Ventilation Systems

FANPLASTIC RR140 AND RR100

Fanplastic is fully made of rust resistant materials.It was designed and constructed without turbulent elements to avoid dust deposits, impurities or anything else found in any environment, eliminating annoying maintenance.Bearing are permanently self-lubricating and purposely oversized, guaranteeing maximum maintenance-free durability.

The single volume bearing frame is made of polyethylene (patented) to grant the fan many important advantages:• greater durability• lack of vibrations• more silent operation• long lasting• resistant to ultraviolet rays.

Furthermore, thanks to the innovative frame, it is the only one with a conveyor that extends for the entire fan depth, permitting more air flow and thus higher capacity with limited energy consumption.

Protection mesh is standard installed according to European regulations on both sides of the fan.

FANPLASTIC RRS140 AND RRS100

The fan is made up of six stainless steel blades characterised by a special profile designed to provide greater air flow at low rpm, keeping the noise and energy consumption levels at a minimum.

Threaded holes are included on the sides of the frame to secure the fan where lifting rings can be screwed in to hook them to a chain or brackets for wall mount.

The electric motor was designed and manufactured specifically for the FANPLASTIC series, thus achieving higher operating yield at real and heavy-duty work conditions. All motors have variable speed, IP55 type, F insulation class, cooled by their fans.

The automatic opening shutters are balanced with counter-weights and characterised by gentle movement and thus particularly accurate and silent

The trapezoidal belt is simply tensioned from inside the fan using a specific and practical tensioner.

The frame is the only one on the market to be made of a single polyethylene block, eliminating oxidation and guaranteeing maximum durability. (patented)

TECHNICAL SHEET

Specifications and dimensions

Model 140

Model 100

Dimension A

(mm)

1385

1090

Dimension B

(mm)

1385

1090

Dimension C

(mm)

340

350

Dimension D

(mm)

425

435

Dimension E

(mm)

286

266

Dimension F

(mm)

1310

1015

Dimension G

(mm)

40

37,5

Dimension H

(mm)

30

42

Dimension I Ø

(mm)

1280

950

Nominal flow ∆P=0

(m3/h)

40500

26000

Nominal fan speed

(rpm)

450

640

Fanplastic RR weight

(Kg)

64,5

43

Fanplastic RRS weight

(Kg)

80

55,5

Number of blades

6

6

Maximum working temperature

11

8

Number of shutter blades

(°C)

50

50

Motor power

(hp/Kw)

1/0,75

1/0,75

Electrical motor IEC protection grade

IP55

IP55

Electric motor windings insulation class

F

F

The fan was tested according to UNI standards without shutter and without protection mesh. The capacity and technical specifications may be subject to change without prior notice.

VENTILATION DIAGRAM

FANPLASTIC, thanks to its construction simplicity, is extremely versatile for used wherever air ventilation is required: farms, industries and greenhouses.