Quick Details

After-sales Service Provided:Engineers available to service machinery overseas

Packaging & Delivery

Packaging Details

International Export Wooden Case Packing, Water Proof

Delivery Time

Delivery it in 2 months after received the downpayment

Osmosis Pure MachineDesign and Manufacturing According to FDA&cGMP Standard

Provide customization according to customer's requirement,welcome to call us for consultation !

DESCRIPTION

When the original water flow through the first feed water pump, the pressure reach 0.3mPa and flow into the mechanical filter which filled with five types of relined quartz sand, at the moment, the floats, turbidity, sit, quick sand which are more than 100um will be retained by the mechanical filter.

The water treated by the mechanical filter are less than 100um and then flow into the activated carbon filter that is filled with Nut shell activated carbon filter of iodine value more than 900. The activated carbon filter can absorb the residual chlorine, peculiar smell, and some inorganic salt and organic salt in the water. The above two steps we call it pretreatment.

Then the water flow into a cartridge filter (also we can call it precision filter) of 1um, it filled with five melt spinning cartridge of 20 inches made by PP, the water filtered by it can reach the inlet standard of RO.

Water filtered by cartridge filter will flow into one stage reverse osmosis system, the recovery rate of pure water is 60%-70%, the waste water will be drain out. Pure water will flow into the second feed water pump and then come into two stage reverse osmosis system, the recovery rate is 80%. At the same time 20% of concentration will be recycled and utilized, one part flow back into one stage reverse osmosis system and another part flow into two stage reverse osmosis system so as to achieve full recycle and utilization. Furthermore, it also adjust the PH value of the water coming into the second stage reverse system, generally PH(7-7.5) and reduced carbon dioxide in the second reverse osmosis system greatly and Improve the desalination rate.

TECHNICAL DATA

Categorization

Name

Capacity

One Stage Reverse Osmosis Equipment

All-in-one Single Stage Reverse Osmosis Pure Water Machine

0.5m³/h

1m³/h

2m³/h

3m³/h

15m³/h

20m³/h

Reverse Osmosis Pure Water Machine

5m³/h

Single Stage Reverse Osmosis Pure Water Machine

10m³/h

One Stage Reverse Osmosis Equipment

FRP1m³/h

Double Stage Reverse Osmosis Pure Water Machine

All-in-one Double Stage Reverse Osmosis Pure Water Machine

1m³/h

2m³/h

3m³/h

Double Stage Reverse Osmosis Pure Water Machine

0.5m³/h

0.25m³/h

Double Stage Reverse Osmosis Equipment

3m³/h

2m³/h

Double Stage Reverse Osmosis Pure Water Equipment

3m³/h

Transaction History of the Supplier

Below is the information about the supplier's transactions conducted via Alibaba.com. If you require further details regarding the transaction data, please contact the supplier directly.