Segment Protectors

Segment Protectors are fieldbus couplers for connecting instruments to the fieldbus segment. They provide short-circuit protection to the trunk line. This is important where hot work performed on a field instrument would cause the entire segment to fail through unintended short circuits to the spur line.

For hazardous areas main line Segment Protectors (R2-SP* and F2-SP*) can be installed in Zone 2 / Div. 2. Some Segment Protectors are certified for Zone 1 installation. Spurs are installed with ignition protection method:

Increased safety for instruments in Zone 1/Div. 1

Intrinsic safety Ex ic for instruments in Zone 2/Div. 2

Segment Protectors for DIN-Rail installation are available with pre-engineered enclosures in GRP or stainless steel housings. The spur count can be up to 24 and accessories are selectable for easy installation. The housing is delivered installation ready with all internal wiring prepared. All components are covered with a single certificate for explosion hazardous areas when needed. Please note our extremely compact and robust Segment Protectors in aluminum housing.

Segment Protector R2-SP-N*

Segment Protector R2-SP-N*

The R2 series of Segment Protector features innovative design supporting efficiency in many aspects of daily fieldbus work:

Easy connection of multiple Segment Protectors via T-connector

Incorrect termination is prevented by design, since the terminator can be placed only on the T-connector of the last Segment Protector

Exchange of Segment Protector via T-connector

Durable installation due to connectors with retaining screws

Test points allow the connection of diagnostic tools such as the Mobile Advanced Diagnostic Module without disturbing the wiring

High-availability termination

Ex ic and Ex nL energy limitation

Segment Protector R2-SP-IC*

Segment Protector R2-SP-IC*

Segment Protector R2-SP-IC* features the same mechanical design as the R2-SP-N* with added features for superior availability:

The Segment Protector R2-SP-IC* communicates status from the diagnostic-enabled enclosure leakage sensor and surge protector to the Advanced Diagnostic Module. This communication does not interfere with normal process communication and requires no addressing, configuration or bandwidth on the bus.

Segment Protector F2-SP-IC*

Segment Protector F2-SP-IC*

Segment Protector F2-SP-IC* offers all the intelligent features for fault detection and protection of the R2-SP-IC*. It is installed in our most compact aluminum enclosure (F2-SP-IC*) with:

Quick and convenient local diagnostics: LEDs visible from the outside

4, 6, 8, 10 spurs selectable

Cable glands or connector plugs (M12) selectable

Optional spring terminals

Modular Segment Protector RM-SP*

Modular Segment Protector RM-SP*

The Modular Segment Protector simply clips onto the DIN-Rail. Two modules, the trunk module and the expansion module, enable the following features:

Smallest footprint in the cabinet per device

Easy expandability on the DIN-Rail via Power Rail

Ex nL energy limitation

Segment Protector R-SP-E12 for Flameproof Devices in Zone 1/ Div. 2

Segment Protector R-SP-E12

The Segment Protector R-SP-E12 can supply power to Ex d field devices. The Segment Protector and the instrument can be installed in Zone 1.

Pepperl+Fuchs is a leading developer and manufacturer of electronic sensors and components for the global automation market. Continuous innovation, enduring quality, and steady growth guarantees continued success, since more than 60 years. Pepperl+Fuchs employs 5,700 people worldwide and has manufacturing facilities in Germany, USA, Singapore, Hungary, Indonesia and Vietnam, most of them ISO 9001 certified.