Tripp Lite’s Hot-swap PDU systems enable live-replacement of standard UPS systems for maintenance with no interruption of connected server or networking loads. Dual input power cables support PDU connection to separate Utility and UPS power sources. Manual transfer switch with lighted status indicators controls the source of power to connected equipment between Utility and UPS. Set the switch to UPS during normal operation and connected equipment will receive full-time conditioned power from the UPS. Set the switch to Utility to momentarily power connected equipment from the Utility line cord and bypass the UPS while the UPS system is removed and replaced with a fresh one. Once the new UPS is up and running with all data and electrical connections restored, set the switch back to the UPS setting to once again provide fully-conditioned UPS power to connected equipment.

PDUBHV10 is universally compatible with any Tripp Lite or other brand of 200-240V UPS rated up to 1500VA with a C14 input cable option. Pair of detachable PDU input cables connect to separate Utility and UPS power sources (set of 2 C13-C14 interconnect cables included; user supplied alternate cabling supported). 8 C13 outlets support critical networking loads in both Utilty and UPS operating modes. 2U rackmount installation in 2 or 4 post racks with support for space saving rear-post mounting in the same rack space as your Tripp Lite Rackmount UPS (select installations, see manual).

Tripp Lite Hot-swap PDU systems support live-replacement of standard UPS systems for maintenance with no interruption of connected server or networking loadsPDUBHV10 is universally compatible with any Tripp Lite or other brand of 200-240V UPS rated up to 1500VA with a C14 input cable option2U horizontal rackmount form factor compatible with 2 or 4 post racksSupports space saving rear-post mounting in the same rack space as many Tripp Lite Rackmount UPS systems (select installations, see manual)Pair of detachable PDU input cables connect to separate Utility and UPS power sources (2 C13-C14 interconnect cables included - user supplied alternate cabling supported)8 C13 outlets support critical networking loads in both Utility and UPS operating modesOne additional C13 pass-through outlet supports UPS input power cordDual input power cables support PDU connection to separate Utility and UPS power sourcesManual transfer switch with lighted status indicators controls the source of power to connected equipment between Utility and UPSSet the switch to UPS during normal operation and connected equipment will receive full-time conditioned power from the UPSSet the switch to Utility to bypass the UPS and provide connected equipment with unfiltered power directly from the Utility line cord while the UPS system is removed and replaced with a fresh oneOnce the new UPS is up and running with all connections restored, set the switch back to the UPS setting to once again provide fully-conditioned UPS power to connected equipment ApplicationsHot-swap PDUs are ideal to install along with standard UPS systems to ensure that connected networking equipment will see no power interruption as the UPS is serviced, replaced or upgraded