FTKL-S

Stabilizer Inside Advance Anti-Corrosion

Daikin's new FTKL-S Series is designed to withstand at high corrosive Environment like dump yards and chemical waste areas. Its good sleep off timer provides an un-interrupted night's rest by automatic temperature adjustment.

Product category:

Split Hi-Wall Air Conditioner›FTKL-S

Available in (kW):

Salient Features

Anti corrosion treatment

The Outdoor Units heat exchanger fins are processed using a special anti-corrosion treatment. The surface is covered with a thin acrylic resin layer to enhance the fins resistance to acid rain and salt corrosion

Coanda airflow

Coanda airflow operation gives you the best air-conditioning experience. The powerful air draft does not fall on your head directly, but it is steered upward letting air circulate into the corners of the room creating a comfortable ambience.

Econo mode

This function enables efficient operation by limiting the maximum power consumption. It is useful when using the air-conditioner and other electrical devices simultaneously on a shared electrical circuit.

PM2.5 filter

Traps fine particles for cleaner airflow

Power chill operation

When the rooms needs to be cooled quickly in extreme heat, power chill ensures that the room temperature drops fast for immediate comfort.

Specification

Model name

Indoor unit

FTKL35TV16XS

FTKL50TV16US

FTKL60TV16US

Outdoor unit

RKL35TV16XS

RKL50TV16US

RKL60TV16US

Power supply

1 50Hz 230V

1 50Hz 230V

1 50Hz 230V

(220-240V)

(220-240V)

(220-240V)

Power supply intake

Outdoor unit

Outdoor unit

Outdoor unit

Cooling capacity Rated Full/Half (min.~max.)

kW

3.5/1.75 (1.75~3.5)

5.0/2.5 (2.5~5.0)

6.0/3.0 (2.5~6.0)

Cooling capacity Rated Full/Half (min.~max.)

Btu/h

11900/5970(6000~11900)

17100/8500(8500~17100)

20500/10240(8500~20500)

Power consumption Rated Full/Half (min.~max.)

W

1110/468 (468-1110)

1752/615 (615-1752)

1970/780 (720-1970)

Annual Power consumption

kWh

732

1045

1255

ISEER / Star Rating

Wh/Wh

3.70/3*

3.70/3*

3.70/3*

Voltage Range

V

160-265

160-265

160-265

Operating current

Cooling

A

4.87

7.71

8.67

Indoor unit

Panel colour

White

White

White

Dimensions HxWxD

mm

283x800x198

298 x 885 x 229

298 x 885 x 229

(Package dimensions)

(265x855x340)

(375 x 980 x 325)

(375 x 980 x 325)

Weight (Gross)

kg

8 (12)

11 (16)

11 (16)

Airflow rate

m3/min.

9.6

16.2

16.3

Operation sound H/M/L/SL

Cooling

dBA

40/36/32/29/26

45/42/40/38/35

47/45/43/40/38

Outdoor unit

Dimensions HxWxD

mm

550 x 765 x 285

595 x 845 x 300

595 x 845 x 300

(Package dimensions)

(642x932x380)

(680x1035x410)

(680x1035x410)

Weight (Gross)

kg

26(33)

34 (42)

35(43)

Operation sound H/SL

Cooling

dBA

51/--

54/--

56/--

Breaker size

A

15

20

20

Piping length

Charge-less

m

10

10

10

Max. length

m

20

20

30

Max. height

m

15

10

20

Piping connection

Gas/Liquid

mm

9.5/ 6.4

12.7 / 6.4

12.7 / 6.4

Operation limit

Cooling

oCDB

19.4~50

19.4~50

19.4~50

Measurement conditions:

Sound levels are based on temperature conditions 1. above with 5m piping length. These are anechoic conversion values. These values are normally somewhat higher during actual operation as a result of ambient conditions.

Cooling and heating capacities above are rounded off to first decimal. 1TR (Ton of Refrigeration) = ~3.517 kilowatt.