7
Natural Disasters These disasters include Cyclones, Floods, earthquakes, volcanic eruptions, Drought, and Landslides etc Out of total deaths by Floods in the world, (1/5) are from India. The main causes of floods are excessive rains in river catchments, poor natural drainage, Change of river course, Landslide restricting river flow, cyclone and very intense rainfall Providing clean water is usually one of the highest priorities in the event of an emergency

8
Impacts of Natural Disasters on Water Supply Draught and earth quake –Shortage of water –Bacterial Contamination of water Cyclones and floods –Contamination of water sources Turbidity and suspended solids Organic matter due to plan decay, animal carcasses Bacterial contamination

9
Water Supply Management During Draught Demand assessment How much water is needed? Location and protection of water sources Where are the nearest/most convenient sources of water and How can they be protected? Water treatment What is the level of water treatment required for use/consumption? What methods are available for treatment Water distribution Where will people collect water from? How will the water be collected? How will it be stored for domestic use?

10
Water Supply Management During Flood Flood waters can move animal carcasses closer to intakes which increases the chance of organic and bacteria contaminating the drinking water supply. The spread of bacteria also occurs when rising levels of water cause sewage to back up into lower lying areas such as home interiors and public throughways through toilets and manholes. The turbidity (cloudiness) of water can increase during flooding as can pollution from other contaminants.

11
Water Supply Management During Flood Phased action plan Immediate measures (to sustain life) Intermediate measures (from about 2 to 6 weeks after the disaster, or the arrival of refugees in a camp) Long-term solutions (from about 6 weeks). Factors affecting the duration of action phases Accessibility of the disaster area or refugee camp for local, national, and international assistance; The nature of the disaster Availability of water, materials, and skilled labour

15
NEERI-ZAR : Portable Instant Water Filter Water purification system suitable for potable water supply particularly under emergency situation with a wide range of flood water quality A typical unit, with two 100 L vessels, can serve about 20- 30 persons, when operated for 10 hours a day, on the basis of 6-10 litres per capita/day for drinking and cooking purposes Removes turbidity and suspended matter as well as the micro-organisms. No change in the dissolved mineral concentrations in raw and filtered water Can be used to treat the pond/lake water for the villages or small colony situated at the isolated places Operating cost Rs. 3 per 100 L

16
NEERI-ZAR : Performance NEERI-Zar produces filtered water with turbidity in the range of 1.1 to 3.8 NTU and 90 – 99% reduction in bacterial load from the raw water with the turbidity in the range 10 - 300 NTU and Total coliform and E.coli counts in the range 6800–78300 CFU/100ml and 100-7900 CFU/100 ml respectively. Zooplankton species like cyclops, nauplius, daphnia, branchionus are also removed during filtration. The operation of the unit includes disinfection by chemical agent.

17
Installed 100 units in the flood affected remote areas of Barmer District in October 2006

18
Installed 400 units in the Aila Cyclone affected villages of Sundarban district (West Bengal) in 2009 to treat pond water

21
Pot Chlorinator for Disinfection of Dug Well and Storage Tanks Waters Single Pot system Single Pot system Suitable for Community dug wells and storage tanks of 9000 to 13000 L capacity Earthen pot of 7 to 8 L capacity is used in the system Dry mixture of 1.5 kg bleaching power (BP) and 3 kg coarse sand is placed in the pot over the pea gravel Addition of sodium hexametaphosphate (5% of BP) helps in prolonging the chlorination period Pot is lowered in the well/tank and kept 0.9 to 1.2 m below water level with the help of rope Chlorine residual : 0.2 to 1.0 mg/L for 15 to 20 days One pot is enough for daily drawl of 900 to 1300 L (40-50 people per day) With higher drawl rates two pots are necessary per well

22
Pot Chlorinator for Disinfection of Dug Well and Storage Tanks Waters Double Pot system Suitable for household dug wells of 4000 L or less capacity having withdrawal rate of 360 to 450 L of water per day Unit consist of two cylindrical pots, one inside the other Moist mixture of 1 kg bleaching power (BP) and 2 kg of sand is kept in the inner pot with 0.6 cm diameter hole above the level of sand and BP mixture Pot is lowered in the well and kept 0.9 to 1.2 m below water level with the help of rope Chlorine residual : 0.15 to 0.5 mg/L for 15 to 20 days

25
Electrolytic Defluoridation Technique Removal of fluoride by active species of hydroxide of aluminium produced by passing DC power through aluminium electrode Process is effective to remove excess fluoride and also bring down the bacterial load of the raw water Simple to fabricate, easy to operate with minimum maintenance Suitable for treatment of raw water with fluoride concentration upto 10 mg/L Produces potable water with palatable taste as against the other available chemical treatment methods Quantity of sludge produced is much less (60-70%) than conventional treatment methods Simultaneous reduction in bacterial contamination in treated water Treatment cost upto Rs. 20 per 1000 L

26
Electrolytic Defluoridation Plants working in the field Dongargaon, Chandrapur Dist. (Maharashtra) Installation year 2002 Working on Solar power Capacity - 600 lit / Batch Usaravara village, Durg district (Chhattisgarh) and Sargapur village Seoni Dist.(M.P.) Installation year 2010 Working on Solar power Capacity - 2000 lit / Batch UNICEF provided funds for installation of 16 plants in Madhya Pradesh

28
NEERI-ZAR : Domestic Iron Removal Unit Oxidation of iron by KMnO 4 and removal of precipitated iron by sand filtration The dose of KMnO 4 required is about 50% of the iron concentration in the water Suitable for remote places such as reserve forest, police /military camps 20 plants are installed in Tadoba Tiger Reserve Forest, Maharashtra for supply of water to forest guards

29
NEERI-ZAR : Domestic Fluoride Removal Unit Process involves formation of insoluble fluoride complex with salts of calcium and phosphorous and filtration through sand filter Reduces the fluoride concentration in water to <1 mg/L Suitable for treating the water upto fluoride concentration of 10 mg/L Taste of the treated water is palatable Installed 60 demonstration units at Sakhara village in Maharashtra Cost of treatment Rs. 0.30 per liter

30
NEERI-ZAR : Domestic Arsenic Removal Unit Process involves formation of insoluble arsenic complex with Chemical A and B and filtration through sand filter Reduces the arsenic concentration in water below 0.01 mg/L Suitable for treating the water upto arsenic concentration of 100 to 3000 ppb Taste of the treated water is palatable Installed 5 demonstration units at C.G.