Maxlite's LED PL Replacement Lamps are designed to replace inefficient compact fluorescent plug-in lamps (PLs) with easy installation. Available in either 6 watt or 8 watt and with your choice of either an E26, GU24, GX23 (2 pin) or G24q (4 pin) base option. These LED PL lamps deliver uniform consistency, and a long, 50,000-hour life. Designed as a replacement for 13- and 18-watt fluorescent PL lamps, these LED PL retrofits offer a variety of retrofit opportunities in commercial fixtures, including fluorescent recessed cans, sconces, and ceiling fixtures commonly used to light retail stores, hotels, motels, resorts and apartment buildings. Constructed with a lamp holder that rotates 270 degrees, these LED retrofits require only a simple ballast bypass to ensure maintenance-free, energy-saving operation and higher performance. The lamps are backed by a five-year, limited warranty.

Welcome to MaxLite's new generation of ballast bypass LED PL Lamps. This item is the Maxlite 8PLG24QLED50 (76492) which replaces part number 7PLG24QLED50 (73908). This G24q base, 4-pin LED PL bulb consumes just 8 watts and will operate on any 120 to 277 volt system. Designed as an LED PL replacement for 18 watt fluorescent PL tubes, this non-dimmable LED will generate 725 lumens (that's a very nice 91 lumens per watt efficacy) of 5000K, 82 CRI light output. Installation requires that you bypass your existing ballast thus ensuring maintenance-free operation. As not all applications are alike, once you secure this LED PL retrofit to the socket, it will rotate up to 270 degrees, giving you the flexibility that you need to light what you what! Click here to see the complete Maxlite 6W and 8W LED PL Retrofit Lamp Specification Sheet.

The physical dimensions of these G24q base ballast bypass LED PL lamps are 6.50" long by 1.38" wide. These LED PL retrofit lamps are suitable for totally enclosed luminaires as well as dry and damp locations. Operating temperatures are between -4 degrees Fahrenheit and +113 degrees Fahrenheit. RoHS Compliant and cULus Classified, they are rated for a long 50,000 hour lifetime and are backed by Maxlite's 5 year limited warranty. The MaxLite 8PLG24QLED50 is not intended for use with emergency exits.

Please NOTE: When retrofitting LED to a fluorescent fixture, the ballast must be by-passed or removed from the fixture. Additionally, by-passing the ballast will insure no RFI interference. Are you working on bidding or ready to start a project or job? Click here to Request a Job Quote.

* Everyday discounts on all products. Additional quantity discounts on many products.

** Our cross referenced part numbers (Sylvania, Phillips, GE, Maxlite, Universal, Grainger, Sola, etc) are intended only as guides and may represent another lamp/ballast company's most similar product rather than an identical match. Individual manufacturer's performance values should always be consulted.