It is used to transmit and distribute power in power transmission and distribution system of 35kV or lower. It is generally applied to the fields including power, construction, mines, metallurgy, petrochemical industry and communication in complete replace of oil immersed paper insulated power cable and in partial replace of PVC insulated power cable. Power cables for power networks, underground, outdoors and in cable ducting

1.Rated voltage: Uo/U:3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).2. No. of core: Single core or three cores.3. The highest allowed operating temperature of conductor for long-term working is 90oC. In short-circuit (Max. long-term is no more than 5 seconds). The highest temperature for conductor is no more than 250ºC.4. D.C. resistance of the conductor complies with the stipulations of 3.6/6kV, 6/10kV(11kV), 12/20kV(24kV), 19/33kV, 26/35kV(35kV).5. The environment temperature should be no lower than 0oC when lay. Otherwise it should be preheated.6. The cable is laid without horizontal drop limit.7. Working Frequency Voltage Test: 3.5Uo/5min without puncture.8. Partial Discharge Test: The discharge volume should be no more than 10pC under 1.73Uo for the cable.

Company Introduction:HeBei huatong wires&cables Group Co.,ltd.It was established in 1993, we are JV with Furukawa(Japanese company) for rubber serious cables and JV with Riken(Japanese company) for elevator cables. Besides these,our submersible oil pump cable and shipboard cable are very influential in domestic, and, the traditional cables are also produced such as PVC powercables, XLPE power cables, ABC cables, wires, control cables, screened cables,communication cables, conductors.We areOEM for many USA, Europen, Australia cable company,70% of our products are exported, most customers are from developed countries. We got ISO,UL,TUV,KEMA,CE and many other certifications.