Welcome to HVAC-Talk.com, a non-DIY site and the ultimate Source for HVAC Information & Knowledge Sharing for the industry professional! Here you can join over 150,000 HVAC Professionals & enthusiasts from around the world discussing all things related to HVAC/R. You are currently viewing as a NON-REGISTERED guest which gives you limited access to view discussions

To gain full access to our forums you must register; for a free account. As a registered Guest you will be able to:

Participate in over 40 different forums and search/browse from nearly 3 million posts.

OMG, Found this gem the other day. The picture should speak for itself.

How's this one? Hot water pressure was very low, two 40 gal gas fired water heaters run in series, the outlet from heater 1 to heater two had deposit about 1/4" thick, both thermostats nearly maximum. Cleared debris by using CLR to dissolve, then set heater 1 at 110F output and heater 2 at 140, everything is fine now...

How's this one? Hot water pressure was very low, two 40 gal gas fired water heaters run in series, the outlet from heater 1 to heater two had deposit about 1/4" thick, both thermostats nearly maximum. Cleared debris by using CLR to dissolve, then set heater 1 at 110F output and heater 2 at 140, everything is fine now...

Nice picture!

I usually wear a ball cap while i'm working, no one ever breaks your stones about the tiara?

Every customer you take for granted today will be someone else's tomorrow.