The system consists of gas-jet block and safety automated mechanisms block. DBAES is designed for installation on heating hot-water boilers as per GОSТ 20548-87, with thermal power up to 30 kW, operating at low pressure natural gas. DBAES provides for safe boiler operation and automatic output boiler water and air temperature keeping in heated premises, as well as efficient fuel combustion.

Application:

DBAES -1

for boiler of the type

КS-ТG-10;

DBAES - 2

- - - - - - - - - - - - - - - - -

КS-ТG-12.5;

DBAES - 3

- - - - - - - - - - - - - - - - -

КS-ТG-16;

DBAES - 4

- - - - - - - - - - - - - - - - -

КChМ-2М «Zh» 3-section;

DBAES - 5

- - - - - - - - - - - - - - - - -

КS-ТG-20;

DBAES - 6

- - - - - - - - - - - - - - - - -

КChМ-2UE «К» 4-sect.;

DBAES - 7

- - - - - - - - - - - - - - - - -

КChМ-2М «Zh» 4-sect.;

DBAES - 8

- - - - - - - - - - - - - - - - -

КChМ-2UE «К» 5-sect.;

DBAES - 9

- - - - - - - - - - - - - - - - -

from 7.1 to 7.6.

Note: the plant manufactures automated mechanisms for DBAES-1, 2, 3, 5 and 8.Upon request of the Customer, the question of manufacture of other automated mechanisms modifications can be discussed.

Technical characteristics

1

Number of protection parameters, not less than-

4;

2

Rated gas pressure in the circuit, Pа -

1300;

3

Inertial time of automatics’ response under fuse burner ignition, s., not more than -

60;

4

Inertial time of gas supply cutoff by the automatics under traction absence, s, in the limits of -

from 10 to 60;

5

Inertial time of gas supply cutoff by the automatics under fuse burner extinction, s, not more than

60;

6

Inertial time of gas supply cutoff by the automatics under non-compactness
of pulse system, s, not more than