'Easy' control family version history (PEC+, PEC, SEC-HD, SEC-DC, TVS)

PEC+1.18- Improved actuator positioning when near the end of its range. Some actuator motors have problems positioning when using their maximum range. 1.16- Fixed bug that sometimes causes a lockup (requires hardware modification on display boards s/n 20121204-20130623)1.15- Fixed bug where if VAR 2 is configured as OFF, it will still follow its settings and turn on if VAR 1 is not configured as OFF.- Fixed bug where if one VAR stage is configured as heat and the other for cool, the two stages will cycle on and off if one stage is calling to be off while the other is on.1.14- Added 2 motor curves (CL3, CL4) 1.12- Increased temperature range to (-13F to 125F) and (-25C to 51C) - Fixed bug where if in the temperature override mode and the menu timed out and exited, it would continue using the override temperature- Fixed bug where sometimes an updater would not be recognized

PEC1.18- Improved actuator positioning when near the end of its range. Some actuator motors have problems positioning when using their maximum range.1.16- Fixed bug that sometimes caused a lockup (requires hardware modification on display boards s/n 20121204-20130623)1.15- Added 2 motor curves (CL3, CL4)1.11- Fixed bug that could cause corrupted settings after 24 hours of use.- Fixed bug where sometimes an updater would not be recognized.- Prevented an open probe from causing a high temperature alarm. It will now cause a probe damaged alarm.

SEC-HD1.09 - Fixed a bug that caused the control to use the default settings instead of the backup settings1.08- Fixed stage 5 proportional timer. It would only turn on the stage for 30 seconds regardless of temperature.1.07- Fixed bug that sometimes caused a lockup (requires hardware modification on display boards s/n 20121204-20130623).1.06- Added 2 motor curves (CL3, CL4).1.05- Fixed bug where sometimes an updater would not be recognized.- Prevented an open probe from causing a high temperature alarm. It will now cause a probe damaged alarm.

SEC-DC1.06 - Fixed a bug that caused the control to use the default settings instead of the backup settings 1.05- Fixed stage 5 proportional timer. It would only turn on the stage for 30 seconds regardless of temperature.1.04- Fixed bug that sometimes caused a lockup (requires hardware modification on display boards s/n 20121204-20130623)1.02- Fixed bug where sometimes an updater would not be recognized- Prevented an open probe from causing a high temperature alarm. It will now cause a probe damaged alarm.

TVS1.08 - Fixed a bug that caused the control to use the default settings instead of the backup settings 1.07- Fixed bug that sometimes caused a lockup (requires hardware modification on display boards s/n 20121204-20130623)1.06- Added 2 motor curves (CL3, CL4)1.05- Fixed bug where sometimes an updater would not be recognized- Prevented an open probe from causing a high temperature alarm. It will now cause a probe damaged alarm.