I see internal PLC Controller type as pic. I don't know what is it? Nothing but some "dummy" controller. Value stored in an 800xA memory. How to use it? I created a input bar and link to integer variable. But the value is not change. In "Signal Configuration" aspect set checkbox "Is Controllable" a...

You can change RPBA address in the "DP-Parameters".
For sending/receiving data you must declare variable in the "DP-Module I/O Mapping". For example: declare ACS550_VAR (WORD type) for %QW1.4. Later connect it in your program.

No. You have one connectivity server node with one RTDB (realtime database) and you are used it for the MatrikonOPC simulator. Therefore no unconnected servers left.
If you need OPC functionality without RTDB - create "Generic OPC Control Network".

You overconfigure something before it happens... Delete your system and create new one. Load PLC Connect Extension and try all steps again. Do not create other control networks if they are not using in the system. You can skip "Connect to server" in the Matrikon OPC Explorer. This is just for Matrik...

Did you configure "Generic Control Network Configuration" aspect in the PLC Generic Control Network?
I don't see this step on your pictures...
Is OpcDA_Connector service running? Service provider of the OpcDA_Connector service "looks" on OPC server node?

In brief: Download user's manual for ACS550 from ABB. It is necessary to know MSW and MCW structure before config something. Add device for CM572-DP in your PS501 project and specify .gsd file for the RPBA-01. (Here you can download that gsd: https://hotfile.com/dl/179206600/8ac4402/abb10812.zip.htm...

Is Profibus in Siemens-side redundant? If not you are probably need allocate a redundancy link module (such as ABB RLM01) between DP-DP coupler and 2 redundant Profibuses of AC 800M. Check at: http://www05.abb.com/global/scot/scot296.nsf/veritydisplay/728ac8ac49df0770c1256bc20060098b/$file/3BDD01164...

Added possibility to unprotect data blocks too (using any password): http://www.4shared.com/rar/S7Jl2n65/datamanagers200dll_for_V40_STE.html S7-MicroWIN version: 4.0.9.25 I have a PLC project that was password protected and i unlocked it using olly but still some subroutines are still protected. Ple...

If recovered after failure 800xA system is running the last downloaded version of the project must be in the Control Structure... of course if you did not create a new system.
If you did so - contact ABB, they maybe will send a specialist with PLC memory dumping and conversion toolkit on your site

Your question is lack of information: 1. What kind of backup? 800xA full system backup or Control Builder project only? 2. What did you mean under "recover program from CPU"? PLC? If so, what kind of PLC/CPU? 3. Was that external drive or system drive (Windows with 800xA)? If that was external - why...

Another options are upgrade 800xA system 5.1 to the Rev.B or Feature Pack 3 installation. System 800xA 5.1 Rev B is released at July 2012 and includes support for Internet Explorer 8 and 9, SQL Server 2008 SP3 and VMware ESXi 5.0. 800xA 5.1 Rev.B installation media: http://www.4shared.com/folder/kGs...

I was started this topic by PM request to remove or reveal password from Step 7 project. I couldn't find any password popups in the project... later requester said that password requested only in online mode (when Step7 connected to the PLC). So the request has been cancelled (I don't have any Sieme...

The Central Licensing System (CLS) used in 800xA systems replaces the license handling used in earlier versions. One FCB_AC100 license is required for each PC running Function Chart Builder with node type AC100, e.g. AC55, AC70, AC110 or AC160. One FCB_AC400 license is required for each PC running ...

I need help on this CodeSys library. If you explain me how to do, it would be great. https://rapidshare.com/files/355085887/ModbusTCP.lib I will explain: type 3SMODTCP when that library request for a password. http://dl.dropbox.com/u/36769999/WINDER-1-0-0.rar i would like to have your service again...

I think the best way will be to make an upgrade of the win 7 machine with 800xA installed. Please comment if any ideas! Regards! (fback) I can show what should you expect if you try install 800xA on Win 8 (no upgrade from Win 7): Automated installation: http://desmond.imageshack.us/Himg856/scaled.p...

Yesterday I've tried to install 800xA on a Windows 8 platform, since it's written that support for the higher version is available. Where did you get such information? Only Windows 7 and Windows Server 2008 are officially supported by 800xA SV5.1. And message with thrown exception is required (bett...

I thought that gabbi sent you the software. Passwords to be good to these libraries. I do not have "Wago Automation Cockpit", but I have a last version of WAGO I/O PRO CAA based on CoDeSys v2.3.9.35, and I'm writing you a personal message and translate it through Google translator and the translati...