Forum for Trainees.

If you are a trainee and haven’t already applied to join our trainee forum then clickHEREThe trainee forum is a closed area of the forum where the Forum Mentors will freely share their vast experience within the industry.

how come there isnt a terminal for the cpc even on mains halogen fire rated downlights when the can is made of metal?? is it cos the terminals are insulated and then sit inside a plastic housing so they are double insulated i.e class 2?

this is why i asked, went to a guys house the other day cos he built his own kitchen extension years ago but now wants to sell the house, anyway he never got it signed off by BC and now the inspector has come round he wants to see Part P documentation for the wiring, well i pulled one of the downlights down ( theres 20 overall!!) and he has just looped in and out with the live and neutrals and cut the cpc's off!!, am i correct in thinking that the reason there has to be continuity of the cpc is for obvious reasons in the event of a fault, hence not just using twin live and neutral cable?
The BC wants them to all be fire rated too so its a case of replacing them all so i shall be stripping back all the cables and using wagos and line enclosures anyway.

i would ask for the inspector to quote the building reg. that says they have to be fire rated. sounds like a case of a jobsworth in a suit asserting his authority. in would also ask him if he has any idea of why and when fire rated downlights should be fitted.

I'm just the 3rd party here, i did ask the client, and told him that in my opinion they didnt NEED to be, but he just wants to get it sorted and get the paperwork so the sale of his house can go through. Im not even sure what is meant by Part P paperwork ??? I shall be doing a MWC for changing the lights, as i will test the circuit once im done.

TBH I'm surprised its just the lights he wants sorting, surely BC would want paperwork for the whole extension? In which case it would be an EICR on it, but if you were selling you house why not get an EICR on the whole house? mine is not to question why, mine is just to do as i am asked sometimes lol

how come there isnt a terminal for the cpc even on mains halogen fire rated downlights when the can is made of metal?? is it cos the terminals are insulated and then sit inside a plastic housing so they are double insulated i.e class 2?

Click to expand...

These types of light fittings are Class 2, the outer metalwork is separated from live parts by double or reinforced insulation and should be IEC 60617:Class 2 double square marked.

priming self levelling compound posted by David Bingham.
i have used this to level out a bathroom floor (link below)
Ultra Level It One Fibre Plus | Topps Tiles -...
priming self levelling compound

Random photo from your day posted by Plan Tec Tiling.
The 'Good morning' thread continues to be very successful, a chance for us all to say hi and discuss...
Random photo from your day

It’s New tools tuesdays posted by Adey1980.
i popped into topps tiles to pick up a Rubi 40ltr tub bucket and free trowel for £12.
I bought the bucket to make life easier cleaning as was told it’s pretty tough.
View attachment 93799 ......

Expansion Vessel Placement Advice posted by Tozzy.
View attachment 35537
Hi,
I intend to install an EV (expansion vessel) to my cold water line as I'm having problems with pressure affecting my water heater and taps. When the water gets really...

dripping drain off on vented central heating posted by Mgrant.
If a drain off valve is leaking on a vented central heating system, due to not shutting off. As the washer has perished. Has anyone had success in swapping the inners over in this without draining...