All necessary boiler controls and secondary plumbing are in place and pre wired, and the vessels easily fit through a 32″ doorway, resulting in a very quick start-up. Each vessel contains a 97 foot copper coil through which the domestic hot water is circulated. This coil is surrounded by the hot boiler water, which transfers heat to the coil. Firing rates for the Series 900 Combination Boiler are available from 600,000 Btu/hr to 1,000,000 Btu/hr. However, many millions of Btu’s can be delivered by creating an efficient, fully modular system of up to 24 vessels operated by our computerized control panel.

Standard features include nationally known parts and controls that are available at most supply houses, allowing for quick and easy repair and maintenance, which can dramatically reduce down time.

Options

ZHONGYUAN Boiler offers several options to customize your boiler. A job is not complete until the boiler has been properly equipped for the application.

Design

The Series 900 Combination Boiler is manufactured to exceed ASME Section IV standards and typically is used to provide supply temperatures from the coil of between 140-180°F, yet can accept extremely low return temperatures (below 100°F) without shocking the boiler. The Space Heating side of this boiler can provide supply temperature up to 200°F, and return temperature can go as low as 140°F. The temperature of the coil water is impacted by the temperature of the Space Heating side because the coil is immersed in that water. These vessels contain 73 vertical firetubes, each of which is 1½” diameter, each fitted with a high-efficiency turbulator for maximum heat transfer. The combustion chamber is fully water-backed, with burners that are UL listed. The vessel capacity is 75 gallons with a heating surface of 78 sq. ft. This boiler qualifies as a Category I gas appliance with industry standard controls wired to NEC specifications.

Safety

A well-made, heavy vessel is naturally a safer boiler. But ZHONGYUAN Boilers also have a firebox design that is completely backed by water, along with extra safety controls on the boiler that results in a very safe and secure package.