Designed to meet or exceed ADA/NFPA/UFC/ANSI Standards and Accessibility Guidelines

Complies with OSHA 29, Part 1910.165

Series MT appliances have IN and OUT wiring terminations that accept two #12 to #18 American Wire Gauge (AWG) wires at each terminal. Inputs are polarized for compatibility with standard reverse polarity type supervision

One alarm appliance with (8) eight selective signals to provide superior sound penetration for various ambient and wall conditions with two field selectable sound output levels

Audible and strobe can operate from a single NAC circuit or from separate NAC circuits with any of the (8) eight audible sounds

MT Strobe models are available with Wheelock patented MCW Multi-Candela strobes with field selectable candela settings at 15/30/75/110cd or with single candela 1575cd strobes. The strobes can be synchronized using Wheelock sync modules or power supplies with built in Sync Protocol

Selectable input voltage on non-strobe versions. Strobe versions are factory set for either 12 or 24VDC, with wide- Listed voltage range, filtered (DC) and FWR

Details

The MT-121575W-FR, from Wheelock is a Red Wall Mount Multitone Electronic Red Horn Strobe with "Fire" Lettering and is ideal for designs that require a choice of 8 selectable alerting sounds for various ambient and wall conditions and 2 selectable sound output levels.