The ASCO 7000 Series Power Transfer Switchis available in the conventional, two-position transfer configuration, and closed or delayed transition modes of operation. Additionally, switched or overlapping neutral options provide for reliable operation of ground fault protection systems and reduction of voltage transients from unbalanced load switching. Click here to read an article describing the sizing considerations when using a closed transition mode of operation.​

Conventional two-position transfer configuration, plus closed and delayed transition modes of operation. All configurations available with either automatic or non-automatic control.

Available in bypass-isolation configuration. The bypass and isolation features allow power transfer switches to be inspected, tested, and maintained without any interruption of power to the load. Click here to view the instructions on how to use the bypass and isolation handles. Click here to view the transfer switch draw out features.

The addition of accessory 12 requires the product to be labeled "Non-Automatic Transfer Switch" as defined in UL1008.Engine controls containing engine stop positions should be located at the engine generator. (Consult ASCO for application assistance).

Indicators

14A/14B

Additional auxiliary contact sets to indicate switch position. Two sets are standard. Specify total number of sets if more are required.

Our comprehensive service portfolio extends beyond routine maintenance to include solution upgrades and technology training that ensure you get the most from your emergency power systems. 1 800 800 ASCO (2726) customercare@asco.com