Spectrex Inc.

Spectrex Inc.

40/40I Triple IR (IR3) Flame Detector

40/40I Triple IR (IR3) Flame Detector

The 40/40I, a multi spectrum based on three IR bands (IR3), detects fuel and gas fires at long distances with the highest immunity to false alarms. The 40/40I IR3 can detect a 1ft2 (0.1 m2) gasoline pan fire at 215 ft (65m) in less than 5 seconds. The 40/40I is the most durable and weather resistant flame detector currently on the market. Its new features include a heated window, to eliminate condensation and icing; HART capabilities for digital communications; lower power requirements; and a compact, lighter design.

40/40UFI Ultra-Fast Triple IR (IR3) Flame Detector

40/40UFI Ultra-Fast Triple IR (IR3) Flame Detector

The 40/40UFI, an Ultra-Fast multispectrum IR3 Flame Detector, detects hydrocarbon fuel and gas fires at long distances, and is especially designed to detect an explosive 1 ft (0.3m) diameter gas cloud explosion in max. 50 msecs for 1ft diameter sphere methane-air mixture explosion at 66 ft (20m) with the highest immunity to false alarms. The 40/40UFI IR3 can also detect a 1 ft2 (0.1m2) gasoline/n-Heptane pan fire at up to 300 ft (90m). The 40/40UFI is part of the 40/40 Series, the most durable and weather resistant range of flame detectors currently on the market. Features include a heated window, to eliminate condensation and icing; HART capability for digital communications; lower power requirements; and a compact, lighter design.

40/40L-LB UV/IR Flame Detector Series

40/40L-LB UV/IR Flame Detector Series

Model 40/40L (or LB, with Built-in-test option) provides a combination of UV and IR sensors, where the IR sensor operates at a wavelength of 2.5-3.0 µm, and can detect hydrocarbon-based fuel and gas fires, hydroxyl and hydrogen fires, as well as metal and inorganic fires.

The UV/IR flame detector senses radiant energy in the short wave section of both the ultraviolet and infrared portions of the electromagnetic spectrum. The signals from both sensors are analyzed for frequency, intensity and duration. Simultaneous detection of radiant energy in both the UV and IR sensors triggers an alarm signal.

40/40UFL Ultra Fast UV/IR

40/40UFL Ultra Fast UV/IR

The new SharpEye UV-IR High-Speed Optical Flame detector 40/40UFL is designed to meet two major requirements:

- High-Speed Response (20 msec)

- High Reliability (immunity to false alarm)

This detector is based on our well known military detector used in Armored Vehicle Explosion Suppression System combined with the industrial detector 40/40LB.

The 40/40UFL can detect hydrocarbon-based fuel and gas fires, hydroxyl and hydrogen fires, as well as metal and inorganic fires.

The UV/IR flame detector senses radiant energy in the short wave section of both the ultraviolet and infrared portions of the electromagnetic spectrum. The signals from both sensors are analyzed for frequency, intensity and duration. Simultaneous detection of radiant energy in both the UV and IR sensors triggers an alarm signal.

40/40L4-L4B UV/IR Flame Detector Series

40/40L4-L4B UV/IR Flame Detector Series

Model 40/40L4 (& L4B, with Built-in-test option) provides a combination of UV and IR sensors, where the IR sensor operates at a wavelength of 4.5 µm, and can detect hydrocarbon-based fuel and gas fires.

The UV/IR flame detector senses radiant energy in the short wave section of both the ultraviolet and infrared portions of the electromagnetic spectrum. The signals from both sensors are analyzed for frequency, intensity and duration. Simultaneous detection of radiant energy in both the UV and IR sensors triggers an alarm signal.

40/40U-UB - UV Flame Detector

40/40U-UB - UV Flame Detector

The new 40/40 UV Flame Detector detects hydrocarbon-based fuel and gas fires, invisible hydrogen flames, and fires from hydrides, ammonia, silane and other organics. The 40/40U-UB is the most durable and weather resistant UV flame detector currently on the market. Its new features include a heated window to eliminate condensation and icing; HART capabilities, for digital communications; lower power requirements; and a compact, lighter design.

Due to increased reliability, the 40/40 Series warranty period has been extended to 5 years and is SIL2 (TUV) approved to IEC 61508.

The model 40/40UB includes a Built-in-Test (BIT) feature, whereas the 40/40U model does not.

Note: This type of detector should not be exposed to UV radiation sources such as welding, sparks, and electric arcs as it will cause false alarms.

40/40R - Single IR Flame Detector

40/40R - Single IR Flame Detector

The 40/40R Single IR Flame Detector detects hydrocarbon-based fuel and gas fires using advanced flame analysis tools. The detector provides early warning of flaming fires working at 4.5 μm for maximum sensitivity, and immunity to false alarms from IR sources such as sunlight and IR projectors.

The 40/40R is the most durable and weather resistant single IR flame detectors currently on the market. Its new features include a heated window, to eliminate condensation and icing; HART capabilities, for digital communications; lower power requirements; and a compact, lighter design.

40/40M Multi IR Flame Detector

40/40M Multi IR Flame Detector

The 40/40M Multi IR Flame Detector is specifically designed for detection of hydrocarbon and hydrogen flames. It detects hydrocarbon-based fuel and gas fires at long distances with the highest immunity to false alarms. The 40/40M can detect a gasoline pan fire at 215 ft (65m) or a hydrogen flame at 125 ft (38m) in less than 5 seconds.

The 40/40M is the most durable and weather resistant flame detector currently on the market. ts new features include a heated window, to eliminate condensation and icing; HART capabilities, lower power requirements, and a compact, lighter design.

The 20/20MI is an economical and compact Triple IR (IR3) Flame

The 20/20MI is an economical and compact Triple IR (IR3) Flame

Detector with the highest immunity to false alarms, in a rugged stainless steel housing.