Great Service

MARILYN - Northborough, MA76 days ago

Tri State services 87 of our locations and does a great job. Their customer service is excellent and their pricing is reasonable.

Overall Experience 5 / 5

Quality

Price

Convenience

Nick was fantastic

Texas BBQ - Northborough, MA112 days ago

Nick provided the service for our retrofit/repair/code work whatever this job is titled. He was nothing but professional and courteous. I would recommend him to anyone for their work with Tri-State. I we are able to request technicians for future jobs, he would be my go to guy. Thanks for the great job.

Overall Experience 5 / 5

Quality

Price

Convenience

Professional and on time

Kris - Northborough, MA452 days ago

everyone was very professional and on time made sure that everybody was on the same page before the work started, testing was completed and successful as always on top of the inspection.

Overall Experience 5 / 5

Quality

Price

Convenience

64 days ago

mark g.

Near Shops Way, Northborough, MA01532

76 days ago

Derek D.

Near Shops Way, Northborough, MA01532

113 days ago

Nicholas L.

Kitchen Hood Suppression System - NON COMPLIANT
Recently one of our licensed technicians was at your location to perform the service on your fire suppression system. During that inspection the following deficiencies were found on order 14236181Nozzle for first fryer is installed too low per Amerex requirements. Nozzle must sit between 40"-50" inches. Currently at 30"
The 10 burner range has a back shelf. The nozzles installed would protect this unit if the back shelf was not in place. If the back shelf remains the line would need to be repiped under the shelf with nozzle type 11982 protection (5 nozzles total)
Pipe one additional appliance to the smaller cylinder to allow proper flow capacity on the larger cylinder. (only supports 11 flows and has 11.5 piped into it). The smaller cylinder can spare 2 flows if back shelf is removed or 3 if the shelf remains and new coverage added.
Replace and update the 3 male threaded nozzles over the griddle and fryers that are no longer supported b

Derek D.

Derek D.

Near E Main St, Northborough, MA01532

217 days ago

Derek D.

Near E Main St, Northborough, MA01532

454 days ago

Robert O.

Near Bearfoot Rd, Northborough, MA01532

454 days ago

Nicholas L.

The appliance line has recently been modified. The fire suppression system will need to be re-piped to accommodate these changes. Tri State proposes to re-pipe the appliance line.Fire Suppression Repair
Kitchen System -R 102 7.5 G
Hydro: 2012 newKS TO BE DONE WITH FX & EL
system is non compliant due to improper coverage of the appliances. customer rearranged the line by switching the fryers and one of the griddle. see pictures. These appliances need to be moved back where they were or the appliance line will need to be repiped. - repair

Near Shops Way, Northborough, MA01532

606 days ago

Nicholas L.

Kitchen System -R 102 7.5 G
Hydro: 2012 newKS TO BE DONE WITH FX & EL
Deficiency: system is non compliant due to improper coverage of the appliances. customer rearranged the line by switching the fryers and one of the griddle. see pictures. These appliances need to be moved back where they were or the appliance line will need to be repiped.
Fire Suppression Inspection