of
5 by
Deer954 from
1/0 thhn wireVery good quality wire , fairly easy to pull through # 2 inch conduit . And the employees of NW Dade Home Depot in Miami Fl were super helpful in helping load this 500 ' roll of wire into my truck . Thank you Home Depot for the good prices , quality and service.

Related Searches

Related Products

1000 ft. 3/0 Black Stranded THHN Wire

The Southwire Company 1 000 ft. Black 3/0The Southwire Company 1 000 ft. Black 3/0 Stranded THHN Cable is mainly used in conduit and cable trays for services feeders and branch circuits in industrial or commercial applications as specified in the NEC2. It is rated at 600-Volt. It is also used as a conductor in NM-B UF-B ... More +Product DetailsClose

1000 ft. 6 Black Stranded CU THHN Wire

The Southwire Company 1 000 ft. Black 6-GaugeThe Southwire Company 1 000 ft. Black 6-Gauge Stranded THHN Cable is primarily used in conduit and cable trays for services feeders and branch circuits in commercial or industrial applications as specified in the NEC2. It can be used as a conductor in NM-B UF-B SER SEU and MC. This ... More +Product DetailsClose

2,500 ft. 2-Gauge Black Stranded CU SIMpull THHN Wire

Southwire’s THHN and THWN-2 is a multi-purpose buildingSouthwire’s THHN and THWN-2 is a multi-purpose building wire used in conduit and cable trays for service feeders and branch circuits in commercial and industrial applications. It is also used as a conductor in NM-B UF-B SER SEU and MC. Southwire’s THHN is rated for 600-Volt and has a heat ... More +Product DetailsClose

2,500 ft. 3-Gauge Black Stranded CU SIMpull THHN Wire

Southwire’s THHN and THWN-2 is a multi-purpose buildingSouthwire’s THHN and THWN-2 is a multi-purpose building wire used in conduit and cable trays for service feeders and branch circuits in commercial and industrial applications. It is also used as a conductor in NM-B UF-B SER SEU and MC. Southwire’s THHN is rated for 600-Volt and has a heat ... More +Product DetailsClose