How do you determine if an area is high risk and requires 10% of the maintained (normal) illuminance. Is this via risk assessment?

My reason for asking the question is that i'm looking at a scheme which involves a distillery for Gin. Now the area is classed as a Zone 1 Atex space but this is purely because the danger in the flammable content of the air due to the alcohol. The area itself contains no moving machinery or any further risks to human life. So is this space classed as high risk due to the nature of the air or can this be classed as open space with escapes routes where 1 Lux is required.

high risk task area lightingthat part of emergency escape lighting that provides illumination for the safety of people involved in a potentially dangerous process or situation and to enable proper shut down procedures for the safety of
the operator and other occupants of the premisesalso

4.4 High risk task area lighting

4.4.1 In areas of high risk the maintained illuminance
on the reference plane shall be not less than 10 % of
the required maintained illuminance for that task,
however it shall be not less than 15 lx. It shall be free
of harmful stroboscopic effects.

4.4.2 The uniformity of the high risk task area lighting
illuminance shall be not less than 0,1.

Personally speaking, i wouldn't say that walking through or escaping from the space was a high risk task despite the environment. You don't need to do anything other than get out. Obviously your client will advise the outcome of his risk assessment. Depending on the size I'd go with an anti panic area with a minimum of 0.5 lux overall.

If it's ATEX Zone 1 you might just have a problem with integral batteries though - it's quite probable that with conversion of the ATEX general luminaires (or operation from a battery and invertor outside the zone) you'll get above 15 lux anyway.

The Atex fittings will adopt an integral PL lamp and battery back up, the problem i have is that if every luminaires within the space incorporates this i achieve 15 Lux, however the space achieves an overall 300 lux value for general lighting so for hazardous areas i would need to a achieve 10% of this which would be 30 Lux. I just cant achieve this.

So shall i just settle at 15 Lux or do i say that 0.5 Lux is acceptable. Other than the flammable atmosphere there it no risk to human life.