... Model: T210P

Cooling Towers are typically used to supply cooling temperatures between 5°F to 10°F above the ambient wet bulb conditions.

Cooling Towers provide cooling water to multiple processes, including hydraulics, chiller condensers, temperature control units and other equipment.

Temptek offers cooling towers in capacities from 45 to 540 tons in single and expanded cell systems.

Specifications

T210P (1)

Capacity (2)

Capacity : 210 tons

Flow Rate : 630 GPM

Direct Drive Fan

Quantity : 2

RPM : 1,170

CFM : 50,930

Motor

Quantity : 2

HP : 20

Full Load Amperage (3)

230/3/60 : 57.6

460/3/60 : 28.8

575/3/60 : 24.0

Connection Sizes (5)

To Tower : 6"

From Tower : 10"

Dimensions

Height : 138"

Width : 145"

Depth : 84"

Weight

Dry : 2,250 lbs

Operating : lbs

Shipping : 2,250 lbs

Specification Notes:

1. Since product innovation and improvement is our constant goal, all features and specifications are subject to change with notice or liability. Selection of certain optional features may change listed specifications.

2. Cooling water from 95°F to 85°F at 3 gpm per ton and 78°F web bulb temperature.

3. Full load amps are higher than run load amps and must be used for sizing disconnects and supply wiring. Not for construction. Consult factory for power requirements of unit as configured and on selected options.

4. Consult factory for 50HZ operation.

5. When used with remote sump consult factory for connection size when the base of the tower will be used as the reservoir.

Features

Cooling Tower Design

Total non-ferrous construction materials

Multi-cell design

Single inlet and drain connections

Counter-flow air movement

Structural painted steel base

Fan

Air foil shaped blades for increased air flow

Blades are made of a glass fiber reinforced polymer

Blades are factory set at best angle for maximum air movement

Direct drive mechanics

Distribution Header

Non-ferrous PVC 'cross' construction

Stationary

Computer designed spray pattern

Large orifice spray heads

PVC spray heads

Drift eliminator prevents over spray and water loss

Inspection Covers

Easily removed

eamless gasket sealing

Allows for inspection on cell interior and replacement of wet deck

Inlet Louvers

Stacked honeycomb pattern maximizes water and air flows for greater cooling efficiency

Temptek, Inc. 525 East Stop 18 Road, Greenwood, IN 46142 Phone: 317-887-6352 Fax: 317-881-1277
Product innovation and improvement is our constant goal. All features and specifications are subject to change without notice or liability. Products are
assembled in the United States of America. Site Map

2019 TEMPTEK, INC

Close

This site uses cookies to offer you a better browsing experience. Learn more about how Temptek, Inc. uses cookies by contacting the site administrator at
admin@temptek.com. By closing this banner, scrolling this page, clicking a link or continuing to browse otherwise, you agree to the use of cookies.
Please refer to the Privacy Policy for more information.