The eze System 111-0010-2 ezeio Web-Based Input/Output I/O Controller, Standard is flexible, low cost, easy to install, configure and use. It can be used to monitor/record for example energy use, temperature, pressure, flow, gases, activity, speed, vibration and anything else that there is a sensor for.The eze System ezeio Controller comes ready to use out of the box. Simply attach the power supply to the controller and Internet connect it to the Internet using the Ethernet cable, and it will start communicating with the eze System servers. There is no need for special software or network setup. The ezeio connection is encrypted, bidirectional and very efficient. The ezeio comes complete with a power supply, an Ethernet cable and 4 months of basic service. Additional service is easily purchased via the web interface.

The ezeio Controller is a general purpose Input/Output device, capable of monitoring, logging and controlling a wide range of devices and equipment through industry standard connections over the Internet. The ezeio Controller automatically establishes a secure link to an array of redundant and secure servers, allowing live access from a standard web browser and eliminating the need for fixed IP, complex firewall setup or special software. Multiple ezeio Controllers can be set up under a single user account, thus providing a simple overview of the status of any number of sites spread out geographically from anywhere in the world. All configuration, control, and access is accomplished by logging into the secure servers via the Internet.

The ezeio includes four (4) analog inputs, two (2) relay outputs, Microloan and Mudbugs connectivity. The ezeio can be expanded to a maximum of 40 inputs and 40 outputs, which can be a mix of analog, digital, pulse, Mudbugs and Microloan inputs/outputs.

Additional Features
• Runs on 8-25VDC, <1W typical draw
• Logging interval configurable from 10 seconds up to 4 hours for each input
• Up to four alarm thresholds for every input
• Alarms can send email, control outputs, set modes and more
• Live access from standard web interface
• No special firewall or network configuration
• HTTP XML API available for easy integration with other systems
• Zero on-site configuration required

Associations
• Each controller must be associated with a single account.
• Each user is associated with a single account.
• An account may have any number of controllers and any number of users associated with it.

Individual logging on each input. 5s to 4h interval. Automatically communicated and stored on redundant servers.

Input Triggers

Up to four alarms per input, each with alarm/restore thresholds and separate hold off times. Each alarm and restore can trip up to four separate actions, such as sending messages, controlling outputs or counters.

Schedules

Up to 20 schedules, each with four intervals and flags for each day in the week. Up to four actions for each schedule on entry/exit of an interval.

Timers

Up to 20 timers, each can be set to repeat hourly, daily, weekly or monthly. Each timer can trip up to four actions.

Scripts (Optional)

Up to 64kB compiled script code, with 6kB of RAM. Extensive function library with support for floating point math, string manipulation and communication functions.